SAPMT has reviewed the subject submittal dated May 31, 2015 and has the following comments:

1.	Reflect the existing IDAS Fiber Optic Cables that utilized the spare conduit of Electrical duct bank at sta.1+000.
2.	Identify in the detail drawing IC-AB-714490 the location of PVC direct buried conduit.
3.	IC-AB-846492 sht. 010 cannot be considered as as-built, the disconnect switch, dry transformer and main distribution panel were not install along KAM road.
4.	IC-AB-714489 is not available on site and cannot be considered as as-built. Submittal for switch racks of KAM access road electrical system shall include the irrigation control wiring schedule and cabling layout.
5.	These are as built drawings for electrical system only and IC is urged to expedite the submission of drawings for all disciplines providing coordinates of all as built utilities including manholes, light poles etc.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
