#Provide clear vertical dimensions on Dwg VA-847048-0F2 Section C.
#The line texture is not consistent, some places one line goes thicker and thinner but still representing the same thing.
#clouding change on revision 0F2 is drawn across the drawing detail information
#IC to maintain the exact level control during concreting to avoid water ponding at different location since there is only 6 mm gradient allowed from Inlet to Outlet for a distance of 53200 m and 87286 m.
#IC to provide the bending schedule for all rebar and concrete works and other details as indicated on the drawing. 
