1.	Ensure the underground 13.8kV MV cable shall be installed as per SAES-P-104.
2.	Redundant Medium Voltage Feeders shall have a clearance of 1.8 meters as per SAES P-104 para. 14.5.
3.	Ensure that switch rack numbering is accurate.
