SAPMT has reviewed the subject submittal dated June 18, 2014 and has the following comments:
1.	Exhaust fans shall comply with all the notes stated on the Schedule of Exhaust fans in each drawing.
2.	Exhaust fans on drawings # VA- 846 541/001 & VA-846 934/001 shall be of Explosion proof type.
3.	Attach copies of the missing relevant drawings of the exhaust fans given in the Bulk Material Take-off list which are as the following: VA- 846 630/001, VA-846 631/001, VA-846 636/001, VA-846 909/001, VA-846 910/001, VA- 846 969/001, VA- 846 970/001.
4.	The Exhaust fans specifications on the drawing VA-846 934/001 & VA-846941/001 are not included in the MTO-List. It shall be included.
5.	Contractor should select and highlight the different Exhaust fans with the Model number on the Vendor Catalogue cut sheets according to the specification stated on the respective drawing.
6.	Arrange the submittal is a systematic order where unnecessary information is not included and approvals required are enlisted explicitly.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
