-- Table structure for table `resources`
--

CREATE TABLE `resources` (
  `serial` int(11) NOT NULL auto_increment,
  `companyID` int(11) NOT NULL,
  `name` varchar(100) NOT NULL,
  `unitID` int(11) NOT NULL,
  `rate` float NOT NULL,
  `rescat` int(11) NOT NULL,
  `restype` int(11) NOT NULL,
  `rescode` varchar(11) NOT NULL,
  `discipline` varchar(50) NOT NULL,
  `vendname` int(50) NOT NULL,
  `desig` int(30) NOT NULL,
  `vendmobile` int(20) NOT NULL,
  `vendemail` int(20) NOT NULL,
  `vendphone` int(20) NOT NULL,
  `vendfax` int(20) NOT NULL,
  `vendweb` int(30) NOT NULL,
  `prod` int(11) NOT NULL,
  `dateCreated` varchar(40) NOT NULL,
  `resnotes` text NOT NULL,
  PRIMARY KEY  (`serial`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1 AUTO_INCREMENT=1 ;

--
-- Dumping data for table `resources`
--


-- --------------------------------------------------------

--
-- Table structure for table `resourcetype`
--

CREATE TABLE `resourcetype` (
  `resourceCode` int(11) NOT NULL auto_increment,
  `name` varchar(40) NOT NULL,
  `description` text NOT NULL,
  `creationDate` varchar(40) NOT NULL,
  `companyID` int(11) NOT NULL,
  PRIMARY KEY  (`resourceCode`)
) ENGINE=InnoDB  DEFAULT CHARSET=latin1 AUTO_INCREMENT=29 ;

--
-- Dumping data for table `resourcetype`
--

INSERT INTO `resourcetype` VALUES(1, 'rr1', 'rr1', '2013-06-16', 2);
INSERT INTO `resourcetype` VALUES(2, 'COMPMPR', 'Company Maintained Manpower', '2013-06-17', 3);
INSERT INTO `resourcetype` VALUES(3, 'COMPEQP', 'Company Owned Equipment', '2013-07-27', 3);
INSERT INTO `resourcetype` VALUES(4, 'NEWMAT', 'New Material to be purchased', '2013-06-17', 3);
INSERT INTO `resourcetype` VALUES(5, 'RENTEQP', 'Equipment to be Rented', '2013-07-27', 3);
INSERT INTO `resourcetype` VALUES(6, 'TRAEQP', 'Equipment to be Transferred to the Client', '2013-07-27', 3);
INSERT INTO `resourcetype` VALUES(7, 'NEWEQP', 'New Equipment to be purchased', '2013-07-27', 3);
INSERT INTO `resourcetype` VALUES(8, 'NEWMAT', 'New Materials', '2013-12-01', 28);
INSERT INTO `resourcetype` VALUES(9, 'SUBTRADE', 'SubTrade', '2013-12-01', 28);
INSERT INTO `resourcetype` VALUES(10, 'CRT80', 'Crane RT 80T', '2014-01-11', 63);
INSERT INTO `resourcetype` VALUES(11, 'CRT60', 'Crane RT 60T', '2014-01-11', 63);
INSERT INTO `resourcetype` VALUES(12, 'CMO30', 'Crane Mobile 30T', '2014-01-11', 63);
INSERT INTO `resourcetype` VALUES(13, 'ML22', 'Manlift 22m', '2014-01-11', 63);
INSERT INTO `resourcetype` VALUES(14, 'ML27', 'Manlift 27m', '2014-01-11', 63);
INSERT INTO `resourcetype` VALUES(15, 'ML34', 'Manlift 34m', '2014-01-11', 63);
INSERT INTO `resourcetype` VALUES(16, 'ML37', 'Manlift 37m', '2014-01-11', 63);
INSERT INTO `resourcetype` VALUES(17, 'ML40', 'Manlift 40m', '2014-01-11', 63);
INSERT INTO `resourcetype` VALUES(18, 'TH10', 'Telehandler 10T', '2014-01-11', 63);
INSERT INTO `resourcetype` VALUES(19, 'DT', 'Diesel Truck', '2014-01-11', 63);
INSERT INTO `resourcetype` VALUES(20, 'RENT', 'Rental Equipment', '2014-01-25', 28);
INSERT INTO `resourcetype` VALUES(21, 'TEMP', 'Temporary Manpower', '2014-01-25', 28);
INSERT INTO `resourcetype` VALUES(22, 'OWN', 'Own Forces', '2014-01-30', 28);
INSERT INTO `resourcetype` VALUES(23, 'TEMPMPR', 'Temporary Manpower', '2014-04-26', 34);
INSERT INTO `resourcetype` VALUES(24, 'RENTEQP', 'Rental Equipment', '2014-04-26', 34);
INSERT INTO `resourcetype` VALUES(25, 'OWNMPR', 'Company Owned Mapower', '2014-04-26', 34);
INSERT INTO `resourcetype` VALUES(26, 'Code !', 'sftwstf', '2014-08-24', 198);
INSERT INTO `resourcetype` VALUES(28, 'shftg', ';kkd', '2014-08-24', 198);

-- --------------------------------------------------------

--
-- Table structure for table `resourseassignment`
--

CREATE TABLE `resourseassignment` (
  `RID` int(11) NOT NULL auto_increment,
  `resourseID` int(11) NOT NULL,
  `resourseSortCode` varchar(22) NOT NULL,
  `Days` float NOT NULL,
  `Times` float NOT NULL,
  `ESTID` int(11) NOT NULL,
  `WBSID` int(11) NOT NULL,
  `ItemID` int(11) NOT NULL,
  `companyID` int(11) NOT NULL,
  `quantity` float NOT NULL,
  `cost` float NOT NULL,
  PRIMARY KEY  (`RID`)
) ENGINE=InnoDB  DEFAULT CHARSET=latin1 AUTO_INCREMENT=152 ;

--
-- Dumping data for table `resourseassignment`
--

INSERT INTO `resourseassignment` VALUES(40, 6, 'subcontractorresource', 1, 5, 1, 31, 1, 2, 5, 0);
INSERT INTO `resourseassignment` VALUES(49, 2, 'manpower_resource', 3, 3, 7, 109, 29, 3, 9, 0);
INSERT INTO `resourseassignment` VALUES(50, 3, 'manpower_resource', 3, 3, 7, 109, 29, 3, 9, 0);
INSERT INTO `resourseassignment` VALUES(51, 4, 'manpower_resource', 3, 3, 7, 109, 29, 3, 9, 0);
INSERT INTO `resourseassignment` VALUES(52, 5, 'manpower_resource', 3, 6, 7, 109, 29, 3, 18, 0);
INSERT INTO `resourseassignment` VALUES(53, 20, 'subcontractorresource', 43, 1, 7, 109, 27, 3, 43, 0);
INSERT INTO `resourseassignment` VALUES(54, 7, 'subcontractorresource', 2, 2, 7, 109, 27, 3, 4, 0);
INSERT INTO `resourseassignment` VALUES(58, 25, 'manpower_resource', 8, 0, 25, 3314, 521, 3, 8, 0);
INSERT INTO `resourseassignment` VALUES(61, 23, 'manpower_resource', 8, 18, 25, 3314, 521, 3, 144, 0);
INSERT INTO `resourseassignment` VALUES(62, 24, 'manpower_resource', 8, 1, 25, 3314, 521, 3, 8, 0);
INSERT INTO `resourseassignment` VALUES(63, 16, 'equipment_resource', 8, 2, 25, 3314, 521, 3, 16, 0);
INSERT INTO `resourseassignment` VALUES(64, 17, 'equipment_resource', 8, 2, 25, 3314, 521, 3, 16, 0);
INSERT INTO `resourseassignment` VALUES(66, 16, 'material_resource', 0, 696, 25, 3317, 560, 3, 696, 0);
INSERT INTO `resourseassignment` VALUES(68, 15, 'material_resource', 2, 25, 25, 3312, 544, 3, 50, 0);
INSERT INTO `resourseassignment` VALUES(69, 17, 'equipment_resource', 5, 2, 25, 3313, 547, 3, 10, 0);
INSERT INTO `resourseassignment` VALUES(70, 20, 'equipment_resource', 2, 5, 25, 3313, 547, 3, 10, 0);
INSERT INTO `resourseassignment` VALUES(71, 16, 'equipment_resource', 1, 1, 25, 3313, 547, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(72, 18, 'equipment_resource', 5, 1, 25, 3313, 547, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(73, 23, 'manpower_resource', 5, 2, 25, 3313, 547, 3, 10, 0);
INSERT INTO `resourseassignment` VALUES(74, 24, 'manpower_resource', 5, 1, 25, 3313, 547, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(75, 25, 'manpower_resource', 5, 1, 25, 3313, 547, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(76, 19, 'equipment_resource', 5, 1, 25, 3313, 547, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(77, 17, 'equipment_resource', 5, 2, 25, 3316, 519, 3, 10, 0);
INSERT INTO `resourseassignment` VALUES(80, 25, 'manpower_resource', 5, 1, 25, 3316, 519, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(81, 24, 'manpower_resource', 5, 1, 25, 3316, 519, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(83, 23, 'manpower_resource', 5, 2, 25, 3316, 519, 3, 10, 0);
INSERT INTO `resourseassignment` VALUES(85, 18, 'equipment_resource', 5, 1, 25, 3317, 560, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(86, 16, 'equipment_resource', 5, 1, 25, 3317, 560, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(87, 23, 'equipment_resource', 1, 1, 25, 3316, 519, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(88, 24, 'manpower_resource', 5, 1, 25, 3317, 560, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(89, 23, 'manpower_resource', 5, 2, 25, 3317, 560, 3, 10, 0);
INSERT INTO `resourseassignment` VALUES(90, 25, 'manpower_resource', 5, 1, 25, 3317, 560, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(91, 19, 'equipment_resource', 8, 1, 25, 3318, 592, 3, 8, 0);
INSERT INTO `resourseassignment` VALUES(92, 17, 'equipment_resource', 8, 1, 25, 3319, 520, 3, 8, 0);
INSERT INTO `resourseassignment` VALUES(93, 18, 'equipment_resource', 5, 1, 25, 3318, 592, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(94, 17, 'equipment_resource', 3, 1, 25, 3318, 563, 3, 3, 0);
INSERT INTO `resourseassignment` VALUES(95, 25, 'manpower_resource', 8, 1, 25, 3319, 520, 3, 8, 0);
INSERT INTO `resourseassignment` VALUES(96, 24, 'manpower_resource', 8, 1, 25, 3319, 520, 3, 8, 0);
INSERT INTO `resourseassignment` VALUES(97, 23, 'manpower_resource', 15, 8, 25, 3319, 520, 3, 120, 0);
INSERT INTO `resourseassignment` VALUES(99, 17, 'material_resource', 1, 60, 25, 3319, 570, 3, 60, 0);
INSERT INTO `resourseassignment` VALUES(100, 24, 'manpower_resource', 2, 1, 25, 3319, 570, 3, 2, 0);
INSERT INTO `resourseassignment` VALUES(101, 25, 'manpower_resource', 5, 1, 25, 3318, 592, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(102, 24, 'manpower_resource', 3, 1, 25, 3318, 563, 3, 3, 0);
INSERT INTO `resourseassignment` VALUES(103, 23, 'manpower_resource', 3, 2, 25, 3318, 563, 3, 6, 0);
INSERT INTO `resourseassignment` VALUES(104, 24, 'manpower_resource', 8, 1, 25, 3318, 592, 3, 8, 0);
INSERT INTO `resourseassignment` VALUES(105, 23, 'manpower_resource', 8, 2, 25, 3318, 592, 3, 16, 0);
INSERT INTO `resourseassignment` VALUES(106, 26, 'manpower_resource', 5, 1, 25, 3322, 509, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(107, 26, 'manpower_resource', 5, 1, 25, 3324, 510, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(108, 27, 'manpower_resource', 1, 1, 25, 3322, 529, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(109, 27, 'manpower_resource', 1, 1, 25, 3322, 513, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(110, 16, 'equipment_resource', 1, 1, 25, 3314, 523, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(111, 17, 'equipment_resource', 1, 1, 25, 3314, 524, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(112, 17, 'equipment_resource', 1, 1, 25, 3309, 526, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(113, 23, 'equipment_resource', 1, 1, 25, 3309, 574, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(114, 27, 'manpower_resource', 2, 1, 25, 3324, 536, 3, 2, 0);
INSERT INTO `resourseassignment` VALUES(115, 17, 'equipment_resource', 1, 1, 25, 3315, 528, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(116, 23, 'equipment_resource', 1, 1, 25, 3311, 575, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(117, 17, 'equipment_resource', 1, 1, 25, 3315, 539, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(118, 16, 'equipment_resource', 1, 1, 25, 3315, 538, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(119, 11, 'manpower_resource', 1, 1, 25, 3314, 524, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(120, 5, 'manpower_resource', 1, 5, 25, 3314, 524, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(121, 11, 'manpower_resource', 1, 1, 25, 3309, 526, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(122, 5, 'manpower_resource', 1, 5, 25, 3309, 526, 3, 5, 0);
INSERT INTO `resourseassignment` VALUES(123, 22, 'equipment_resource', 1, 1, 25, 3309, 526, 3, 1, 0);
INSERT INTO `resourseassignment` VALUES(138, 31, 'manpower_resource', 60, 4, 41, 3683, 924, 3, 240, 0);
INSERT INTO `resourseassignment` VALUES(139, 16, 'manpower_resource', 5, 0, 42, 3187, 479, 28, 5, 0);
INSERT INTO `resourseassignment` VALUES(140, 16, 'manpower_resource', 2, 16, 42, 3187, 480, 28, 32, 0);
INSERT INTO `resourseassignment` VALUES(141, 18, 'manpower_resource', 3, 0, 42, 3187, 481, 28, 3, 0);
INSERT INTO `resourseassignment` VALUES(142, 15, 'equipment_resource', 4, 0, 42, 3187, 481, 28, 4, 0);
INSERT INTO `resourseassignment` VALUES(143, 32, 'manpower_resource', 0.5, 0, 43, 3875, 1083, 28, 0.5, 0);
INSERT INTO `resourseassignment` VALUES(144, 32, 'equipment_resource', 0.5, 0, 43, 3875, 1083, 28, 0.5, 0);
INSERT INTO `resourseassignment` VALUES(145, 15, 'manpower_resource', 3, 2, 44, 4091, 1601, 2, 6, 0);
INSERT INTO `resourseassignment` VALUES(146, 1, 'material_resource', 3, 1, 44, 4091, 1603, 2, 3, 0);
INSERT INTO `resourseassignment` VALUES(147, 15, 'manpower_resource', 1, 1, 45, 4152, 1781, 2, 1, 0);
INSERT INTO `resourseassignment` VALUES(148, 1, 'material_resource', 2, 2, 45, 4152, 1781, 2, 4, 0);
INSERT INTO `resourseassignment` VALUES(149, 1, 'equipment_resource', 3, 3, 45, 4152, 1781, 2, 9, 0);
INSERT INTO `resourseassignment` VALUES(150, 17, 'assemblies', 4, 4, 45, 4152, 1781, 2, 16, 0);
INSERT INTO `resourseassignment` VALUES(151, 32, 'manpower_resource', 2, 2, 42, 2346, 127, 28, 4, 0);

-- --------------------------------------------------------

--
-- Table structure for table `resourseassignmentcontrols`
--

CREATE TABLE `resourseassignmentcontrols` (
  `RID` int(11) NOT NULL auto_increment,
  `resourseID` int(11) NOT NULL,
  `rate` float NOT NULL,
  `resourseSortCode` varchar(22) NOT NULL,
  `Days` float NOT NULL,
  `Times` float NOT NULL,
  `ESTID` int(11) NOT NULL,
  `WBSID` int(11) NOT NULL,
  `ItemID` int(11) NOT NULL,
  `companyID` int(11) NOT NULL,
  `quantity` float NOT NULL,
  `cost` float NOT NULL,
  PRIMARY KEY  (`RID`)
) ENGINE=InnoDB DEFAULT CHARSET=latin1 AUTO_INCREMENT=1 ;

--
-- Dumping data for table `resourseassignmentcontrols`
--


-- --------------------------------------------------------

--
-- Table structure for table `review`
--

CREATE TABLE `review` (
  `review_id` int(11) NOT NULL auto_increment,
  `review_receipt_id` int(11) NOT NULL,
  `review_int_id` int(11) NOT NULL,
  `review_comments` text NOT NULL,
  `review_comment_status` int(11) NOT NULL,
  `review_status` varchar(10) NOT NULL,
  `review_comment_date` varchar(10) NOT NULL,
  PRIMARY KEY  (`review_id`),
  KEY `review_receipt_id` (`review_receipt_id`),
  KEY `review_int_id` (`review_int_id`)
) ENGINE=InnoDB  DEFAULT CHARSET=latin1 AUTO_INCREMENT=3813 ;

--
-- Dumping data for table `review`
--

INSERT INTO `review` VALUES(7, 33, 14, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(13, 62, 10, 'ssdsad', 1, 'sent', '2013-04-21');
INSERT INTO `review` VALUES(14, 43, 10, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(51, 80, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(52, 81, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(53, 82, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(54, 83, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(55, 85, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(57, 87, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(60, 92, 33, 'No comment.', 1, 'sent', '2013-05-08');
INSERT INTO `review` VALUES(72, 101, 33, '', 1, 'sent', '2013-05-22');
INSERT INTO `review` VALUES(74, 97, 11, 'No further comment.', 1, 'sent', '2013-08-03');
INSERT INTO `review` VALUES(75, 98, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(76, 99, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(77, 109, 11, '1. The proposed contractor has a field proven work integrity in KAUST for Security systems.', 1, 'sent', '2013-05-11');
INSERT INTO `review` VALUES(78, 111, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(79, 112, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(82, 102, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(83, 103, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(84, 104, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(85, 108, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(86, 114, 11, 'No more further comment. Contractor Agreed in compliance with statement of SAPMT in a letter with reference number K&TPD/KRP&SFPD/SF/L-065/13 dated April 10, 2013 that SAMPT has no responsibility for the design and construction in an LSTK contract. and ICC is wholly responsible for all aspects of the project, ensuring that the project is delivered according to the scope of work, specification and ARAMCO standards.', 1, 'sent', '2013-05-11');
INSERT INTO `review` VALUES(87, 116, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(88, 116, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(89, 116, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(91, 115, 33, 'SAPMT has reviewed your subject submittal and has the following comments:\r\n\r\n1.	Information protection or security is the practice of defending electronic or physical information from unauthorized access, use, disclosure, disruption, modification, perusal, inspection, recording or destruction.  The submitted documents shall be revised to show in-house systems within ICC that shall ensure information security, authenticity and integrity.\r\n2.	Software or hardware or mechanical systems used to protect data shall be highlighted.\r\n3.	Methods of limiting Computer Access to sensitive project data on ICC computers and file servers, etc; shall be provided.\r\n4.	Data protection in case of natural disasters shall be included.\r\n5.	Information protection shall also provide methods employed to ensure correctness of data, revision controls, archiving systems and security of document control systems.\r\n6.	KAUST Security system is a sensitive project and all data, drawings and specifications shall be kept secure and confidential. ', 3, 'sent', '2013-05-22');
INSERT INTO `review` VALUES(93, 140, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(94, 152, 33, '', 1, 'sent', '2013-05-22');
INSERT INTO `review` VALUES(95, 145, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(96, 146, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(97, 153, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(98, 154, 33, 'The submittal is rejected as it does not provide the required information as given below;\r\n(1) Dated Schedule of planned Constructability reviews.\r\n(2) Stages at which constructability reviews shall take place are not sufficient, e.g. Post development, pre-construction, mid-constriction and post construction, pre-procurement, post procurement etc. shall be included.\r\n(3) Constructability reviews are a cross-check of construction documents for accuracy, completeness, and systems coordination issues and to find inconsistencies between plans and specifications. These reviews shall also highlight limitations of access for work to be conducted. \r\n(4) Compatibility of materials, List of foreseen complexities envisaged during construction, Necessary Coordination of selective trades, Sequencing and project scheduling etc shall be checked\r\n(5) Team members/ experts for constructability reviews shall be mentioned\r\n(6) How and when the construction teams be reviewed for maximum efficiency and monitored with respect to the schedule requirements.\r\n(7) There is no need to rewrite the project specifications and a one small paragraph shall be sufficient to describe the nature of the project.\r\n(8) Plans provided with submittal are irrelevant as no constructability issues if any are explained\r\n(9) How and when traffic shall be managed during construction\r\n(10) How and when security issues be reviewed and handled during construction\r\n(11) What safety related problems are envisaged and how and when shall they be reviewed/ handled.\r\n(12) How existing under ground utilities shall be taken care of and what might become an obstacle and how and when will it be resolved.\r\n(13) How is the project phased and how will the manpower and equipment be allocated/ divided/ managed\r\n(14) older reviews shall be used as an appendix and not a part of the original document.\r\n(15) The document is poorly organized with appendices as well as attachments and pictures with no connection with the paras in the document or captions. ', 4, 'sent', '2013-05-22');
INSERT INTO `review` VALUES(123, 29, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(124, 163, 33, '1. The candidate does not have sufficient and relevant engineering design experience or the qualification levels to manage a project of diverse nature such as the Kaust Perimeter Security System. \r\n\r\n2. ICC shall adhere with the positions/ nominations made during the bid submission.\r\n', 4, 'sent', '2013-06-02');
INSERT INTO `review` VALUES(125, 158, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(126, 157, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(127, 159, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(128, 166, 11, 'No further comment. The Proposed format is approve.', 1, 'sent', '2013-08-24');
INSERT INTO `review` VALUES(129, 164, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(130, 168, 11, 'To obtain a final approval, the candidate must pass the Final Interview of Saudi Aramco Inspection Representative (SAIR). ', 2, 'sent', '2013-08-03');
INSERT INTO `review` VALUES(131, 169, 11, 'The subject submittal complies with all the previous comments.\r\n\r\nNo more further comment.', 1, 'sent', '2013-08-03');
INSERT INTO `review` VALUES(132, 174, 11, 'No more further comment', 1, 'sent', '2013-08-03');
INSERT INTO `review` VALUES(133, 177, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(134, 177, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(135, 177, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(136, 178, 21, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(137, 178, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(138, 178, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(139, 178, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(140, 190, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(141, 209, 11, 'SAPMT has reviewed your letter KPSS/SA/B/PR/SAT/13/0051 dated July 27, 2013 and has no objection, However, it is contractor’s responsibility to ensure full compliance with IFC drawings, Saudi Aramco standards and specification.', 1, 'sent', '2013-08-03');
INSERT INTO `review` VALUES(142, 203, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(144, 271, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(145, 259, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(146, 259, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(147, 261, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(148, 266, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(149, 266, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(152, 275, 25, 'OK', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(153, 274, 25, 'OK', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(154, 275, 33, 'No Comment', 1, 'sent', '2013-11-25');
INSERT INTO `review` VALUES(156, 282, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(157, 282, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(158, 282, 47, 'no comment', 1, 'sent', '2014-06-23');
INSERT INTO `review` VALUES(159, 283, 47, 'no comment', 1, 'sent', '2014-06-23');
INSERT INTO `review` VALUES(160, 283, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(161, 283, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(162, 289, 47, 'no comment', 1, 'sent', '2014-06-23');
INSERT INTO `review` VALUES(163, 291, 47, 'no comment', 1, 'sent', '2014-06-23');
INSERT INTO `review` VALUES(164, 298, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(165, 301, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(166, 233, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(167, 189, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(168, 303, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(169, 304, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(170, 305, 11, 'No comment', 1, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(171, 306, 25, 'Accepted via SAP', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(172, 307, 25, 'Accepted via SAP', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(173, 308, 25, 'Accepted via SAP', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(174, 309, 33, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(175, 311, 11, 'No comment in my side. This is civil materials.', 2, 'sent', '2013-10-01');
INSERT INTO `review` VALUES(176, 310, 25, 'Agreed', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(177, 312, 25, 'ICC shall expedite submission of MOM to SAPMT as discussed in the meeting. Every action item shall be assigned a date of completion. The commitment dates shall be respected and changed only after SAPMT approval. Every MOM shall reflect the date of the next meeting.', 2, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(178, 312, 11, 'No comment', 1, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(179, 312, 47, 'no comment', 1, 'sent', '2014-06-23');
INSERT INTO `review` VALUES(180, 312, 45, 'MOM is in order', 1, 'sent', '2013-12-03');
INSERT INTO `review` VALUES(181, 313, 47, 'no comment', 1, 'sent', '2014-06-23');
INSERT INTO `review` VALUES(182, 313, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(184, 237, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(185, 303, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(186, 320, 47, 'No comment', 1, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(187, 320, 11, 'No comment', 1, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(188, 319, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(189, 319, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(190, 321, 47, 'The final weekly report is been finalised by ICC scheduler and SAPMT', 3, 'sent', '2013-10-08');
INSERT INTO `review` VALUES(191, 321, 11, '1. Procured materials (Major Items) shall be mentioned and highlighted. \r\n2. All Purchased Order (PO) copy''s must be provided for PMT reference. The amount can be hide and deleted.', 2, 'sent', '2013-10-01');
INSERT INTO `review` VALUES(192, 322, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(193, 322, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(194, 318, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(195, 318, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(196, 318, 12, '', 0, 'sent', '');
INSERT INTO `review` VALUES(197, 323, 47, 'My comments\r\n1. the existing culvert is not reflected on the IFC drawings, please provide\r\n2. provide a detailed cross section on the culvert and indicate if the existing width of the culvert is enough or will requires extension and by how much.\r\n3. Dwg KA-714498-002 indicates some utilities will be carried by KAM and some by ICC, please clarify since all the road works are under ICC.\r\n4. Please indicate all the locations of all existing utilities\r\n5. provide a method / composite drawing showing all the interfacing.\r\n6. provide the details of the electrical foundation structures, connection details, steel structure details', 2, 'sent', '2013-10-02');
INSERT INTO `review` VALUES(198, 323, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(199, 323, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(200, 323, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(201, 323, 11, '\r\n1. Procured materials (Major Items) shall be mentioned and highlighted.\r\n2. All Purchased Order (PO) copy''s must be provided for PMT reference. The amount can be hide and deleted.', 2, 'sent', '2013-10-01');
INSERT INTO `review` VALUES(202, 324, 47, 'No Comment', 1, 'sent', '2013-10-27');
INSERT INTO `review` VALUES(205, 324, 25, 'This Method Statement is acceptable for areas where there are no interfaces with underground or above ground  utilities. ICC shall submit a separate method statement for every location with a problem that requires a special procedure. Mention the Quality/ RFI requirements for verification of depths and elevations. Nevertheless, it is contractors responsibility to meet with the Saudi Aramco Quality and Safety standards.// ', 1, 'sent', '2013-09-30');
INSERT INTO `review` VALUES(207, 332, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(208, 328, 47, 'No Comment', 1, 'sent', '2013-10-27');
INSERT INTO `review` VALUES(209, 328, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(210, 328, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(211, 328, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(212, 329, 11, '1. ICC shall communicate with STC in all related excavation works and to follow strictly rules and procedure in the method of statement. \r\n2. ICC shall provide topographical drawings to be attached with the work permit showing the cable markers to easily identify the location.\r\n3. ICC shall also communicate with all service providers, contractors that has interface with KPSS project  as stated in schedule B of the contract.', 2, 'sent', '2013-10-01');
INSERT INTO `review` VALUES(213, 329, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(214, 330, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(215, 330, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(216, 331, 47, 'ICC to ensure compliance with both ARAMCO standards and the manufactures application methods. ', 1, 'sent', '2013-10-03');
INSERT INTO `review` VALUES(217, 331, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(218, 331, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(219, 331, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(220, 257, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(221, 333, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(222, 333, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(223, 333, 11, 'Comments were incorporated in e-review.', 2, 'sent', '2013-10-21');
INSERT INTO `review` VALUES(224, 333, 47, 'provide design elevation coordinates on all structures and utilities\r\nPlease refer to DWG VA-847146-001-00 Detail 3;Section B_B; change the internal dimension 6000 mm to 600 mm and 4000 mm to 400mm. And also provide fitting details of the steel plate coveras well as the operation and maintenance arragement.', 2, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(225, 333, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(226, 334, 11, 'comments has been forwarded in e-review.', 1, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(227, 334, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(228, 334, 47, 'Icc to ensure that all shop drawing are issued with a correct and approved numbering to avoid number dublication, proper tracing when the need arrises.', 1, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(229, 334, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(230, 334, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(231, 336, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(232, 336, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(233, 337, 57, '', 1, 'sent', '2013-10-08');
INSERT INTO `review` VALUES(234, 337, 11, '1. In the submitted sub-contracting plan it was noticed that Mechanical and Electrical Works were not included in the submitted sub-contracting plan. it is assumed that ICC will take care of it, as per their contractual obligation. \r\n\r\n2. It is the contractors responsibility to ensure full compliance with the contract specification, and aramco standards.', 2, 'sent', '2013-10-12');
INSERT INTO `review` VALUES(235, 338, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(236, 338, 11, '1. In the submitted sub-contracting plan it was noticed that Mechanical and Electrical Works were not included  in the submitted sub-contracting plan. it is assumed that ICC will take care of it, as per their contractual obligation.\r\n\r\n2. It is the contractors responsibility to ensure full compliance with the contract specification, and aramco standards.', 2, 'sent', '2013-10-12');
INSERT INTO `review` VALUES(237, 338, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(238, 338, 47, 'No comment.', 1, 'sent', '2013-10-26');
INSERT INTO `review` VALUES(239, 338, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(240, 340, 12, 'No comment, It seems he is qualified we will give him approval for 6 months to see his work quality ', 1, 'sent', '2013-10-09');
INSERT INTO `review` VALUES(241, 340, 47, 'The CV looks ok, and shows that he is better qualified.\r\nAcceptance/ rejection will be determined after the interview, if passed the 3 month probation as per employment standards. ', 2, 'sent', '2013-10-08');
INSERT INTO `review` VALUES(242, 340, 11, 'The candidate is pre-approve for three months and subject for re-evaluation after the probationary period.\r\n\r\n\r\n\r\n', 2, 'sent', '2013-10-07');
INSERT INTO `review` VALUES(243, 339, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(244, 339, 11, 'No comment.', 1, 'sent', '2013-10-07');
INSERT INTO `review` VALUES(245, 339, 47, 'No comment', 1, 'sent', '2013-10-08');
INSERT INTO `review` VALUES(247, 284, 25, 'DRAFT Referring to 50% Detailed Design Drawings and Comment No 68 from Kaust, such as “Provide 90 days recording for all systems i.e. IDAS and IP-CCTV and SACS Cameras “. After detailed discussions with the designer and security sub-contractor, your above request impacts the scope of work as follows; 1. The approved FSD being a part of the Kaust approved Project Proposal mentions in para 5.12 that, “Recorded videos of both fixed and PTZ cameras of the associated alarmed IDAS zone shall be stored and available for investigative viewing upto thirty (30) days from the date the video was captured. 2. According to recently revised security directives, HCIS para 4.2.16 also requires the same 30 days as mentioned above. (Note that HICIS has been changed from 90 days to 30 days.) 3. Changing the storage capacity from 30 to 90 days in addition to 50% free space, is an exponential increase which effects not only the quantity of servers, but also the number of racks and ultimately the size of the room. 30 day storage requires a storage capacity of approximately 430 TB; whereas 90 day storage shall require approximately 2400TB space. Thus almost 80U of extra rack space shall be required and the existing room does not have enough space.', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(248, 341, 11, '1. For MoM item number 15, 16 & 17, The power requirements for the vehicle x-ray machine was not included in the 50% and 90% detail design. Contractor must resolve the voltage conflict from 230 volts line to neutral into 230 volts line to line.\r\n2. Vehicle x-ray contractor must share the power requirements of their machine not only the voltage requirement but also the power rating and amperage.\r\n3. For MoM item number 22, Contractor must ensure that sharing the UPS system for both UVIS and Vehicle X-ray machine is sufficient and calculation must be provided.\r\n4. In any case that the permanent power is not yet available for the vehicle x-ray, it is the responsibility of the contractor to ensure that temporary power is available to operate the vehicle x-ray for testing and commissioning.\r\n5. The human interface machine shall be installed as per manufacturer recommendation.\r\n6. All electrical and civil works, must be reviewed comprehensively by SCEC designer to ensure that the vehicle x-ray machine installation requirements will be met.', 2, 'sent', '2013-10-21');
INSERT INTO `review` VALUES(249, 341, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(250, 343, 32, '', 0, 'sent', '');
INSERT INTO `review` VALUES(251, 344, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(252, 344, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(253, 345, 32, '', 0, 'sent', '');
INSERT INTO `review` VALUES(254, 346, 32, '', 0, 'sent', '');
INSERT INTO `review` VALUES(255, 348, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(256, 348, 32, '', 0, 'sent', '');
INSERT INTO `review` VALUES(257, 348, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(258, 349, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(259, 349, 11, '1. So many drawings for security systems are still not available in the 90% detail design package. ICC should share this drawings for further review prior issuing any IFC drawings for security systems.\r\n\r\n2. The proposed date for the final IFC drawings should not be applicable to the drawings which is missing in the 90% detail design.', 2, 'sent', '2013-10-12');
INSERT INTO `review` VALUES(260, 349, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(261, 350, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(262, 350, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(263, 350, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(267, 350, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(268, 351, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(269, 351, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(270, 351, 32, '', 0, 'sent', '');
INSERT INTO `review` VALUES(271, 352, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(272, 352, 47, 'No comment', 1, 'sent', '2013-10-26');
INSERT INTO `review` VALUES(273, 352, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(274, 352, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(275, 353, 47, 'ICC to comply with comments made during MST for earthworks review and also all the specifications to be adhered to.', 2, 'sent', '2013-10-27');
INSERT INTO `review` VALUES(276, 353, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(277, 353, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(278, 354, 47, 'All stockpile material should be kept away from overhead cables and existing MH on site.\r\nICC QA/QC to provide a schedule to visit to borrow pit and SAPMT to conduct servilience on site as and when is necessary.', 2, 'sent', '2013-10-26');
INSERT INTO `review` VALUES(279, 354, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(280, 355, 32, '', 0, 'sent', '');
INSERT INTO `review` VALUES(281, 355, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(282, 356, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(283, 357, 47, '•Show detailed extent, position/level of Geo-grid and Geotextile layers.\r\n•Provide ditch design complete with profile, direction of  flow, discharge points, designed invert levels, detailed ditch type and cross sections but not limited to the foregoing. \r\n•Provide complete culvert (if any) design hydraulic and structural.', 2, 'sent', '2013-10-27');
INSERT INTO `review` VALUES(284, 357, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(285, 354, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(286, 359, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(287, 359, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(288, 359, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(289, 359, 32, '', 0, 'sent', '');
INSERT INTO `review` VALUES(290, 162, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(291, 361, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(292, 364, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(293, 364, 11, 'The fence to ditch area were covered by the video object detection feature of the camera. Once the intruder climb and jump from the fence it is automatically detected by the camera and will give an alert status, And finally once the intruder reach the sensor zone of the microwave it will give a major alarm to the security operators thru alarm management system of IDAS.\r\n\r\nThus the claim of the proponent can be rejected.', 4, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(294, 364, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(295, 360, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(296, 360, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(297, 360, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(298, 365, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(299, 365, 11, 'Sir,\r\n\r\n1. The letter is in arabic.\r\n2. SAPMT/KAUST should finalize and make action to this concern the soonest possible time to avoid any double job, in case of relocation of cables.\r\n', 3, 'sent', '2013-10-12');
INSERT INTO `review` VALUES(300, 366, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(301, 367, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(302, 367, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(303, 367, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(304, 369, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(305, 369, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(306, 370, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(307, 370, 57, '', 0, 'sent', '');

