SAPMT has reviewed the subject submittal dated June 22, 2014 and has the following comments:
1.	A shop drawing to show the designated areas shall be developed with proper annotations as necessary, in coordination with the equipment manufacturer.
2.	Ensure to meet the enclosure requirements of SAES-P-104 and SAES-P-100 para 8, and mention in the notes section.
3.	Consider classifying the area between the two buildings as Zone 2 (Class 2, Div.2)
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
