SAMPT has reviewed the subject submittal dated April 19, 2015, and has no objection with following comment;


1.	Ensure that all equipment is fastened to the rack with SS or hot dip galvanized hardware/ fittings as per 16-SAMSS-512 Para. 11 
2.	Ensure that for outdoor locations, enclosures shall be: (a) NEMA Type 3R, 3 or 4; or (b) IEC 60529 Type IP34 or better as per SAES-P-104 Para 7.4