INSERT INTO `review` VALUES(309, 371, 12, '1- Provide a plan to how deal with Mangrove\r\n2- Method of statement shall include  a plan to relocate the existing fence in the lagoon\r\n', 3, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(310, 371, 47, 'My Comments\r\n#ICC to provide shop drawings indicating the start and end point for individual relocation''s\r\n#ICC to indicate which materials are they going to use for temporary fence\r\n#The material to be used must comply with Aramco standards as well as National guard requirements\r\n#ICC to indicate the degree of safety they will use to maintain the safety of unauthourised personnel trespassing to KAUST\r\nICC to provide a detailed sequence of works for relocation; to build the temporary fence first and remove the existing fence nor to remove the existing fence first and use the materials to construct the temporary fence later.', 2, 'sent', '2013-10-24');
INSERT INTO `review` VALUES(311, 371, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(312, 373, 12, '1-provide accurate plan how  to deal with mangrove for this project  \r\n2-proposed location to replant the mangrove \r\n', 3, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(313, 373, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(314, 373, 47, 'My Comments"\r\n#To change the word"sages to stages, on the first line under the heading No. 1 Introduction\r\n#ICC to install profiles on the road reserve and indicate all the area affected\r\n#ICC to indicate the methods of transplantion, ie dig manually up to root level or use equipment/ machine to carry out the works\r\n#ICC to include the schedule of mangrove transplantation on the main schedule or separately as the schedule provided is not clear/ or doesn''t indicate any mangrove relocation\r\n#ICC to include the proposed areas to be used as temporary transplantation on "Appendix 02"', 2, 'sent', '2013-10-24');
INSERT INTO `review` VALUES(315, 372, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(316, 372, 47, 'No comment', 1, 'sent', '2013-10-24');
INSERT INTO `review` VALUES(317, 374, 12, 'No comment ', 1, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(318, 374, 47, 'No Comment', 1, 'sent', '2013-10-24');
INSERT INTO `review` VALUES(319, 374, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(320, 372, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(321, 368, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(322, 375, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(324, 375, 11, 'No comment', 1, 'sent', '2013-10-22');
INSERT INTO `review` VALUES(326, 377, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(327, 377, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(328, 376, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(329, 376, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(330, 375, 32, '', 0, 'sent', '');
INSERT INTO `review` VALUES(331, 375, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(354, 380, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(355, 380, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(356, 380, 11, '1. Provide the coordinates of the proposed location.\r\n2. Mobily and KAUST has to investigate and agree in the proposed location. ', 2, 'sent', '2013-10-29');
INSERT INTO `review` VALUES(357, 380, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(371, 378, 23, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(373, 381, 47, 'No comment', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(374, 381, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(375, 383, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(376, 383, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(377, 382, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(378, 382, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(379, 410, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(380, 410, 47, '#Aramco responded to the first submittal and not all the request were replied to;\r\n# provide the GPS coordinates of the borrow pit location and where it is and not the name only\r\n#provide the layout plan of the proposed stockpile area/ location\r\n#Provide a proposal schedule for visiting the borrow pit area\r\n#provide the delivery note from the borrow pit company or alternatively provide their stamp on Ayash delivery note  ', 2, 'sent', '2013-10-29');
INSERT INTO `review` VALUES(381, 410, 12, 'incomplete method of statement', 4, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(382, 411, 47, 'NO COMMENT', 1, 'sent', '2013-10-30');
INSERT INTO `review` VALUES(383, 411, 12, 'no comment', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(384, 411, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(385, 412, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(386, 412, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(388, 413, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(389, 413, 47, '# please provide a soft copy and hard of all the submittals to ARAMCO\r\n#provide clear and readable copies on every submittal\r\n#provide a catalogue showing the materials to be used', 2, 'sent', '2013-10-30');
INSERT INTO `review` VALUES(390, 414, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(391, 414, 47, 'No comment', 1, 'sent', '2013-11-03');
INSERT INTO `review` VALUES(392, 414, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(393, 415, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(394, 415, 47, '#Provide color copies on all your catalogues submission\r\n#The final approved materials description to be confirmed on the IFC drawings\r\n#Provide readable copies on all your submissions', 2, 'sent', '2013-11-03');
INSERT INTO `review` VALUES(396, 417, 32, 'No Comments', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(397, 417, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(398, 417, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(399, 404, 11, '1. The definition as per FSD is acceptable, however in relation with the moving of Microwave sensor 1 meter towards ditch, Contractor has to justify and provide sufficient coverage calculation to support the 95% claim. \r\n2. State also the time impact.', 2, 'sent', '2013-11-03');
INSERT INTO `review` VALUES(400, 404, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(401, 404, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(402, 405, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(403, 406, 12, 'the Elcitrcal duct bank shal be concured by SCEC \r\n.prodide list od DCL drwaings \r\n. Provide Auto-CAD drawings ', 3, 'sent', '2013-11-06');
INSERT INTO `review` VALUES(404, 406, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(405, 406, 11, '1. As agreed in MoM # 6, all shop drawings has to be concurred by the designer.\r\n2. The top of the ductbank shall have a red oxide cement for utility identification and in addition a yellow electrical marker tape must be laid prior final backfilling.\r\n3. Use bell end on both edge of the ductbank.\r\n4. Specify the number of spare.\r\n5. Specify the material to be used.\r\n6. Provide cross section profile of the ductbank showing the ditch and the underground IDAS, Transformers, and Perimeter lighting cables.\r\n7. The installation and construction of ductbank shall be in accordance with Saudi Electric Company Standard, SAES P-104 and NFPA-70.', 3, 'sent', '2013-10-29');
INSERT INTO `review` VALUES(406, 406, 47, '#provide a detailed design showing the elevation coordinates, rebar design since this duct bank will be under the ditch, patrol/ national guard road, and the precast wall.\r\n#provide the composite drawing showing the interface with all the structures as mentioned above\r\n#Provide an alternative cable routing if any, and reflect the variance in cost implications \r\n#All the duct banks to be designed and constructed as per Aramco standard', 2, 'sent', '2013-10-29');
INSERT INTO `review` VALUES(407, 407, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(408, 408, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(409, 418, 12, 'the revised report has not been attched ', 3, 'sent', '2013-11-03');
INSERT INTO `review` VALUES(410, 418, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(411, 409, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(412, 409, 47, '# discussed in the meeting dated 23 October, 2013 IC was requested to define mobilization based on:total  number of personnel proposed both on site and office and site office completion; IC to change mobilization of 30 % to 15%, IC site offices from 10 % to 5% and Aramco offices5% to 2.5%\r\n#Site preparation works done at this stage was grading only, Ic to change 25% to 15 %', 2, 'sent', '2013-11-03');
INSERT INTO `review` VALUES(414, 409, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(415, 409, 32, '* Claim on Issue of 100% IFC(1.1.100) is not acceptable. Still 90% Review only in Progress.\r\n* Claim on Site Prepration(1.3.2.1.10) is progressed 31%(Cumulative). So, Contractor claim 40% Shall be resuced to 31%.', 3, 'sent', '2013-10-31');
INSERT INTO `review` VALUES(416, 409, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(417, 416, 32, 'No Comments', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(418, 416, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(419, 420, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(420, 419, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(421, 419, 11, 'SAMPT needs to negotiate with KAUST/STC in relation with underground FIBER optic cables, The cable detector being used is not 100% accurate. \r\n\r\nIf we hit this fiber optics, they might charged us million of riyals, due to service operational issue.\r\n\r\n', 2, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(422, 419, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(423, 423, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(424, 423, 47, 'No comment', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(425, 423, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(426, 422, 11, '1. Contractor to fully implement the approved methodology in dealing with the list of interface provided.\r\n2. The interface list provided is not yet final, for we are encountering supprises just like the underground water line. ICC to closely monitor and study comprehensively all possible underground utilities.', 2, 'sent', '2013-11-04');
INSERT INTO `review` VALUES(427, 422, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(428, 422, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(429, 421, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(430, 421, 11, 'SAMPT needs to negotiate with KAUST/STC in relation with underground FIBER optic cables, The cable detector being used is not 100% accurate. \r\n\r\nIf we hit this fiber optics, they might charged us million of riyals, due to service operational issue.', 2, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(431, 421, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(432, 424, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(433, 424, 47, 'No comment', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(434, 425, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(435, 425, 47, 'ensure that the surface is thoroughly cleaned before application and maintain the cleanness prior to concrete casting ', 2, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(436, 426, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(437, 426, 47, 'Confirm the water temperature to be used; the correct temperature should be kept constant throughout the entire operation as well as the use of ice(steam / normal ice block)', 2, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(438, 427, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(439, 427, 47, 'No comment', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(440, 428, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(441, 429, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(442, 429, 47, 'No comment', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(443, 428, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(446, 428, 12, 'no comment ', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(447, 429, 12, 'no comments ', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(448, 431, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(449, 431, 11, 'SAMPT needs to negotiate with KAUST/Mobily in relation with underground FIBER optic cables, The cable detector being used is not 100% accurate. \r\n\r\nIf we hit this fiber optics, they might charged us million of riyals, due to service operational issue.', 2, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(450, 431, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(451, 384, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(452, 384, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(453, 385, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(454, 385, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(455, 386, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(456, 386, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(457, 387, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(458, 387, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(459, 388, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(460, 388, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(461, 389, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(462, 389, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(463, 435, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(464, 435, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(465, 435, 32, '•	Plan dates shall be filled against “Pâ€ instead of “Fâ€. Forecast Dates shall be provided only when there is slippage expected in Plan Dates. It has to be filled against “Fâ€.\r\n•	Planned Dates for few items are already exhausted in Procurement Plan. For Example: Ready Mix concrete, Filler Board, Curing Agent, Concrete Repair, Bonding Agent, etc.,\r\n•	S Curve shall highlight the Recovery Curve along with Recovery Progress %.\r\n', 3, 'sent', '2013-11-06');
INSERT INTO `review` VALUES(466, 434, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(467, 434, 47, 'The contractor to provide a utilities detector machine on site before carrying all the excavations, and it should be followed by the signatures of all the foremen, operator and site engineers witnessing the testing and then it should be forwarded to SAPMT for confirmation.\r\nAll excavation machinery must have a sportter/ banksman who will be located at a clear sight distance\r\nfrom the machinery and the excavated area at all times.', 2, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(468, 434, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(469, 433, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(470, 433, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(471, 437, 11, '1. ICC has to work closely with other contractors in which they have interface.\r\n2. ICC has to provide interface status on every interface concern.\r\n3. ICC has to ensure that all interface concerns were highlighted and listed.\r\n4. All interface concerns has to be shared with SCEC to reflect in the IFC drawings.', 2, 'sent', '2013-11-08');
INSERT INTO `review` VALUES(472, 437, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(473, 437, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(474, 437, 47, '#provide the coordinates of all the existing utilities, all the coordinates must be sent to the designer and should be included on the final designer with all the proposals from the service providers.\r\n#A detailed composite drawing design should include all the utilities and how they will interface with each other.\r\n# All the correspondence must be kept and recorded for interfacing up to design, construction and commissioning stages \r\n', 2, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(475, 438, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(476, 438, 11, 'No comment.', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(477, 438, 32, 'No Comments', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(478, 439, 12, 'no comment', 1, 'sent', '2013-11-05');
INSERT INTO `review` VALUES(479, 439, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(480, 439, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(481, 440, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(482, 440, 11, 'No comment', 1, 'sent', '2013-11-12');
INSERT INTO `review` VALUES(483, 441, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(484, 441, 11, 'No comment', 3, 'sent', '2013-11-12');
INSERT INTO `review` VALUES(485, 441, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(486, 442, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(487, 442, 11, 'No comment.', 2, 'sent', '2013-11-12');
INSERT INTO `review` VALUES(488, 390, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(489, 391, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(490, 391, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(491, 391, 45, '\r\nThe 4-months HSE Implementation Plan should be attached as part of the minutes to show commitments of ICC Management.', 3, 'sent', '2013-12-03');
INSERT INTO `review` VALUES(492, 392, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(493, 392, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(494, 392, 45, 'Please attached in the minutes of meeting the 4-months Proposed HSE Implementation Plan containing the 13 points discussion to be implemented from September to December 2013. Attach the signed and agreed document.', 3, 'sent', '2013-12-03');
INSERT INTO `review` VALUES(495, 393, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(496, 393, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(497, 393, 45, '\r\nOkay in order as stated.', 1, 'sent', '2013-12-03');
INSERT INTO `review` VALUES(498, 394, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(499, 394, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(500, 394, 45, '\r\nIn order however there was no participation from SAPMT c/o Mark Vernon/Shibin ', 2, 'sent', '2013-12-03');
INSERT INTO `review` VALUES(501, 395, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(502, 395, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(503, 395, 45, '\r\nNo comment. it is in order', 0, 'sent', '2013-12-03');
INSERT INTO `review` VALUES(504, 396, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(505, 396, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(506, 397, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(507, 397, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(508, 398, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(509, 398, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(510, 399, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(511, 399, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(512, 400, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(513, 400, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(514, 401, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(515, 401, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(516, 402, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(517, 402, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(518, 403, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(519, 403, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(520, 445, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(521, 445, 11, 'SCEC has to review once again the approved project proposal documents versus the 90% submittal document number VE-846472 page 64 of 68. As per KAUST comment item number 179, 185, 193, and 202, phase 800 instrumentation work has been introduce wherein, there is no such instrumentation appendix approved project proposal document.\r\nDrawing PA-00381 and PA-000363 of 100% project proposal and IFB drawings, has never mentioned connecting the DDC to BMS or having allotted workstation in the JFCC control room. SAPMT thru ICC/SCEC has to finalize and define this additional requirement to KAUST since this VE-846472 page 64 of 68 document was already submitted to them.', 2, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(522, 445, 47, '', 0, 'sent', '');
INSERT INTO `review` VALUES(523, 444, 11, '1. SAPMT has to write letter with building 102 SAPMT manager to advise Saudi Bin Laden Contractor that ICC are using the access gate (Bin Laden Gate) being monitored by SBG security personnel''s, in relation with BI-25-00026 King Abdullah Monument Access road project.\r\n2. Interface coordinator of ICC has to work closely with SBG security to obtain access requirements.\r\n3. ICC has to ensure that all of his personnel''s including its sub-contractors has valid KAUST ID. ', 2, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(524, 444, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(525, 444, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(526, 449, 47, 'IC to expedite on MOM review submission to SAPMT as discussed in the meeting.', 2, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(527, 449, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(528, 449, 25, 'ICC shall expedite submission of MOM to SAPMT as discussed in the meeting. Every action item shall be assigned a date of completion. The commitment dates shall be respected and changed only after SAPMT approval. Every MOM shall reflect the date of the next meeting.', 2, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(529, 449, 11, '1. ICC has to respect commitment dates stated in the Minutes of the Meeting.\r\n2. The MoM has to be shared with SAPMT a day after the progress meeting for counterchecking of the minutes.\r\n3. It has been noticed that entry date has not been reflected in every new item being highlight during the progress meeting.\r\n ', 2, 'sent', '2013-11-08');
INSERT INTO `review` VALUES(530, 449, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(531, 450, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(532, 451, 25, 'The letter shall be forwarded to KAUST. ICC to ensure that conduits/ ductbanks/ sleevs are placed as per future requirements of SEC', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(533, 451, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(534, 451, 47, 'SEC to provide a standard drawing to IC and IC must get a design concurrence from the consultant\r\nThe consultant to provide a detailed drawing taking into consideration the interfacing with the Ditch, fence and all the other utilities along the corridor.', 2, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(535, 451, 11, '1. ICC has to submit the final electrical ductbank coordinates and layer arrangement for Saudi Electric Company (SEC) and KAUST approval.', 2, 'sent', '2013-11-08');
INSERT INTO `review` VALUES(536, 452, 25, 'ICC shall ensure that sleeves/ ductbanks/ conduits are placed as per future requirements of Mobily', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(537, 452, 12, 'will forward to KAUST ', 1, 'sent', '2013-11-10');
INSERT INTO `review` VALUES(538, 452, 47, 'IC to provide a detailed utilities interfacing drawing with all the coordinates,a clear drawing reference number and not a hand written sketch/ overall survey layout drawing.\r\nIC to follow up on all the items promised by Mobily and then provide the design concurrence from SCEC.', 2, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(539, 452, 11, '1. It is the responsibility of SAPMT and KAUST to negotiate with MOBILY in relocating the existing Fiber Optic Cables.\r\n2. While the construction is in progress, and no further agreement with MOBILY is taking place, ICC must implement its full safety in taking care of the existing underground cable by using approved methodological procedure in excavating with existing utilities.\r\n', 2, 'sent', '2013-11-08');
INSERT INTO `review` VALUES(540, 453, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(541, 453, 25, 'No Comment', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(542, 453, 12, 'no comment ', 1, 'sent', '2013-11-10');
INSERT INTO `review` VALUES(543, 455, 11, '1. ICC must conduct exploration complying with the approved method of statement prior any excavation works.\r\n', 2, 'sent', '2013-11-11');
INSERT INTO `review` VALUES(544, 455, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(545, 456, 47, 'IC to provide SAPMT the expected delivery date of all the site vehicle and their dedicated personnel.\r\nIC must from time to time provide the transport to personnel who requires to use the toilet facilities.', 2, 'sent', '2013-11-10');
INSERT INTO `review` VALUES(546, 456, 11, 'For comment a : ICC has to provide immediate standby vehicle to assist personnel''s that will be using toilets.\r\nFor comment b : ok\r\nFor comment c : ok\r\nFor comment d : ok', 2, 'sent', '2013-11-11');
INSERT INTO `review` VALUES(547, 456, 12, 'please try to provide Portable toilets next week\r\n\r\nPlease confirm/ ensure that your camp is well lit in the dark and the night watchman is on duty Also, your Safety, Quality and Site Management staff should have separate means of transportation.\r\n\r\n', 2, 'sent', '2013-11-10');
INSERT INTO `review` VALUES(548, 455, 12, 'SAPMT will send letter to KAUST ', 1, 'sent', '2013-11-10');
INSERT INTO `review` VALUES(549, 457, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(550, 457, 12, 'ICC safety team must be sure that  workers are following safety rules in the site ', 2, 'sent', '2013-11-10');
INSERT INTO `review` VALUES(551, 458, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(552, 458, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(553, 459, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(554, 459, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(555, 460, 12, 'accepted ', 1, 'sent', '2013-11-10');
INSERT INTO `review` VALUES(556, 461, 12, 'no comment as SAPMT has alreday sent a letter for the subject letter ', 1, 'sent', '2013-11-10');
INSERT INTO `review` VALUES(557, 461, 11, '1. ICC has to expedite the material take of list (MTO), with the corresponding inspection level agreed with VID representative.\r\n', 2, 'sent', '2013-11-11');
INSERT INTO `review` VALUES(558, 463, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(559, 463, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(560, 462, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(561, 462, 12, 'no comment ', 1, 'sent', '2013-11-09');
INSERT INTO `review` VALUES(563, 465, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(564, 465, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(567, 460, 25, 'The appointment of Mr Anwar Shammout is acceptable and ICC is advised to ensure that shuffling of key roles is not sudden and prevalant through out the life of the project.', 2, 'sent', '2013-11-12');
INSERT INTO `review` VALUES(589, 467, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(590, 467, 25, 'Mr Quino is acceptable as a design coordinator for the duration of the project and to work as an engineering manager temoporarily. Meanwhile ICC shall make all necessary and prompt arrangements to submit CVs for a separate engineering manager suited for the job before 30 November 2013.', 2, 'sent', '2013-11-12');
INSERT INTO `review` VALUES(591, 468, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(592, 468, 25, 'Refer to the reply regarding this issue already being drafted...', 3, 'sent', '2013-11-19');
INSERT INTO `review` VALUES(593, 471, 25, 'Already consolidated', 2, 'sent', '2013-11-19');
INSERT INTO `review` VALUES(594, 471, 11, 'No comment', 1, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(595, 471, 47, '#GRADING/ LEVELLING COMPLETED FROM CH 5+700 TO 8+800 = 3100 KMS AND THAT INCLUDES THE 2NO. GATES 2/3 AND THE CABLE/ PIPE CROSSINGS\r\n#SOME AREAS HAVE EXCAVATION AND SOME ONLY BACKFILLING, BECAUSE CLEARLY DEFINE YOUR AREA LIMITATION.\r\n#THERE IS NO AREA WHICH REQUIRES BOTH EXCAVATION AND BACKFILLING, SO PLEASE DEFINE YOUR TABLE CORRECTLY.', 2, 'sent', '2013-11-16');
INSERT INTO `review` VALUES(596, 471, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(597, 461, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(598, 472, 32, 'No Comments', 1, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(599, 472, 12, 'no comment ', 1, 'sent', '2013-11-24');
INSERT INTO `review` VALUES(600, 472, 11, 'Undelivered Items in SA office as per SCHEDULE B of the contract\r\n\r\nSOFTWARE (latest version) to accommodate the above computers:\r\n\r\n•	Latest MS Office Professional and MS Visio Professional\r\n•	Latest Adobe Acrobat Professional\r\n•	Latest PRIMAVERA P6\r\n\r\n4.4.7	Fire Alarm System \r\n\r\n	  manual call points strategically located \r\n\r\n5.1.5	Large Conference Room\r\n\r\n	Conference rooms shall include the following features:\r\n\r\nï‚§	Latest model of Polycom spider phone or equivalent with national dial access (phone jack under conference table)\r\n\r\n\r\n8.0	OFFICE SHREDDERS\r\n\r\n	The specified shredders shall be WILHELM DAHLE BURO-TECHNIK GMB or equivalent with the following specifications.  Solid wooden cabinet, For extremely sensitive documents, Compact Design, Easy to use, Feed width 400mm, Shred capacity A4 70 gsm 8-10 sheets, Shred Speed 15 m/min, Shred Size 2x15 mm Heavy Duty Shredder, Cross Cut, 12 Sheet Capacity, 37 liters.\r\n', 2, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(601, 472, 47, '#GRADING FOR KAM ACCESS ROAD AND OTHER AREAS TO BE AS PER THE RFI RAISE AND SIGNED BY SAPMT.\r\n#MONTHLY REPORT SHOULD CONSIST OF ALL THE COMBINED WEEKLY REPORTS AND AGREED BY SAPMT WITH ALL THE BACKUPS IN PLACE.\r\n#GRADING/ LEVELLING COMPLETED FROM CH 5+700 TO 8+800 = 3100 KMS AND THAT INCLUDES THE 2NO. GATES 2/3 AND THE CABLE/ PIPE CROSSINGS #SOME AREAS HAVE EXCAVATION AND SOME ONLY BACKFILLING,CLEARLY DEFINE YOUR AREA LIMITATION. #THERE IS NO AREA WHICH REQUIRES BOTH EXCAVATION AND BACKFILLING, SO PLEASE DEFINE YOUR TABLE CORRECTLY.\r\n#ANY OTHER AREA OTHER THAN THOSE DEFINE FOR GRADING TO BE AGREED WITH SAPMT(CH 8+900 - 14+450)', 2, 'sent', '2013-11-16');
INSERT INTO `review` VALUES(602, 473, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(603, 473, 32, 'No comments', 1, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(604, 474, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(605, 474, 32, 'No Comments', 1, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(606, 475, 47, '#Provide names and signatures on the front page of the Method statement submission', 2, 'sent', '2013-11-17');
INSERT INTO `review` VALUES(607, 475, 11, 'No comment. I would recomment if this submittal be shared also with the following CIVIL engineers PMT.\r\n1. Jonathan\r\n2. Abu Hanifa\r\n3. Zackaria', 0, 'sent', '2013-11-16');
INSERT INTO `review` VALUES(608, 475, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(609, 475, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(610, 476, 12, 'no comment ', 1, 'sent', '2013-11-24');
INSERT INTO `review` VALUES(611, 476, 32, 'No Comments', 1, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(612, 476, 47, 'No comment', 1, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(613, 476, 11, 'No comment', 1, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(614, 477, 12, 'no comment ', 1, 'sent', '2013-11-24');
INSERT INTO `review` VALUES(615, 477, 47, 'No comment', 1, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(616, 477, 11, 'No comment', 1, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(617, 477, 32, 'No Comments', 1, 'sent', '2013-11-14');
INSERT INTO `review` VALUES(618, 478, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(619, 478, 11, 'Provide the following documents:\r\n1. Proof of placement and acceptance by Vendor and Purchase Order PO) copy. \r\n2. Storage handling and preservation of the X-ray machine.', 2, 'sent', '2013-11-17');
INSERT INTO `review` VALUES(620, 478, 12, 'As per schsule C CONTRACTOR shall invoice SAUDI ARAMCO for the Major Materials Price detailed in Pricing Attachment I upon the achievement of each of the following milestones to SAUDI ARAMCO’s satisfaction:\r\n\r\n1. Ten percent (10%) of the Major Materials Price allocated to each separable Major Materials item upon CONTRACTOR’s placement of SAUDI ARAMCO-approved purchase order for such item and providing SAUDI ARAMCO with proof of placement and acceptance by Vendor.\r\n2. Seventy percent (70%) of the Major Materials Price allocated to each separable Major Materials item on shipment of such item, including all its parts, by the supplier(s) thereof to CONTRACTOR in Saudi Arabia supported by the supplier''s proof of shipment from the country of origin to Saudi Arabia.\r\n3. Twenty percent (20%) of the Major Materials Price allocated to each separable Major Materials item on final receipt of such item, including all its startup spare parts and non-material requirements by CONTRACTOR at the WORK Site.\r\n', 4, 'sent', '2013-11-24');
INSERT INTO `review` VALUES(621, 479, 11, 'ESE has conducted a site investigation on November 7 and 10, 2013 to validate the availability of the switches and if available ports does exists:\r\n\r\n1. For Gate 2 and 3 guardhouses, data switch and vacant ports are available.\r\n2. For IRC building, data switch and vacant ports are available.\r\n3. For SONAR shelter # 1, data switch and vacant port is not available.\r\n4. For Marine Building, available data switch and vacant ports are available.\r\n\r\nFor buildings that have available switches and ports item number 1, 2 & 4 of the above, it is the responsibility of ICC/ESE to identify the port assignment to be used and provide technical reasoning to justify the request of usage.\r\n\r\nFor Sonar shelter # 1, it was already known and highlighted before that the nearest King Abdullah Monument Communication Room will be covering the necessary port assignment for the Emergency Notification System (ENS).\r\n\r\nThe marine building has been identified as the existing boat house near the yatch club and KAUST Beacon.\r\n\r\nRelated drawings for KAM and Marine Building or Boat House will be provided for your reference.', 3, 'sent', '2013-11-17');
INSERT INTO `review` VALUES(622, 479, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(623, 479, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(624, 480, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(625, 480, 11, 'The correct stationing was not reflected.', 3, 'sent', '2013-11-23');
INSERT INTO `review` VALUES(626, 480, 12, 'no comment ', 1, 'sent', '2013-11-25');
INSERT INTO `review` VALUES(627, 484, 47, 'No further comment', 1, 'sent', '2013-11-19');
INSERT INTO `review` VALUES(628, 484, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(630, 485, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(631, 486, 32, 'No comments', 1, 'sent', '2013-11-19');
INSERT INTO `review` VALUES(632, 486, 11, 'No comment..             ', 1, 'sent', '2013-11-23');
INSERT INTO `review` VALUES(633, 486, 47, '# Check spelling before any submittal to Aramco; refer to progress summary, change 200 ml to 200 m each side of gate # 2 and -------(missing info)\r\n# SAPMT still waiting for IFC for Ditch and Perimeter Fence final review prior to construction(Engineering)\r\n# verify the percentages allocated under construction - external civil works', 2, 'sent', '2013-11-19');
INSERT INTO `review` VALUES(634, 486, 12, 'PROVIDE PICTUE FOR MAJOR WORK IN THE MOM', 2, 'sent', '2013-11-24');
INSERT INTO `review` VALUES(635, 483, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(636, 483, 12, 'no comment ', 1, 'sent', '2013-11-25');
INSERT INTO `review` VALUES(637, 481, 25, 'To be sent by email: Provide a more legible copy of the accreditation and ensure that it is valid at the time of testing.', 3, 'sent', '2013-11-19');
INSERT INTO `review` VALUES(638, 482, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(639, 482, 11, 'The list provided is not the updated list. \r\n* The updated feedback from SAPID and meeting clarification held on November 14, 2013 with SCEC was not included in the list.\r\n* SCEC updated response with LPD comments was not included.', 3, 'sent', '2013-11-23');
INSERT INTO `review` VALUES(640, 487, 47, '# as agreed all the rebar numbers/ quantities,cutting and bending will be fully detailed on the shop drawing bar bending schedule. ', 2, 'sent', '2013-11-21');
INSERT INTO `review` VALUES(641, 487, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(642, 487, 12, '\r\nSubmit Method Statement for Construction the Precast Concrete Fence on the lagoon \r\nSubmit Method Statement for  installation  the Precast Concrete Fence \r\nSubmit all implanted precast material for approval prior to installation\r\n', 2, 'sent', '2013-11-24');
INSERT INTO `review` VALUES(643, 488, 47, 'no comment', 1, 'sent', '2013-11-21');
INSERT INTO `review` VALUES(644, 488, 11, 'The drawings must contain the stamped of SCEC.', 3, 'sent', '2013-11-23');
INSERT INTO `review` VALUES(645, 489, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(646, 489, 47, '# INSPECTION ASSIGNMENT PACKAGE PLAN TO BE SIGNED BY ALL ICC IN CHARGE\r\n# NMR/ DRAWING ATTACHED IS AN OLD COPY, PLEASE ATTACH THE LATEST APPROVED IFC DRAWING\r\n# MOST PAGES/ HEADING IN THIS DOCUMENT HAVE BEEN TIPEXED', 2, 'sent', '2013-11-20');
INSERT INTO `review` VALUES(647, 485, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(648, 493, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(649, 492, 11, 'Long range surveillance system LRSS has a dedicated fiber connected to KAUST Network as shown in the BID drawing PA0001006 sht 003. ICC/ESE has to provide technical justification for deviating the scope of work.', 3, 'sent', '2013-11-23');
INSERT INTO `review` VALUES(650, 492, 30, '', 0, 'sent', '');
INSERT INTO `review` VALUES(651, 491, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(652, 490, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(653, 496, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(654, 496, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(655, 496, 11, 'No comment', 1, 'sent', '2013-11-20');
INSERT INTO `review` VALUES(656, 495, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(657, 494, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(658, 498, 10, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(659, 497, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(660, 497, 11, 'As stated in the approved project proposal document, crash rated bollard will be provided in WADI Khulais.\r\n\r\nPE-000002 para. 1.2.2.1.1 bullet 5 states that Culvert at Wadi Khulais to support the route of the new fence with the provision of crash rated bollards and security grill at flood control channel, and construction of concrete slab towards sea-outfall immediately after the proposed box culvert in coordination with Thuwal Town flood control project.', 2, 'sent', '2013-11-23');
INSERT INTO `review` VALUES(661, 499, 47, 'All structural IFC must be signed or stamped by the the designer/ SCEC, before the review by SAPMT', 3, 'sent', '2013-11-20');
INSERT INTO `review` VALUES(662, 500, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(663, 500, 47, 'NO COMMENT', 1, 'sent', '2013-11-24');
INSERT INTO `review` VALUES(664, 501, 11, 'Communication drawings for King Abdullah Monument Project and Water Sports Facility will be provided in a CD. SAPMT reiterates that it is the responsibility of the contractor to evaluate and investigate the existing conditions of the data switches and manholes in IRC building and Water Sports Facilities for design accuracy.\r\n', 2, 'sent', '2013-11-25');
INSERT INTO `review` VALUES(665, 501, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(666, 502, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(667, 502, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(668, 502, 12, 'The security procurement schedule is missing', 3, 'sent', '2013-11-25');
INSERT INTO `review` VALUES(669, 503, 11, 'It is regularly noticed in the advance copy of MoM provided to SAPMT for review, that new entries with target dates were not incorporated and included in the list of action items. SAPMT reiterates that it is the obligation of the contractor as per contract schedule B 5.6.5 to list down all action items without any missing notes which was highlighted and discussed during progress meeting.\r\n\r\nContractor is advise to ensure that everything must be listed and monitored.\r\n', 2, 'sent', '2013-11-26');
INSERT INTO `review` VALUES(670, 503, 12, 'provide pictures for project progress  in the MOM ', 2, 'sent', '2013-11-24');
INSERT INTO `review` VALUES(671, 504, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(672, 504, 47, 'No comment', 1, 'sent', '2013-11-24');
INSERT INTO `review` VALUES(673, 506, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(674, 506, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(675, 507, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(676, 507, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(677, 507, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(678, 508, 12, 'no comment ', 1, 'sent', '2013-11-25');
INSERT INTO `review` VALUES(679, 509, 47, '#ICC to make sure that during relocation of the fence the security system is not compromised.\r\n#Provide a proper sketch showing all your logistics routing.\r\n#provide the location with coordinates for your proposed storage area and new temporary fence respectively\r\n', 2, 'sent', '2013-11-28');
INSERT INTO `review` VALUES(680, 509, 11, '1. Provide the CV/resume of the personnels that will be relocating the IDAS.\r\n2. The submitted method of statement needs to be signed by the QA manager and not by QC manager.\r\n3. Downtime for IDAS relocation was not included.\r\n4. Include the breakdown and quantity of PTZ, Fixed, Poles and FEC that will relocated.\r\n5. Since it was already highlighted that existing FOC cable cannot be removed, ICC/ESE to highlight the proposal to route new FOC cables.\r\n6. ICC/ESE must nominate interface coordinator to start accumulating the required documents to KAUST IDAS O&M.\r\n7. This method of statement does not mention any single word for the existing lights and its panelboards. Provide the plan for this lighting system for this is part of relocation.\r\n8. Provide detail sequence of events from removal of IDAS to storage handling and preservation, and vice versa from storage to erection.\r\n', 3, 'sent', '2013-11-27');
INSERT INTO `review` VALUES(681, 509, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(682, 509, 12, 'provide accurate  plan for the point which will start the location of existing  fence system', 3, 'sent', '2013-11-25');
INSERT INTO `review` VALUES(683, 510, 45, ' \r\n1. The Environmental Impact Register (EIR) included mitigating measures that need to be regularly monitored and recorded to show compliance. Submit sample forms to be used in substantiating compliance efforts;\r\n2. Attach a job procedure how the relocation/transplanting of affected mangroves are done and have it coded for reference purposes. This will be used in assessing performance during implementation;and\r\n3. Finalize encoding other handwritten addenda and legend in your proposed drawing.', 3, 'sent', '2013-11-28');
INSERT INTO `review` VALUES(684, 510, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(688, 513, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(689, 513, 47, 'ICC to use use the utilities detector to avoid similar incidence in the future.\r\nICC to mark and protect the pipe for the duration of the project.\r\nICC to request and submit the AS-Built drawing of the existing water pipes from the Water Affairs Company.', 2, 'sent', '2013-11-28');
INSERT INTO `review` VALUES(690, 513, 45, 'RECEIVED REPORT: 28 NOVEMBER 2013 @ 6:30AM\r\n\r\n1. The notification to KAUST and SAPMT was done within the 24-hour reporting standard.\r\n2. Conduct thorough investigation from the witnesse/s, ICC Site Supervisor and/or Foreman and ICC Safety. This will be the FACTS and FINDINGS/OBSERVATIONS.\r\n3. Complete the final Incident Report to include the Causal Analysis; Immediate and Basic causes and costing of damages and opportunity losses to show the magnitude of the loss\r\n4. Review previous incidents of the same nature and evaluate compliances to the committed corrective and preventive actions.\r\n5. Revise and re-submit', 3, 'sent', '2013-11-28');
INSERT INTO `review` VALUES(691, 514, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(692, 514, 47, 'No comment', 1, 'sent', '2013-11-30');
INSERT INTO `review` VALUES(693, 514, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(694, 514, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(695, 515, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(696, 515, 47, 'No comment', 1, 'sent', '2013-11-30');
INSERT INTO `review` VALUES(697, 515, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(698, 516, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(699, 516, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(700, 516, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(701, 516, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(702, 517, 12, 'no comment ', 1, 'sent', '2013-12-01');
