Include power cable for relocation of security system (IDAS/MIDS), also attach as-built drawing and cable specification details.
5 KV insulation tester is not required for testing of LV cable,remove from the list of equipment shown in paragraph 5.3.1
Contractor to make sure that there will not be any damages to existing utilities during the removal and relocating of existing fence, light poles and security systems (IDAS/MIDS)
consider only applicable points from the description of sequence of U/G cable pulling shown in paragraph 5.3.4 for LV cable installation work. 