•Operator Building - as per IFC drawing VA-846706-01 and drawing VA-846711-01show the Window Air Conditioner ( WAC-01) mounted above the Power Panel and Lighting Contactor Panel, this is a safety issue due to any type of condensate water may drop on them.
•Operator Building - regarding to drawing IC-SD-846730-101, the plan title Operator Building (SG #2) is wrong it should be Operator Building (SG #3).
•Sleeves are penetrating structural concrete shall meet the applicable requirement of the ACI 318 for reinforced concrete, chapter 6 section 6.3.
•I prefer Electrical Engineer ( Mr. Mark ), Communication Engineer ( Mr. Marwin ) and Mechanical Engineer review the submittal to verify the size, location ….etc.