INSERT INTO `review` VALUES(703, 517, 47, 'No comment', 1, 'sent', '2013-11-30');
INSERT INTO `review` VALUES(704, 517, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(705, 518, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(706, 518, 47, 'NO COMMENT', 1, 'sent', '2013-11-28');
INSERT INTO `review` VALUES(707, 518, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(708, 518, 12, 'no comment ', 1, 'sent', '2013-12-01');
INSERT INTO `review` VALUES(709, 523, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(710, 523, 12, 'no comment ', 1, 'sent', '2013-12-01');
INSERT INTO `review` VALUES(711, 523, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(712, 521, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(713, 519, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(714, 520, 12, '\r\nMTO schedule  for security and communication  are not provided\r\n', 3, 'sent', '2013-12-02');
INSERT INTO `review` VALUES(715, 520, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(716, 522, 45, '1. The investigation is limited to the activity done on the day of the incident. It did not mention that a backhoe was used some 2 to 4 days prior which could have struck the pipe with a minor dent and was aggravated by repeated vibration of passing HE vehicles atop that de-scaled the incrustated old metal pipe.\r\n2. Review the corrective actions in the 1st incident of this nature in order to see which of them is implemented and not. Are the controls in the Work Permit for excavation complied and enforced by the Supervisors? Did they use the metal detector as per condition in the work permit?\r\n3. Convene a meeting between concern supevisors, witnesses if any, Safety and the Project Manager to finalize your action plan to prevent recurrence. Do not forget the reccommendations in the first pipe damage incidents and compliance to the excavation work permit.\r\n4. To be discussed by supervisors during the toolbox meeting and Weekly Safety Committee meeting.', 3, 'sent', '2013-11-28');
INSERT INTO `review` VALUES(717, 522, 12, 'no comment ', 1, 'sent', '2013-12-01');
INSERT INTO `review` VALUES(718, 527, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(719, 525, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(720, 526, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(721, 526, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(722, 526, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(723, 524, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(724, 528, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(725, 528, 12, 'ICC to inform Inspection department  about Internal quality Audit and provide report once completed', 2, 'sent', '2013-12-02');
INSERT INTO `review` VALUES(726, 529, 45, ' The comments were effected by ICC HSE.', 2, 'sent', '2013-12-03');
INSERT INTO `review` VALUES(727, 530, 21, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(728, 531, 47, '#this MTO is for all the buildings structural and architectural take off however the following is missing for both SG #2 & 3\r\nSG#2\r\nProvide K-9 Shelter MTO\r\nProvide the Inspection Pit MTO\r\n\r\nSG#3\r\nProvide the inspection Pit MTO\r\nProvide Packing Shades MTO\r\n# It is the contractors responsibility to provide the MTO to avoid any justification or delay in payments because of insufficient information.\r\n# ICC QS to review this MTO and raise all the concerns before the submittal to SAPMT for review.\r\n#ICC to provide a breakdown every activity on site to the nearest unit area for review by SAPMT so that all the works carried on site can be paid before a completed item can be build. ', 2, 'sent', '2013-12-05');
INSERT INTO `review` VALUES(729, 531, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(730, 532, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(731, 532, 12, 'no comment ', 1, 'sent', '2013-12-01');
INSERT INTO `review` VALUES(732, 533, 12, '•	Reference your letter KPSS/SA/B/ANW/13/0235 dated November 30,2013, SAPMT has repeated requested ICC  by letters and verbal to provide a method statement showing as to how ICC shall conduct detection surveys to ensure protection of underground utiltities, to be used for detection, which ICC has failed to provide\r\n•	ICC has to comply with  schedule A clause 5.3 ‘’CONTRACTOR shall protect from damage all existing structures, improvements or utilities at or near the WORK Site, and shall repair and restore any damage thereto resulting from CONTRACTOR''s failure to exercise reasonable care in protecting the same during CONTRACTOR''s performance of the WORK.  If CONTRACTOR fails or refuses to promptly repair any such damage, SAUDI ARAMCO may perform such repairs, or have them performed by others.  Paragraph 15.2 shall control with respect to CONTRACTOR''s financial liability arising from or related to such damage’’.\r\n\r\n•	Also it is mention clear in schedule A clause 7.6 &26.2 , ICC Performs all other obligations required of it by the terms of this Contract in such time and manner as to facilitate the orderly prosecution of the WORK .\r\n•	In the schedule A 26.2 The term "force majeure" as used in this Contract shall mean any act, event, cause or occurrence rendering a party unable to perform its obligation which is not within the reasonable control and not caused by the negligence or fault of such party. SAPMT has right to reserve all right as ICC negligence to follow   \r\n', 4, 'sent', '2013-12-03');
INSERT INTO `review` VALUES(733, 534, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(734, 534, 12, 'no comment ', 1, 'sent', '2013-12-01');
INSERT INTO `review` VALUES(735, 535, 12, 'ICC to make sure and confirm  all subcontractors personals  have medical insurance', 3, 'sent', '2013-12-01');
INSERT INTO `review` VALUES(736, 536, 45, ' The credentials from the submittal are good, however we request the following to be satisfied:\r\n   \r\n   1. Schedule an interview meeting with the applicant on Wednesday, 11November 2013 at 1:30PM in which he\r\n      should bring the original or certified true copies of training certificates earned in HSE;\r\n   2. Bring along with him his College Diploma/Certificate and Trancript of Records  to suffice the   \r\n      educational background and Certificates of employments;\r\n   3. Include in his CV, a recent colored 2X2 ID photo, personal information, work experiences  stating the \r\n      start and end of each employment and a summary of assigned duties and responsibilities per position;\r\n   4. Since he is an active employee of your Company in one of your Projects, I suggest that you re-assign\r\n      him for a week in this Project to initially assess his capability as an HSE Manager; and\r\n   5. As per my initial evaluation on the submitted credentials, his exposure is mostly of Safety Officer or\r\n      Senior Safety Supervisor and not as a HSE Manager.\r\n \r\n The intent of this submittal is to officially replace Mr. Yassir Azam as the HSE Manager from your \r\n organization and should the latter comes back into the Project, he will undergo the same process as a \r\n new applicant.\r\n\r\n', 0, 'sent', '2013-12-04');
INSERT INTO `review` VALUES(737, 536, 25, 'Pulled Back by ICC', 4, 'sent', '2013-12-09');
INSERT INTO `review` VALUES(738, 537, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(739, 537, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(742, 538, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(743, 538, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(744, 538, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(745, 539, 12, 'ICC to provide  the type more details of detection equipment which is used   in the project ', 3, 'sent', '2013-12-04');
INSERT INTO `review` VALUES(746, 539, 47, 'no comment', 1, 'sent', '2013-12-04');
INSERT INTO `review` VALUES(747, 540, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(748, 541, 12, 'no comment ', 1, 'sent', '2013-12-10');
INSERT INTO `review` VALUES(749, 541, 45, 'Please take note of my comments, as follows:\r\n \r\n1. The Environmental Impact Register (EIR) included mitigating measures that need to be regularly monitored and recorded to show compliance. Submit sample forms to be used in substantiating compliance efforts;\r\n2. Attach a job procedure how the relocation/transplanting of affected mangroves are done and have it coded for reference purposes; \r\n3. Include in your procedure the materials, supplies and equipment compliments i n the implementation;\r\n4. Come up with a definite action plan for the implementation; and\r\n5. Finalize encoding other handwritten addenda and legend in your proposed drawing.\r\n6. Revise and resubmit.\r\n\r\n*** When do we see your Environmental Protection/Pollution Control Officer on board? ***', 0, 'sent', '2013-12-04');
INSERT INTO `review` VALUES(750, 542, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(751, 542, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(752, 544, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(753, 545, 12, 'no comment ', 1, 'sent', '2013-12-10');
INSERT INTO `review` VALUES(754, 545, 47, 'MOM#11 was reviewed and all corrections were done and sent back to ICC to action.\r\nICC to report all the issues discussed in the meeting and not delete any item unless reported closed.', 2, 'sent', '2013-12-04');
INSERT INTO `review` VALUES(755, 546, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(756, 546, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(757, 546, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(758, 547, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(759, 548, 33, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(760, 548, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(761, 548, 47, '#ICC to expedite on the recruitment of the construction and engineering manager as they void is always exposed because the current personnel does not have the capacity to handle both construction and engineering issues.\r\n#The current 2 No. QC personnel''s are overloaded and cannot coordinate properly with the construction team.\r\n#2 No. site engineers and foremen are urgently required who have the valid experience and knowledge of planning, coordinating and handling concrete works.\r\n#The current ICC survey team is inactive as all the works are by subcontrator i.e FCC / Ayash\r\n', 2, 'sent', '2013-12-08');
INSERT INTO `review` VALUES(762, 550, 30, 'With refernce to your subject letter dated December 8, 2013, SAPMT has reviewed your letter with the following comments:\r\n\r\n1. Any changes required by the proponent (KAUST) to the scope of work without official documentation and proper channel is not acceptable.\r\n2. ICC/ESE is responsible to ensure the project scope of work is applied without fail in the detail design package with full functionality.\r\n3. For locating the IPCCTV cameras, you must ensure that it will cover all facilities of gatehouses, parking lots and vehicle inspection areas as per Project Proposal Document PE-000002.', 4, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(763, 550, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(764, 551, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(765, 551, 12, 'ICC to provide two weeks look ahead for RFI', 3, 'sent', '2013-12-10');
INSERT INTO `review` VALUES(766, 551, 47, '#QA/QC personnel to liase with the construction team or project manager to plan the activities accordingly with specific locations and not generalize the sequence of works.', 2, 'sent', '2013-12-08');
INSERT INTO `review` VALUES(767, 552, 12, 'no comment ', 1, 'sent', '2013-12-10');
INSERT INTO `review` VALUES(768, 552, 45, '1. The suggested presentation of 1tem 8.1 should be in landscape matrix format composed of 4-coulumns and labelled ON TOP starting from the leftmost coulumn ACTIVITIES/ ENVIRONMENTAL ASPECTS/ ENVIRONMENTAL IMPACTS/MITIGATING MEASURES or CONTROLS. You can now include the timetable of implementation and responsibility so make it an action plan similar to Appendix L. It was repeatedly suggested in the previous coordination and Safety Committee meetings to include your presentation following your Appendix "L" format so it can be managed.\r\n2. All the possible mitigating measures or controls are enumerated from 8.2 to 8.11, this is alright however the expectation as to when you will implement your controls to mitigate the impacts to the workplace is indefinite and can not be audited whether you are living up to your commitments or not. In fact, at this point in time, SAPMT should be receiving environmental performance updates from your end.\r\n3. Your submittal coded ICC/104/MS/004 - MS on mitigating measures to minimize project impact on flora and fauna is an example of a detailed proposal how you will be doing your program in addressing the impact to the affected mangrove area. On a summarized format, you can reduce it to conform with your Item 14 in Appendix "L".\r\n4. It is very necessary for ICC to refer Item 8.7 to KAUST HSE Department for comments by furnishing them a copy of your proposal in handling the disturbance of the mangrove in the KAM Access Road. \r\n5. Revise and re-submit', 3, 'sent', '2013-12-10');
INSERT INTO `review` VALUES(769, 552, 47, 'No Comment', 1, 'sent', '2013-12-08');
INSERT INTO `review` VALUES(770, 549, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(771, 549, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(773, 553, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(774, 554, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(775, 555, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(776, 556, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(777, 557, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(778, 557, 47, '#A meeting was held between all parties concerned and SEC to provide the start and finish date of this works.\r\n#electricity to be de-energised before any removal by SEC.', 2, 'sent', '2013-12-12');
INSERT INTO `review` VALUES(779, 557, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(780, 558, 47, 'This report was sent back to ICC for corrections, the report is misleading and not presented propoerly.\r\nI had numerous meetings with the project controller and the site engineers and advised them not to use the daily report that is sent to us everyday without my comments or reviews.', 4, 'sent', '2013-12-12');
INSERT INTO `review` VALUES(781, 558, 32, 'No Comments', 1, 'sent', '2013-12-15');
INSERT INTO `review` VALUES(782, 559, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(783, 559, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(784, 561, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(785, 561, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(786, 561, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(787, 562, 65, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(788, 563, 47, '#IC to update the utilities matrix each time a new utility is discovered\r\n#IC to protect and own the utilities up until the utility owner diverts or abandon it.\r\n#IC to reflect all the utilities on the officicial drawing, to be red lined and shown on the as-built at the completion of the project.', 2, 'sent', '2013-12-14');
INSERT INTO `review` VALUES(789, 563, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(790, 564, 47, 'No comment', 1, 'sent', '2013-12-12');
INSERT INTO `review` VALUES(791, 564, 45, '1. Item 5; The presentation of methodology in accessing and performing the cited activity must be specific following the tasks or procedural steps in the Risk Assessment Matrix. The approach done is good however, it should be catered to the actual job needing the Confined Space Entry (CSE)procedure.\r\n2. The chronological arrangement of tasks in item 11-JSEA is incomplete. The order should be from "start-to- finish". Unless the team will stay inside the culvert forever.\r\n3. Refer to Safety Process #3- Confined Safety Entry Permit of the Saudi Aramco Safety Handbook, pp 11 to 13,5th Edition as the minimum requirement.\r\n4. A gas testing must be administered to determine oxygen deficiency and presence of other toxic gases.\r\n5. Conduct pre-entry briefing to all concerned team before the activity.\r\n6. An Emergency Preparedness and Response Team should be organized and stationed near/outsde the work area.\r\n7. Aside from the CSE permit, other required permit such as Cold Work Permit, hot work permit, or other applicable work permits should be complied prior to the activity.\r\n8. Revise and Re-submit', 3, 'sent', '2013-12-13');
INSERT INTO `review` VALUES(792, 564, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(793, 565, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(794, 565, 12, 'approved ', 1, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(795, 566, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(796, 566, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(797, 566, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(798, 566, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(799, 567, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(800, 568, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(801, 569, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(802, 570, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(803, 570, 47, '# ICC was advised to follow their scope of works which the said culvert is not part of.\r\n# The logic behind the culvert backfilling is understandable however since all our works requires excavation, ICC to create a berm not to allow any water to damage their structures.\r\n# The backfilling of the culvert should be treated like the areas where the MOT road was stopped pending the Municipality action- removal of tenants', 3, 'sent', '2013-12-16');
INSERT INTO `review` VALUES(804, 570, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(805, 571, 47, 'Please refer to the rejected daily and weekly report and correct accordingly', 4, 'sent', '2013-12-16');
INSERT INTO `review` VALUES(806, 571, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(807, 572, 47, 'No comment', 1, 'sent', '2013-12-12');
INSERT INTO `review` VALUES(808, 572, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(809, 572, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(810, 573, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(811, 573, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(812, 573, 47, 'NO comment', 1, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(813, 573, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(814, 574, 47, '#ICC to provide the details and highlight the materials that requires reviewing instead of submitting the whole package to SAPMT.\r\nE.g Geotextile - Alyaf A301 and Geogrid - BI-AX 3030', 3, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(815, 574, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(816, 574, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(817, 575, 12, '\r\n\r\n1-ICC to make sure the proposal electrical cables does not interface with the existing facilities as CSD gate is congested  for existing facilities\r\n\r\n2- In the second option shall provide cable tray two culverts \r\n\r\n\r\n', 3, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(818, 575, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(819, 576, 47, '#ICC were requested to take notes during the meeting for a proper recording and documentation\r\n#ICC to rectify all the correction and resubmit the MOM as revision 01', 2, 'sent', '2013-12-15');
INSERT INTO `review` VALUES(820, 576, 12, 'no comment ', 1, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(821, 576, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(822, 577, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(823, 577, 47, 'No Comment', 1, 'sent', '2013-12-16');
INSERT INTO `review` VALUES(824, 577, 12, 'ICC to insure all agreed with inspection shall be documented ', 2, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(825, 577, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(826, 578, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(827, 578, 47, 'No comment', 1, 'sent', '2013-12-16');
INSERT INTO `review` VALUES(828, 578, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(829, 578, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(830, 581, 30, '1. ICC shall conduct actual site survey to locate all the affected existing facilities and cables with reference to the coordinates mentioned in the as-built drawings.\r\n2. ICC shall propose methods of securing the cables used for both SONAR and RADAR without affecting or interrupting the service.\r\n3. A schedule plan detailing the activities and duration of works has to be included and submitted for approval.\r\n4. ICC/ESE shall submit list of personnel with certifications approved by ARAMCO on performing the fiber cable splicing, termination and testing.', 2, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(831, 581, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(832, 581, 12, 'provide  complete Method Statement for Removal and re-installation of existsing fence \r\nprvoide accurate  information   which area will be started  the relocation\r\nprovide a plan ICC how to deal with the power of   existing Readr and Sonar \r\n', 3, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(833, 581, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(834, 582, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(835, 582, 12, 'provide  complete Method Statement for Removal and re-installation of existsing fence \r\nprvoide accurate  information   which station  will be started  the relocation\r\nprovide a skitch for chain-link fence between naval bast and KASUT land \r\nmore details to deal with exisitings RADAR and SONAR\r\n \r\n', 3, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(836, 583, 47, 'no comment', 1, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(837, 583, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(838, 583, 12, 'ICC to provide table sheet and date for RFI  two weeks look ahead \r\nICC QC staff must check the quality of work before issues RFI \r\nICC quality team must be presented during major activates ex.  pour concrete \r\n', 3, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(839, 583, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(840, 584, 47, 'NO COMMENT', 1, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(841, 584, 12, 'ICC to insure no water comes from outer side  to the ditch', 3, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(842, 584, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(843, 584, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(844, 586, 30, 'SAPMT has reviewed your subject letter and has the following comments:\r\n1. Upgrading of the existing KAUST eRAM software is under the full responsibility of the contractor as part of integration to existing SACS as per FSD-002, Section 3.1.2 and 3.1.3.\r\n2. Enable the propose system to provide the proper functionality and performance, the required software has to be provided by the contractor as per FSD-002, Section 3.1.5 and 3.1.6.', 4, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(845, 586, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(846, 588, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(847, 588, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(848, 589, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(849, 589, 47, 'no comment', 1, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(850, 589, 12, 'no comment ', 1, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(851, 590, 47, 'no comment', 1, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(852, 590, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(853, 587, 30, 'Note: To be addressed to KAUST, Nabeel Sharqawi\r\n\r\nWith reference to last Communication System Meeting dated December 8, 2013, please find the attached updated Minutes of Meeting with the latest bandwidth calculation and network diagram to close the issues related to High Level Design (HLD). However, there is one item remain open as this is pending with KAUST IT and Security to decide. Kindly let us know the final decision as soon as possible.\r\n\r\nIn addition, please be informed that any issues deviating the design in accordance to the Approved Project Proposal Document cannot be entertained unless otherwise a Purchase Change request (PCR) will be issued to SAPMT.\r\n\r\nNote: attachments to be collected from me', 2, 'sent', '2013-12-23');
INSERT INTO `review` VALUES(854, 587, 12, 'ICC to follow  on the approved project proposal', 2, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(855, 585, 32, 'Construction Progress Claim has been inflated. It shall reflect the real construction works accomplished at site and the same has to be endorsed by SAPMT.\r\n\r\nProcurement Progress may get reduced for Civil & Structural Material according to the progress measurement as agreed between SAPMT & ICC on December 16, 2013 at SAPMT office.', 0, 'sent', '2013-12-19');
INSERT INTO `review` VALUES(856, 585, 12, 'In the Progress highlights for the week , ICC to explain why project in the construction  and procurement are  behind schedule and what the action shall be taken  it\r\n\r\nICC to provide a plan for activities  will be started  for two weeks \r\n', 3, 'sent', '2013-12-17');
INSERT INTO `review` VALUES(857, 585, 47, '#ICC still disregarding SAPMT comments to rectify the information as reflected on site.', 4, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(858, 585, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(859, 591, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(860, 591, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(861, 591, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(862, 591, 12, 'ICC to set date when NCR will be closed ', 2, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(863, 592, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(864, 592, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(865, 592, 47, '# ICC to follow the correct procedure if they are planning to use a new vendor; please refer to the comment by SAPMT materila specialist;.\r\n1.	Please use the correct 9Com number along with the specified description for that 9Com number.\r\n2.	9Com#6000000597 is for ANCHOR,HOLLOW WALL &MASONARY, but the submittal is for Lifting & Fixing socket for Precast.\r\n3.	In the material submittal specify the Correct material along with the description as per the 9Com.\r\n4.	Specify the Vendor ID number starting from 100…….. or 300……..\r\n5.	Material has to be procured through approved vendor.\r\n\r\nSTATUS: REJECTED. D.\r\n', 4, 'sent', '2013-12-19');
INSERT INTO `review` VALUES(866, 593, 47, 'NO COMMENT', 1, 'sent', '2013-12-19');
INSERT INTO `review` VALUES(867, 593, 12, 'no comement ', 1, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(868, 593, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(869, 594, 12, 'Provide Data sheet for proper detector for fiber optical cable \r\nICC is responsible for any damage for any cable in the site \r\n', 2, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(870, 594, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(871, 594, 47, '#ICC was instructed to purchase a cable detector that is capable of detecting all kinds of utilities e.g water/sewer pipes upvc/HDPE/RTR, fibre optic cables,electrical or non electrical cables etc.\r\n', 2, 'sent', '2013-12-18');
INSERT INTO `review` VALUES(872, 594, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(873, 595, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(874, 595, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(875, 595, 30, '1. Provide letter of Compliance from Design Consultant, SCEC that all the comments on the 90% review has been complied and incorporated in the IFC for all discipline.\r\n2. Provide certification letter or stamp with design consultant concurrence to all Communications and Security drawings. Certification shall indicate that the OSP and SCS design has been reviewed by a certified BICSI/RCDD Engineer.\r\n3. Cross section details of duct banks and direct buried cables installed in trenches are incorrect due to violation to Saudi Aramco Standards SAES-T-624 and SAES-T-911.\r\n4. In gate house #2 and #3 area, all fiber optic cables shall be placed inside the duct banks provided with the cable pulling tension calculations. Orientation of telecom manholes has to be corrected in accordance to the standard. Also provide all the coordinates, stations and curves of duct banks and manholes.\r\n5. Fiber cabling assigned to SHQ and BDC shall be installed inside duct banks. Correct the type of fiber cable used inside duct banks and direct buried.\r\n6. High level Design (HLD) shall be revised in accordance to SAPMT/KAUST comments.\r\n7. Drawing for Emergency Notification System (ENS) shall be corrected in accordance to SAPMT comments.\r\n8. Service Manhole Construction details violates Saudi Aramco Standard Drawing.\r\n9. Fiber Optic Cable Budget Link Loss Calculation shall be provided.\r\n10. All rack mounted UPS to be provided and installed for all new buildings shall be under this project scope of work. UPS sizing calculation shall be provided.\r\n11. Grounding Bus Bar shall be provided to all communication room.\r\n12. Most of the comments of SAPMT during the 90% review has yet not complied.\r\n ', 3, 'sent', '2013-12-26');
INSERT INTO `review` VALUES(876, 595, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(877, 595, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(878, 596, 47, 'No comment', 1, 'sent', '2013-12-22');
INSERT INTO `review` VALUES(879, 596, 12, 'ICC shall reply for SAPMT letter Preliminary Incident Report - 003(DS165)', 3, 'sent', '2013-12-22');
INSERT INTO `review` VALUES(880, 596, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(881, 596, 45, 'The notification is in order, however a final incident report of the incident must be done. The immediate and basic or root causes must be properly identified. The loss causation analysis must satisfied in order to address the basic causes at which the recommended corrective/preventive actions will be arrived at which will effectively prevent recurrence.\r\n\r\nThere should be a "lessons-learned" or recommendations in the report so it will guide ICC in effecting the needed controls.', 0, 'sent', '2013-12-22');
INSERT INTO `review` VALUES(882, 598, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(883, 598, 12, 'ICC to check the project schedule and prepare for which items interface with bis Hazza will be effected on the schedule\r\nICC to make plan how to deal with National Guard cable at Wadi Khulais and check the cable will be effected on our project \r\n', 3, 'sent', '2013-12-22');
INSERT INTO `review` VALUES(884, 598, 47, 'ICC to keep all the records/correspondance and monitor the progress up until the handover date.', 2, 'sent', '2013-12-22');
INSERT INTO `review` VALUES(885, 599, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(886, 599, 47, 'No comment', 1, 'sent', '2013-12-22');
INSERT INTO `review` VALUES(887, 599, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(888, 597, 45, 'The candidate is new in the field where he is assigned to as a Safety Officer. He possesses the basic knowledge from orientations however he needs still guidance on how the theories are applied to the real working life setting. In as much that nobody from his sub-Contractor Company is willing to take the SHE responsibility, Mr. Ilyas shall be accepted meantime as a Safety Trainee and be given at least 3 months probationary to prove his competence to handle the roles of a Safety Inspector. If he is successful in hurdling the 1st 3 months starting January 01, 2014, he will be again subjected to another 3 months probation for the safety Officer position. In the event he will not pass a very satisfactory evaluation he will remain as Safety Inspector until he can prove his worth in the Team.\r\n\r\nThe candidate should be more regular and punctual in his attendance, religious in the submission of equipment checklists, prompt documentation of toolbox talks meetings, ensure compliance of his drivers/operators to the use of PPEs. He should observe timely submission of Observation Reports and/or incident reports and be participative in the resolution of concerns addressed to his Company. He should further improve the general condition of AYASH accommodation as part of his daily responsibility.', 0, 'sent', '2013-12-28');
INSERT INTO `review` VALUES(889, 600, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(890, 600, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(891, 603, 32, 'For Info.', 1, 'sent', '2014-01-09');
INSERT INTO `review` VALUES(892, 603, 47, '#ICC still not reporting the activities as discussed with the SAPMT.', 4, 'sent', '2013-12-24');
INSERT INTO `review` VALUES(893, 603, 12, 'no comment ', 1, 'sent', '2013-12-29');
INSERT INTO `review` VALUES(894, 603, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(895, 604, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(896, 604, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(897, 605, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(898, 605, 47, '#On reviewed item No.3, please ensure that there is no water penetration from the walls; the ditch design to be water tight and as per your response only the water coming from the bottom of the ditch was calculated.\r\n#On reviewed item No.5, please provide a separate shop drawing for a liquid joint sealant plus a rubber strip combination expansion joint.', 2, 'sent', '2013-12-24');
INSERT INTO `review` VALUES(899, 605, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(900, 605, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(901, 606, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(902, 606, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(903, 608, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(904, 608, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(905, 608, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(906, 607, 12, 'no comment ', 1, 'sent', '2013-12-29');
INSERT INTO `review` VALUES(907, 607, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(908, 607, 45, 'The Evacuation Drill was done in high spirit and observations were noted with positive reactions. The true evacuation started from the time the Chairman ordered the activation of the alarm until the Fire Wardens arrived at the Assembly Point and report rendered to the Chirman. It took them 4.5 minutes to evacuate the buildings. Lessons- learned from the exercise is what matters. The elapsed time is good however there are more improvements to be done.', 2, 'sent', '2013-12-28');
INSERT INTO `review` VALUES(909, 609, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(910, 609, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(911, 609, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(915, 611, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(916, 612, 45, 'In order, no comment.', 2, 'sent', '2013-12-28');
INSERT INTO `review` VALUES(917, 612, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(918, 616, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(919, 616, 32, 'Planned Dates for many items have already exhausted, \r\n\r\nFor example:\r\n\r\n- PO Placement of Interlock for Ditch  Concrete Hollow Blocks\r\n- Material Submittal for Planting Soil, Boulders, Road Signage & Markings, Plastering Accessories, Metal Doors\r\n- Material Approval for Sub base, Geo Textile, Curing Agent, Paints, etc.,\r\n- Material Submittal for Package Substations, Switch Gears, Boxes, Wires & Switches, Electrical Conduits & Fittings, Cable Trays, Fire Alarm System, Data network System, etc.,\r\n- Material Submittal for Potable & Fire Water Pipes, Valves & Acces., Fire Hydrants & Accs., Fire Extinguisher & Acces., Sewer FRP Manholes, uPVC Pipes, DDC Panel for HVAC, Diesel Generator, etc.,\r\n- PO Placement for Security and Access Control System such as Reader Interface, Badging Stations, Operator workstations, Intercom Interface, Barriers & Turnstiles, SACS LAN Network, etc., \r\n\r\nIt is the repeated comment on all revision of this document.', 3, 'sent', '2014-01-05');
INSERT INTO `review` VALUES(920, 616, 12, 'no comment ', 1, 'sent', '2014-01-05');
INSERT INTO `review` VALUES(921, 613, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(922, 614, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(923, 614, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(925, 615, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(926, 615, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(927, 617, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(928, 617, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(929, 618, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(930, 618, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(931, 620, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(932, 620, 12, 'no comment ', 1, 'sent', '2013-12-30');
INSERT INTO `review` VALUES(933, 620, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(934, 621, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(935, 621, 12, 'the target date must be provided in the minutes of meetings \r\nIC to provide date when CV of Engineering Manager will be submitted\r\n', 2, 'sent', '2013-12-30');
INSERT INTO `review` VALUES(936, 621, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(937, 622, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(938, 622, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(939, 622, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(940, 622, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(941, 623, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(942, 623, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(943, 623, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(944, 623, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(945, 627, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(946, 627, 32, 'For Information', 1, 'sent', '2014-01-09');
INSERT INTO `review` VALUES(947, 627, 12, 'In the progress highlights  for the week, ICC to provide the causes and action for any slip on the schedule ', 3, 'sent', '2014-01-05');
INSERT INTO `review` VALUES(948, 628, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(949, 628, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(951, 628, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(952, 628, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(953, 628, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(954, 629, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(955, 629, 12, '•	Remove the Garbage  and avoid to dump in material inside KAUST land not in e project area \r\n•	No screenings is allowed inside KAUST \r\n•	Provide Geotechnical report \r\n•	Submit material submittal for class-3 chain link fence for approval \r\n•	Coordinates with Rabia contractor  for interfaces \r\n', 3, 'sent', '2013-12-30');
INSERT INTO `review` VALUES(956, 629, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(957, 626, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(958, 626, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(959, 630, 45, 'The attached is "for client information" purposes since it is a "force majeure" issue. The case however, has a direct effect to the progress of the Project. Can ICC provide and expedite provision of an Employeess'' Accommodation within the vicinity of the Project to minimize exposure to the dictation of nature between Thuwal and Jeddah which most often "we do not see".', 0, 'sent', '2014-01-06');
INSERT INTO `review` VALUES(960, 630, 12, 'no comment ', 1, 'sent', '2014-01-05');
INSERT INTO `review` VALUES(961, 631, 12, 'is conditionally approved for full time and dedicated  Construction Manager position after resume and business  review•Provide complete details of the candidates including necessary certificates.. This approval is valid for three months SAPMT will revoke his approval on the base of his unsatisfactory performance and evaluation', 3, 'sent', '2014-01-05');
INSERT INTO `review` VALUES(962, 631, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(963, 632, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(964, 634, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(965, 633, 47, 'no comment', 1, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(966, 633, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(967, 635, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(968, 635, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(969, 635, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(970, 642, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(971, 639, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(972, 639, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(973, 639, 11, '1. Ensure that the Security Access Control System (SACS) software to be used are the latest and will be compatible with KAUST SACS software.\r\n2. Ensure that NEMA 4X enclosure will protect outdoor card readers.\r\n3. Ensure that the pole/stand of proximity reader is similar to the existing stand in KAUST.\r\n4. Provide Barlock processor enclosure.\r\n5. Provide the technical specification of power supply. \r\n6. Provide the technical submittal of AXIS server.\r\n7. Ensure that all major system components are included in the submittal.', 3, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(974, 639, 30, 'Ensure to provide IP-65 rating equipment such as card reader if installed outside buiding in compliance to PE-000071 Section 6.14.2.\r\n\r\nSACS shall include all related equipment and parts such as the access controller enclosure, magnetic locks, cameras, power supply and other required deliverables with reference to PE-000071 Section 3.4', 3, 'sent', '2014-01-12');
INSERT INTO `review` VALUES(975, 639, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(976, 640, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(977, 640, 47, 'NO COMMENT', 1, 'sent', '2014-01-16');
INSERT INTO `review` VALUES(978, 641, 66, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(979, 641, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(980, 641, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(981, 643, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(982, 643, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(983, 643, 66, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(984, 636, 11, '1. Ensure that drop arm barrier has the provision to interlock with the crash barrier.\r\n2. Shall comply with IFC drawing, project specification and SAES O- 116 and SAES O-123', 2, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(985, 636, 30, '1. Provide shop drawing to reflect the measurements and dimensions of the proposed drop arm in order to select the appropriate model according to the requirement.', 2, 'sent', '2014-01-11');
INSERT INTO `review` VALUES(986, 636, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(987, 636, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(988, 636, 12, 'no comment ', 1, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(989, 637, 11, '1. Ensure that table dimensions are suitable in the command and control room floor space, reflect the console dimension into equipment layout/floor plan to view space clearance.\r\n2. Ensure that the cable management and power strip are sufficient for each console.', 2, 'sent', '2014-01-15');
INSERT INTO `review` VALUES(990, 637, 30, 'A shop drawing has to be provided to detail the installation of the proposed console with the IFC drawing VA-847173 sheet 5.', 2, 'sent', '2014-01-12');
INSERT INTO `review` VALUES(991, 637, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(992, 637, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(993, 637, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(994, 638, 11, 'Shall comply with IFC drawing, SA standard and project specification.', 2, 'sent', '2014-01-15');
INSERT INTO `review` VALUES(995, 638, 30, 'Highlight the model of the turntile you are going to use wherein it has to comply according to the IFC drawing.', 2, 'sent', '2014-01-11');
INSERT INTO `review` VALUES(996, 638, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(997, 638, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(998, 638, 12, 'no comment ', 1, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(999, 644, 45, 'Define in the "Definition of Terms" who is the; Work Permit Issuer and Work Permit Receiver in the procedure. In this way, we have a clear-cut idea who will administer the "gas tests" and must ensure by now a ready instrument to be used. A log-in/log-out form should also be included as attachment. Warning signages, barricade materials and the likes should also readied in advance. Include these inputs in the procedure.', 3, 'sent', '2014-01-06');
INSERT INTO `review` VALUES(1000, 645, 45, 'The candidate is qualified as per credentials. Proceed for his immediate dispatch to jobsite.', 0, 'sent', '2014-01-06');
