1. Manufacturer is not approved for 9com # 6000001075.
2. Vented Lead Acid and Valve Regulated Lead Acid (VRLA) shall meet the requirements of SAES P-103 and project specification.
3. Provide shop drawing for the equipment layout inside the room.
4. UPS and Batteries inside the rooms shall meet the required maintenance clearance.
5. Provide Battery Racks and Maintenance Cabinet as per SAES P-103 para. 6.2.12.
6. Provide the summary sheet of each building.