INSERT INTO `review` VALUES(1001, 646, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1002, 647, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1003, 647, 11, '1. Provide the bill of quantity,list of materials and the corresponding make/model for the alarm management system hardware and software.\r\n2. It is the full responsibility of the contractor to ensure that the proposed materials will meet Saudi Aramco Standard, IFC Drawing and IDAS operational requirements as per High Commission for Industrial Security (HCIS) and Functional Specification Document (FSD-02) PE-000002.', 3, 'sent', '2014-01-11');
INSERT INTO `review` VALUES(1004, 648, 11, '1. This submittal is only for License plate recognition system, UVIS and other similar system attached in the submittal shall be removed.\r\n2. Provide the equivalent lux of the proposed illuminator and ensure that it will meet or exceed the requirements of 50 lux as per appendix H document page 19 of 40.\r\n3. Ensure that the camera housing is vandal-proof as stated in appendix H document page 19 of 14.\r\n3. Ensure that the proposed LPRS gatekeeper model is a field proven system by enumerating list of projects it was installed and used.', 3, 'sent', '2014-01-11');
INSERT INTO `review` VALUES(1005, 648, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1006, 649, 11, 'Under Vehicle Inspection system (UVIS) shall comply and meet the requirements of IFC drawing and Appendix H para. 3.3.1.2 with two major items to meet or exceed with:\r\n\r\n1. UVIS illuminator must provide at least 50 LUX or better at the viewed portion of the vehicle to ensure intelligible clarity of captured image. The illuminator must be equipped with an automatic switching device such as a photo-detector switch to turn-on the illuminator on poor lighting situations. Preferred illuminator shall be the bright LED.\r\n2. Ensure that the top glass/plate of the enclosure must be impervious to scratch and should be able to withstand a car with load of up to 10 ton.\r\n3. Identify the number of IP cameras.', 3, 'sent', '2014-01-15');
INSERT INTO `review` VALUES(1007, 649, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1008, 653, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1009, 653, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1010, 652, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1011, 652, 32, 'No comments', 1, 'sent', '2014-01-09');
INSERT INTO `review` VALUES(1012, 650, 25, 'STC is looking at the cables today to see if they are live or dead. Lets wait before giving our comments to ICC. Also, we have to decide internally how much minimum clear height is necessary on the inner side of the wall while maintaining 4m on the outer side of the wall. ', 3, 'sent', '2014-01-12');
INSERT INTO `review` VALUES(1013, 650, 66, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1014, 650, 57, '1-THE DRAWINGS ARE NOT APPROVED BY THE DESIGN OFFICE.\r\n2- THE DRAWINGS SHALL SHOW THE DEFERENCE OF ELEVATION BETWEEN THE WALL AND MOT ROAD AFTER THIS MODIFICATION.\r\n', 3, 'sent', '2014-01-08');
INSERT INTO `review` VALUES(1015, 651, 25, 'A letter shall be drafted to be send the key IFC to KAUST. ////////Moreover, we shall revert to IC saying that the IFC is only partly accepted to continue with Civil works only, as still many issues related to Communications and security are still pending.', 2, 'sent', '2014-01-12');
INSERT INTO `review` VALUES(1016, 651, 66, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1017, 651, 11, 'No further comment.', 2, 'sent', '2014-01-11');
INSERT INTO `review` VALUES(1018, 654, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1019, 654, 66, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1020, 658, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1021, 657, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1022, 657, 32, 'No Comments', 1, 'sent', '2014-01-15');
INSERT INTO `review` VALUES(1023, 655, 66, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1024, 655, 11, 'Proposed vendor and shop drawings numbering system shall comply with the standard requirement of Saudi Aramco Engineering Procedure SAEP-334 para. 17 and SAES A-202.', 2, 'sent', '2014-01-11');
INSERT INTO `review` VALUES(1025, 655, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1026, 655, 30, 'List of shop drawings required for both Communications and Security shall be included and provided.', 3, 'sent', '2014-01-13');
INSERT INTO `review` VALUES(1027, 659, 45, '•	Accepts Mr. Mallick''s temporary appointment as a Health, Safety and Environmental (HSE) Safety Officer, however subject to a 3-month probationary period during which he will prove his capability in discharging the roles of the HSE position; \r\n•	SAPMT reserves the right to revoke the conditional approval if his performance is deemed unsatisfactory;\r\n.       He should pass a written test and interview which maybe administered to check his general HSE knowledge; and\r\n.       Photocopies of original College and HSE training credentials shall be submitted for verification within the probationary period.\r\n\r\n', 2, 'sent', '2014-01-12');
INSERT INTO `review` VALUES(1028, 660, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(1029, 660, 11, 'No further comment.', 1, 'sent', '2014-01-11');
INSERT INTO `review` VALUES(1030, 660, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1031, 660, 66, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1032, 661, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1033, 662, 12, 'Icc to make survey to identify  the coordinate of STC cables from KAUST North\r\n to South\r\nIcc to show in drawings which STC cables are effected by our  facilities (Fence , Ditch, etc)\r\n', 3, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(1034, 662, 57, '', 0, 'sent', '');
INSERT INTO `review` VALUES(1035, 663, 47, '#ICC to use the daily report as a baseline for this report to avoid the rejection of the monthly report as well as the monthly payment certificates.\r\n#ICC SAPMT have tried in numerous occasion to indicate to ICC which items are important for recording purpose in order to avoid and eliminate items that are misleading to other project team members.\r\n#In the beginning of the project we discussed and agreed that all the work done will be consolidated by SAPMT and ICC construction team before it is officially sent to Aramco scheduler/ costing/ QS personnel for review to avoid delay on the monthly payment certificates and that never happened since there is no capable engineer from ICC.  ', 2, 'sent', '2014-01-19');
INSERT INTO `review` VALUES(1036, 663, 12, 'no comment ', 1, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(1037, 663, 32, 'For Information. No Comments', 1, 'sent', '2014-01-15');
INSERT INTO `review` VALUES(1038, 663, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1039, 665, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1040, 664, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1041, 664, 12, 'we need to accelerate the change order in the KAM access road and push ICC to provide KAUST requirement for Fence Relocation', 2, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(1042, 664, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1043, 669, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1044, 670, 47, 'NO COMMENT', 1, 'sent', '2014-01-16');
INSERT INTO `review` VALUES(1045, 670, 32, 'For Information. No Comments', 1, 'sent', '2014-01-15');
INSERT INTO `review` VALUES(1046, 670, 12, 'provide current pic for major activities   in the project', 2, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(1047, 671, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1048, 671, 11, 'Ensure that it will comply with IFC drawing, and project specification document appendix H.', 2, 'sent', '2014-01-16');
INSERT INTO `review` VALUES(1049, 672, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1050, 672, 30, '1. Consider and include all passive equipment and make a summary list of all of these equipment.\r\n2. Attached the Structured cabling scope of work that will serve as reference.\r\n3. Fiber optic cable shall be submitted in a separate submittal and include all the details such as types, cross section and parameters of the cable.\r\n4. Fiber optic cable is inspection level 2.', 3, 'sent', '2014-01-13');
INSERT INTO `review` VALUES(1051, 672, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1052, 674, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1053, 674, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1054, 675, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1055, 675, 47, '#ICC and FCC to follow the Project Quality Plan and avoid unnecessary LBE and NCR\r\n#This Quality Plan should shared with the construction team so that they may have a better understanding of the quality requirements.', 2, 'sent', '2014-01-19');
INSERT INTO `review` VALUES(1056, 675, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1057, 676, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1058, 676, 11, 'No further comment.', 1, 'sent', '2014-01-18');
INSERT INTO `review` VALUES(1059, 676, 47, 'NO COMMENT', 1, 'sent', '2014-01-16');
INSERT INTO `review` VALUES(1060, 676, 12, 'Add Marwain comment for the OSTP must be certified as per SA standards', 2, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(1061, 677, 45, '1 Mr. Muhammad Farook Shah''s exposure to the fucntions of his current designation as FCC Safety Officer is a big surprise and adjustment to him since the implemented Saudi Aramco Practices (according to him) are more stringent than his previous employers.\r\n2. The seminar(s) attended are basic and there are no available certificates of employment to refer to in proving his Occupational Safety and Health experiences. This is observable from him when we discuss OSH issues and regular reportorial responsibilities to ICC.\r\n3. Require him to show the original credentials such as certificates of employments, original diploma and Safety Training certificates.\r\n4. He posesses an acceptable command of the English language and composition both necessary in discharging his functions.\r\n5. From the forgoing, we will give him 3-month probation starting January 01, 2013 until end of March 2014 to prove his effectiveness in handling the duties and responsibilities of his position. \r\n6. An unsatisfactory performance during the probationary period shall  be enough ground for his disqualification. ', 0, 'sent', '2014-01-16');
INSERT INTO `review` VALUES(1062, 677, 12, 'no comment ', 1, 'sent', '2014-01-14');
INSERT INTO `review` VALUES(1063, 678, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1064, 678, 30, 'Ensure to submit the shop drawing for the detailed installation of the Video Wall.', 2, 'sent', '2014-01-18');
INSERT INTO `review` VALUES(1065, 678, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1066, 679, 11, '1. Provide the dimensions of the crash barriers.\r\n2. Provide the dimensions of the remote control panel and Isometric view.\r\n3. Ensure the local power available will match with the proposed crash barrier, the proposed is 208 volts, 3phase, 4Wire, while the available power as per schedule is 400 volts 3 phase 4 Wire, 230 line to neutral.\r\n', 3, 'sent', '2014-01-15');
INSERT INTO `review` VALUES(1067, 679, 30, '1. The attached reference standard SAES-O-123 is no longer applicable. \r\n2. Ensure the proposed crash barrier will comply to SAES-O-206 Paragraph 4.4.3.\r\n3. Use 220 VAC power supply instead of 208 VAC\r\n4. Dimension and measurements shall be provided in the attached IFC drawing VA-847162 007 to indicate the required minimum distance of the barriers to other security elements such as drop arms with reference to SAES-O-203, Paragraph 4.14\r\n', 2, 'sent', '2014-01-18');
INSERT INTO `review` VALUES(1068, 679, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1069, 682, 11, '1. Ensure that the proposed video wall screen is the latest and the best video wall screen available in the market.\r\n2. Ensure that the bezel to bezel width or the screen to screen clearance shall be the least size.\r\n3. Ensure that wall brackets has future provision for spare space video wall screen as specified in drawing VA-847191 sht 005.\r\n4. Ensure that power and communication cables will be running in a workmanlike manner in the video wall bracket shop drawing must be provided.', 2, 'sent', '2014-01-18');
INSERT INTO `review` VALUES(1070, 682, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1071, 684, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1072, 684, 47, '# ICC submitted an incomplete drawing;\r\n- no cross section of the road at different chainages \r\n- no limit of works from the 2 edges of the road\r\n- the shop drawing submitted is incomplete and cannot be used on site.\r\n- the site visual inspection is different to the geotechnical report, please clarify??\r\n- ICC was requested on the 50 & 90% design review to design KAM Road the same as the other roads inside KAUST but refused to chance because they were relying on their misleading geotechnical report.\r\n-ICC to clarify the design arrangement of the geotextiles and geogrid to define the basic precaution.', 3, 'sent', '2014-01-21');
INSERT INTO `review` VALUES(1074, 681, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1075, 681, 32, 'No Comments', 1, 'sent', '2014-01-21');
INSERT INTO `review` VALUES(1076, 681, 11, '1. IC needs to expedite the material submittal for approval and technical justification for materials that is not meeting Saudi Aramco Material System Specification (SAMSS) to avoid delay in issuing Purchase Orders.\r\n2. SAMSS requirements for package transformer that cannot be complied has to be waived IC/SCEC has to provide engineering reasoning and the uniqueness of the concern to obtain approval with Consulting Services Division CSD.', 2, 'sent', '2014-01-22');
INSERT INTO `review` VALUES(1077, 683, 47, '# A copy of all the offenses to be shared with SAPMT in the weekly meeting.', 2, 'sent', '2014-01-21');
INSERT INTO `review` VALUES(1078, 683, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1079, 683, 45, 'The submitted document needs to be enhanced so that it would be in congruence to most conventional documentary standards in writing policies and procedures. The document presentation should follow an outline, that is;I. Objective/s of the document; 2, Scope/Coverage of the policy; 3. Roles and Responsibilities; 4. Definition of Terms; 5. "Cut and Paste" the texts in first and second pages of the submittal; 6. References and other Applicable Documentations; 7. Revision History (if Any) 8. Review and Approval of the document.\r\n\r\nThe above elements plus official logo and template of an organization will satisfy minimum writing conventions.', 3, 'sent', '2014-01-19');
INSERT INTO `review` VALUES(1080, 685, 47, 'ICC submitted an incomplete drawing; - no cross section of the road at different chainages - no limit of works from the 2 edges of the road - the shop drawing submitted is incomplete and cannot be used on site. - the site visual inspection is different to the geotechnical report, please clarify?? - ICC was requested on the 50 & 90% design review to design KAM Road the same as the other roads inside KAUST but refused to chance because they were relying on their misleading geotechnical report. -ICC to clarify the design arrangement of the geotextiles and geogrid to define the basic precaution.', 3, 'sent', '2014-01-21');
INSERT INTO `review` VALUES(1082, 685, 25, 'please share with PID also. Also we need to know how and where the geotextile and geogrid will be terminated, the width of the corridor to be improved (we dont need gravel under tress etc), how will the soil strengthening work around utilities.', 3, 'sent', '2014-01-20');
INSERT INTO `review` VALUES(1084, 624, 60, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1085, 624, 61, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1086, 625, 64, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1087, 625, 62, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1088, 686, 61, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1089, 686, 62, 'ZJFFGJ SRHRT RTU RU SRRTU U', 1, 'sent', '2014-01-16');
INSERT INTO `review` VALUES(1090, 687, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1091, 688, 30, '1. Cameras shall be submitted separately as per requirement of each system such as for IPCCTV, SACS, IDAS and LRSS.\r\n2. In future submittals, ensure to submit and include all the material and components of each system. Also provide summary sheet to list down all the proposed equipment with their models.', 3, 'sent', '2014-01-21');
INSERT INTO `review` VALUES(1092, 688, 11, 'The proposed CCTV cameras shall not be used in IDAS system.', 2, 'Pending', '2014-01-25');
INSERT INTO `review` VALUES(1093, 689, 11, 'The proposed vessel barrier is acceptable.', 1, 'sent', '2014-01-20');
INSERT INTO `review` VALUES(1094, 690, 62, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1095, 691, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1096, 692, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1097, 692, 47, '#This submittal is only for Architectural presentation of the precast perimeter wall only and the foundation should be submitted with the structural elements.\r\n#Provide dimension ''C" for shamfer at the corners on drawings SD-FCC-846522-103/01&02', 2, 'sent', '2014-01-26');
INSERT INTO `review` VALUES(1098, 692, 25, 'a.	This submittal shall include the architectural shop drawings of the Precast wall for above ground members only and separate submittal shall be done by IC for the structural details and foundations of the precast wall.\r\nb.	More details shall be provided about the bar size and depth of the lifting hook, sockets and inserts in structural shop drawings\r\nc.	All steel reinforcement details shall be given in the structural shop drawings according to SAES-Q-012, para 5.8 to 5.12\r\nd.	Surface preparation for applying grouts shall be according to the manufacturers recommendations\r\ne.	Dimensions of the chamfers shall be shown in architectural shop drawings\r\nf.	Consider options to add color pigments in concrete instead of surface painting of precast concrete wall\r\ng.	Suggest RAL numbers for the logo before the time paint works are to be done for the 4-color logo\r\n', 2, 'sent', '2014-02-03');
INSERT INTO `review` VALUES(1099, 693, 11, '1. IC management and interface coordinator shall work intensively to communicate in the identified obstructions.\r\n2. IC has to applied extra care while doing works in the identified obstruction list.\r\n3. IC has to regularly update SAPMT for the status of the interface matrix.', 2, 'sent', '2014-01-25');
INSERT INTO `review` VALUES(1100, 693, 47, '#ICC to attach the updated utilities matrix table to give more meaning to the obstruction drawing.\r\n#ICC to indicate how in terms of the current construction these utilities are affective them.\r\n#ICC was advised to continue with the construction process up to the said obstructions', 2, 'sent', '2014-01-25');
INSERT INTO `review` VALUES(1101, 694, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1102, 694, 47, '#ICC to show the blow-out section of what they want to present SAPMT on the shop drawing\r\n#All Shop drawings must have cross sections taken at different place along the alignment of the ditch/fence/road\r\n#ICC to improve on the Shop drawings and should know why they have to do a Shop drawing.\r\n#When submitting a Shop drawing an IFC copy at that particular area must be attached\r\n#ICC to present the intention of the Shop drawing and how it will help to define the situation on site', 3, 'sent', '2014-01-21');
INSERT INTO `review` VALUES(1103, 694, 11, 'No comment', 1, 'sent', '2014-01-22');
INSERT INTO `review` VALUES(1104, 695, 47, 'No Comment', 1, 'sent', '2014-01-21');
INSERT INTO `review` VALUES(1105, 695, 32, 'No Comments. However. Procurement Progress will change upon the revision of Schedule.', 1, 'sent', '2014-01-23');
INSERT INTO `review` VALUES(1106, 695, 11, 'No comment', 1, 'sent', '2014-01-22');
INSERT INTO `review` VALUES(1107, 697, 47, '#ICC to urgently increase the number of Civil QC Inspectors according to Project Quality Schedule Q\r\n#The interfacing coordinator link is not clearly defined\r\n#Engineering department structure to be relooked at.\r\n#ICC to check all spelling mistakes before any submittals', 2, 'sent', '2014-01-21');
INSERT INTO `review` VALUES(1108, 697, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1109, 696, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1110, 696, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1111, 696, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1112, 698, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1113, 698, 11, 'No comment', 0, 'sent', '2014-01-27');
INSERT INTO `review` VALUES(1114, 698, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1117, 699, 68, 'hell', 1, 'sent', '2014-01-21');
INSERT INTO `review` VALUES(1118, 699, 62, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1119, 700, 62, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1120, 700, 60, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1121, 700, 61, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1122, 700, 51, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1123, 700, 68, 'how', 4, 'sent', '2014-01-21');
INSERT INTO `review` VALUES(1124, 704, 11, 'No comment.', 1, 'sent', '2014-01-25');
INSERT INTO `review` VALUES(1125, 704, 47, 'No Comment', 1, 'sent', '2014-01-25');
INSERT INTO `review` VALUES(1126, 704, 12, 'no comment ', 1, 'sent', '2014-01-28');
INSERT INTO `review` VALUES(1127, 703, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1128, 703, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1129, 705, 30, '1. The monitor screen size shall be at least 24 inches as per PA-000381 and PE-000002.\r\n2. Provide the latest with the highest processor CPU and built with DVD drive.', 3, 'sent', '2014-01-26');
INSERT INTO `review` VALUES(1130, 705, 11, 'Workstation shall have a 24 inches monitors as per project scope document PE-000002 page 24 of 71.', 3, 'sent', '2014-01-25');
INSERT INTO `review` VALUES(1131, 705, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1132, 701, 30, '1. There are alot of missing equipment/materials for Communications Systems such as for OSP Fiber Cabling System, OSP manhole and duct Bank System, Structured Cabling System, Data Network System, IPTV End user device and IP telephone End User device.\r\n2. Provide separate columns for the equipment description and its part number/model number.\r\n3. Include all materials/equipment accordingly to their systems.', 3, 'sent', '2014-01-26');
INSERT INTO `review` VALUES(1133, 701, 11, 'Below are missing item which must be included in the detail list.\r\n\r\n1.	Electronic Marquee Display for indoor and outbound lanes\r\n2.	Fire alarm control panel and notification devices\r\n3.	Traffic lights\r\n4.	Lighting Fixtures for buildings.\r\n\r\nSpare parts and data package not identified in the list will be determine using Non Material Requirments (NMR) once the material submittal has been approved.\r\n', 3, 'sent', '2014-01-25');
INSERT INTO `review` VALUES(1134, 701, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1135, 702, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1136, 702, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1137, 702, 22, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1138, 706, 30, '1. All Edge, access, industrial and distribution switches including routers shall have redundant power supplies and fully supports POE.\r\n2. Provide and include all the following equipment/material:\r\n   a. all network/line cards and modules/ports\r\n   b. fiber patch cords\r\n   c. rack mounted UPS with network line cards (attached UPS sizing calculation)\r\n3. Power cords shall be british type.', 3, 'sent', '2014-01-26');
INSERT INTO `review` VALUES(1139, 706, 11, 'No comment, kindly get the comment to Marwin.', 0, 'sent', '2014-01-25');
INSERT INTO `review` VALUES(1140, 706, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1141, 708, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1142, 710, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1143, 711, 30, '1. Include specifications and attached datasheets for the stainless steel base plinth and sunshade.\r\n2. Provide stainless steel breather as per SAES-P-104 and SAES-J-102.', 3, 'sent', '2014-01-26');
INSERT INTO `review` VALUES(1144, 711, 11, 'The proposed model can easily open the lock using a screw driver, This cabinet is enclosing the essential parts of CCTV it is mandatory to replace the lock with a secured key lock.', 3, 'sent', '2014-01-25');
INSERT INTO `review` VALUES(1145, 711, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1146, 712, 47, '# ICC to follow ASTM A 615/A 615M-00 item 1.2 &1.3 for dowels installations', 2, 'sent', '2014-01-26');
INSERT INTO `review` VALUES(1147, 712, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1148, 709, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1149, 711, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1150, 713, 47, '#The revised shop drawing should also indicate the available corridor to be used by Rabya for the construction of their utilities at the affected section.\r\n#A revised MST to be attached with this proposals to indicate the discontinuity of the IDAS/ MIDAS system to allow the contruction stages.\r\n#An alternative route(road diversion) to be defined to access KAM for RABYA personnel and ICC construction team', 2, 'sent', '2014-01-25');
INSERT INTO `review` VALUES(1151, 713, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1152, 713, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1153, 714, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1154, 714, 47, 'This is as per PID requirement!!!No Comment', 1, 'sent', '2014-01-26');
INSERT INTO `review` VALUES(1155, 715, 47, '', 0, 'sent', '');
INSERT INTO `review` VALUES(1156, 715, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1157, 715, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1158, 715, 11, 'For mechanical and electrical the only activities that requires Method of statement are the following:\r\n1. Works which requires tie-in point with the existing KAUST Fire Water, Portable Water and Sewer line.\r\n2. Electrical connection with the existing KAUST substation.\r\n3. Excavation for electrical ductbanks and pipe/conduit trenches in areas wherein there are underground utilities were laid and if the excavation is crossing/parallel KAUST roads which may result to traffic.\r\n\r\nIn addition to the above list, items for security and communication system that requires downtime, relocation and re-installation, removal and salvaging of equipments needs to have an approved methodology.\r\n\r\n\r\n\r\n', 2, 'sent', '2014-01-27');
INSERT INTO `review` VALUES(1159, 716, 47, 'No comment', 1, 'sent', '2014-01-29');
INSERT INTO `review` VALUES(1160, 716, 12, 'no comment ', 1, 'sent', '2014-01-28');
INSERT INTO `review` VALUES(1161, 716, 11, 'No comment', 1, 'sent', '2014-01-28');
INSERT INTO `review` VALUES(1162, 717, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1163, 717, 47, 'No comment', 1, 'sent', '2014-01-30');
INSERT INTO `review` VALUES(1164, 717, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1165, 718, 12, 'ICC to put justificaton why the shcedule is behind and the action plan ', 2, 'sent', '2014-01-28');
INSERT INTO `review` VALUES(1166, 718, 32, 'No Comments. For Information only.', 1, 'sent', '2014-01-29');
INSERT INTO `review` VALUES(1167, 718, 47, '#SAPMT agreed to review the weekly report with IC construction team before submittal to Aramco.\r\n#IC management to assign a construction team that is capable of interpreting the work done into percentage for the purpose of this submittal.\r\n#The quantities and percentages reported on this report are still incorrect even after a constant reminder to the construction team to report on work done on site only ', 2, 'sent', '2014-01-29');
INSERT INTO `review` VALUES(1168, 719, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1169, 719, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1170, 719, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1171, 579, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1172, 579, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1173, 721, 12, 'ICC to revise IFC drwaings for approval ', 2, 'sent', '2014-02-01');
INSERT INTO `review` VALUES(1174, 721, 47, 'ICC to comply as highlighted above, send a design proposal for you review', 3, 'sent', '2014-02-04');
INSERT INTO `review` VALUES(1175, 722, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1176, 723, 12, 'as Per SCEC , no need for shipping ', 2, 'sent', '2014-02-01');
INSERT INTO `review` VALUES(1177, 723, 47, 'No chipping of concrete is allowed on site as per SAPMT and PID agreement', 2, 'sent', '2014-01-29');
INSERT INTO `review` VALUES(1178, 724, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1179, 725, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1180, 726, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1181, 727, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1182, 727, 47, 'no comment', 1, 'sent', '2014-02-04');
INSERT INTO `review` VALUES(1183, 728, 11, 'Electrical:\r\n1. IC has to follow single ended type switchgear as per IFB package, provided only to upgrade the incomer breakers (from 600AT to 1200 AT) to match the new SEC substation.\r\n2. IC/SCEC/Generator manufacturer needs to certify that the calculated size of 2500KW is capable to feed the KPSS demand load as per IFC drawing without any deviation on generator efficiency during daytime operation. \r\n3. Indoor Switchgear has always a DC power supply as per Saudi Aramco standard.\r\n4. IC/SCEC needs to re-calculate the 15 KVA UPS rating and must follow the electrical load given by security and communication contractor. \r\n5. Patrol road lighting  and transformers were included in the bid package REQUISITION NO. 3000440288 Addendum 01 drawing # PA000095 sht 001 to 018.\r\n6. Power System Automation is out of scope.\r\n\r\nMechanical:\r\n\r\n1. If the electrical duct heater is included in the PAC unit, and requires only same temperature in all rooms duct heater can be built-in in the unit. however, if in QRT rooms it requires different temperatures independent duct heater can be provided.\r\n2. Guard house in Wadi Khulais were mentioned and included in bid documents PE-000002 section 1.2.2.1.5', 3, 'sent', '2014-02-10');
INSERT INTO `review` VALUES(1184, 728, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1185, 729, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1186, 729, 12, 'A)\r\n\r\n1)Vehicle inspection is part of project proposal \r\n2)The space of car/truck Bay is not identify in the project proposal and needs to be Details design\r\n3)Same comment#2\r\n4)agree\r\n5)Agree , It was not in project proposal and it is miner item\r\n6)no change only orientation modified \r\n7)agree\r\n8)agree \r\n9)agree\r\n10)agree\r\n\r\nB)\r\n*ICC can find other solution for Slope protection \r\n\r\nC)agree\r\n\r\n1', 2, 'sent', '2014-02-05');
INSERT INTO `review` VALUES(1187, 730, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1188, 731, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1189, 734, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1190, 733, 47, '#IC and FCC to commit to 2 shifts a day and comply with the inspection times and schedule provided.\r\n#Both IC & FCC site engineer, foremen and QC inspector to be available on site at all times, before and after concreting\r\n#Before SAPMT & PID inspection there should be a join inspection between IC and FCC construction and QC team to rectify all the issues concerned.\r\n#All the rebars/ formwork/ cleaning inspection will be conducted during the day to give way to the concreting team', 2, 'sent', '2014-02-04');
INSERT INTO `review` VALUES(1191, 733, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1192, 735, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1193, 735, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1194, 732, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1195, 732, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1196, 740, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1197, 740, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1198, 740, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1199, 741, 32, 'No comments. For Info.', 1, 'sent', '2014-02-06');
INSERT INTO `review` VALUES(1200, 741, 12, 'no comment ', 1, 'sent', '2014-02-05');
INSERT INTO `review` VALUES(1201, 741, 47, 'no comment', 1, 'sent', '2014-02-04');
INSERT INTO `review` VALUES(1202, 742, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1203, 742, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1204, 737, 47, 'IC was advised to go ahead with the final design proposal pending Kaust response', 3, 'sent', '2014-02-06');
INSERT INTO `review` VALUES(1205, 737, 12, 'We are waiting KAUST approval if not received , we will proceed ', 2, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1206, 738, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1207, 738, 45, 'Directional signsges to indicate ingress and egress according to traffic flow plan and emergency exit and assembly point/s must be complied.', 2, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1208, 739, 47, 'No comment', 1, 'sent', '2014-02-06');
INSERT INTO `review` VALUES(1209, 739, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1210, 739, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1211, 743, 47, 'IC was advised to go ahead with the revised drawing and ensure that there is no security breach on the tie in points.', 3, 'sent', '2014-02-06');
INSERT INTO `review` VALUES(1212, 743, 12, 'provide modified IFC drwaings from STA9200 to 10750 ', 2, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1213, 745, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1214, 744, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1215, 748, 12, 'The prposal was sent to KAUSt for further action. KAUST will send the prposal to water pipe company ', 2, 'sent', '2014-02-05');
INSERT INTO `review` VALUES(1216, 747, 12, 'Mobily recieved our proposal , we will wait Mobliy aprorval \r\n\r\n', 2, 'sent', '2014-02-05');
INSERT INTO `review` VALUES(1217, 747, 11, 'No comment', 2, 'sent', '2014-02-08');
INSERT INTO `review` VALUES(1218, 747, 30, '1. Location A''s proposed manholes 7 and P are not necessary since Gate #3 has provisions of manhole and duct banks used for communications that can be utilized for mobily cable.\r\n\r\n2. A Shop drawing has to be provided to clearly locate the proposed manholes Q and R of LOcation A at the ends of the culvert and how the mobily cable will pass through the culvert.\r\n\r\n3. Update and revise the mobily cable route at Location A according to Item 1 and 2.\r\n\r\n4. It is appropriate to relocate proposed manhole G between existing manhole 1d and duct bank K at Location B since the current location of manhole G is not necessary due to the distance between proposed manholes F and H are not far.\r\n\r\n5. Provide details for the proposed duct bank crossings for all locations.\r\n\r\n6. Provide detailed Material Take-off List (MTO).\r\n\r\n7. Ensure the drawings, scope and MTO will be reviewed by design consultant with their concurrence.', 3, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1219, 749, 47, 'IC to report only on issues discussed and agreed in the meeting and not add items that were not discussed.', 3, 'sent', '2014-02-06');
INSERT INTO `review` VALUES(1220, 749, 12, 'no comment ', 1, 'sent', '2014-02-05');
INSERT INTO `review` VALUES(1221, 749, 47, 'IC to report only on issues discussed and agreed in the meeting and not add items that were not discussed.', 3, 'sent', '2014-02-06');
INSERT INTO `review` VALUES(1222, 746, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1223, 746, 11, '1. The proposed cable tray mounting plan is not feasible to construct with the existing culvert (see attached photo of the culvert). Provide more details for the cable tray routing plan. \r\n2. Provide shop drawing for duct bank to cable tray transition.\r\n3. Provide cable profile for the SEC cables running across KAUST Gate 3 road.\r\n4. Provide Saudi Electric Company (SEC) signature acceptance for the shop drawings provided.', 3, 'sent', '2014-02-08');
INSERT INTO `review` VALUES(1224, 746, 12, 'The propsal was sent to KAUST ', 2, 'sent', '2014-02-05');
INSERT INTO `review` VALUES(1225, 750, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1226, 750, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1227, 759, 47, 'NO COMMENT', 1, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1228, 759, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1229, 758, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1230, 758, 12, 'the prposed KAUST Logo, Colors does not match the KASUT logo. We need to send to KAUST for approval ', 3, 'sent', '2014-02-10');
INSERT INTO `review` VALUES(1231, 757, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1232, 757, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1233, 757, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1234, 755, 12, 'ICC to attach Rabyishop drwaings for tie-in point for KAM Aceess road \r\nICC to provide agreed drwaings between ICC and Rabyi', 3, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1235, 755, 47, '#IC AND RABYA SURVEYOR TO SET-UP THEIR SURVEY EQUIPMENT AT DIFFERENT LOCATION FOR SAPMT CONFIRMATION.\r\n#RAISE RFI AND SAPMT WILL CONFIRM THE COORDINATES TO BE USED AND BOTH RABYA AND IC TO COMPLY', 2, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1236, 756, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1237, 756, 47, 'NO COMMENT; FOR SAPMT & PID RECORD', 1, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1238, 754, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1239, 754, 12, 'ICC to confirm the stael bars and Concerte are as the IFC drawaings \r\n', 2, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1240, 753, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1241, 753, 32, 'No Comments', 1, 'sent', '2014-02-11');
INSERT INTO `review` VALUES(1242, 752, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1243, 752, 47, '#IC/ ESE TO COMPLY WITH KAUST AND SAPMT REQUIREMENTS BEFORE ANY WORK STARTS, \r\n#A CHECKLIST FOR ALL THE EQUIPMENTS/UTILITIES REMOVED TO BE AVAILABLE BEFORE AND AFTER DISMANTLING.', 2, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1244, 752, 30, '1. Clarify and revise the attached Overall Work Schedule since it is contradicting to the detailed  work schedule.\r\n\r\n2. Any work exclusion by ESE shall be removed and all of these activities shall be included if required to complete the relocation work. ICC shall review the document, do quality check and avoid such phrases prior sending to SAPMT for review.\r\n\r\n3. ICC/ESE shall start on technical submission of the fiber optic cable to be used in this activity and to place purchase order as soon as possible.\r\n\r\n4. Equipment and tools for splcing, terminationa and testing of fiber optic cable shall be included in the list.\r\n\r\n5. Ensure the fiber optic cable splicers are with certifications approved by ARAMCO or equivalent as per SAES-T-928. List down the name of the splicers and attached their certificates.\r\n', 2, 'sent', '2014-02-09');
INSERT INTO `review` VALUES(1245, 752, 11, '1. The RADAR power supply has to be connected in sonar shelter # 1 prior the removal of IDAS Distribution panel DP-01.', 2, 'sent', '2014-02-11');
INSERT INTO `review` VALUES(1246, 751, 47, 'No comment', 1, 'sent', '2014-02-11');
INSERT INTO `review` VALUES(1247, 760, 11, 'a. Refer to IFB write-up PE-000002 page 7 of 71.\r\nc. Refer to Q & A item 12 page 3 of 23.\r\nd. Refer to addendum drawing # PA-000095 sht 001 to 018 for lighting pole layout and sht # 003, 006, 009, 012, 014, 017 for transformer layout.', 2, 'sent', '2014-02-10');
INSERT INTO `review` VALUES(1248, 760, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1249, 760, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1250, 762, 32, 'SAPMT has reviewed the referenced subject submittal dated February 09, 2014 and has no objection. However, Saudi Aramco will not entertain any further revision of the schedule and the contractor is requested to take all necessary actions to deliver the project ahead or as per the schedule.', 1, 'sent', '2014-02-10');
INSERT INTO `review` VALUES(1251, 762, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1252, 762, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1253, 761, 32, 'No Comments. However, Procurement progress shall be revised in the future reports upon the approval of new revision of schedule.', 1, 'sent', '2014-02-10');
INSERT INTO `review` VALUES(1254, 764, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1255, 763, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1256, 765, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1257, 751, 70, '', 1, 'sent', '2014-02-13');
INSERT INTO `review` VALUES(1258, 751, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1259, 766, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1260, 767, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1261, 767, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1262, 767, 70, '', 1, 'sent', '2014-02-13');
INSERT INTO `review` VALUES(1263, 767, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1264, 767, 11, 'No comment...', 2, 'sent', '2014-02-15');
INSERT INTO `review` VALUES(1265, 768, 47, 'No comment', 1, 'sent', '2014-02-17');
INSERT INTO `review` VALUES(1266, 768, 70, '', 0, 'sent', '');
INSERT INTO `review` VALUES(1267, 769, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1268, 770, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1269, 770, 11, 'No further comment.', 1, 'sent', '2014-02-12');
INSERT INTO `review` VALUES(1270, 44, 10, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1271, 771, 10, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1272, 775, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1273, 776, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1274, 776, 47, 'No comment', 1, 'sent', '2014-02-17');
INSERT INTO `review` VALUES(1275, 776, 70, 'No Comment.', 1, 'sent', '2014-02-13');
INSERT INTO `review` VALUES(1276, 777, 47, '# IC to clarify note 6. on the shop drawing and provide a method statement based on the item\r\n# IC to follow or revise the project specification before shop drawing submittals to SAPMT', 2, 'sent', '2014-02-16');
INSERT INTO `review` VALUES(1277, 777, 70, 'No comment', 1, 'sent', '2014-02-14');
INSERT INTO `review` VALUES(1278, 777, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1279, 778, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1282, 780, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1283, 780, 47, '#ICC to follow SAES-A-114 Cl 6.2.2  for all selected fill under the structure and Cl 6.3.2.2 can be granted if they have proper skilled manpower who can carry the work without supervision and at this moment SAPMT is always on site to monitor and enforce the procedures.\r\n#ICC to provide specifications and standards to qualify their request and not cost effective reasons to avoid expenditure.\r\n', 4, 'sent', '2014-02-17');
INSERT INTO `review` VALUES(1284, 780, 70, 'As per SAES-A-114 para 6.3.2.2 SAPID is authorized to approve other lift thickness. my suggation to get prior approval from SAPID.', 2, 'sent', '2014-02-16');
INSERT INTO `review` VALUES(1285, 781, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1286, 781, 47, '', 0, 'sent', '');
INSERT INTO `review` VALUES(1287, 781, 70, 'As Per SAES-A-114 para 6.3.3.3 SAPID authorize to decrease the number of tests. My suggetion to get prior approval from SAPID and this does not relieve the contractor of the responsibility as per SAES-A-114 para 5.1.3.', 2, 'sent', '2014-02-16');
INSERT INTO `review` VALUES(1288, 150, 10, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1289, 150, 41, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1290, 150, 23, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1291, 150, 44, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1292, 784, 11, '1. The submitted list is an equipment list and not a spare part list.\r\n2. IC needs to coordinate for all its vendor/manufacturer to identify the spare parts needed.\r\n3. Following requirements are essential for every submittal SPDP: \r\n•PO copy with any change order/amendment to the PO. \r\n•Certified equipment data specification sheets. (ISS) for instrumentation equipment. \r\n•Nameplate data including Serial No. Model No., Type No. for applicable equipment. \r\n•Certified cross-sectional drawing showing parts mentioned in BOM, assembly, dimensional & general arrangements drawings for applicable equipment. \r\n•Bill of materials (BOM) indicating unique P/N, description & materials of construction for each item "on manufacturer letter head or certified". \r\n•Recommended priced parts list (for wearing and consumable items) for 2 years operation for each equipment “on manufacturer letter-head or certifiedâ€ including OEM/OCM part numbers and Qty per equipment. Or as certified exhibit "Sâ€, attached. \r\n•Manufacturer''s catalog cuts (generally for instrumentation & electrical items) for applicable equipment. \r\n•P& IDs is required for skid mounted equipment. \r\n', 4, 'sent', '2014-02-22');
INSERT INTO `review` VALUES(1293, 784, 30, '1. The list must be revised to provide a clear description of the equipment required for spare parts that will include equipment description, model number, part number and manufacturer.\r\n\r\n2. The provided list of equipment for communication is incomplete such as for IPTV, Intercom, IP Phone, UTP/Fiber Patch Panels and rack mounted UPS.', 3, 'sent', '2014-02-19');
INSERT INTO `review` VALUES(1294, 784, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1295, 783, 32, 'No Comments.', 1, 'sent', '2014-02-23');
INSERT INTO `review` VALUES(1296, 783, 47, '#ICC to revise the report as agreed in the quantity site review meeting.\r\n#ICC to propose the revised work redistribution of weights for February weekly and monthly report submission\r\n', 3, 'sent', '2014-02-18');
INSERT INTO `review` VALUES(1297, 783, 70, 'As per yesterday afternoon meeting ( Feb. 18, 2014 ) held with SA Project Engineers & ICC Planner there are some data should be change for Ditch Wall Activities. In additional I prefer to delete the Site Preparation of Fence due to No Soil Inprovement will add under the Foundation, The area is not ready to receive the Fence Foundation.', 3, 'sent', '2014-02-18');
INSERT INTO `review` VALUES(1298, 782, 32, 'Since the Rev. 2 Schedule not yet approved officially, the Weekly Report shall follow Rev.1 Schedule only.', 3, 'sent', '2014-02-23');
INSERT INTO `review` VALUES(1299, 785, 12, 'Reference  to your letter of February 16,2014  explaining your need for an extension of time for submission bid of change order request #2 .SAPMT is  pleased to inform you this request has been approved on the date you suggested', 2, 'sent', '2014-02-17');
INSERT INTO `review` VALUES(1300, 787, 32, 'No Comments', 1, 'sent', '2014-02-23');
INSERT INTO `review` VALUES(1301, 790, 70, 'To relocate the Ditch as mentioned in the drawing ( ICC/SK-0060 001 )is not a perfect solution because possibly  the buried pipes & Cables will intersect with the ditch. The better way to relocate all utilities to be far from KAUST Perimeter Security System ( Inside KAUST ) due to maintenance reasons to be easy maintaine them and for Security reasons the transformer, lift station ...etc. should be far at safe distance.\r\n\r\non the other hand if the ditch cancel the transformer and the lift station still need to relocate.', 0, 'sent', '2014-02-21');
INSERT INTO `review` VALUES(1302, 790, 11, '1. Even the ditch will be relocated, the new wall will also hit the subject utilities based on the shop drawing provided.\r\n2. IC has to provide options if the existing transformers loads and lift station can be shifted and accommodated by the nearby transformers and lift stations. ', 3, 'sent', '2014-03-13');
INSERT INTO `review` VALUES(1303, 790, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1304, 790, 12, 'we have to wait until we get final aprroval from de-scoping the ditch ', 2, 'sent', '2014-02-22');
INSERT INTO `review` VALUES(1305, 791, 70, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1306, 791, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1307, 791, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1308, 792, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1309, 792, 11, 'SAPMT will coordinate to KAUST IT, to obtain approval of port reservation.', 2, 'sent', '2014-02-22');
INSERT INTO `review` VALUES(1310, 793, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1311, 794, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1312, 795, 47, '#As discussed in our design meeting, ICC will consult all the disciples concerned and finalize the design according ARAMCO standard, no deviations will be approved on the drawings.', 2, 'sent', '2014-02-26');
INSERT INTO `review` VALUES(1313, 795, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1314, 795, 70, 'I don''t have any background about this topic. No comment', 0, 'sent', '2014-02-21');
INSERT INTO `review` VALUES(1315, 796, 30, '1. The candidate does not possess sufficient knowledge to the position of QC Inspector.\r\n2. The candidate also failed to answer most of the basic questions during the interview that subject for his rejection.', 4, 'sent', '2014-03-01');
INSERT INTO `review` VALUES(1316, 796, 11, 'Due to the magnitude of security system scope, the candidate must pass the oral interview to be conducted by SAPMT and SAPID.', 2, 'sent', '2014-02-23');
INSERT INTO `review` VALUES(1317, 796, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1318, 798, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1319, 797, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1320, 800, 47, '#ICC to submit only the agreed quantities as per SAPMT request and all will sign as a confirmation.', 2, 'sent', '2014-02-26');
INSERT INTO `review` VALUES(1321, 800, 70, 'Regarding to Ditch Quantity Mr. Azwinndini has the right quantity. I prefer Fence Site Preparation to be zero. ', 2, 'sent', '2014-02-26');
INSERT INTO `review` VALUES(1322, 800, 32, 'Only for Information. No Comments.', 1, 'sent', '2014-02-27');
INSERT INTO `review` VALUES(1323, 801, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1324, 801, 47, 'No Comment', 1, 'sent', '2014-03-02');
INSERT INTO `review` VALUES(1325, 801, 70, 'If the concrete stress become 14 Mpa, subcontractor can start production of some panales as mock-up to evaluate. conditionally accepted', 2, 'sent', '2014-02-26');
INSERT INTO `review` VALUES(1326, 802, 30, '1. Use plenum rated fiber optic cable instead of Low Smoke Zero Hallogen (LSZH)cable.\r\n2. Ensure all cables will comply to the requirements of 18-SAMSS-625', 2, 'sent', '2014-02-26');
INSERT INTO `review` VALUES(1327, 802, 11, 'No further comment.', 1, 'sent', '2014-02-26');
INSERT INTO `review` VALUES(1328, 802, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1329, 803, 47, 'NO comment', 1, 'sent', '2014-02-25');
INSERT INTO `review` VALUES(1330, 803, 70, 'No comment.', 1, 'sent', '2014-02-26');
INSERT INTO `review` VALUES(1331, 803, 32, '* Progress Summary shall be corrected in align with last approved schedule.\r\n* MOM shall be submitted the immediate next day of meeting for SAPMT approval.', 3, 'sent', '2014-02-27');
INSERT INTO `review` VALUES(1332, 804, 47, '#ICC to use the same dimension fond size on their drawings for visibility purpose\r\n#ICC to use the same SI units for all the dimension(mm/ cm/ m) on their drawings\r\n#ICC to submit colour copies to SAPMT for review and different colours/ pen sizes to be coordinated for clarity', 2, 'sent', '2014-02-26');
INSERT INTO `review` VALUES(1333, 804, 70, '', 0, 'sent', '');
INSERT INTO `review` VALUES(1334, 805, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1335, 805, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1336, 806, 47, '#As discussed and agreed on our interface meeting, ICC will follow the coordinates give by RABYA at the tie-in point.', 2, 'sent', '2014-02-26');
INSERT INTO `review` VALUES(1337, 806, 70, 'Reviewed & No comment.', 1, 'sent', '2014-02-26');
INSERT INTO `review` VALUES(1338, 807, 53, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1339, 807, 47, '#Icc to specify the duration of the geotechnical study to expedite the finalization of the shop drawing.', 2, 'sent', '2014-03-02');
INSERT INTO `review` VALUES(1340, 808, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1341, 809, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1342, 809, 47, 'For Info only, no comment', 1, 'sent', '2014-03-02');
INSERT INTO `review` VALUES(1343, 809, 70, 'Regarding to points A.1.2.2 & A.1.2.3 activities at St. 5+900 to 8+800 the ditch activity is suspended as per PMT letter so you need to revisit those point with actual works. Point A.1.2.4 & A.1.2.5 will be more clear if mentioned at Gate #2 and Gate #3 which we believe IC can complete the Select fill material within two weeks. Regarding point A.1.3 at St. 10+800 to 13+500 no body is working and we don''t believe the Subcontractor ( Ayash ) has enough equipment to work at this station while he is so busy in many locations.', 2, 'sent', '2014-03-02');
INSERT INTO `review` VALUES(1344, 811, 11, 'No further comment.', 1, 'sent', '2014-03-02');
INSERT INTO `review` VALUES(1345, 811, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1346, 812, 11, '1. The MV switchgear outgoing feeders shall be 600 ampere trip and not 1200 ampere trip.', 3, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1347, 812, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1348, 811, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1349, 812, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1350, 814, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1351, 814, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1352, 814, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1353, 814, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1354, 814, 70, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1355, 815, 47, 'NO COMMENT', 1, 'sent', '2014-03-03');
INSERT INTO `review` VALUES(1356, 815, 70, '* All drawing notes – 03 mentioning 34 Mpa but as per Aramco Standard SAES – Q - 012 Para. 4.6 The minimum 34.5 Mpa (5000 psi).\r\n\r\n* All drawing titles PRECAST CONCRETE FENCE - TYPE K4 (30M) instate of K12 (50M) except first drawing.\r\nSD – FCC – 846521 – 207 Section A-A The rebar space should be maintain to avoid the honeycomb as per ACI 318 - 08 sec. 7.6 and General Note VA – 846497 – 001 Section III Reinforcement – i. \r\n\r\n* The K12 (50M) Footing Dimension is 1500 * 2500 mm while drawing SD – FCC – 846521 – 207- 01 and drawing SD – FCC – 846521 – 208 – 01 is showing footing dimension 1500 * 1500 mm with wrong Rebar schedule.\r\n\r\n** This submittal is rejected wrong information.\r\n', 4, 'sent', '2014-03-04');
INSERT INTO `review` VALUES(1357, 816, 47, 'nO cOMMENT', 1, 'sent', '2014-03-03');
INSERT INTO `review` VALUES(1358, 816, 70, '* All drawing notes – 03 are mentioning 34 Mpa but as per Aramco Standard SAES – Q - 012 Para 4.6 The minimum 34.5 Mpa (5000 psi).\r\n\r\n* At drawing SD - FCC – 846521 – 210 & SD - FCC – 846521 – 211 The title of the drawing mentioned PRECAST CONCRETE FENCE - TYPE K4 (50M) instate of (30M).\r\n\r\n* SD – FCC – 846521 – 207 Section A-A The rebar space should be maintain to avoid the honeycomb as per ACI 318 - 08 sec. 7.6 and General Note VA – 846497 – 001 Section III Reinforcement – i.\r\n', 2, 'sent', '2014-03-04');
INSERT INTO `review` VALUES(1359, 818, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1360, 818, 11, 'Correct the voltage requirements of the automatic sliding door.', 2, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1361, 817, 32, 'No Comments. It for info only.', 1, 'sent', '2014-03-06');
INSERT INTO `review` VALUES(1362, 819, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1364, 813, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1365, 822, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1366, 822, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1367, 822, 47, '#ICC follow proper coordination with Material Specialist and PID on all the material submittals and also enquire the use/ where & how of bonding agent on SAES.', 2, 'sent', '2014-03-06');
INSERT INTO `review` VALUES(1368, 822, 70, 'As per ACI 308R " Curing … The continued hydration of the cement in the presence of sufficient water and heat â€ while Masterkure, 161, Bitumen is not control the heat. As per ASTM C 309 there is a White-pigmented membrane-forming compounds serve the additional purpose of reducing the temperature rise in concrete exposed to radiation from the sun. I prefer to follow project specification without strong justification.', 4, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1369, 823, 11, 'Include in the submittal the tapping point handhole connection details which include the terminal blocks, fuses and non conductive metallic plate.', 3, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1370, 823, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1371, 823, 47, 'ICC to provide all otstanding items as per Mark and Alla'' discussion', 2, 'sent', '2014-03-10');
INSERT INTO `review` VALUES(1372, 823, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1373, 824, 47, 'No Comment', 1, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1374, 824, 70, 'Regarding to the main reinforcement of the base slab at top and the cover slab at bottom, as per Details And Detailing Of Concrete Reinforcement ( ACI 315-99 ) all main reinforcement cannot stop or splice in the Maximum Bending Moment Zone ( positive moment at mid span ) some of them  should be extend to the supports theoretically  but practically all these rebar should extend into supports to give more stiffness and rigidity. In the drawing some of reinforcement has the mentioned issue which needs to rearrange. ', 4, 'sent', '2014-03-08');
INSERT INTO `review` VALUES(1375, 825, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1376, 826, 47, '#ICC was advised to resurvey the edges of both the lagoon and the high tide area again and redo the study again to re-align the boundary fence from the ditch.\r\n#SAPMT requested ICC to urgently provide a from CH 0+000 to CH 2+200 next to the lagoon with an aim of providing more working area for FCC - Preimeter Fence Installation', 2, 'sent', '2014-03-08');
INSERT INTO `review` VALUES(1377, 826, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1378, 826, 70, 'At St. 10+750 to St. 13+150 the space 7 meter is slightly narrow.', 2, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1379, 829, 11, 'No comment.', 1, 'sent', '2014-03-07');
INSERT INTO `review` VALUES(1380, 829, 47, '#ICC to submit the draft MOM a day after the meeting for review and comments\r\n#ICC to submit the MOM approval to SAPMT within a week.\r\n', 2, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1381, 829, 70, 'No comment', 1, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1382, 828, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1383, 828, 47, '# Icc to provide a checklist with all the steps discussed in a joint inspection by SAPMT, PID, FCC to avoid any details on the works.', 2, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1384, 828, 70, 'I prefer to share this method of statement with SAPID for review and comment.\r\n\r\nAs per SAES – H – 003 Para 7.4 contractor shall fill the crack or the void not exceeding 10 mm by approved material, the sharp edge shall be rounded. Regarding to tie – rod hole contractor should make the surface rough and chipping the edge of the hole.  Regarding to any reinforcement expose contractor should repair it as per approved procedure.\r\n', 2, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1385, 827, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1386, 827, 70, 'The Contractor should follow the project specification section 03300 para. 2.04 while they are not providing strong justification.', 4, 'sent', '2014-03-06');
INSERT INTO `review` VALUES(1387, 827, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1388, 827, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1389, 830, 11, 'Power System Automation is not included in the approved project proposal, however, It is the obligation of SCEC to ensure that metering is considered in the switchgear, IC/SCEC has to provide a provision of Power Monitoring Limited (PML). ', 2, 'sent', '2014-03-08');
INSERT INTO `review` VALUES(1390, 830, 30, 'No comment. Please ask Mark for comments.', 2, 'sent', '2014-03-11');
INSERT INTO `review` VALUES(1391, 831, 11, 'No further comment.', 1, 'sent', '2014-03-05');
INSERT INTO `review` VALUES(1392, 832, 11, '1. Since the Switchgear BUS is considered as a single ended bus, only one spare and one space feeder breakers are needed and this set up complies with Saudi Aramco Material System Specification (SAMSS) requirements and IFB drawing electrical one line diagram.\r\n2. Only tie breaker will be considered additional to comply with Consulting Services Division (CSD) comment.\r\n3. IC/SCEC has to revised the drawing and must show the following quantities\r\n* 3 -1200 Amp Breakers\r\n* 3- 600 Amp Breakers\r\n* 1- Space\r\n', 2, 'sent', '2014-03-12');
INSERT INTO `review` VALUES(1393, 833, 11, '1. Dummy load for generator is for Maintenance purposes only and is not part of the approved Project Proposal.\r\n2. SAPMT agrees with the sizing of the Generator as confirmed by the vendor and with the assurance coming from SCEC that it will run in good efficiency even at 30% of the generator size.\r\n', 2, 'sent', '2014-03-08');
INSERT INTO `review` VALUES(1394, 835, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1395, 836, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1396, 836, 58, 'They shall attach CD of this request so we can send it to VID (in Dhahran) for approval', 3, 'sent', '2014-03-12');
INSERT INTO `review` VALUES(1397, 837, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1398, 838, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1399, 838, 47, 'No comment', 1, 'sent', '2014-03-10');
INSERT INTO `review` VALUES(1400, 839, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1401, 839, 32, 'No Comments. For info only.', 1, 'sent', '2014-03-13');
INSERT INTO `review` VALUES(1402, 840, 33, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1403, 840, 70, 'The ditch activity is suspended as per PMT letter so my suggetion to suspend any submittal. On the other hand we need prior approval from KAUST to expose the ditch in the future.', 2, 'sent', '2014-03-09');
INSERT INTO `review` VALUES(1404, 840, 47, '#The initial ditch design and construction was to follow the design gradient slopes from CH0+000 to Ch14+000,which could have cause the ditch at some points to be +/-15 m and as a result SAPMT allowed ICC to design the ditch elevetion to be above the water table which they did and all parties have reviewed and approved the IFC. ICC is now requesting yet again to change the design elevation due to invalid reasons which are known to themselves. \r\n#ICC were advised to reduce the height of 3m to 2,4m were they can will valid reasons but now they opted to construct the ditch IL above the perimenter fence foundation and the drainage system. ', 3, 'sent', '2014-03-09');
INSERT INTO `review` VALUES(1405, 841, 45, 'Rectify entries in Coulumns 1 and 2 for Aspects and Impacts respectively. Observe how an environmental aspect should be stated and its corresponding impact to the environment. Follow the examples the SAPMT-Safety has briefed you so there would be no re-works again.\r\n\r\nBy working out from the same format, start submitting your monthly progress/accomplishment report for January and February 2014. It is in this way that ICC can demonstrate compliance to your Environmental Management Program. This will also train the SHE team to give equal importance to this aspect of ICC Project operation not only on Safety and Health.', 3, 'sent', '2014-03-12');
INSERT INTO `review` VALUES(1406, 834, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1407, 834, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1408, 842, 32, 'No Comments. For Info Only.', 1, 'sent', '2014-03-13');
INSERT INTO `review` VALUES(1409, 842, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1410, 843, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1411, 843, 30, 'This document has been pulled back by the contractor.', 4, 'sent', '2014-03-22');
INSERT INTO `review` VALUES(1412, 843, 11, 'The candidate will not join anymore as per ESE.', 4, 'sent', '2014-03-20');
INSERT INTO `review` VALUES(1413, 844, 12, 'no comment ', 1, 'sent', '2014-03-12');
INSERT INTO `review` VALUES(1414, 844, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1415, 845, 32, 'No comments. For Info only.', 1, 'sent', '2014-03-13');
INSERT INTO `review` VALUES(1416, 845, 47, 'ICC to report all the activities as they happen on site.', 3, 'sent', '2014-03-10');
INSERT INTO `review` VALUES(1417, 845, 70, 'There is some wrong information. I sent to Mr. Seenivasan email with corrected information to be resubmitted.', 3, 'sent', '2014-03-14');
INSERT INTO `review` VALUES(1418, 845, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1419, 846, 32, 'No Comments. For Info only', 1, 'sent', '2014-03-13');
INSERT INTO `review` VALUES(1420, 846, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1421, 847, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1422, 851, 11, 'This panelboard shall be used only for RADAR near shelter # 1.', 2, 'sent', '2014-03-12');
INSERT INTO `review` VALUES(1423, 851, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1424, 849, 58, '1) they submit bunch of materials without it''s inspection level and 9com.\r\n\r\n2) at least they have to provide the inspection levels of all the items and we will help them to find the correct 9com.', 3, 'sent', '2014-03-11');
INSERT INTO `review` VALUES(1425, 849, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1426, 850, 11, 'This Uninterruptalbe Power Supply (UPS) shall only be used for the existing RADAR near shelter # 1.', 2, 'sent', '2014-03-11');
INSERT INTO `review` VALUES(1427, 853, 11, '1. Ensure that energy efficient electronic ballasts having less than 10% THD (voltage total harmonic distortion) shall be used for fixtures with type T8 flourescent fixtures.\r\n2. Ensure that the luminaire efficiency of flourescent fixtures shall meet the minimum requirements of SAES P-123 table 2.\r\n3. Ensure that Efficacy of Compact fluorescent lights (CFL) shall not be less than 80 Lumen / Watt.\r\n4. Model NLC MHD2/232.E6 type C is not approved, project requirements is High Pressure Sodium type with 110 watts as per IFC drawing VA846993. \r\n6. Ensure that luminaires installed outdoor shall be approved as weather proof and dust tight.\r\n7. Clarify and correct the catalog provided for model NLC490/70W.MH.220IP65, the project requirements is 150 watts High Pressure Sodium (HPS) and not 70 Watts Metal Halide.\r\n8. For JFCC control room, and in Generator buildings the emergency lighting back up requirements shall meet SAES P-123 para. 5.6.3\r\n9. Ensure that proposed model NLC650HP/218.E2.A.M31 Illuminated exit signs shall be manufactured in accordance with NFPA 101 requirements\r\n10. Lighting fixture for King Abdullah Monument (KAM) access road shall match with the existing fixtures in road # 2 as discussed by SAPMT.\r\n11. All lighting fixtures and accessories shall meet Project specification, IFC drawing, SAES P-123 and SAES 0-204.\r\n\r\n', 2, 'sent', '2014-03-23');
INSERT INTO `review` VALUES(1428, 853, 58, 'No comment.', 1, 'sent', '2014-03-12');
INSERT INTO `review` VALUES(1429, 862, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1430, 862, 70, '*IC-SD-846532-01-00 ( Roof Framing Plan ) the exterior corner of two way slab need additional reinforcement as per ACI 318-08 code section 13.3.6 to resist the bending moment at the corner. * The Rebar of Roof Framing Plan is mentioning for example 14ᴓ12@200 .... ether use 14ᴓ12 or ᴓ12@200 it''s same. IC-SD-846532-02-00 ( Plan ) what is the distance between the GB-01 and the face of the col or what is the distance between the GB-01 Center line and the axis? ', 2, 'sent', '2014-03-17');
INSERT INTO `review` VALUES(1431, 861, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1432, 854, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1433, 860, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1434, 860, 70, 'No comment', 1, 'sent', '2014-03-17');
INSERT INTO `review` VALUES(1435, 859, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1436, 858, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1437, 857, 11, '1. The revised calculation were based on the calculated load by security contractor ESE dated Feb. 23, 2014 2. IC has to ensure that the rating is sufficient including the required 30 % spare as stated in High Commission on Industrial Security (HCIS).\r\n', 2, 'sent', '2014-03-30');
INSERT INTO `review` VALUES(1438, 856, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1439, 856, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1440, 855, 70, '', 0, 'sent', '');
INSERT INTO `review` VALUES(1441, 863, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1442, 869, 70, 'KAM Access Road Progress still slow.\r\nICC slightly improves to plan the daily activities but still poor which need more enhancements \r\nThe works at gate 2 & gate 3 still slow and we are afraid of delay.\r\nIC needs to concentrate on the Quality of works also and avoid any kind of violation.', 2, 'sent', '2014-03-17');
INSERT INTO `review` VALUES(1443, 869, 11, '1. IC is not yet submitting material submittal for buildings such as doors, windows, paint, and other materials for building constructions. \r\n2. Many lighting pole, MIDS and Camera poles foundations were damaged during the removal process, IC has to conduct rectification in addition to a proper storage and handling.\r\n3. Many fence and columns were damaged during the removal process, IC has to conduct rectification in addition to a proper storage and handling.\r\n4. IC has to extend the lighting fixtures coverage in order to comply with KAUST Security comments.\r\n5 - 6. IC has to put more efforts in providing quality material submittals.\r\n7. Qualtiy Control personnels for Electrical and Communication is not yet available.\r\n8. Not applicable anymore.\r\n9. No feedback from IC\r\n10. For interfaces issues in STC, Mobily, SEC and SWCC under process by SAPMT.\r\n11. No need to wait for the handing over, IC has to start the shop drawing and related details for wadi wesami culverts.\r\n12. No feedback from IC\r\n13. The performance of Mr. Karar is still under evaluation.\r\n14. Needs more improvement.\r\n15. IC has to extent more in recruiting locals by going to the university and other manpower pooling strategy.\r\n16. IC knows very well that ESE is always claiming issues such as out of scope items, during many occasions of progress meetings and in front of SAPMT. This issue of scope of work between has to be finalized by IC.\r\n17. Needs more improvement.\r\n18. Needs more improvement.\r\n19. No feedback from IC\r\n20. The performance of Mr. Karar is still under evaluation.', 3, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1444, 868, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1445, 868, 70, 'Regarding to the soil improvement cross section, the granular layers 200 mm ( Granular fill / stone 50 – 200 mm ) plus 50 mm ( crush stone 20 – 50 mm ) are not practical. The practical way is one layer 400 mm (  Granular fill / stone  50 – 200 mm ) well graded.', 2, 'sent', '2014-03-18');
INSERT INTO `review` VALUES(1446, 867, 11, 'The scope of work is accepted with the following comments:\r\n1. The concept of the new power supply routing is to avoid down time interruption for the RADAR system during the relocation works of existing wall, power supply for lighting poles and security systems.\r\n2. IC has submit related red-line drawings and Quality records for documentation purposes.', 2, 'sent', '2014-03-31');
INSERT INTO `review` VALUES(1447, 865, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1448, 865, 70, '* A5. Concrete Placement and Consolidation:- Contractor should avoid any type of Honeycomb and Air Bubbles.\r\n** A6. Concrete Curing:- Curing after the stripping by water is not enough, fresh concrete needs some kind of curing as per ACI 308R-01 (Initial curing measures should be applied immediately after the bleed water sheen has disappeared, because the concrete surface is protected against drying as long as it is covered with bleed water.). *** Contractor should avoid to break the panel edge during the stripping process.\r\n\r\n', 2, 'sent', '2014-03-22');
INSERT INTO `review` VALUES(1449, 864, 70, 'Item No. 13 - Box Culvert related to Wadi Khulais IC should complete their part due to resubmitting of the shop drawing and needs long time to purchase the material.', 2, 'sent', '2014-03-18');
INSERT INTO `review` VALUES(1450, 864, 11, '1. The interface coordinator is not visible in ICC office and in site. IC coordinator must be always visible daily.\r\n2. Underground Fiber optic cable thru ITC cable marker located near gate # 3, might be affected by Turnstile Building, this should be added on the list of interface matrix.\r\n', 2, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1451, 864, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1452, 866, 11, 'The comment of CSD has been applied to KPSS switchgear based on March 10, 2014 conference call with SCEC.', 2, 'sent', '2014-03-23');
INSERT INTO `review` VALUES(1453, 873, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1454, 873, 11, '1. CONTRACTOR shall ensure that Intrusion Detection and Assestment System (IDAS) shall meet the requirements stated in the Functional Specification Document PE-000072, IFC Drawings, High Commission on Industrial Security (HCIS) and Saudi Aramco Engineering Standard (SAES-O series).\r\n2. CONTRACTOR shall ensure the quality and performance of the IDAS as a fully integrated system.\r\n', 2, 'sent', '2014-03-23');
INSERT INTO `review` VALUES(1455, 872, 30, 'Approved with no further comments.', 1, 'sent', '2014-03-23');
INSERT INTO `review` VALUES(1456, 872, 11, 'No comment.', 2, 'sent', '2014-03-23');
INSERT INTO `review` VALUES(1457, 877, 58, 'No comment.', 1, 'sent', '2014-03-18');
INSERT INTO `review` VALUES(1458, 877, 70, 'No comment.', 1, 'sent', '2014-03-19');
INSERT INTO `review` VALUES(1459, 876, 30, 'Intercom diagram in VA-847173 sheet 13 contradicts to VA-847191 sheet 6 and equipment installation details. Correct and revise the drawing to eliminate the contradiction and misleading information. ', 2, 'sent', '2014-03-23');
INSERT INTO `review` VALUES(1460, 876, 11, 'No further comment', 2, 'sent', '2014-03-23');
INSERT INTO `review` VALUES(1461, 876, 58, 'No comment.', 1, 'sent', '2014-03-18');
INSERT INTO `review` VALUES(1462, 878, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1463, 878, 11, '1. Provide ICC/ESE/DMT responses to the comments raised by the proponent during the Factory Acceptance Test (FAT).\r\n', 3, 'sent', '2014-03-18');
INSERT INTO `review` VALUES(1464, 879, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1465, 875, 11, '1. This submittal is only for Operator console furniture. Computer monitors and servers, must be submitted separately.\r\n2. Ensure that monitors and servers to be positioned within the console shall fit with the proposed console.\r\n3. Power strips shall be UL listed or approved equal and shall matched with the plugs of computers. \r\n4. Wiring ducts, data and phone outlet shall be UL listed or approved equal.\r\n5. Ensure that the console furniture final paint is coordinated with building/room ambiance.', 2, 'sent', '2014-03-20');
INSERT INTO `review` VALUES(1466, 875, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1467, 874, 11, '1. The lighting pole for King Abdullah Monument (KAM) access road shall match with the existing lighting pole in road # 2.\r\n2. Submit the lighting pole catalog for KAM access road with its related lighting fixtures and foundation details.', 2, 'sent', '2014-03-18');
INSERT INTO `review` VALUES(1468, 870, 53, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1469, 871, 32, 'No Comments. For Info Only.', 1, 'sent', '2014-03-24');
INSERT INTO `review` VALUES(1470, 880, 11, 'No futher comment', 1, 'sent', '2014-03-18');
INSERT INTO `review` VALUES(1471, 880, 70, 'No comment', 1, 'sent', '2014-03-18');
INSERT INTO `review` VALUES(1472, 883, 30, 'Please check SAPID response.', 0, 'sent', '2014-03-26');
INSERT INTO `review` VALUES(1473, 883, 11, 'No futher comment', 1, 'sent', '2014-03-26');
INSERT INTO `review` VALUES(1474, 883, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1475, 884, 30, 'Approved. Please check SAPID response.', 1, 'sent', '2014-03-26');
INSERT INTO `review` VALUES(1476, 884, 11, 'No futher comment', 1, 'sent', '2014-03-26');
INSERT INTO `review` VALUES(1477, 884, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1478, 885, 11, 'Ensure that the proposed Generator will run efficiently for at least 30 percent of its rating as confirmed by the designer SCEC on Feb. 09 2104 meeting.', 2, 'sent', '2014-03-26');
INSERT INTO `review` VALUES(1479, 885, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1480, 886, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1481, 886, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1482, 886, 30, 'Ensure to follow all the specifications and parameters mentioned in 18-SAMSS-625.', 2, 'sent', '2014-03-25');
INSERT INTO `review` VALUES(1483, 887, 30, '1. Drawings shall be rectified specifically for VA-847193 sheets: 22. 23, 24 and 32 with clear details and texts to be seen clearly in A3 size.\r\n2. OSP Cable route Lay-out shall include FOC going to BDC.\r\n3. Refer to VA-847193 sheet 32, detail provided is incomplete without specifying the tie-in connection between new duct naks to the existing duct banks with the existing Manhole #5.\r\n4. Service Manhole Construction details VA-847193 sheet 34 shall comply to SASD AA-036794 and bar bending schedule shall also be included.\r\n5. Manhole Type 1-b Construction Details shall also be provided.\r\n6. FOC Lay-out and diagram including sub-ducting going to BDC were still not ptovided.\r\n7. IDAS FOC Trench Lay-out shall include the trenching up to the point of destination or end of trench. This will also include the lenght of trench. Manhole''s stubouts shall be extended to 12 meters with installed sub-ducts.\r\n8. In addition, the following comments are applicable to drawings VA-847193 sheets 22 and 23\r\na. Include and attached the Cable Pulling Tension Calculation.\r\nb. Provide and indicate the start and end of evry duct bank curves.\r\nc. Two marker tapes shall be provided for the telecom duct banks, refer to SAES-T-911 for details.\r\nd. All occupied ducts with FOC installed shall have a 4x1" sub-ducts installed, refer to SAES-T-624 for details.\r\ne. Provide coordinates to every tie-in points and Electronic Marker System (EMS) shall be provided at each end.\r\nf. Duplication of manhole numbering shall be avoided. Assign dedicated number per each new manhole that will be applied to other drawings such as for Manhole Fold-outs and schematic diagrams.\r\ng. Rectify the number of ducts per ductbanks since it contradicts to manhole call-out''s ductbank assignments.\r\nh. Consider to provide spare ducts to be used for future and for maintenance.\r\ni. Indicate the applicable FOC type whereas B for buried, U for underground and H for Indoor rated cable.\r\nj. Include and specify the manhole type and dimension of each manhole.\r\nk. Include and assign stub-out ducts with 12 meter lenght for evry manhole for future use.\r\nl. Rectify and correct Manhole call-outs details since duct assignments provide misleading information and details.\r\nm. Consider a manhole on duct bank crossings for cable pullthrough, refer to sheet 22 for details.', 3, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1484, 888, 11, '1. This material approval is for Medium Voltage cable size 185 mm2 including its grounding cable size 95 mm2.\r\n2. Shall comply with project specification, Saudi Aramco Standard SAES 104 and 15-SAMSS-502.\r\n3. The revised compliance matrix sent thru email dated April 2, 2014 shall supersede the attachment provided in MS-0055 -A.  ', 2, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1485, 888, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1486, 857, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1487, 857, 70, 'it''s Electrical. Mr. Mark can help.', 2, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1488, 889, 11, '1. Ensure that the proposed Under Vehicle camera is capable of viewing all angles underneath the vehicle and has the characteristics to determine suspected foreign objects.\r\n2. The final approval of UVIS proposed material will be upon the successful Site Acceptance Test.\r\n3. Ensure that the specifications of Power supply, communication switches, softwares, not included in this material submittal shall be approved type.\r\n', 2, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1489, 889, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1490, 889, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1491, 899, 45, '!. Proceed with his selection and placement, however;\r\n2. Performance shall be evaluated within 3-month probationary period to qualify for the vacant slot.\r\n3. He should work-out the renewal of his Aramco Accreditation within his proby period.', 0, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1492, 890, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1493, 901, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1494, 891, 45, '1. Complete all information required in the application Form.\r\n2. Complete all the requirements specified yourself and not the Saudi Aramco ICC Project Team\r\n3. Submit/mail the application form together with the attachment to:\r\n   *MAIL TO SUPERVISOR FOR LOCATION LISTED AT BOTTOM OF PAGE of the Application Form\r\nSUPERVISOR, WAITD-Driver/HEOPTU, PO Box 5250, Jeddah 21422 KSA. Phone: 02-427-4214/4147; Fax: 02-427-4202\r\n4. Contact Safety Team for further explanation if need be.', 0, 'sent', '2014-03-25');
INSERT INTO `review` VALUES(1495, 892, 70, 'I prefer if IC add lean concrete activities under the buildings at Gate2 & Gate 3.', 2, 'sent', '2014-03-25');
INSERT INTO `review` VALUES(1496, 892, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1497, 893, 30, 'No comment', 2, 'sent', '2014-03-31');
INSERT INTO `review` VALUES(1498, 893, 11, 'The candidate should pass on oral interview.', 2, 'sent', '2014-03-26');
INSERT INTO `review` VALUES(1499, 893, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1500, 894, 70, 'For info. IC has a lot of works at many locations ready for construction and in the same time IC will not work at Wadi Wesami if NBH handed over the area to them that moment.', 2, 'sent', '2014-03-26');
INSERT INTO `review` VALUES(1501, 895, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1502, 896, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1503, 900, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1504, 897, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1505, 904, 70, 'Reviewed & No comment.', 1, 'sent', '2014-03-26');
INSERT INTO `review` VALUES(1506, 905, 70, 'Reviewed & No comment.', 1, 'sent', '2014-03-26');
INSERT INTO `review` VALUES(1507, 902, 25, 'The revised scope of work has addressed all the comments, thus the scope of work is approved. The geotechnical approval form attached.  Geotechnical file number 2013/14A is assigned to this supplementary investigation. This geotechnical approval form is to be submitted together with the report. //\r\n\r\nAs per SAES-A-113,  the selected Geotechnical contractor shall provide a letter of endorsement to the geotechnical scope of work. IC is urged to expedite all pending items and shall be completed before starting work. //\r\n\r\nThe work on site for geotechncial investigation shall start with intimation to SAPMT.', 2, 'Pending', '2014-03-26');
INSERT INTO `review` VALUES(1508, 903, 32, 'No comments. Document submitted for information only.', 2, 'sent', '2014-03-27');
INSERT INTO `review` VALUES(1509, 898, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1510, 898, 70, 'No comment', 1, 'sent', '2014-03-26');
INSERT INTO `review` VALUES(1511, 898, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1512, 902, 70, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1513, 902, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1514, 907, 11, '1.Final material approval will depend on the Factory Acceptance Test.\r\n2.Ensure that there will be no blind spot in the IDAS system, the Bill of Quantity stipulated in the subject submittal shall be subjected for final evaluation during commissioning/site acceptance test (SAT).\r\n3.Ensure that the proposed IDAS system will meet the Functional Specification (FSD), High Comissioning on Industrial Security (HCIS) and IFC drawings.', 2, 'sent', '2014-03-28');
INSERT INTO `review` VALUES(1515, 907, 30, '1. The Summary Sheet has misleading information wherein the listed devices with their model number and quantities are not intended for IDAS System such as the camera, camera lens and mounting adaptors.', 3, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1516, 907, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1517, 908, 11, '1. Ensure that the illuminator is equip with an automatic switching device such as a photo-detector switch to turn-on the illuminator on poor lighting situations.\r\n2. The proposed License plate recognition cameras, poles, control cables, shall comply with IFC drawing and Project specification.\r\n3. Ensure that the client workstations, softwares, control cables which is part of LPRS system not included in this material submittal shall be submitted separately.', 2, 'sent', '2014-03-28');
INSERT INTO `review` VALUES(1518, 908, 30, 'No further comment', 2, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1519, 908, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1520, 910, 30, 'Ensure all installation materials and brackets are included and also universal remote control units to be used for both the TV and STB.\r\nEsnure all the proposed models of the devices are up to date.', 2, 'sent', '2014-03-27');
INSERT INTO `review` VALUES(1521, 910, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1522, 910, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1523, 909, 30, 'The type of license shall be provided complying to SAPMT response letter with number L-343/13 dated December 3, 2013.\r\nEnsure to include and provide the installation kits and other accessories such as power adaptor and UTP cable per each phone.\r\nEnsure proposed phone models are up to date with support from manufacturer, otherwise the contractor shall replace and provide the latest upgrade with no addtional cost to SAPMT.', 3, 'sent', '2014-03-27');
INSERT INTO `review` VALUES(1524, 909, 11, 'No comment', 1, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1525, 911, 30, 'Ensure to provide all the infrastructure materials, cabling, groundings and FECs with all of its active components required as per the scope and IFC drawing VA-847192 will be submitted in a separate submittal prior for review of SAPMT.\r\nEnsure that the system will function as stated in the SOW.\r\nEnsure shop drawings will be submitted to detail all the connections.', 2, 'sent', '2014-03-27');
INSERT INTO `review` VALUES(1526, 911, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1527, 911, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1528, 912, 11, 'I forwarded the submittal to Azwinn.', 0, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1529, 912, 70, 'Drawing IC-SD-846864-101-OF1 the section B-B of Footing 2 shows C2 while the Foundations plan shows C1 on F2. The rebar details of detail - 1 (Footing F1) shows 8 bars in each direction while the correct number is 9 bars in each direction. The rebar details of detail - 2 (Footing F2) shows 11 bars in each direction while the correct number is 14 bars in each direction. The total numbers of bars at the rebar schedules are not correct such as total rebar of F1 is 108 instead of 64 …etc.please review all rebar schedules again. The exterior corner of two way slab need additional reinforcement as per ACI 318-08 code section 13.3.6 to resist the bending moment at the corner.', 4, 'sent', '2014-03-28');
INSERT INTO `review` VALUES(1530, 913, 11, 'I forwarded the submittal to Azwinn.', 0, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1531, 913, 70, 'The pipe culverts will intersect with the Rabya utilities ( pipes, electrical cable and telecom cable ) as per soil improvement approved drawing shows the invert level is 1.2 m to the top of the 200 mm Fire Water pipe … etc. IC has to study the utilities invert level and resolve any kind of intersection. I advise IC to submit a drawings show all Rabya utilities with IC’s pipe culverts.', 3, 'sent', '2014-03-29');
INSERT INTO `review` VALUES(1532, 914, 11, 'A provision of direct buried sleeves which consists of 4-6 inches schedule 80 conduit has to be provided nearby STA 0+000.', 2, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1533, 914, 70, 'No comment', 1, 'sent', '2014-03-27');
INSERT INTO `review` VALUES(1534, 915, 70, 'Regarding to drawing, No comment but KAUST still did not confirm the ditch cancelation.', 2, 'sent', '2014-03-27');
INSERT INTO `review` VALUES(1535, 916, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1536, 925, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1537, 925, 70, 'No Comment.', 1, 'sent', '2014-04-02');
INSERT INTO `review` VALUES(1538, 929, 70, 'As per General Note VA-846497 – all elements expose to earth or weather should have 75 mm cover; this is applicable for underground and above the ground elements. The drawing shows the cover less than 75 mm. IC should revise the drawings and comply with the General Notes.\r\nRegarding to Drawing: FOUNDATION & GROUND BEAM DETAIL:\r\n1-Missing Staircase Rebar at Bent Rebar Schedule and No details or Section. 2-check the number of column ties.\r\nRegarding to Drawing: ROOF, BEAM, ELE AND COLUMN DETAILS & PLAN:\r\n1-Parapet wall steel details show the length of the vertical rebar L=4.6 which is wrong. 2- Rebar No. 8 is repeated at two locations, one for roof rebar and the other at stirrup of beam. 3- Rebar No. 11 mentioned in Rebar schedule but it isn’t show in the drawing.  \r\n', 4, 'sent', '2014-04-02');
INSERT INTO `review` VALUES(1539, 929, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1540, 928, 70, 'Attachments No. 3 are Dish wall drawing. 2- ASTM C 309 Type 1 Class B para 3. Classification:  Type 1 is clear or translucent without dye and Class B is Resin base as per ASTM D 883 – terminology “resin, n—a solid or pseudosolid organic material often of high molecular weight, which exhibits a tendency to flow when subjected to stress, usually has a softening or melting range, and usually fractures conchoidally. DISCUSSION— In a broad sense, the term is used to designate any polymer that is a basic material for plastics. (1982â€), while Masterkure 161 is bitumen base. 3- IC/FCC will apply this material immediately after stripping then they will store the footing under the sun where Masterkure 161 is not control the heat that mean the concrete temperature will be more than the required which effect the strength of it. 4- If IC/FCC submits the right curing material, we are still afraid that IC/FCC will not apply the curing material after stripping immediately; they use to take time to start the curing process. My recommendation is to use water, burlap...etc. for curing process.', 4, 'sent', '2014-03-31');
INSERT INTO `review` VALUES(1541, 928, 58, 'No comment.', 1, 'sent', '2014-04-06');
INSERT INTO `review` VALUES(1542, 927, 30, '1. Rectify the model of fiber patch panel and ensure the proposed models can accomodate 8 cores, 16 cores, 48 cores and 96 cores fiber optic cables accordingly. All accessories shall be included and clearly identified.\r\n', 3, 'sent', '2014-04-02');
INSERT INTO `review` VALUES(1543, 926, 30, '1. It is contractor''s responsibility to ensure all components are provided with reference to IFC drawing VA-847227 Sheet 3 and ensure system functionality and integration to KAUST existing Data Network System.\r\n2. Ensure Devices power plugs shall match to the Project scope power outlets.\r\n', 2, 'sent', '2014-03-31');
INSERT INTO `review` VALUES(1544, 926, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1545, 927, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1546, 924, 11, '1. Ensure that the width and the alignment of the turnstile is coordinated with the width of metal detector and x-ray machine.\r\n2. Internal wirings, and materials to be provided inside the turnstile for control purposes shall be certified by the manufacturer.\r\n3. Shall comply with IFC drawing and Project specification.', 2, 'sent', '2014-04-02');
INSERT INTO `review` VALUES(1547, 924, 58, 'No comment.', 1, 'sent', '2014-04-06');
INSERT INTO `review` VALUES(1548, 923, 30, 'No further comment', 2, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1549, 923, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1550, 923, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1551, 922, 11, 'No further comment.', 1, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1552, 922, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1553, 922, 30, 'The proposed materials are spproved however, other FEC components such as tamper switch, breather, fiber patch panel, temperature sensor and others shall be provided and submitted prior for review of SAPMT', 2, 'sent', '2014-03-31');
INSERT INTO `review` VALUES(1554, 921, 32, 'No Comments', 1, 'sent', '2014-03-30');
INSERT INTO `review` VALUES(1555, 921, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1556, 920, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1557, 920, 30, 'approved with no further comment. Ensure the power plugs are matching with the electrical outlets required by the project.', 2, 'sent', '2014-03-30');
INSERT INTO `review` VALUES(1558, 920, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1559, 919, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1560, 919, 11, 'No more futher comment', 1, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1561, 919, 30, 'No further comment', 2, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1562, 918, 11, '1. The battery back up time shall meet the requirement of 4 hours as per 4.3.5 of SEC 07 HCIS.\r\n2. Ensure that the VRLA type battery has the service life of less greater than 10 years as per SAES P-103 ', 2, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1563, 918, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1564, 917, 30, 'see email for my comments', 2, 'sent', '2014-04-07');
INSERT INTO `review` VALUES(1565, 917, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1566, 917, 11, '1. Installation detail for Vessel Barrier missing.\r\n2. Boat Identification System missing\r\n3. Electronic Marquee Display, Traffic light details are missing\r\n4. Identify the correct height of RADAR # 3, in VA-847226 it shows 8 meter while in VA-847174 sht 007 is 15 meters.\r\n5. Each FEC shall have an individual drawings, and shall not be typical (power cable and control cable are different, power supply circuit number/UPS building source is different)\r\n6. In UPS building the location of the Telecommunication Cabinet is in confilct with the location of readers, Designer has to ensure that there is no encroachment of equipments.\r\n7. The name of SONAR is SONAR # 1, SONAR # 2, SONAR # 3 and SONAR # 4 not KAUST # 1, and so on. see VA-847174 sht 006.\r\n8. Clarify the title Cause and Effect diagram of drawing #''s VA-847159 sht 001 to 007, while the drawings are showing cross section. \r\n9. Ensure that all conduits/control cable serving MIDS and Cameras going out from the equipment cabinet (FEC) is from bottom entry, VA-847156 sht 001 is showing in the side and on the top.\r\n10. The security corridor must be re-design due to the removal of the ditch.\r\n11. Clarify the location of Security Head Office in VA-847161 sht 005.\r\n12. Provide dry contact connection between SACS maxess with Fire alarm control panel (FACP) VA-847164 sht 008 (This comment is applicable to all buildings with FACP and SACS system.)\r\n13. Provide details for loop/sensor cables underneath asphalt pavement for Crash barriers, UVIS,, Drop arm, and RFID.\r\n14. Identify the type of back boxes and conduits that will be used for cameras to be installed outdoor and under sunshade VA-847162 sht 004\r\n15. Clarify why the position of the LPRS and Proximity (SACS) reader for outbound lane are after the first drop arm barrier? VA-847162 sht 007, ensure that it is meeting the HCIS requirements and best practices.\r\n16. Ensure that all telecom cabinets shall secure a dedicated power supply from building panel. This power supply has to be indentified thru panel and circuit number.\r\n17. Provide installation details for SONAR head # 4.\r\n18. The coordinates of the Vessel barrier shall be in Ain Al abd system VA-847174 is showing wrong representation of coordinates.\r\n19. Provide conduit run/raceway detail for Long Range Camera from TER room to the building roof top.\r\n20. Provide installation detail of the wall display inside JFCC building.\r\n21. Provide grounding and bonding details for the underground race floor in JFCC building.\r\n22. Ensure that field equipment cabinet (FEC) has a security door lock as shown in VA-847196 sht 001\r\n23. Ensure thal all poles to be used for camera pole, MIDS are hot dip galvanized, and all nuts and bolts are stainless steel this type of materials needs to reflect in drawing VA-847199 sht 001. (Except for the drop arm barrier the bolt and nut shall be made of plastic)\r\n\r\nGeneral Notes:\r\n1. The IDAS camera, microwave quantities and coverage provided in the drawings are for reference only, any blind spot that will be discovered during the commissioning are subject for addition of camera/s as stated in the contract documents IDAS FSD - PE-000072 page 18 of 13\r\n2. For all network block diagrams, it is the sole responsibility of the designer to ensure that the network will comply with system requirements and project specifications.\r\n\r\n\r\n\r\n\r\n\r\n', 2, 'sent', '2014-04-06');
INSERT INTO `review` VALUES(1567, 917, 72, '1.	Cable Schedule to be provided including cable tag list.\r\n2.	Work station details for all workstations ( LPRS,UVIS,X-Ray,IDAS,LRDAS ) to be provide.\r\n3.	VA- 847226:- UVIS system to be include in the security integration drawing.\r\n4.	Drawing reference number column is empty for most of the drawings, corresponding drawing reference  to be included.   \r\n5.	Dwg no VA 847174 – ENS block diagram is missing in the submittal.\r\n', 2, 'sent', '2014-04-08');
INSERT INTO `review` VALUES(1568, 930, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1569, 930, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1570, 934, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1571, 939, 32, 'No Comments. For information only.', 2, 'sent', '2014-04-02');
INSERT INTO `review` VALUES(1572, 938, 11, '1. IC has to follow the size of the 185 mm2 MV cable as well as the package substations stated in BID package, this instruction has been highlighted in numerous occasions such as SAPMT/IC/SCEC meeting dated Feb. 9, 2014, SAPMT/IC/SCEC conference call dated March 10, 2014 and progress meeting # 28 dated March 31, 2014. \r\n2. IC has to provide only provision for power system automation.\r\n3. IC has to follow IFB configuration for the switchgear except as to add only one 1200 AT as a tie breaker, to comply with Consulting Services Division (CSD) comments.', 4, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1573, 938, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1574, 932, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1575, 933, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1576, 933, 11, '1. Rename the description of the submittal with "PVC CONDUITS NEMA TYPE DB and EB for ELECTRICAL AND COMMUNICATION conduits and duct banks".\r\n2. Include in the submittal the proposed conduit spacers and conduit fittings.\r\n3. Ensure that the PVC conduits to be used will comply with SAES P-104, IFC drawings and Project Specification.', 3, 'sent', '2014-04-02');
INSERT INTO `review` VALUES(1577, 941, 45, 'Please proceed with his hiring, however he will undergo a 3-month probation to show his capabilities or he will be re-assigned to perform other Safety related jobs in the Department where he is best fitted.', 0, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1578, 940, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1579, 940, 70, 'Fence should be grounded as per SAES-M-006 Para 5.1.\r\nAll post should be extending 975 mm into concrete footing as per SAES-M-5.2.1.\r\nFootings for all posts shall extend 100 mm below the end of the post.\r\nThe Chain link has a 50 mm diamond mesh and the standard length of roll shall be 15 m or greater and shall be woven continuously without splices as per SAES-M-006 Para 5.5.1 and HCIS-4.12.2.1\r\nThe tension wires should provide at the middle zone as per the attached drawing GI-AS-62037 and the other at the bottom of the fence as per Saudi Aramco Standard Drawing AB-036677-001-02 which is not mentioned in the drawing attached. When fully constructed the barbed wire, tension wire, fabric, and truss rods shall be taut.\r\nContractor should submit the shop drawing of concrete footing and beam. In general the submittal should follow the Aramco Standards and HCIS.\r\n', 2, 'sent', '2014-04-04');
INSERT INTO `review` VALUES(1580, 940, 11, '1. Ensure that the chain link fence has the provision to be connected in the grounding grid.', 2, 'sent', '2014-04-03');
INSERT INTO `review` VALUES(1581, 936, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1582, 935, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1583, 933, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1584, 942, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1585, 942, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1586, 942, 70, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1587, 942, 47, 'NO COMMENT', 1, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1588, 943, 70, 'The attached drawing is not the last approved drawing. provide the depth od duct bank is not there. The number and the diameter of the upper reinforcement are not mentioned.', 3, 'sent', '2014-04-03');
INSERT INTO `review` VALUES(1589, 943, 47, '#ICC to revise the DWG on the submittal and resubmit as discussed.\r\n#ICC to to use the correct DWG for all their submittal and RFI', 2, 'sent', '2014-04-03');
INSERT INTO `review` VALUES(1590, 944, 47, 'No comment', 1, 'sent', '2014-04-03');
INSERT INTO `review` VALUES(1591, 944, 70, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1592, 944, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1593, 944, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1594, 944, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1595, 945, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1596, 946, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1597, 947, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1598, 949, 11, 'See comment of Mr. Jun Angeles \r\n\r\nDear Ditta, Kindly attached in the PM anywhere his comment, I saved it as pdf and send to your email', 3, 'sent', '2014-04-05');
INSERT INTO `review` VALUES(1599, 949, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1600, 950, 45, 'This document and similar submittals shall be maintained on file for records verification purposes by 3rd party during external audits. \r\nIt serves as basis of the PEs,SPE and Safety Advisor in closing-out Safety, Health and Environmental issues related to the Project Safety Index (PSI) System.\r\nTo be maintained in the Register of Corrective Actions of ICC Records.\r\n', 0, 'sent', '2014-04-01');
INSERT INTO `review` VALUES(1601, 952, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1602, 952, 30, 'No Comment. The personnel was interviewed by SAPID without notifying SAPMT. PLease check SAPID.', 2, 'sent', '2014-04-06');
INSERT INTO `review` VALUES(1603, 953, 11, '1. PVC conduits and fittings shall comply with SAES P-104 para. 8.1.1 and 8.1.2\r\n2. EGA Honeywell does not belong to the recommended manufacturers provided in construction specification document section 16110 page 2 of 10.\r\n3. IC has to segregate the submittal of PVC Conduits and Fittings, Wire way and Back boxes to avoid confusion.', 4, 'sent', '2014-04-06');
INSERT INTO `review` VALUES(1605, 955, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1606, 957, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1607, 958, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1608, 956, 47, 'ICC to comply with SAPMT response 1-3 and the manufactures application instruction\r\nICC use the well trained personnel''s to execute the works and avoid any construction, safety and quality deviation', 2, 'sent', '2014-04-09');
INSERT INTO `review` VALUES(1609, 956, 70, 'Regarding to Nonshrankage grout the minimum 28 days compressive strength shall be 34.5 MPA (5,000 psi) as per SAES-Q-10 para 4.2.1. Regarding to Anti climb spike I prefer to be same as the existing ( V shape ).', 2, 'sent', '2014-04-06');
INSERT INTO `review` VALUES(1610, 909, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1611, 953, 58, 'Approved with no comment.', 1, 'sent', '2014-04-19');
INSERT INTO `review` VALUES(1612, 910, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1613, 918, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1614, 960, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1615, 960, 70, 'Reviewed & no comment. If SAPID approved him, we still have the right to revoke his approval on unsatisfactory performance.', 2, 'sent', '2014-04-07');
INSERT INTO `review` VALUES(1616, 961, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1617, 962, 21, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1618, 962, 11, 'I would like to endorse the subject material submittal to SAPID Mechanical and to Material Specialist (Fahad Zahrani) since the inspection level is 2.', 0, 'sent', '2014-04-07');
INSERT INTO `review` VALUES(1619, 964, 32, 'No Comments. For Info Only', 2, 'sent', '2014-04-07');
INSERT INTO `review` VALUES(1620, 965, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1621, 965, 11, 'Please add the following long lead items /  Building Mandatory equipment’s:\r\n\r\nElectrical:\r\n•	Package Substation\r\n•	MV cable\r\n•	Switch racks\r\n•	UPS and Batteries\r\n•	Fire alarm control panel and notification devices.\r\n•	LV cable /  Building wires\r\n•	Grounding rods / grounding conductors / Lighting Protection\r\n•	Direct Digital Controller and sensors\r\n\r\nHVAC:\r\n•	Package Air-conditioning Unit\r\n•	Fan Coil Unit\r\n•	Exhaust Fans\r\n', 2, 'sent', '2014-04-09');
INSERT INTO `review` VALUES(1622, 965, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1623, 965, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1624, 973, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1625, 966, 32, '* The Subject of submitted letter shall be changed as "Request for Time Extension".\r\n\r\n* Contractor has to provide the Proposed Project Completion date along with this letter.\r\n\r\n* Contractor has to provide complete data when the reasons for highlighted for Time Extension.\r\n\r\n* Contractor has to provide the proper Time Impact Analysis for the highlighted reasons by using their approved baseline Schedule.\r\n\r\n* As highlighted in the letter(Clause 19 of Schedule H), contractor has the contractual rights for Additional time request subject to how the delays affects the Mechanical Completion Date shown on Critical Path in the detailed work schedule(Refer Clause 19.2.2 of Schedule H).', 3, 'sent', '2014-04-13');
INSERT INTO `review` VALUES(1626, 967, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1627, 968, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1628, 970, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1629, 970, 70, 'No Comment.', 1, 'sent', '2014-04-14');
INSERT INTO `review` VALUES(1630, 970, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1631, 971, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1632, 972, 30, 'approved', 2, 'sent', '2014-04-10');
INSERT INTO `review` VALUES(1633, 972, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1634, 972, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1635, 974, 11, '', 1, 'sent', '2014-04-10');
INSERT INTO `review` VALUES(1636, 974, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1637, 975, 21, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1638, 975, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1639, 975, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1640, 975, 72, 'No comments.', 1, 'sent', '2014-04-13');
INSERT INTO `review` VALUES(1641, 976, 47, '#The backfilling and excavation to be reduced by +/- 40% and the construction of Perimeter fence to be expedited;\r\n#Provision of stormwater drainage system and low areas to be omitted and can only be considered after the installation of the perimeter fence and the maintenance road;\r\n#The Perimeter fence elevation/ alignment must be revised to match the MOT and avoid too much excavation/ backfilling.\r\n#The construction schedule to be reduced/ revised by +/-20% before the initial completion date.\r\n#Access gates for the maintenance road to the ditch to be cancelled\r\n#Ditch connection with the flood damage structures(Wadi Wesami/ Khulais) to be cancelled and a revised IFC drawing is is required and should meet KAUST security requirements.', 2, 'sent', '2014-04-19');
INSERT INTO `review` VALUES(1642, 976, 11, 'Sir,\r\n\r\nNo changes in cable length, below can be added on the list.\r\n\r\n1. Removal of Electrical Duct banks\r\n2. Removal of swing gate access\r\n\r\n', 2, 'sent', '2014-04-17');
INSERT INTO `review` VALUES(1643, 976, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1644, 976, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1645, 976, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1646, 968, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1647, 977, 11, 'No comment ', 1, 'sent', '2014-04-15');
INSERT INTO `review` VALUES(1648, 977, 47, 'ICC to provide cross section at different intervals to show the tie-in between the MOT, Patrol Road,Perimeter Fence, Idas/ Midas and Maintenance Road and also indicate the gradual slope change as per previous discussions.', 3, 'sent', '2014-04-13');
INSERT INTO `review` VALUES(1649, 977, 70, 'The fence changes from K4 to K12 at St.4+150, we need more details of foundation and columns. The contractor shall add the expansion joints if the system will not maintain the expansion stresses, we need more details. When the elevation change with 100 mm as mentioned in the drawing, what is the column height? We need more details.', 3, 'sent', '2014-04-14');
INSERT INTO `review` VALUES(1650, 978, 70, 'No Comment.', 1, 'sent', '2014-04-13');
INSERT INTO `review` VALUES(1651, 978, 47, 'No Comment', 1, 'sent', '2014-04-13');
INSERT INTO `review` VALUES(1652, 979, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1653, 979, 32, 'No Comments', 1, 'sent', '2014-04-14');
INSERT INTO `review` VALUES(1654, 979, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1655, 980, 32, 'No Comments. Submittal is For info only.', 2, 'sent', '2014-04-14');
INSERT INTO `review` VALUES(1656, 980, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1657, 981, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1658, 981, 47, '#ICC to check the heading provided and report only at that area;Sub heading A.1.2 have no relation to item A.1.2.6\r\n#Please verify if Sub heading A.1.3.7 (Soil Improvement)and the items that follows from A.1.4.1-7 are okay or if it should be Sub heading A.1.4 followed by A.1.4.1-7 sequencing.\r\n# Sub heading A.1.5 ''Naval Base Area'' and item A.1.5.3(Wadi Wesami) have no relation', 2, 'sent', '2014-04-13');
INSERT INTO `review` VALUES(1659, 981, 70, 'No comment.', 1, 'sent', '2014-04-13');
INSERT INTO `review` VALUES(1660, 789, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1661, 789, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1662, 789, 57, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1663, 789, 70, 'No comment', 1, 'sent', '2014-04-19');
INSERT INTO `review` VALUES(1668, 982, 70, 'No Comment', 1, 'sent', '2014-04-14');
INSERT INTO `review` VALUES(1669, 982, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1670, 982, 47, 'ICC to provide a bending schedule for the rebar and to construct accondingly', 2, 'sent', '2014-04-13');
INSERT INTO `review` VALUES(1671, 982, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1672, 983, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1673, 983, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1674, 983, 32, 'No Comments. However, releasing the payment shall be concurred by SAPMT Material department and Cost Engineer.', 2, 'sent', '2014-04-14');
INSERT INTO `review` VALUES(1675, 983, 11, '1. Redundant server for SONAR SYSTEM is missing in the provided SONAR Purchased order list of materials.\r\n2. Ensure that system training and familiarization shall be included purchased order, as per contract requirement Appendix H section 7.0', 3, 'sent', '2014-04-13');
INSERT INTO `review` VALUES(1676, 985, 11, 'The variation order is fair as per the following, the new SEC substation has 1200 ampere feeder breakers and we must follow their feeder sizing, for the additional tie breaker this was resulted with the comment of Consulting Services Division for Switchgear optimization.', 2, 'sent', '2014-04-13');
INSERT INTO `review` VALUES(1677, 985, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1678, 986, 39, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1679, 988, 11, 'Sir,\r\n\r\nContractor cannot produce A1 size of communication and security drawing. They only give A3 size drawing.\r\n', 2, 'sent', '2014-04-15');
INSERT INTO `review` VALUES(1680, 988, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1681, 988, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1682, 989, 11, '1. Identify the power supply of SONAR Head # 4, Power supply from Uniterruptable Power Supply (UPS) shall be different from the existing.\r\n2. In IFB drawing and 50 percent detail design package, new SONAR servers will be installed in JFCC building server room, however in IFC drawing it was stated that existing KAUST Sonar servers located in SHQ will be used to accomodate SONAR # 4, IC/ESE has to include document or signed MoM for this changes.\r\n3. In addition to this method of statement, IC/ESE has to provide a construction specification for work execution.', 2, 'sent', '2014-04-16');
INSERT INTO `review` VALUES(1683, 989, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1684, 989, 72, '1. Sonar head tag to be changed to # SONAR 1,2,3.', 2, 'sent', '2014-04-17');
INSERT INTO `review` VALUES(1685, 989, 70, 'Regarding to Civil works: (a) As per point (2) the contractor refer to Drawing 8162 for the concrete foundation we need this drawing also we need details of foundation & column.  (b) As per point (2) the contractor refer to the Sonardyne Procedure to seal bolts with resin, we need the procedure and which is the material of resin they will use? (c) In point (3) what is the Excavation method the contractor will use? And after excavation which is the method or the test that the contractor will use to ensure the ground is strong enough to carry the foundation? And which type of material the contractor will use for backfilling. (d) After installation, is the foundation need any type of protection like boulders around it to protect it from water wave or water current erosion? (f) As per point (10) we need more details about the Sonar Marker Buoys such as the type of fixing, the material etc...\r\nRegarding to Quality: the contractor should attach the Inspection and Test Plan ( ITP ) and the Saudi Aramco Check Lists.\r\n', 3, 'sent', '2014-04-16');
INSERT INTO `review` VALUES(1686, 989, 47, 'no comment', 1, 'sent', '2014-04-17');
INSERT INTO `review` VALUES(1687, 990, 32, 'SAPMT has reviewed the subject submittal and rejected with following comments.\r\n\r\n* "For the Week Progress" at Level I & Level II Summary shown as 0%. It can''t be 0% for both the Plan and Actual.\r\n\r\n* Data date for the submitted Weekly Report No. 33 shall be April 11, 2014 whereas it is wrongly mentioned as April 04, 2014.\r\n\r\nContractor key personnel are advised to review the document before signing and submitting to SAPMT.', 4, 'sent', '2014-04-15');
INSERT INTO `review` VALUES(1688, 997, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1690, 997, 72, '  1. Badging station to be included in the submittal as per PE-000071.\r\n\r\n  2. Operator work station to be included in the submittal as per PE-000071. \r\n  \r\n  3. Enclosure,Power supply,door lock/open relays and push button details to be submitted.\r\n\r\n  4. All Reader interface shall be supplied with internal DC battery back up for minimum 8 hour including\r\n     power to energize door lock.  ', 2, 'sent', '2014-04-20');
INSERT INTO `review` VALUES(1691, 991, 58, 'Approved with no comment.', 1, 'sent', '2014-04-20');
INSERT INTO `review` VALUES(1692, 991, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1693, 991, 52, 'Inspection has reviewed and accepted except as noted:\r\n 25mm & 50mm spacers are to be used as chair and wheel spacers where 25mm is allowed for vertical clearence only.', 0, 'Pending', '2014-04-16');
INSERT INTO `review` VALUES(1694, 992, 58, '1) use the correct 9com 6000000573 with the correct discribtion (Bolt Assembly, Anchor)\r\n\r\n2) It shall has inspection level 1\r\n\r\n3) It has to be procured through an approved manufacturer', 3, 'sent', '2014-04-20');
INSERT INTO `review` VALUES(1695, 992, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1696, 992, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1697, 993, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1698, 994, 32, 'No Comments', 1, 'sent', '2014-04-17');
INSERT INTO `review` VALUES(1699, 995, 32, 'No Comments', 1, 'sent', '2014-04-17');
INSERT INTO `review` VALUES(1700, 999, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1701, 1001, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1702, 1003, 21, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1703, 1003, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1704, 1003, 58, 'Sappco is limited to Pipe Sizes ½" to 10"', 2, 'sent', '2014-04-20');
INSERT INTO `review` VALUES(1705, 1003, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1706, 997, 11, '1. Provide the missing items which is part of SACS system deliverables such as Badging Station and Fingerprint System.\r\n2. Contractor has to ensure that all materials stated in IFC, and project specification will be submitted wihtout further delay.\r\n\r\n\r\n', 3, 'sent', '2014-04-22');
INSERT INTO `review` VALUES(1707, 1004, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1708, 1004, 70, 'No comment', 1, 'sent', '2014-05-15');
INSERT INTO `review` VALUES(1709, 1004, 47, 'Comments were adopted on the revised schedule', 2, 'sent', '2014-05-13');
INSERT INTO `review` VALUES(1710, 1004, 11, '1. Civil works for package substation such as backfilling, compaction, blinding and foundations, curing missing.\r\n2. Radio Frequency Identification (RFID) system with acvity ID CSF-1050 to 1080 shall be deleted. RFID is part of SACS system and must be included under activity SDF-1010.\r\n3. Provide the schedule of upgrading the existing guardhouse, and demolision of existing turnstile.\r\n4. The construction schedule of IDAS system (activity ID CSF-1000) must be adjusted according to the readiness of the security corridor KPSS wall and maintenance road schedule.\r\n5. Provide the construction schedule of Batteries, Chargers and UPS inside JFCC building\r\n6. Specify which activity does Fire water/Portable water lines belongs.\r\n7. Specify if holding tanks, oily tanks were included in the buildings.\r\n8. Pavillion is missing in the procurement plan\r\n9. Include the MEP commissioning schedules\r\n10. Provide the Procurement, and Construction Schedule of Switchrack\r\n11. Provide the construction schedule of Generator buildings.\r\n', 3, 'sent', '2014-04-26');
INSERT INTO `review` VALUES(1711, 1004, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1712, 1004, 70, 'No Comment', 1, 'sent', '2014-05-15');
INSERT INTO `review` VALUES(1713, 1004, 47, 'Comments were adopted on the revised schedule', 2, 'sent', '2014-05-13');
INSERT INTO `review` VALUES(1714, 1004, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1715, 1005, 11, 'No further comment', 1, 'sent', '2014-04-27');
INSERT INTO `review` VALUES(1716, 1005, 47, '#Concern about IC deleting some items that were not closed on the previous MOM.\r\n#Not all IC attendees are reviewing MOM before a draft submittal to SAPMT.', 2, 'sent', '2014-04-24');
INSERT INTO `review` VALUES(1717, 1005, 70, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1718, 1007, 11, '1. Provide a sample materials of the lighting poles, to be delivered here in Thuwal. \r\n2. Galvanization process shall comply with American Society for Testing and Materials (ASTM) and or approved related international standard.', 2, 'sent', '2014-04-22');
INSERT INTO `review` VALUES(1719, 1007, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1720, 1008, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1721, 1009, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1722, 1010, 11, 'Reference to the subject matter SAPMT is requesting KAUST to reserve feeder breakers number 8 and 19 of SEC main substation under construction, instead of connecting to sub-station number 4 under research park project due to the following: 1- Readiness of substation number 4. 2- High risk in running 1.6 km of cabling that will cross congested underground utilities in road number 5 3- KPSS Generator building is only 200 meters away from new SEC -2 substation compared to substation number 4 which is about 1600 meters away. Enclosed in this letter is Building locations of Generator Building, Substation # 4 and New SEC-2 Building, and new SEC-2 switchgear breaker assignment for your reference. Should have any question contact Fahad A. Al Balawi ', 2, 'sent', '2014-04-24');
INSERT INTO `review` VALUES(1723, 1011, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1725, 1013, 70, 'General notes are not correct which are related to MV cables. Please revise them.\r\nDuct Bank 1:\r\n1.	The elevation 2.96 is not correct, please check the remaining elevation and raise the duct bank to the minimum depth requirement by Aramco standard to avoid the water table area. \r\n2.	ICC pipe sleeve should be the first one and RABYA is the second pipe sleeve to avoid crossing each other.\r\n3.	The Duct height is not mentioned.\r\n4.	Delete the soil improvement word because no soil improvement will be there.\r\nDuct Bank 2:\r\n1.	Add elevation to the section.\r\n2.	The hook length 300 mm of the horizontal (top and bottom) rebar is not correct\r\n', 2, 'sent', '2014-04-26');
INSERT INTO `review` VALUES(1726, 1013, 11, 'No further comment.', 1, 'sent', '2014-04-26');
INSERT INTO `review` VALUES(1727, 1014, 30, 'approved', 1, 'sent', '2014-04-26');
INSERT INTO `review` VALUES(1728, 1015, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1729, 1017, 58, 'No comment.', 1, 'sent', '2014-05-06');
INSERT INTO `review` VALUES(1730, 1017, 11, 'Sir,\r\n\r\nThe sample lighting fixture provided is similar with the existing, in terms of shape and lighting lux.', 1, 'sent', '2014-05-05');
INSERT INTO `review` VALUES(1731, 1017, 72, '  1. Ensure the colour for the lighting fixture shall match with the pole.\r\n\r\n  2. Provide a fixture sample along with the pole for the final approval.\r\n\r\n  3. Contractor responsibility to ensure full compliance of the specification with the existing lighting fixture as per KA714490 ,note 3.', 2, 'sent', '2014-04-27');
INSERT INTO `review` VALUES(1732, 1018, 58, 'No comment.', 1, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1733, 1018, 11, 'No further comment.', 1, 'sent', '2014-04-27');
INSERT INTO `review` VALUES(1734, 1018, 72, 'No comments', 1, 'sent', '2014-04-30');
INSERT INTO `review` VALUES(1735, 1019, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1736, 1020, 47, '#QA manager to check and correct all mistakes/ errors before any document submission to Aramco\r\n#Method statement should be self explanatory to the foremen / labour to carry out the job with all the steps to be followed.\r\n#IC to check the site conditions before finalising any sketch or shop drawing to avoid reworks or resubmittals and determine the best possible way to carry out the works..', 2, 'sent', '2014-04-29');
INSERT INTO `review` VALUES(1737, 1020, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1738, 1021, 11, 'Sir, This is only for information.\r\n\r\nThe site survey will be held on May 5, 2014 from 10:00 am to 11:00 am.\r\n\r\nBelow are the names of the personnel:\r\n\r\nName	\r\nKhalied Makki	\r\nKhalied Alkojok	\r\nIbrahim Osama	', 2, 'sent', '2014-05-05');
INSERT INTO `review` VALUES(1739, 1021, 72, 'No comments', 1, 'sent', '2014-04-30');
INSERT INTO `review` VALUES(1740, 1022, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1741, 1022, 70, 'Its contractual issue; IC did not provide a single contractual reference supporting their claim that Saudi Aramco have to coordinate with the other contractors to solve the interface issues. ', 4, 'sent', '2014-04-27');
INSERT INTO `review` VALUES(1742, 1023, 45, 'The requested candidates passed our performance evaluation covering their probationary period. Messrs Mallik and Farouk are therefore qualified to be regularized and be designated as Safety Officers for ICC and FCC respectively. However, any gross misconduct or negligence of duties and responsibilities as Safety Officer shall be dealth with accordingly as per established ICC Code of Discipline.\r\n\r\nPlease proceed with their official acceptance. Thank you', 0, 'sent', '2014-05-06');
INSERT INTO `review` VALUES(1743, 1024, 58, 'No comment.', 1, 'sent', '2014-04-28');
INSERT INTO `review` VALUES(1744, 1024, 11, 'Below comment is from Wenceslao Angeles: I have no further comment.\r\n\r\n\r\n* Protective devices  and controls shall comply with Appendix A of 16-SAMSS-504 for the list of approved manufacturer and model with its corresponding ANSI function number that will be used in the proposed 13.8KV Switchgear at Generator Building\r\n• Comply with all the required protection for Generator as per SAES-P-114, paragraph 6.0 in the breaker compartment of Emergency Generator \r\n• Provide all the required vendor drawings such as Single Line Diagram, Three Line Diagram, set up 13.8KV Switchgear with corresponding dimensions of each compartment, mounting details  and accomplished Data Schedule in the NMR-601 submittal\r\n', 2, 'sent', '2014-04-28');
INSERT INTO `review` VALUES(1745, 1024, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1746, 1025, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1747, 1025, 47, '#IC to expedite on documents approval/ resubmission after SAPMT comments, SAPMT spent only 1 week to review and response on this document and IC took 1.5 months to only correct and resubmit the very same document. \r\n#IC to revise this method statement and include the approved lifting hook shop drawing and the repair methodology.\r\n#IC to provide a minimum of 10 mm chipping when using this product as per manufactures recommendation.\r\n# water:powder ratio to be maintained at all time as well as the use of ice blocks/ working shelter to maintain the mixing water temperature as per manufactures recommendation.', 2, 'sent', '2014-04-29');
INSERT INTO `review` VALUES(1748, 1025, 70, 'RENDERROC TG has compressive strength 30 Mpa after 28 days which is less than 34.5 Mpa the compressive strength of the concrete, as per SAER 5803 Para 4.1 the good repair improves the strength... etc.', 2, 'sent', '2014-04-29');
INSERT INTO `review` VALUES(1749, 1026, 32, 'No Comments. For Information only.', 2, 'sent', '2014-04-28');
INSERT INTO `review` VALUES(1750, 1027, 32, 'No Comments. For Information only.', 2, 'sent', '2014-04-28');
INSERT INTO `review` VALUES(1751, 1027, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1752, 1028, 32, 'No Comments. For Information only.', 2, 'sent', '2014-04-28');
INSERT INTO `review` VALUES(1753, 1028, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1754, 1029, 11, '1. Provide the switchrack dimension and panel arrangement shop drawings.\r\n2. All breakers shall pass the required testing procedure and commissioning requirements as per Saudi Aramco Pre-Commissioning form P -030 for molded case circuit breakers.\r\n3. Switchrack Lighting fixtures and receptacle outlets shall be outdoor type.\r\n4. Ensure that switchrack structure will meet ANSI requirements for hot dip galvanization.\r\n5. Ensure that all panel enclosure will meet SAES P-104 and 16-SAMSS-512 ', 2, 'sent', '2014-04-29');
INSERT INTO `review` VALUES(1755, 1030, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1756, 1032, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1757, 1033, 30, 'Ensure that the proposed 8 core FOC may fit to the cable entrance of the proposed fiber patch panel.', 2, 'sent', '2014-04-29');
INSERT INTO `review` VALUES(1758, 1031, 11, '1. Provide the organizational chart of the MEP personnels.\r\n2. Provide the Curriculum Vitae''s (CV''s) of Site Engineer, Supervisor, Quality Control and Electricians that will perform the work. These personnels shall pass SAPMT/SAPID interview.\r\n3. Testing and commissioning of electrical equipments such as but not limited to LV panel boards, Switchracks, Switchgears, Package Substations, HVAC Air Balancing, shall be executed by an approved thirdy party. \r\n4. ICC shall provide correct tools and calibrated measuring meters.', 3, 'sent', '2014-05-02');
INSERT INTO `review` VALUES(1759, 1031, 12, '-ICC is urged to provide breakdown for all buildings and must provide bill of quantities for all buildings.\r\n -All buildings must be constructed by one subcontractor', 3, 'sent', '2014-04-30');
INSERT INTO `review` VALUES(1760, 1035, 12, 'the comment was sent by email to Sohail ', 3, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1761, 1036, 12, '\r\n-ICC is urged to provide breakdown for all buildings and must provide bill of quantities for all buildings.\r\n-All buildings must be constructed by one subcontractor\r\n', 3, 'sent', '2014-04-30');
INSERT INTO `review` VALUES(1762, 1033, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1763, 1029, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1764, 1015, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1765, 1037, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1766, 1037, 47, '#ICC to submit the design calculations of the lifting hooks to justify load capacity.\r\n#No section detail of the lifting hook pockets, ICC to provide a complete foundation shop drawing indicating the rebar fixing / arrangement\r\n#ICC to revise the method statement and include all the changes.', 2, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1767, 1037, 70, 'No comment', 1, 'sent', '2014-04-30');
INSERT INTO `review` VALUES(1768, 1038, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1769, 1040, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1770, 1040, 47, '#ICC to submit all the supporting documents to justify their early warning letter.\r\n#ICC were suppose to verify the SOW during bidding as KAUST LOGO/ Emblem has 4No. color on it.\r\n#ICC to submit relevant drawings to base all their calculations.  ', 2, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1771, 1040, 12, 'It is not required to paint on the precast Fence all ', 2, 'sent', '2014-04-30');
INSERT INTO `review` VALUES(1772, 1041, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1773, 1041, 47, '#Icc to provide all supporting documents to justify their quantity\r\n#Icc to submit different international recogmised claiming methods as a bases for their claim\r\n#Icc to also consider the IFB documents agreed before any change was implemented to the IFC\r\n#Icc generate or provide a detailed BOQ to justify the weightage on their claim\r\n#All the activities listed comparison from IFB to IFC versas the current work completed.', 3, 'sent', '2014-05-08');
INSERT INTO `review` VALUES(1774, 1041, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1775, 1042, 58, '1) For batteries 6000000951 and 6000001075 the contractor did not propose the approved manufacturer for both of them in the submittal sheet.\r\n\r\n2) All the inspectable items shall be procured through an approved manufacturer', 3, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1776, 1042, 11, 'No further comment.', 1, 'sent', '2014-05-03');
INSERT INTO `review` VALUES(1777, 1043, 58, '1) York Johnson is not an approved manufacturer for ACU.\r\n\r\n2) there is one approved manufacturer for this specific material;\r\n\r\n30006889 PETRA ENGINEERING INDUSTRIES (Jeddah) and its limitation is: UNITS SHALL BE CERTIFIED AT MANUFACTURING FACILITY TO COMPLY WITH UL-1203 & UL-1995 BY AN APPROVED 3RD PARTY.\r\n\r\n\r\n\r\n', 3, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1778, 1043, 21, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1779, 1043, 11, 'No need to review for this submittal, since the our material specialist Mr. Fahad Zahrani has rejected it due to vendor issue.', 4, 'sent', '2014-05-05');
INSERT INTO `review` VALUES(1780, 1044, 11, 'No further comment.', 1, 'sent', '2014-05-03');
INSERT INTO `review` VALUES(1781, 1048, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1782, 1049, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1783, 1050, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1784, 1051, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1785, 1052, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1786, 1052, 11, '1. In drawing KA-714490 sht 002, add in the note the grounding pit and provide a reference detail.\r\n2. In drawing KA-714490 sht 001 detail number 1, conduit ductbank shall be reinforced concrete.', 2, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1787, 1052, 30, 'Ensure minimum cover of 760 mm from the finish grade level will be provided for the communication duct bank.', 2, 'sent', '2014-05-06');
INSERT INTO `review` VALUES(1788, 1053, 30, 'Use the recommended SFP FIber modules by the same manufacturer ADDERLink rather than proposing for SFP modules by other manufacturer (CISCO).', 2, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1789, 1053, 11, 'No further comment', 1, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1790, 1053, 58, 'No comment.', 1, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1791, 1054, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1792, 1052, 12, '1-Provide more details for irrigation  the both shoulder and the median \r\n2-In drawing KA-714494 sht 001 shows to construct a  culvert crossing and ICC is argued to follow the IFC drawings  \r\n', 3, 'sent', '2014-05-07');
INSERT INTO `review` VALUES(1793, 1055, 12, '1-The CV of M. Izzeldeen Ajeeb is accepted for coordination between the designer and site construction activities and shall be responsible for the following:\r\n\r\na-Review and interpret Project Engineering drawings and specifications for scope and requirements. \r\nb-Implement and apply standard code and project specifications . \r\nc- Assist Engineering Manager to generate calculations and sketches for better engineering alternatives and proposals. \r\nd-Lead and co-ordinate a work group to carry out drawing projects. \r\ne- Coordination with other disciplines . \r\n\r\n2-The approval is granted for a period of 3 months for the subject post\r\n', 2, 'sent', '2014-05-04');
INSERT INTO `review` VALUES(1794, 1056, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1795, 1057, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1796, 1058, 45, 'I was on my daily site routine inspection yesterday at Zone A (infront of Bin Laden Gate) and KAM Access Road from 0650 to 0930 Hours when the ICC HSE Manager notified me at around 0930hrs of him suspending the ongoing works thereat. I notified Mr FA Balawi of the matter and his instruction was "to continue the works as the condition is still manageable". The HSE Manager was informed accordingly with the decision to return to work as instructed.\r\n\r\nThe reasoning as pointed out in the letter as a "force majeure due to the sandstorm" can be accepted at the height of the sandstorm between 0845 to 1000hrs. However using the same reasoning from start of the shift to the time the sandstorm escalated should not be tolerated from the point of view of work efficiency since there were no jobs at the sites to be "STOPPED" except the just started hauling work from Ayash Group in KAM Access Road. From a Supervisor Safety point of view, all affected workers should be  grouped at the Emergency Assembly Areas and/or keep in the busses as point of refuge. Upon being notified (with Aramco''s clearance)to evacuate that is the right time to move to a safer place like the Field Office Buildings. Going home or to the quarters should only be done after ICC Management is given by Client to do so unless a RETURN TO WORK ORDER is instructed.\r\n\r\nThis is a classic example of Operational Emergency Preparedness Procedure!', 0, 'sent', '2014-05-06');
INSERT INTO `review` VALUES(1797, 1059, 65, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1798, 1060, 32, '•	S Curves data shows the incorrect Progress % for Procurement and Construction. So, Completely update the S curve data and resubmit.\r\n•	Weekly Safety Report(it should have Man hour details) is missing which should be attached along with every Weekly report.\r\n', 3, 'sent', '2014-05-29');
INSERT INTO `review` VALUES(1799, 1061, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1800, 1062, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1801, 1063, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1802, 1064, 45, 'The candidate is strongly endorsed to the vacant position. However, he will be subject for a 3-month probation to prove his capability as sought. Final evaluation of his fitness to assume the Environmental position will be done after the 3-month probation.\r\n\r\nProceed with his hiring and be on deck soonest.', 0, 'sent', '2014-05-10');
INSERT INTO `review` VALUES(1803, 1065, 45, 'The observations are items for immediate rectification so that issues like these will not pile up from the monthly records. This report should be submitted regularly to the Department Safety Coordinator to be forwarded to concerned Saudi Aramco Offices as one of the attachments in the Departmental SHE performance reports.\r\n\r\nThe task of doing a weekly inspection are carried out internally in coordination with the SAPMT Safety Advisor. Observations are entered ito a register where it is updated regularly until closed by the Contractor.', 0, 'sent', '2014-05-10');
INSERT INTO `review` VALUES(1804, 1066, 72, '\r\n\r\n   \r\n\r\n1.	Ensure that aluminum frame and extrusions shall have powder coated finish with a minimum 3 mm wall thickness (VE 846472, SECTION 8460 para 2.02).Wall thickness for the submitted model is only 1.8 mm.\r\n2.	IC shall ensure that the proposed  sliding door glass thickness, and other accessories are according to the specification mentioned in the document VE 846472 section 8460 and section 8810.\r\n\r\n', 2, 'sent', '2014-05-07');
INSERT INTO `review` VALUES(1805, 1067, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1806, 1068, 32, 'No Comments. For Info only.', 1, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1807, 1069, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1808, 1070, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1809, 1070, 70, 'The Contractor can fabricate the rebar at their yard with right measurement as per the approved shop drawing and they have to apply epoxy coating at cut area and at any damage part of epoxy. It’s negative change order.', 2, 'sent', '2014-05-11');
INSERT INTO `review` VALUES(1810, 1071, 32, 'No Comments', 1, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1811, 1072, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1812, 1069, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1813, 1070, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1814, 1073, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1815, 1074, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1816, 1075, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1817, 1075, 47, 'IC to comply with all the specs and procedures as indicated on this submittal.\r\nIC to use only the approved material to carry out all the works as per Aramco standard\r\nShould there be any change on the materials or specification IC to submit a revise MST/ ITP to accommodate the changes ', 2, 'sent', '2014-05-16');
INSERT INTO `review` VALUES(1818, 1075, 70, '1.Regarding to 6.1 By Curing Compound: it’s not approved yet.\r\n2.Regarding to A7 Stripping / De-molding and Identification: As per Project Specification Section 03400 Precast Concrete is refer to Section 03100 Concrete Formwork Para 3.04 – A which is saying removing formwork after 24 hours. I prefer to remove the formwork when the concrete has attained more than 14 Mpa. The minimum stripping compressive strength will be determined by crushing molded cylinder samples at 12 hours old or more and shall be conducted by Approved Third Party Technician ( TPTL ) and will be witnessed by SAPID Rep.\r\n3.Regarding to B4 Grout / Concrete Procedures: The Contactor has to follow Saudi Aramco Standard (SAES– Q-10)and manufacture recommendation.\r\n4.Any Tests should be done by Approved Third Party and witnessed by SAPID Rep.\r\n5.Honeycomb, voids …etc. will be repaired by the contractor as per approved method statement for concrete repair if within the allowable sizes as per SAES.\r\n', 2, 'sent', '2014-05-12');
INSERT INTO `review` VALUES(1819, 1076, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1820, 1076, 11, '1. Contract addendum 01 has been shared with all bidders reflecting 6 package substations and 449 lighting poles in National Patrol Road. Reference drawings # PA-00095 sht 001 to 018.\r\n2. The rating and quantity of the lighting fixtures were specified in the IFB, it is the obligation of the LSTK contractor to provide sound estimation for the cable sizing and panel schedule.\r\n3. There is no impact in any transformer capacities the minimum KVA rating for the package substation is 75 KVA, and this is also the size that were provided in IFC. \r\n4. The location of the package substations were determine during the released of contract addendum 01 (PA-00095 sht 003, 006, 009, 012, 014 017) the single line diagram has been provided already before the release of contract addendum, it is the obligation of LSTK contractor to incorporate information from the BID Package and reflect in detail design.\r\n5. In the IFC an additional of 37 lighting poles, and few meters of LV cable only are subject for variation, this additional lighting poles were added due to detail positioning to meet project requirements.', 2, 'sent', '2014-05-14');
INSERT INTO `review` VALUES(1821, 1077, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1822, 1077, 11, 'The response letter of ICC with reference KPSS/SA/B/AKR/14/0566 dated May 10, 2014 does not answer SAPMT request to appoint a quantity surveying professionals and technical staff.\r\nICC should provide the estimated time of arrival for its experience quantity surveyor to finalize the quantities and variations without any delay.\r\n', 4, 'sent', '2014-05-15');
INSERT INTO `review` VALUES(1823, 1085, 12, 'Sohile please for your consolidation ', 1, 'sent', '2014-05-11');
INSERT INTO `review` VALUES(1824, 1089, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1825, 1093, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1826, 1078, 45, 'The heavy downpour happened at about mid-lunch break where most of the workers were eating their respective lunch in your accomodation/quarters and /or reporting back to work after lunch. Let us call it another force majeure similar with the last sandstorm where it cost us another personnel downtime which affected the Project progress.\r\n\r\nMay I suggest that instead of blaming nature for these phenomena, come to think of a solution to address and lessen the impact of the heavy downpour to our progress. For instance, invest on buying assorted sizes raincoats/capes which are available for use anytime you experience rain while at work. The truth of the matter is...most of your workers like being under the drizzle and when I asked them to go under a shed they refused as they are enjoying the rain. ( Zone A and KAM Access Road). These happenings are with us so let us try to manage them with the end in mind of lessening there impacts to our progress.', 2, 'sent', '2014-05-13');
INSERT INTO `review` VALUES(1827, 1079, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1828, 1079, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1829, 1080, 21, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1830, 1080, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1831, 1082, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1832, 1082, 11, '1. It is the responsibility of ICC interface coordinator to ensure proper coordination with other parties/contractors and provide soundness solution.', 3, 'sent', '2014-05-22');
INSERT INTO `review` VALUES(1833, 1083, 11, '1. Electronic Display and Traffic lights are within the scope of ICC as stated in document PE-000002 para. 1.2.2.1.3 and drawing number PA-000231 sht 001.\r\n2. It is mandatory for ICC to initiate an internal meeting with their sub-contractors and its contract adviser to determine their scope of work, and not just pass to SAPMT for its review.\r\n3. It has been noticed that so many claims is being raised by ICC without any basis of claims, ICC has to review all BID drawings and write-ups prior claiming any variation order.', 4, 'sent', '2014-05-14');
INSERT INTO `review` VALUES(1834, 1083, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1835, 1083, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1836, 1083, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1837, 1084, 32, 'No Comments. For Info only.', 1, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1838, 1087, 45, 'The report serves as a notification instrument for the client to know the incident in compliance with the 24-hour timeline of reporting. \r\n\r\nICC to come-up with the final report containing the following:\r\n\r\n1. Brief description of the incident;\r\n2. Flow of events leading to the Incident contact;\r\n3. Facts, Findings and/or Observations;\r\n4. Causal Analysis : immediate and basic causes;\r\n5. Remedial Actions to be implemented by ICC to prevent recurrence; and \r\n6. Picture attachments, illustratios of the incident.\r\n7. Sign-offs.\r\n8. Safety Advisory should be posted on Safety Notice Boards.\r\n\r\nThis should be discussed during the next Safety Committee meeting and toolbox talk meetings. \r\nA copy of the report shall be maintained on record.', 0, 'sent', '2014-05-13');
INSERT INTO `review` VALUES(1839, 1086, 11, 'Battery calculation and Specification shall comply with IFC drawings, SAES P-103, and Project Specification.', 2, 'sent', '2014-05-15');
INSERT INTO `review` VALUES(1840, 1086, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1841, 1088, 45, 'Mr. Marrack displayed satisfactory performance of his role as a Project Nurse during his probationary period. Basing from the said premise, I am respectfully endorsing approval to regular employee status as Project Nurse for the remaining period of the Project effective May 16, 2014.\r\n\r\nHowever, any gross misconduct committed (after due process) during his tenure shall be dealt with accordingly including the possibility of separation from the Project.', 2, 'sent', '2014-05-13');
INSERT INTO `review` VALUES(1842, 1090, 30, '1.	Procedure shall include the cut-over of current fiber optic connection of SONAR/RADAR to  the new proposed fiber optic cable line.\r\n2.	Attached the schematic diagram of the Existing IDAS Fiber Cabling System highlighting the splicing points for the new proposed FOC.\r\n3.	Shall include all splicing, termination and testing equipment to be used and attached their calibration certificates.\r\n4.	Shall include the CV or certificate of the fiber optic cable splicer(s).\r\n5.	Shall include the cross section details of the road where the duct bank will cross. Identify and reflect all utilities that will pass on this area and ensure that there are no conflicts and provided with minimum clearances as per Saudi Aramco standard.\r\n6.	Manual excavation must be done to avoid any damage to existing utilities.\r\n7.	Fiber optic cable shall be reel tested prior to installation.\r\n8.	Provide the complete list of communication passive materials and ensure all are available at site prior to any execution of works. \r\n', 3, 'sent', '2014-05-20');
INSERT INTO `review` VALUES(1843, 1090, 11, '1. Ensure that the cable splicer has valid Job Clearance Card (JCC) from Saudi Aramco.\r\n2. In procedure bullet # 9 to 10, conrete red tile has to be provided.\r\n3. Ensure that wood marker pole, with correct arrows is provided after the backfilling.\r\n4. ICC has to provide and reflect red line drawings with the coordinates of the underground FOC cables.\r\n5. Provide documentation such as test results, red line drawings, and signed inspection checklist.', 2, 'sent', '2014-05-14');
INSERT INTO `review` VALUES(1844, 1090, 72, '\r\n1. Methode of statement to be include changeover of existing cable with new cable and details of termination in sonar shelter or shall be submit separately.\r\n\r\n2. Ensure minimum clearance with MV cable and LV cables ( Sonar  transformer MV cable,KAM road lighting LV cable,KAM MV cable ).\r\n\r\n3.Consider risk factors during the FOC cable changeover from existing to new in the risk assesment matrix.', 2, 'sent', '2014-05-13');
INSERT INTO `review` VALUES(1845, 1091, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1846, 1091, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1847, 1092, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1848, 1092, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1849, 1094, 70, '1.Regarding to NOTE 1: it is LV cable not MV cable.\r\n2.Regarding to NOTE 4: delete the Soil Improvement sentence because no more soil improvement above the duct bank.\r\n3.Regarding to the top and bottom rebar hooks should be 230 mm not 300 mm.\r\n4.The contractor  has to apply red dye as per SAES-P-104 Para 10.3.\r\n', 2, 'sent', '2014-05-13');
INSERT INTO `review` VALUES(1850, 1094, 11, '1. Used PVC solvent cement in connecting the conduits as per SAES P-104 10.5.5\r\n2. Ductbank edge shall have bell end as per SAES P-104  para. 10.5.6\r\n3. The top layer of the concrete shall be mixed with red dye as per SAES P-10.5.7', 2, 'sent', '2014-05-13');
INSERT INTO `review` VALUES(1851, 1094, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1852, 1096, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1853, 1097, 70, 'No comment', 1, 'sent', '2014-05-15');
INSERT INTO `review` VALUES(1854, 1097, 47, 'NO COMMENT', 1, 'sent', '2014-05-16');
INSERT INTO `review` VALUES(1855, 1098, 11, 'No further comment', 1, 'sent', '2014-05-14');
INSERT INTO `review` VALUES(1856, 1098, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1857, 1099, 47, 'IC to provide all footing coordinates since they are been constructed as per priorities.\r\nIC is advised to only allow pannel make up as per the designed shop drawing and site conditions to match the pannels with and without logos\r\n', 2, 'sent', '2014-05-16');
INSERT INTO `review` VALUES(1858, 1099, 70, '1.	Consider adding the expansion joints where necessary.\r\n2.	Provide the foundation coordinates (four corners).\r\n3.	The Fence elevations drawings are not clear, we can’t read the numbers.\r\n4.	In the Fence elevations drawings show small size panels, we need more details and the reasons.\r\n \r\n', 3, 'sent', '2014-05-16');
INSERT INTO `review` VALUES(1859, 1100, 11, 'No further comment', 1, 'sent', '2014-05-14');
INSERT INTO `review` VALUES(1860, 1100, 30, 'approved as long as all SAPMT comments will be provided and complied.', 2, 'sent', '2014-05-20');
INSERT INTO `review` VALUES(1861, 1101, 47, 'IC to provide calculation comparison of backfilling by sand dunes vs selected fill.\r\nIC to provide a proof that even if the footing is backfilled by sand dunes it can still pass the crash rating test.', 3, 'sent', '2014-05-16');
INSERT INTO `review` VALUES(1862, 1101, 70, 'No comment', 1, 'sent', '2014-05-15');
INSERT INTO `review` VALUES(1863, 1102, 32, 'No comments', 1, 'sent', '2014-06-26');
INSERT INTO `review` VALUES(1864, 1103, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1865, 1103, 72, ' 1. Ensure that the badging machine shall be integrated to the SACS to allow excahange informations ( As per PE-000071 section 5.2.4 )\r\n\r\n 2.  Password security shall be available to control user access ( As per PE-000071 section 5.2.4 )\r\n\r\n', 2, 'sent', '2014-05-15');
INSERT INTO `review` VALUES(1866, 1103, 11, '1. Contractor has to ensure that during the installation, badging station is the latest version.\r\n2. Badging station should be compatible and integrated with SACS system.\r\n3. Badging station shall comply with IFC drawing, and FSD document PE-000071', 2, 'sent', '2014-05-14');
INSERT INTO `review` VALUES(1867, 1104, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1868, 1105, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1869, 1106, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1870, 1107, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1871, 1107, 70, 'Some comments regarding to the attachment drawings:\r\n1.	VA-847047-001-0F1 Section A_A shows culvert started at St. 13+656 instead of St. 13+643 as per IFC, required confirmation from SCEC.\r\n2.	VA-847047-001-0F1 Section A_A shows 150 mm thickness concrete dike instead of Marl.\r\n3.	VA-847047-001-0F1 Section C-C shows the lean concrete is 75 mm instead of 100 mm as per IFC, required confirmation from SCEC.\r\n4.	VA-847047-001-0F1 Section C-C did not show the base slab details as mentioned in the IFC which are as below:\r\n•	RC foundation for culvert\r\n•	50 mm cement screed  Fc = 14 Mpa\r\n•	4 mm waterproof membrane\r\n•	100 mm lean concrete \r\n•	Will compacted backfill (min. dry density shall be 95% of standard density test).\r\n5.	VA-847047-002-0F1 Blow-up detail 1 shows welded wire mesh 8 mm diameter @ 200 both ways instead of rebar 10 mm diameter @ 200 both ways. Required confirmation from SCEC.\r\n6.	VA-847047-002-0F1 additional to the note (contractor shall provide a shop drawing for expansion joints).\r\n7.	VA-847048-002-0F2 Section D shows a retaining wall with different size than the IFC drawing. Required confirmation from SCEC.\r\n8.	 VA-847048-002-0F2 Section A-A shows the distance between the walls face to face is 4400 mm while VA-847047-001-0F1 shows 4400 mm center to center. Required confirmation from SCEC.\r\n', 3, 'sent', '2014-05-15');
INSERT INTO `review` VALUES(1872, 1107, 47, '#Provide clear vertical dimensions on Dwg VA-847048-0F2 Section C.\r\n#The line texture is not consistent, some places one line goes thicker and thinner but still representing the same thing.\r\n#clouding change on revision 0F2 is drawn across the drawing detail information\r\n#IC to maintain the exact level control during concreting to avoid water ponding at different location since there is only 6 mm gradient allowed from Inlet to Outlet for a distance of 53200 m and 87286 m.\r\n#IC to provide the bending schedule for all rebar and concrete works and other details as indicated on the drawing. \r\n#IC to officially submit a detailed geotechnical report findings as a backup their final design', 2, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1873, 1108, 11, '1. Most of the lists provided were internal and between ESE and ICC, with no obligation from Saudi Aramco. 2.\r\n2. Contractor has to ensure that the all the deliverables and scope of work were identified clearly comprehended and obligations with its sub-contractors were solid, with known interface, required deliverables and shall comply with Saudi Aramco standards and requirements.\r\n3. Revised the notification and only provide the list that has variation to Saudi Aramco.', 0, 'Pending', '2014-05-26');
INSERT INTO `review` VALUES(1874, 1108, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1875, 1108, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1876, 1109, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1877, 1109, 11, '1. Use 15-SAMSS-502  dated December 4, 2012 for compliance statement.', 3, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1878, 1110, 30, '1. Ensure to choose the correct regulatory domain applicable to Saudi Arabia.\r\n2. Ensure to include the installation kit and patchcord required\r\n3. Esnure to include the Smartnet services applicable to the proposed model. ', 2, 'sent', '2014-05-20');
INSERT INTO `review` VALUES(1879, 1110, 11, 'No comment.', 1, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1880, 1111, 70, 'Regarding to the NOTE of the attached drawing ( SD-FCC-846521-111 ) point 2: it says " and at level 500 mm above of the bottom of the foundation levels " this foundation is K4 with height 300 mm and the gap of PVC shim is 50 mm, total height is 350 mm.', 2, 'sent', '2014-05-19');
INSERT INTO `review` VALUES(1881, 1111, 47, '#Provide clear vertical dimensions on Dwg VA-847048-0F2 Section C.\r\n#The line texture is not consistent, some places one line goes thicker and thinner but still representing the same thing.\r\n#clouding change on revision 0F2 is drawn across the drawing detail information\r\n#IC to maintain the exact level control during concreting to avoid water ponding at different location since there is only 6 mm gradient allowed from Inlet to Outlet for a distance of 53200 m and 87286 m.\r\n#IC to provide the bending schedule for all rebar and concrete works and other details as indicated on the drawing. \r\n', 2, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1882, 1112, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1883, 1114, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1884, 1114, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1885, 1114, 11, '1. LV cables and building wires shall comply with SAES-P-104 para. 5.1, IFC drawing and construction specification.', 2, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1886, 1113, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1887, 1115, 47, 'Provide full details for  the EJ tie-in the asphalt road, two foundation connection and crushed rock mulch connection\r\nProvide clarification or standard reference on your notes\r\nRE-Check your rebar calculations for BM 04\r\nProvide a separate cross section on the EJ showing rebar arrangement', 2, 'sent', '2014-05-19');
INSERT INTO `review` VALUES(1888, 1115, 11, '1. Ensure that the propose concrete slab for Z portal is communicated with X-ray machine vendor.\r\n2. The drawing has to be stamped by the X-ray machine vendor.', 3, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1889, 1115, 70, '1.It is not mention the concrete strength in the submittal which is 4000 psi as per the Vendor recommendation (AS&E).\r\n2.Provide 102 mm cover over steel at all concrete surfaces (AS&E Equipment Foundations) facing the AS&E equipment as per Vendor recommendation (AS&E). One of the buildings facing the AS&E equipment is Operator Building; we need Vendor Confirmation if IC has to revisit the concrete cover of any building which is facing the AS&E equipment.\r\n3.IC did not follow the Vendor recommendation at edge of slab, IC providing 4 ᴓ20 mm and ᴓ10 @ 300 mm but as per Vendor recommendation the Rebar at edge of Slab is as mentioned:\r\n•6x6 – 10/10 WWF TEMP REINFORCEMENT AT SLAB TOP.\r\n•(6) #8 BARS LONGITUDINAL HORIZONTAL LONGITUDINAL @ FOOTING EDGE.\r\n•#8 BARS E/W @ 10â€ (254) O.C BEND LATERAL @ EDGE.\r\n4.No details of the drainage pits with opening in the foundation and conduit stub-up (Electrical and Communication)\r\n5.Posts fixations are not mentioned in the submittal how will be … embedded anchor or drilling bolts?\r\n6.No details of Expansion Joints.\r\n7.Provide the Rebar Details for Short and Long bent bar with the hook length.\r\n8.I prefer a drainage system connecting to main drainage system instead of using Drainage pit which will drain the condensate water under the foundation.\r\n9.IC shall provide enough space for maintenance purpose with hard impervious paving as per Vendor recommendation (AS&E).\r\n10.I prefer Mr. Mark, Mr. Marwin and Mr. Prasad to review the submittal for Mechanical, Electrical and Communication disciplines.', 3, 'sent', '2014-05-20');
INSERT INTO `review` VALUES(1890, 1117, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1891, 1117, 47, 'It is evident that this mix design adjustment was done mainly to reduce the moisture content on the aggregate and increasing the admixture content as well as changing the initial supplier, the water cement ratio was kept constant at 0.4 even though there was a reduction on cement/water volume.\r\nThe supply of both admixtures and micro silica''s were changed to provide stability for the mix design parameters ', 2, 'sent', '2014-05-20');
INSERT INTO `review` VALUES(1892, 1118, 47, 'IC personnel should make up their mind before submitting method statement to SAPMT and not change their construction method/ procedure or sequence based on un-engineering suggestions or fast tracking progress and follow the method statement and material to the latter.', 2, 'sent', '2014-05-19');
INSERT INTO `review` VALUES(1893, 1118, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1894, 1118, 70, '1.Regarding to the compressive strength of concrete repair material, the contractor mentioned in his revise submittal that he is noted and comply but he is still using the same material with same strength and the attached documentation of the same material RENDEROC TG (data sheet or brochure of Renderoc TG) shows 30 N/mm² at 28 days.\r\n\r\n2.Page No. 12 - Regarding to Repair for concrete stains: The first category: the contractor has to give excellent finishing not to minimizing the color differences between the precast element finish and the repaired area finish. The second category: No stains or spots will be kept for weather to fade them away; the contractor has to repair with excellent finishing.  \r\n', 2, 'sent', '2014-05-20');
INSERT INTO `review` VALUES(1895, 1119, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1896, 1120, 11, 'In relation with construction note number 8, Contractor has to provide shop drawings and data/load schedule for the lighting and IDAS Power Panels.', 2, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1897, 1120, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1898, 1121, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1899, 1121, 11, 'I forwarded the submittal to civil engineers (Easy nd Sami)', 2, 'sent', '2014-05-18');
INSERT INTO `review` VALUES(1900, 1121, 70, 'No Comment from my side. I prefer Mr. Rey ( Surveyor ) review the submittal.', 1, 'sent', '2014-05-19');
INSERT INTO `review` VALUES(1901, 1121, 47, '#Provide a reference drawing indication the possitions/ locations of all these bench marks\r\n#Provide justification for the change in the origination bench marks if any.\r\n#Aramco and IC surveyor to confirm these BM on site and confirm if they are still in line with the IFC already issued.', 2, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1902, 1122, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1903, 1122, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1904, 1123, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1905, 1123, 11, '1. The submitted EGA PVC conduit is not acceptable and does not comply with SAES P-104.\r\n2. Types of Electrical and Communication conduit uses in Saudi Aramco for concrete and direct buried are only the following:\r\n    1. PVC Conduit TYPE DB - 120 (Direct Buried)\r\n    2. PVC Conduit TYPE EB - 35  (Concrete Encasement)\r\n    3. PVC Conduit TYPE EPC - 40 (Direct Buried and Concrete Encasement)\r\n3. Contractor has to ensure that all materials to be used for conduit and fittings will comply with Saudi Aramco Standard and IFC drawing.', 4, 'sent', '2014-05-20');
INSERT INTO `review` VALUES(1906, 1122, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1907, 1124, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1908, 1127, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1909, 1127, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1910, 1127, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1911, 1125, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1912, 1128, 32, 'The submitted report is incomplete and Procurement Progress % is not matching with detailed report.', 4, 'sent', '2014-05-22');
INSERT INTO `review` VALUES(1913, 1136, 47, 'No Comment', 1, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1914, 1136, 70, 'Consider adding the expansion joints where necessary.\r\nIn the Fence elevations drawings show small size panels, we need more details and the reasons.\r\n\r\n', 2, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1915, 1130, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1916, 1135, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1917, 1135, 70, 'The column with the two different walls elevation, there is a gap between the Top of the lower wall and the column cap we need details if the contractor is going to fill the gap or he will keep it as it.\r\n\r\n', 2, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1918, 1135, 47, 'Please correct description of Item No. 2 and 4 in relation to DWG SD-FCC-846521-113-00 and SD-FCC-846522-113-00\r\nIs it all for Detail Column K4-C02L or K4-C02L and K12-C02L', 3, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1919, 1139, 11, '1. Compliance matrix attachment page 12 of 12 has to be finalized by Contractor and Vendor and ensure that site testing after installation will be performed using portable test bank as stated in 17-SAMSS-518 and project document VE-864472 para. 3.04 B.1 to 4, page 12 of 12.\r\n2. Contractor has to ensure full compliance of IFC drawing, SAES P-113, 17-SAMSS-518 and Project specifications.', 2, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1920, 1139, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1921, 1139, 31, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1922, 1131, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1923, 1133, 47, 'Provide a reference drawing with this submittal to show all the coordinates for clarity and confirmation\r\nClarify why is it sheet 08 of 20, is there other references.', 3, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1924, 1133, 70, 'Mr. Rey can check the coordinates.', 1, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1925, 1134, 45, 'This is a "LESSON LEARNED TYPE" training. What is important here are the "lessons learned" from the exercise. The ICC contractor must rectify the noted observations and put them into practice during the succeeding emergency drills. In general, Contractor must re-visit their Safety Training system to enhance current capabilities.\r\n\r\nThis kind of Emergency Preparedness Training and Response drill should be done quarterly as the minimum. The organizational set-up should also be established to familiarize each employee of his/her respective role in times of emergencies. The report is acceptable and should be maintained on active record.', 0, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1926, 1142, 47, '#Provide connection details from area with soil improvement and without.\r\n#Please revise all your road cross sections as per the latest geotechnical investigation by RGF and final design\r\n#Provide the composite drawing for Kam road, indicating utilities interfacing each other(electrical,communication,irrigation/ valve boxes and pipe culvert) elevation and coordinates.', 3, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1927, 1142, 70, '• The soil improvement continues till 1+900 (actual at site) not till 1+850 as mentioned in the attached drawing, we need clarification.\r\n• Provide details drawing show the MV duct bank and the other utilities. \r\n\r\n', 2, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1928, 1141, 32, 'No Comments', 1, 'sent', '2014-05-26');
INSERT INTO `review` VALUES(1929, 1140, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1930, 1140, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1931, 1132, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1932, 1138, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1933, 1138, 11, 'Since the KAM road earthworks is already done, it is impratical to excavate the area. In addition to it, SAPMT cannot rely to the test result coming from untrusted meter source. \r\nIt is therefore recommended to KAUST and its service provider to conduct FOC re-test using a calibrated instrument for accurate information. And if in any case that the cut proven to be under KAM road corridor, the road contractor will rectify the cut accordingly and provide necessary protection for the cable.', 3, 'sent', '2014-05-24');
INSERT INTO `review` VALUES(1934, 1143, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1935, 1145, 12, 'agree ', 1, 'sent', '2014-06-02');
INSERT INTO `review` VALUES(1936, 1146, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1937, 1147, 47, '#IC should have notified Aramco of any additional building required to make the operation work during the draft or initial stages of the project.\r\n#IC to refer to IFB DWG PA-000035-001-C Notes No. 3 clarity and confirmation on what and what not to include on their final drawing.\r\n#IC should have designed the whole system around the operation area/ room to be full automatic as per the IFB but opted for the Operator Room which is human controlled.\r\n#IC to submit all documents and correspondence indicating that they were aware of all this and other changes during bidding process and have notified Aramco of all the descrapancies', 3, 'sent', '2014-05-27');
INSERT INTO `review` VALUES(1938, 1147, 11, 'Quantities are purely for civil items, submittal is forwarded to SAMI GAFRI.', 0, 'sent', '2014-06-01');
INSERT INTO `review` VALUES(1939, 1147, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1940, 1148, 47, '#IC designer SCEC deviated from the IFB drawing provided as a baseline,\r\n#The IFB drawing clearly indicates 300 mm thick sub base course and 250 mm thick class B base course\r\n# As per IC/ SCEC they went for 300 mm thick sub base course class B and 250 mm thick class A aggregate base course', 4, 'sent', '2014-05-27');
INSERT INTO `review` VALUES(1941, 1148, 70, '•IC has to submit quotation of class A & class B to shows the variance.\r\n•As per IFB there is a Geogrid under the Granular base course class B which will be negative change order.\r\n•IC has to provide the reason why the Designer change the granular base course from class B to class A.\r\n•As per the IFC drawing of KAM Access Road, the Base course quantity is = 4066*17.9*0.25= 18195 cubic meters. With the new alignment the quantity = 4157*17.9*0.25 = 18602 cubic meters. But IC is claiming 23032.5 cubic meters.\r\n•I prefer, the contractor mentions in his submittal a word cost impact or positive change order when they plan to claim in future due to any change in their drawing, SOW … etc.', 4, 'sent', '2014-05-27');
INSERT INTO `review` VALUES(1942, 1149, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1943, 1153, 47, 'IC-SD-846668-102\r\nProvide details or full dimension of the masonry reinforcement rebar or bending schedule\r\nprovide the details of the mortar and ladder mesh\r\nprovide more details or color configuration of the cement planter paint\r\nprovide the fixing details for the galvanised steel box and down pipe.\r\nARAMCO standard requires bituminous coating for all concrete finishing under the NGL and also provide the interface or connection between the sealant and bituminous coatings\r\nProvide more detail of the roof flashing for water proofing\r\nIC-SD-846668-103\r\nThere is no note 6 for galvanized steel cage roof access and fixing details\r\nThere is no note 10 for concrete pad\r\nIC-SD-846668-105\r\nprovide details for the CMU wall insulation\r\nprovide the details of the texture paint on concrete finished wall\r\nmore detail of the corner tie at every 3rd layer\r\nprovide details of the adjustable hangers rods for fixing the acoustic ceiling and the type/ finishing of the panel to be used.\r\nProvide finishing details for the ramps\r\nprovide more details for the removable handicap access', 2, 'sent', '2014-05-29');
INSERT INTO `review` VALUES(1944, 1153, 70, 'Block Works:	\r\n•Required more details of Ladder Mesh, corner tie and dowel.\r\n•The CMU should have rough texture.\r\n•Required Lintels details (Locations, plans, sections …etc.)\r\n•The external walls and external columns faces are in one plane inside the building as per IFC foundation, plan and section details (VA-846673-001) and as per IC shop drawing of foundation, plan and section details.\r\n•The dowel space in attached drawing IC-SD-846668-102 (Block Wall Plan) and IC-SD-846669-102 (Block Wall Plan) show 667 mm space and in same drawing (Block Wall Vertical Sec E-E) shows 400 mm! What is the correct space?\r\nPlastering Works:\r\n•The groove wide of external walls is 20 mm as per IFC VA-846670-001 and it’s mentioned at many location of this submittal Not 32 mm.\r\n•Required more details such section and accessories.\r\nTiles Works:\r\n•The external walls and external columns faces are in one plane inside the building as per IFC foundation, plan and section details (VA-846673-001) and as per IC shop drawing of foundation, plan and section details. Revise the Tiles drawing.\r\n•The tile drawing does not show the Marble thresholds. Required more details such as location, plan …etc.\r\n•What is the finishing of the building ramp?\r\nReflected Ceiling:\r\n•Provide the panel thickness.\r\n•Provide more details of Hangers and runners cross sections.\r\n•Provide the distance between hangers\r\n•Fastening details.\r\n•Runner splicing details.\r\n•Opening at Ceiling details.\r\n•Fixtures and equipment supports details.\r\n•Smoke detectors should be away of HVAC air flow.\r\nBuilding Elevations:\r\n•Monkey Ladder and downspout details excluded and should be submitted individual.\r\nSchedules & Details:\r\n•Provide the shop drawing of Doors and windows. Each element and each type in separate shop drawing with full details shows the plan, section …etc.\r\n', 3, 'sent', '2014-05-29');
INSERT INTO `review` VALUES(1945, 1154, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1946, 1154, 30, '1. Quantities indicated under the Bill of quantities are all wrong. Re-verify the quantities and ensure all requirement shall be provided and installed in this project.\r\n2. The proposed manhole frame and cover is not acceptable since it conflicts to SAES-T-911 requirements.\r\n3. All manhole inside accessories shall be non-corrosive, hot dipped galavanized and ensure all have specifications and dimensions in compliance to SAES-T-911.\r\n4. Specification of fiber marker post is included in the attachment, please clarify since it is not included in the Bill of Quantities.\r\n', 3, 'sent', '2014-06-01');
INSERT INTO `review` VALUES(1947, 1157, 47, 'IC-SD-846859-102\r\nProvide details or full dimension of the masonry reinforcement rebar or bending schedule\r\nprovide the details of the ladder mesh\r\nprovide more details or color configuration of the cement planter paint\r\nprovide the fixing details for the galvanised steel box and down pipe.\r\nIC-SD-846859-103\r\nThere is no note 6 for galvanized steel cage roof access and fixing details \r\nARAMCO standard requires bituminous coating for all concrete finishing under the NGL and also provide the interface or connection between the sealant and bituminous coatings\r\nIC-SD-846859-105\r\nprovide details of the adjustable hangers rods for fixing the acoustic ceiling and the type/ finishing of the panel to be used.\r\nProvide finishing details for the ramps\r\nThere is no note 6 for galvanized steel cage roof access and fixing details\r\nIC-SD-846860-102\r\nprovide deatils for the CMU wall insulation\r\nprovide the details of the texture paint on concrete finished wall\r\nmore detail of the corner tie at every 3rd layer', 2, 'sent', '2014-05-29');
INSERT INTO `review` VALUES(1948, 1157, 70, 'Block Works:	\r\n•Required more details of Ladder Mesh, corner tie and dowel.\r\n•The CMU should have rough texture.\r\n•Required Lintels details (Locations, plans, sections …etc.)\r\n•The external walls and external columns faces are in one plane inside the building as per IFC foundation, plan and section details (VA-846864-001) and as per IC shop drawing of foundation, plan and section details.\r\n•The dowel space in attached drawing IC-SD-846859-102 (Block Wall Plan) and IC-SD-846860-102 (Block Wall Plan) show 667 mm space and in same drawing (Block Wall Vertical Sec E-E) shows 400 mm! What is the correct space?\r\nPlastering Works:\r\n•The groove wide of external walls is 20 mm as per IFC VA-846861-001 and it’s mentioned at many location of this submittal Not 32 mm.\r\n•Required more details such as section and accessories.\r\nTiles Works:\r\n•The external walls and external columns faces are in one plane inside the building as per IFC foundation, plan and section details (VA-846864-001) and as per IC shop drawing of foundation, plan and section details. Revise the Tiles drawing.\r\n•The tile drawing does not show the Marble thresholds. Required more details such as location, plan …etc.\r\n•What is the finishing of the building ramp?\r\nReflected Ceiling:\r\n•Provide the panel thickness.\r\n•Provide more details of Hangers and runners cross sections.\r\n•Provide the distance between hangers\r\n•Fastening details.\r\n•Runner splicing details.\r\n•Opening at Ceiling details.\r\n•Fixtures and equipment supports details.\r\n•Smoke detectors should be away of HVAC air flow.\r\nBuilding Elevations:\r\n•Monkey Ladder and downspout details excluded and should be submitted individual.\r\nSchedules & Details:\r\n•Provide the shop drawing of Doors and windows. Each element and each type in separate shop drawing with full details shows the plan, section …etc.\r\n', 3, 'sent', '2014-05-29');
INSERT INTO `review` VALUES(1949, 1157, 11, 'Consider providing bars to seal the opening above the turnstile, see shop drawing IC-SD-846860 sht 105.', 2, 'sent', '2014-06-01');
INSERT INTO `review` VALUES(1950, 1150, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1951, 1151, 47, '# IC to resubmit a clear copy of the Shop Drawing and include item No. 9 on the submittal\r\n# As the duct bank has already been concreted and the changes will be shown on the as-built and later on on the red line drawing. ', 2, 'sent', '2014-05-27');
INSERT INTO `review` VALUES(1952, 1151, 70, 'No Comment', 1, 'sent', '2014-05-26');
INSERT INTO `review` VALUES(1953, 1151, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1954, 1152, 32, 'No Comments. Submittal is for Info only.', 2, 'sent', '2014-05-27');
INSERT INTO `review` VALUES(1955, 1155, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1956, 1156, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1957, 1160, 78, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1958, 1158, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1959, 1158, 11, 'For reference only.', 1, 'sent', '2014-06-01');
INSERT INTO `review` VALUES(1960, 1159, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1961, 1159, 11, 'Shall comply with SAES P-104 para. 8.4, 8.6 and 8.11.', 2, 'sent', '2014-06-01');
INSERT INTO `review` VALUES(1962, 1161, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1963, 1161, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1964, 1162, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1965, 1163, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1966, 1163, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1967, 1164, 47, 'IC to provide a method statement on how they are going to carry the backfilling on top of the concrete slab protection and avoid any breaking of the slab.\r\nIC can also reduce the sand cover on top of the pipe to 150 mm and cast the slab 150 mm above the sand cover and still maintain the 300mm of sub base material wherein first layer of 150 mm can be proof rolled only and the second layer can be properly compacted and tested to avoid any defects at a later stage \r\n', 2, 'sent', '2014-06-02');
INSERT INTO `review` VALUES(1968, 1164, 70, '•As per Saudi Aramco standard drawing AB-036255-001-04 the slab concrete has top & bottom rebar and stirrups.\r\n•The concrete cover is 75 mm at each direction as per Project general notes VA-846497-001 and as per Saudi Aramco standard drawing AB-036255-001-04.\r\n•IC shall submit the structural shop drawing.\r\n•IC has to get confirmation from the Pipe Vendor.\r\n•Backfilling of sweet sand shall be as per Saudi Aramco Standard.\r\n•Required plan drawing of Pipe culvert shows the concrete slab.\r\n\r\n', 3, 'sent', '2014-05-30');
INSERT INTO `review` VALUES(1969, 1165, 47, 'IC to follow TTI recommendation and well as all the methods discussed during a joint grouting inspection with SAPMT and PID\r\nThe steel shims to be installed on four sides before survey confirmation and the timber stays/ supports to be removed before or after grout setting time as per agreement on site', 2, 'sent', '2014-05-29');
INSERT INTO `review` VALUES(1970, 1165, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1971, 1166, 78, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1972, 1167, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1973, 1168, 11, '1. Contractor has to identify the enclosure rating of the proposed panel boards.\r\n2. Contractor has to identify the cable entry (Top or Bottom) for each of the panel boards.\r\n3. Provide vendor shop drawing for each of the panel board showing Main Circuit Breakers and its branches.\r\n4. Dry type transformer enclosure shall comply with SAES P-104 para. 7\r\n5. Provide vendor shop drawing for dry type transformer to verify the ventilation details.\r\n', 2, 'sent', '2014-06-02');
INSERT INTO `review` VALUES(1974, 1168, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1975, 1169, 32, 'Progress % at Progress Summary has to be revised as per the Approved Rev.01 Schedule.', 3, 'sent', '2014-05-29');
INSERT INTO `review` VALUES(1976, 1172, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1977, 1172, 47, 'NO COMMENT', 1, 'sent', '2014-06-02');
INSERT INTO `review` VALUES(1978, 1172, 70, '•The contractor shall use the right material such as RENDEROC - LA as per Letter K&TPD/KRP&SFPD/SF/L-215/13 or use another approved material has strength same as the precast concrete because the foundation, column and panel are structural elements.\r\n•Section E : to repair spall or broken edge they should add mechanical support material such as corner mesh with the concrete repair material.\r\n•Section H : the contractor should revise this section as per our last response.\r\n•Regarding to Unacceptable Defects are clearly mentioned in ACI 533 R - Quality requirements and tests - Para 7.2 which are:\r\n1.Casting defects – Excessive bug holes (Air Voids).\r\n2.Stains – rust or other stains.\r\n3.Irregular – ragged or irregular edges.\r\n4.Nonuniform color and texture.\r\n5.Cracks and repairs – cracks.\r\n•Any comments related to Repair Works Matrix will be submitted with DS – 308\r\n', 3, 'sent', '2014-06-01');
INSERT INTO `review` VALUES(1979, 1173, 11, 'No comment', 1, 'sent', '2014-05-31');
INSERT INTO `review` VALUES(1980, 1174, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1981, 1171, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1982, 1173, 25, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1983, 1175, 47, 'IC to attach the standard drawing mentioned in the SAES-P 10.3; - AD-036874\r\nThe Heading of the submittal(Backfilling dry sand) is in relation with the drawing attached and not the attached SAES standard\r\n', 2, 'sent', '2014-06-03');
INSERT INTO `review` VALUES(1984, 1175, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1985, 1176, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1986, 1176, 11, 'No comment.', 1, 'sent', '2014-06-01');
INSERT INTO `review` VALUES(1987, 1177, 11, 'No further comment, submittal has been forwarded to Abu Hanifa and Jonathan.', 1, 'sent', '2014-06-04');
INSERT INTO `review` VALUES(1988, 1177, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1989, 1178, 78, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1990, 1178, 12, 'It is ok ', 1, 'sent', '2014-06-02');
INSERT INTO `review` VALUES(1991, 1179, 47, 'IC to proceed as per the approved Matrix only and no further adjustment will be considered except from the Proponent during the final mock-up approval', 2, 'sent', '2014-06-02');
INSERT INTO `review` VALUES(1992, 1179, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1993, 1179, 70, 'There are comments mentioned by Serial Number of the Matrix:\r\n1.Change the Concrete repair material to the right material ( RENDEROC - LA ) as per Letter K&TPD/KRP&SFPD/SF/L-215/13 or use another approved material has strength same as the precast concrete because the foundation, column and panel are structural elements.\r\n2.To repair spall or broken edge they should add mechanical support material such as corner mesh with the concrete repair material as mentioned at point 1.\r\n3.The contractor should repair any crack because the area is close to the sea and all walls panels are expose to weather as per ACI 533 R-93 Para 2.5.3 “Therefore, if the reinforcement is coated for corrosion resistance, wall panels containing cracks up to 0.005 in. wide for surfaces exposed to weather and 0.010 in. wide for surfaces not exposed to the weather should be acceptableâ€ with right material as mentioned at point 1.\r\n4.The contractor has to give excellent finishing not to minimizing the color differences between the precast element finish and the repaired area finish. No stains or spots will be kept for weather to fade them away; the contractor has to repair with excellent finishing.\r\n5.The contractor has to repair any pinhole or bubble at all side as per ACI 533 R Para 7.2 with right material as mentioned at point 1.\r\n6.No comment.\r\n7.Using right material as mentioned at point 1.\r\n8.Using right material as mentioned at point 1.\r\n', 3, 'sent', '2014-06-01');
INSERT INTO `review` VALUES(1994, 1180, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1995, 1181, 53, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1996, 1182, 53, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1997, 1183, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1998, 1184, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(1999, 1185, 11, 'The provided softwares in CD is only a copy version and don''t have original label. \r\n\r\nSir Sohail,\r\n\r\nAccording to our contract schedule B attachment V page 16 of 19, Computers and Communication Equipments are still property of the CONTRACTOR. \r\n\r\nCan we force them to provide the original CD? ', 3, 'sent', '2014-06-01');
INSERT INTO `review` VALUES(2000, 1186, 70, 'No comment.', 1, 'sent', '2014-06-02');
INSERT INTO `review` VALUES(2001, 1193, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2002, 1193, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2003, 1193, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2004, 1187, 72, '\r\n 1. Ensure that quee number indicator display required in each counter and the controller should have capability to connect all required displays.', 2, 'sent', '2014-06-02');
INSERT INTO `review` VALUES(2005, 1187, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2006, 1189, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2007, 1189, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2008, 1192, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2009, 1192, 11, '1. Ensure that the low voltage cable and wires will comply to SAES P-104 para. 5, Project Specification and IFC drawing.', 2, 'sent', '2014-06-02');
INSERT INTO `review` VALUES(2010, 1188, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2011, 1190, 32, 'No comments', 1, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2012, 1191, 32, 'No Comments. For Information Only.', 2, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2013, 1194, 47, 'As per the previous response on the submittal for lifting socket SAPMT instructed IC to  \r\nprovide test certificates from the manufacture or third party before procurement\r\nIC to provide full set of mock-up as per this submittal to close this request.', 2, 'sent', '2014-06-03');
INSERT INTO `review` VALUES(2014, 1194, 70, '•As per Submittals SDS 008 & SDS 009 (Structural shop drawing for precast concrete fence K4 & K12) the sleeve diameter is 50 mm but in this submittal the contractor reduce the diameter to 40 mm. First confirmation from SCEC, if the new size is acceptable by SCEC as per Saudi Aramco Standard and International codes then the contractor has to revise the old submittals to reflect the new diameter or if it is not accepted by SCEC, the contractor has to revise this submittal.\r\n•The Bolt & Sleeve submittal is still not approved by SAPMT.\r\n•As per Material Submittal MS – 0073 the sleeve diameter is 50 mm.\r\n•This is an example of documentation bad quality have been done by SCEC and the contractor.\r\n', 3, 'sent', '2014-06-02');
INSERT INTO `review` VALUES(2015, 1202, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2016, 1202, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2017, 1195, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2018, 1195, 30, '1. Ensure to include all fiber closure accessories upon placement of purchase order.\r\n2. Airvalve shall be installed on all outdoor type closures.\r\n3. Ensure all models selected can accomodate all splicing requirement as per the IFC drawings.', 2, 'sent', '2014-06-04');
INSERT INTO `review` VALUES(2019, 1196, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2020, 1196, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2021, 1197, 30, '1. The attached shop drawing should be revised with more and clearer details to be submitted separately prior review of SAPMT.\r\n2. Ensure the proposed monitor and CPU will be the latest model.', 2, 'sent', '2014-06-04');
INSERT INTO `review` VALUES(2022, 1197, 11, '1. Ensure that Monitor''s CPU and servers to be positioned in the console shall fit with sufficient clearance for cabling, and has sufficient ventilation to avoid accumulation of heat.\r\n2. Ensure that the power strip for computers and servers were compatible and oriented properly.\r\n', 2, 'sent', '2014-06-04');
INSERT INTO `review` VALUES(2023, 1198, 45, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2024, 1199, 45, '', 0, 'sent', '');
INSERT INTO `review` VALUES(2025, 1200, 78, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2026, 1201, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2027, 1201, 11, '1. The quantity of Proximity readers, Bio-metric readers and cameras shall meet the project specification requirements and SACS Functional Specification Document PE-000071.\r\n2. Ensure that the fingerprint system will comply to FSD document PE-000071 para. 4.8 and 5.2.8\r\n3. The pole for proximity readers located in gate 2 and 3 inbound and outbound, shall be capable for small and big cars.', 2, 'sent', '2014-06-04');
INSERT INTO `review` VALUES(2028, 1201, 30, '1. Ensure the proposed camera to be installed outside the building is capable in outdoor environment. Also provide manufacturer recommended enclosure/housing for the camera.\r\n\r\n2. Ensure to submit the required server for SACS provided with capacity calculation in a seperate submittal prior SAPMT approval.', 2, 'sent', '2014-06-04');
INSERT INTO `review` VALUES(2029, 1203, 11, '1. Consider replacing the title Existing MV cable duct bank into Proposed protection for underground SONAR 13.8 KV Power Cable.\r\n2. Delete the FOC cable highlighed in option 2 and replace with 1-3C-35mm2 13.8 KV Power Cable.', 2, 'sent', '2014-06-04');
INSERT INTO `review` VALUES(2030, 1203, 47, 'IC to provide only 1 No. cable inside the pipe sleeve instead of 3 No.\r\nIC to cut the pipe along as shown on site to the construction team\r\nIC to use cable ties, insulation tape and plastic sheet as an extra precaution to avoid any sand inside the pipe for future maintanance purpose.\r\nIC to take extra precaution and have the electrician, permit receiver and site engineer at all time during the excavation, installation of sleeves and backfilling around the pipe since this is an existing cable', 2, 'sent', '2014-06-04');
INSERT INTO `review` VALUES(2031, 1204, 47, 'IC to revise the vertical alignment and indicate all information from this drawing', 2, 'sent', '2014-06-04');
INSERT INTO `review` VALUES(2032, 1204, 70, 'As per submittal SDS 028 SAPMT requested to provide connection details at the area where soil improvement ends and show coordinates because the actual situation of soil improvement exceed the St. 1+850 but till now SAPMT did not receive those information.', 2, 'sent', '2014-06-06');
INSERT INTO `review` VALUES(2033, 1205, 47, ' #Revise the Grid location on XB-S7-S12 indicating Grid B instead of Grid C for both your DWG IC-SD-846877-101/2 and 846842-101/2\r\n #Provide the rebar fixing details/dimensions where the sleeves are positioned to avoid cracks or cover to reinforcement.\r\n #Provide a cross section indicating the vertical alignment/ dimension in relation with the horizintal distance provided for both Operator and Visitors building drawings\r\n #Maintain the consistancy on your drawings and scale SI unit is in meters but pipes are in inches\r\n #Provide notes to highlight the SA standard used in designing these drawings and important information not indicated on the drawing. ', 3, 'sent', '2014-06-08');
INSERT INTO `review` VALUES(2034, 1205, 70, '•Regarding to Mechanical – HVAC Sleeves Schedule - XB-S7, XB-S8, XB-S9, XB-S10, XB-S11 & XB-S12 in all drawing are 230 mm from Grid C not from Grid B.\r\n•Regarding to HVAC sleeves XB-S3, XB-S4, XB-S9 and XB-S10 in all drawing are wrong locations as per IFC drawings.\r\n•As per IFC drawing VA-846676-01 and drawing VA-846685-01show the SPU-05-IU mounted above the Power Panel and Lighting Contactor Panel, this is a safety issue due to any type of condensate water may drop on them.\r\n•As per IFC drawing BA-846682-01 and drawing VA-846685-01show the SPU-01-IU mounted above the Fire Alarm Control Panel, this is a safety issue due to any type of condensate water may drop on it.\r\n•Sleeves are penetrating structural concrete shall meet the applicable requirement of the ACI 318 for reinforced concrete, chapter 6 section 6.3.\r\n•I prefer Electrical Engineer ( Mr. Mark ), Communication Engineer ( Mr. Marwin ) and Mechanical Engineer review the submittal to verify the size, location ….etc.\r\n', 3, 'sent', '2014-06-06');
INSERT INTO `review` VALUES(2035, 1206, 47, '#Provide a cross section indicating the vertical alignment/ dimension in relation with the horizintal distance provided for both Operator and Visitors building drawings\r\n#Change DWG IC-SD-846730-101-00 Operator Building SG#2 but the title block says SG#3\r\n#DWG pen size and color are not the same, QA check missing please improve\r\n#Maintain the consistancy on your drawings and scale SI unit is in meters but pipes are in inches\r\n#Provide notes to highlight the SA standard used in designing these drawings and important information not indicated on the drawing.  \r\n', 3, 'sent', '2014-06-08');
INSERT INTO `review` VALUES(2036, 1206, 70, '•Operator Building - as per IFC drawing VA-846706-01 and drawing VA-846711-01show the Window Air Conditioner ( WAC-01) mounted above the Power Panel and Lighting Contactor Panel, this is a safety issue due to any type of condensate water may drop on them.\r\n•Operator Building - regarding to drawing IC-SD-846730-101, the plan title Operator Building (SG #2) is wrong it should be Operator Building (SG #3).\r\n•Sleeves are penetrating structural concrete shall meet the applicable requirement of the ACI 318 for reinforced concrete, chapter 6 section 6.3.\r\n•I prefer Electrical Engineer ( Mr. Mark ), Communication Engineer ( Mr. Marwin ) and Mechanical Engineer review the submittal to verify the size, location ….etc.\r\n', 3, 'sent', '2014-06-06');
INSERT INTO `review` VALUES(2037, 1209, 11, '1. The quantities provided for grounding rods shall be indicative only, it is the responsiblity of the contractor to provide as required in meeting the required grounding system ohmic value as stated in SAES P-111.\r\n2. The quantities provided for busbar is not sufficient, the catalog provided for the busbar does not match with the project requirements, good for two hole lugs. Provide the correct catalog and related specifications.\r\n3. The proposed earth inspection housing is not matching with the IFC drawing and Saudi Aramco Standard drawing, provide necessary Fiberglass with 250 mm dia, with angle steel plate cover as shown in VA-846492.\r\n4. Grounding rods, aerial rods and copper clamps shall be UL listed and labelled.', 2, 'sent', '2014-06-11');
INSERT INTO `review` VALUES(2038, 1209, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2039, 1209, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2040, 1216, 11, '1. Provide the updated Bill of Quantity as per technical meeting held on ICC office dated June 16, 2014.\r\n2. Contractor has to ensure full compliance of IFC drawing.', 3, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2041, 1216, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2042, 1216, 72, ' 1. Material list of each building to be submitted. ', 3, 'sent', '2014-06-11');
INSERT INTO `review` VALUES(2043, 1216, 30, 'No comment', 0, 'sent', '2014-06-11');
INSERT INTO `review` VALUES(2044, 1215, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2045, 1214, 70, 'No comment regarding to civil part. The attached drawings in this submittal ( SDS – 043 ) and in the other submittal  ( SDS – 037 ) are not show the sleeve of HVAC condensate water drainage. Kindly clarify this issue.', 2, 'sent', '2014-06-10');
INSERT INTO `review` VALUES(2046, 1214, 47, '# Other discpline to comment on the arrangement, size and positioning of the sleeves(electrical/ communication/ mechanical)\r\n# Provide the rebar fixing details around the sleeves and indicate how the structural continuation is gonna be like and how you gonna stop the cracks around the sleeve area.\r\n# Provide a larger scale of all cross section drawing to show the requirements during construction to avoid reworks. \r\n', 2, 'sent', '2014-06-11');
INSERT INTO `review` VALUES(2047, 1214, 11, 'Include the equipment layout of Security, Communication and Electrical panel boards.', 3, 'sent', '2014-06-11');
INSERT INTO `review` VALUES(2048, 1218, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2049, 1218, 47, 'No comment', 2, 'sent', '2014-06-11');
INSERT INTO `review` VALUES(2050, 1218, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2051, 1218, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2052, 1218, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2053, 1217, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2054, 1210, 11, '', 0, 'sent', '');
INSERT INTO `review` VALUES(2055, 1210, 47, 'IC to refer to valid points by SAPMT and respond accordingly or comply', 4, 'sent', '2014-06-11');
INSERT INTO `review` VALUES(2056, 1210, 70, 'No comment', 1, 'sent', '2014-06-10');
INSERT INTO `review` VALUES(2057, 1211, 11, '1. Bid drawing PA-000103 shows the clearance between Microwaves Transmitter and Receiver for about 20 meters to 160 meters distance, this clearance is within the range of manufacturer recommendations (see CIAS letter dated May 29, 2014)\r\n2. High Commission on Industrial Security (HCIS) does not mention distance requirements between Fence to MIDS, contractor has to position the MIDS between camera pole and Fence that will meet Bid Drawing PA-000103 and Manufacturer recommendation without extra cost to Saudi Aramco.\r\n3. Contractor is urged to submit without anymore further delay the revised communication and security IFC drawings.\r\n4. Contractor has to ensure 100% compliance to IDAS Functional Specification Document (FSD) PE-000072.', 4, 'sent', '2014-06-14');
INSERT INTO `review` VALUES(2058, 1211, 30, 'The claim is invalid since the ditch removal has no technical impact in the IDAS System, however changing the locations of the microwave devices to ensure system performance is under the responsibility of the contractor and part of the scope. In addition, both IDAS FSD and HCIS requirement does not limit the distance between two microwaves at exact 160 meters thus it mentioned there that there will be an option to adjust the detection plus/minus 150 meters or better.', 4, 'sent', '2014-07-01');
INSERT INTO `review` VALUES(2059, 1212, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2060, 1213, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2061, 1219, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2062, 1219, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2063, 1220, 32, 'No comments. For Information only,', 2, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2064, 1222, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2065, 1222, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2066, 1223, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2067, 1223, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2068, 1224, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2069, 1224, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2070, 1225, 30, 'no comment', 2, 'sent', '2014-06-11');
INSERT INTO `review` VALUES(2071, 1225, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2072, 1225, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2073, 1226, 32, 'No Comments', 1, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2074, 1227, 11, 'No further comment', 1, 'sent', '2014-06-11');
INSERT INTO `review` VALUES(2075, 1227, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2076, 1227, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2077, 1228, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2078, 1229, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2079, 1231, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2080, 1232, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2081, 1232, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2082, 1232, 72, 'No comments', 1, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2083, 1233, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2084, 1233, 11, 'No comment', 1, 'sent', '2014-06-25');
INSERT INTO `review` VALUES(2085, 1233, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2086, 1233, 72, '', 1, 'sent', '2014-06-16');
INSERT INTO `review` VALUES(2087, 1233, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2088, 1234, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2089, 1234, 11, '1. Ensure that Vented Lead Acid and Valve regulated Lead Acid (VRLA), meets the requirements of SAES P-103 and project specification.\r\n2. Provide shop drawing for the equipment layout inside the room.\r\n3. UPS and Batteries inside the rooms shall meet the required maintenance clearance. \r\n4. Battery Racks, and Maintenance Cabinet shall be provided as stated in SAES P-103 para. 6.2.12', 2, 'sent', '2014-06-18');
INSERT INTO `review` VALUES(2090, 1234, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2091, 1234, 72, '1. Summary sheet of each  buildings to be provided', 2, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2092, 1235, 70, 'It’s the contractor responsibility to communicates and coordinates with the others.\r\n\r\n', 4, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2093, 1235, 47, 'IC to refer back to their demolishing contract and action accordingly\r\nThere is no interface coordinator on site to expedite all this issues and IC is urged again to either replace the current interface coordinator or request his to follow this issues up until its done.\r\nIC has given this demolishing contract to Navy employee to provide a smooth operation during the demolishing process however the said employee is not happy with other things and now IC is requesting SAPMT to resolve.\r\nIC to attach all the agreements and the scope made with the NAVY employee before SAPMT can intervene.', 3, 'sent', '2014-06-15');
INSERT INTO `review` VALUES(2094, 1235, 11, 'Contractually, Interface coordinator of ICC has to work closely with other parties and provide options for SAPMT approval.', 3, 'sent', '2014-06-29');
INSERT INTO `review` VALUES(2095, 1236, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2096, 1236, 30, 'see comment on DS-332', 3, 'sent', '2014-07-13');
INSERT INTO `review` VALUES(2097, 1237, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2098, 1237, 30, 'see comment on DS-331', 3, 'sent', '2014-07-13');
INSERT INTO `review` VALUES(2099, 1238, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2100, 1239, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2101, 1240, 11, 'Reference with your letter number KPSS/SA/B/AKR/14/0646 dated June 12, 2014, enclosed herewith is the As-built drawing of Building 2 area 2,5 level 4 & 5, and Building 5 area 2,5 level 4 & 5. In addition to it, attached is the work permit to be used inside CAMPUS TER to be filled and execute by your work permit receiver.\r\n\r\nContractor is directed to expedite the MEP works, without any further delay.\r\n\r\nShould you have any question please contact Fahad Al Balawi.\r\n', 2, 'sent', '2014-06-20');
INSERT INTO `review` VALUES(2102, 1240, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2103, 1241, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2104, 1241, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2105, 1241, 11, 'No comment', 1, 'sent', '2014-06-16');
INSERT INTO `review` VALUES(2106, 1242, 11, '1. Superimpose the propose routing layout with new KAM access road and King Abdullah Monument drawing plans.\r\n2. Provide the coordinates for every corners and curves of the propose fiber optic cable layout.\r\n3. Ensure that the propose layout is coordinated with the existing underground FOC, and electrical cables running in King Abdullah Monument Project.', 3, 'sent', '2014-06-23');
INSERT INTO `review` VALUES(2107, 1242, 30, 'The drawing must indicate all the locations of the fiber marker posts.\r\nThe drawing must indicate the distance of the fiber cable to the edge of the new KAM road.\r\nProvide manhole fold out details of the new proposed service manhole.\r\nProvide details and schematic diagram and splicing details of the proposed 24 core fiber cable to the existing IDAS cable.\r\nProvide plan and splicing details of the existing primary and redundant 96 core fiber cable of IDAS\r\nProvide plan how the existing optipeds and service manhole to be removed.', 3, 'sent', '2014-07-01');
INSERT INTO `review` VALUES(2108, 1242, 70, 'I don’t have any comment. This area under Mr. Easy Responsibility, he has more information. I prefer to share this submittal with him may be he has some comment.', 1, 'sent', '2014-06-15');
INSERT INTO `review` VALUES(2109, 1243, 11, '1. Contractor has to ensure that Boat Identification system will comply with IFC drawing.\r\n2. The title of the material submittal has to be changed, SOC and SACS has not relation with Boat Identification System.\r\n', 2, 'sent', '2014-06-16');
INSERT INTO `review` VALUES(2110, 1243, 30, 'Contractor''s response cannot be accepted without providing and attaching any documents and references that the proposed model of AIS is compliant to SAPMT previous comments and Appendix H requirements.', 3, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2111, 1243, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2112, 1244, 70, 'It’s contractor responsibility for prior investigation before bidding because any area close to sea 99 % need soil improvement.\r\n\r\n', 0, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2113, 1244, 47, '#During utilities and site investigations IC overlooked these items and all these issues were discovered after the IFC finalization and now a detailed Shop Drawing was required to reflect all these items. \r\n#IC to provide all relevant documentations in relation to these issues.\r\n\r\n ', 3, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2114, 1244, 11, 'Please get the comments to CIVIL discipline Mr. Easy and Sami. In addition below is my comment.\r\n\r\n\r\n1. Provide shop drawing and superimposed the location of communication manhole and Fiber Optic Cable on the affected area.\r\n', 3, 'sent', '2014-06-20');
INSERT INTO `review` VALUES(2115, 1245, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2116, 1245, 47, '#IC should have notified Aramco of any additional building required to make the operation work during the draft or initial stages of the project.\r\n#IC to refer to IFB DWG PA-000035-001-C Notes No. 3 clarity and confirmation on what and what not to include on their final drawing.\r\n#IC should have designed the whole system around the operation area/ room to be full automatic as per the IFB but opted for the Operator Room which is human controlled.\r\n#IC to submit all documents and correspondence indicating that they were aware of all this and other changes during bidding process and have notified Aramco of all the descrapancies', 3, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2117, 1245, 70, 'As per project proposal document ( IFB ) – Para 1.2.2.1.5.7 “With due justification and with PMT approval, the detailed engineering design may elect to establish a separate security control shelter dedicated to functions related to the vehicle inspection centerâ€.', 2, 'sent', '2014-06-15');
INSERT INTO `review` VALUES(2118, 1246, 33, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2119, 1247, 11, '1. Additional pole arm and lighting fixtures cannot be entertain at this stage, wherein the sizing of cables,  switch racks, and pole foundation has been done and ordered.', 4, 'sent', '2014-06-22');
INSERT INTO `review` VALUES(2120, 1247, 33, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2121, 1248, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2122, 1248, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2123, 1249, 11, 'No comment, but kindly get the comment to CIVIL PMT Sami and Azwinn. The main issue is backfilling procedure.\r\n', 2, 'sent', '2014-06-16');
INSERT INTO `review` VALUES(2124, 1249, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2125, 1249, 72, 'NO COMMENTS', 1, 'sent', '2014-06-16');
INSERT INTO `review` VALUES(2126, 1250, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2127, 1250, 47, '#IC to mark/specify which material is to be used which area and indicate on the  shop drawing the description in relation to the installation instead of generalizing.\r\n#Before work starts IC to revise the shop drawing as per material approval.', 2, 'sent', '2014-06-18');
INSERT INTO `review` VALUES(2128, 1250, 70, '•The ladder sample is little bit rusted in Sample Board 2 of 2. The contractor shall provide new and excellent samples.\r\n•The samples accessories attached in the boards without titles.\r\n•Submit two sample, 400 x 400 mm in size illustrating finish color and texture as per project specification section 09220 Para 1.05.\r\n•Avoid cutting the galvanized accessories.\r\n', 2, 'sent', '2014-06-16');
INSERT INTO `review` VALUES(2129, 1251, 32, 'No Comments. For Information only.', 2, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2130, 1252, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2131, 1253, 11, '1. Ensure that all MV cable running under roads were protected by Ductbanks.\r\n2. Ductbanks for MV cable shall SAES P-104.\r\n3. Ensure that MV cable clearance with other utilities are within the minimum requirements of 300 mm as stipulated in Saudi Aramco standards.\r\n4. Provide detail shop drawing for all underground electrical and non-electrical utilities that will pass through box culverts 3 & 4 and Wadi Khulais Culvert.', 2, 'sent', '2014-06-18');
INSERT INTO `review` VALUES(2132, 1253, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2133, 1254, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2134, 1254, 48, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2135, 1254, 70, 'Provide the total manpower for each job title. ', 2, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2136, 1254, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2137, 1254, 47, '', 0, 'sent', '');
INSERT INTO `review` VALUES(2138, 1255, 70, 'No comment', 1, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2139, 1255, 47, 'No comment', 1, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2140, 1256, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2141, 1256, 11, 'No futher comment', 1, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2142, 1256, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2143, 1257, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2144, 1257, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2145, 1258, 45, 'The plan is in order for being compliant with the provisions as provided in the SA Construction Safety Manual.\r\nHaving said this, it is more acceptable if the Contractor will demonstrate religious implementation of the PRACTICES committed as per submittal.\r\n\r\nProceed with the implementation and include in the weekly and/or monthly reports  their percentage compliance performance.', 0, 'sent', '2014-06-17');
INSERT INTO `review` VALUES(2146, 1259, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2147, 1259, 47, '#Proceed as per SCEC recommendations.', 2, 'sent', '2014-06-21');
INSERT INTO `review` VALUES(2148, 1259, 70, 'No Comment.', 1, 'sent', '2014-06-20');
INSERT INTO `review` VALUES(2149, 1260, 11, 'Provide compliance feedback from vendor in relation with SAPMT comments for the material submittal, this must be attached with the Requisition Package.', 2, 'sent', '2014-06-25');
INSERT INTO `review` VALUES(2150, 1260, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2151, 1260, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2152, 1261, 72, 'comments received from Abu hanipah\r\n\r\nComments: (C- Revise & Resubmit)\r\n1.	Not Clear where the Irrigation Tie In Point is located.\r\n2.	Where is the existing Irrigation Line.\r\n3.	Numbering of BFP are not clear.\r\n', 3, 'sent', '2014-08-25');
INSERT INTO `review` VALUES(2153, 1261, 70, 'Regarding to the sleeve of median water supply is o.k. and the tie in concept is o.k.  \r\nThe valve box is excluded from this submittal for civil work, valves …etc.   \r\n', 2, 'sent', '2014-06-20');
INSERT INTO `review` VALUES(2154, 1261, 47, '#Provide all tie-in coordinates to reflect all the points mentioned\r\n#Provide cross section showing all the details eg. bends, joints, elevation etc.', 2, 'sent', '2014-06-21');
INSERT INTO `review` VALUES(2155, 1262, 11, 'No comment.', 1, 'sent', '2014-06-18');
INSERT INTO `review` VALUES(2156, 1262, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2157, 1262, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2158, 1262, 70, 'My recommendation is to cover the gravel by geotextile to avoid settlement at future.\r\nIts contractor responsibility to ensure the elevation of the LV cable is not intersecting with the other utilities & provide enough clearance as per Aramco standard.\r\n', 2, 'sent', '2014-06-20');
INSERT INTO `review` VALUES(2159, 1263, 11, '1. For MV and LV cables running underneath roads, ensure that surface marker electrical sign post area will be provided see standard drawing AB-036273 for your reference.', 2, 'sent', '2014-06-18');
INSERT INTO `review` VALUES(2160, 1263, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2161, 1263, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2162, 1265, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2163, 1266, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2164, 1266, 11, '1. The proposed exhaust fan does not meet the minimum enclosure requirements of SAES P-104 para. 7.3\r\n2. Clarify why there are catalogs attached in this material submittal for duct fans and axial fans.', 3, 'sent', '2014-06-25');
INSERT INTO `review` VALUES(2165, 1266, 21, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2166, 1267, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2167, 1267, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2168, 1268, 11, '1. Ensure that liquid tight flexible conduit is UV resistant.\r\n2. Flexible conduit shall only be used on the defined equipment''s as stipulated in SAES P- Series and National Electrical Code.', 2, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2169, 1268, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2170, 1268, 71, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2171, 1268, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2172, 1269, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2173, 1269, 11, '1. Ensure that traffic signal and controller are heavy duty type.\r\n2. Ensure that shop drawings for mounting of signal lights and conduiting will be provided.\r\n3. Provide the location of the controller.', 2, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2174, 1269, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2175, 1269, 45, 'The item proposed is acceptable from the point of view of Safety. ', 0, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2176, 1270, 70, '1 - The contractor has to start the curing as per ACI 308R and ACI 308.1 – 98 recommendations.\r\n2 - Using curing compound is not allowed:\r\n- As per SAIC – Q – 1028 “Curing compound shall not be used for curing of precast and prestressed concrete elements.â€\r\n- SAES – Q – 012 Para 6.9.2 refers to SAES – Q – 01 sec. 10 which is using steam curing or water curing only.\r\n3 - Precast defect repairs as per my comments in submittals DS – 308 and DS – 207.\r\n\r\n', 2, 'sent', '2014-06-25');
INSERT INTO `review` VALUES(2177, 1270, 47, 'IC to ensure that all the agreed items with SAPMT/ PID that were not part of the ITP are all included with their inspection clarity;Hold point(H) or Witness point (W) or surveillance (S)', 2, 'sent', '2014-06-25');
INSERT INTO `review` VALUES(2178, 1270, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2179, 1271, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2180, 1271, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2181, 1271, 11, '1. Provide the enclosure dimensions.\r\n2. Provide the shop drawing of the panel, showing the arrangment of selector switch, pilot lamps, and push buttons.\r\n3. Provide internal wiring arrangment, showing the transformer and circuit breaker position, wire trunking and relay arrangments.\r\n4. Include necessary catalogs for all related electrical and control devices to be used for the DDC.', 3, 'sent', '2014-06-28');
INSERT INTO `review` VALUES(2182, 1272, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2183, 1273, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2184, 1273, 47, 'no comment', 1, 'sent', '2014-06-26');
INSERT INTO `review` VALUES(2185, 1273, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2186, 1274, 32, 'No Comments', 1, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2187, 1275, 11, 'No comment.', 1, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2188, 1276, 70, 'No Comment', 1, 'sent', '2014-06-25');
INSERT INTO `review` VALUES(2189, 1276, 47, 'No comment', 1, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2190, 1277, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2191, 1277, 11, '1. Ensure that the LED Picture sign display is heavy duty type.\r\n2. Ensure that shop drawings for mounting the sign display and conduiting will be provided.\r\n3. Ensure that the weight load of sign display is coordinate with the structure of the shed.', 2, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2192, 1277, 30, 'No comment', 2, 'sent', '2014-07-01');
INSERT INTO `review` VALUES(2193, 1278, 45, 'The material submitted is for initial notification purposes as per current SA procedure. The final report should be submitted within 24 hours upon discovery of the accident/incident. For the Contractor (ICC) compliance as per standing Incident Reporting System.', 0, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2194, 1279, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2195, 1280, 70, '•Why do IC and SCEC need to fill with granular fill? I think the general fill instead of granular is enough because the area is not sabkha. \r\n•IC should do a soil investigation to inform us the actual dimensions of garbage area (depth and width).\r\n\r\n', 0, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2196, 1280, 47, 'IC to submit the full package with description on this subject formaly to SAPMT.\r\n\r\n', 3, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2197, 1281, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2198, 1283, 47, '#Provide justification of your price break down in relation to the quantity of work.\r\n#Define market price vs demolition of the structure constructed by your company and not by others', 3, 'sent', '2014-06-25');
INSERT INTO `review` VALUES(2199, 1283, 70, 'The quantity has been submitted by Mr. Easy long time ago and Mr. Tang can help regarding to the price.\r\n\r\n', 2, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2200, 1283, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2201, 1284, 32, 'No Comments. For Information only.', 2, 'sent', '2014-06-24');
INSERT INTO `review` VALUES(2203, 1285, 30, 'The document must be reviewed by IC technical and QA Personnel with their stamp or approval.\r\nThis is not different to the submitted Communications Specifications Write Up DS-317, if so then both documents must be combined and submitted to one document only.', 3, 'sent', '2014-07-13');
INSERT INTO `review` VALUES(2204, 1286, 30, 'The document must be reviewed by IC technical and QA Personnel with their stamp or approval.\r\n This is not different to the submitted Security Specifications Write Up DS-316, if so then both documents must be combined and submitted to one document only.', 3, 'sent', '2014-07-13');
INSERT INTO `review` VALUES(2205, 1286, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2206, 1285, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2207, 1205, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2208, 1206, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2209, 1287, 30, 'Provide and attach Heat Load Calculation of your rack or cabinet. Result must show that the heat generated by the installed server can be accomodated by the proposed rack or cabinet.\r\n\r\nEsnure that the proposed model is appropriate to use for high density servers', 3, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2210, 1287, 11, 'No comment.\r\n\r\nMarwin will give comment for this submittal.', 1, 'sent', '2014-06-29');
INSERT INTO `review` VALUES(2211, 1288, 70, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2212, 1288, 47, 'NO COMMENT', 1, 'sent', '2014-06-29');
INSERT INTO `review` VALUES(2213, 1289, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2214, 1289, 70, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2215, 1290, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2216, 1291, 32, 'No Comments', 1, 'sent', '2014-06-30');
INSERT INTO `review` VALUES(2217, 1292, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2218, 1292, 78, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2219, 1293, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2220, 1294, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2221, 1296, 45, '1. This preliminary incident report is in compliance to the Initial Notification Stage in accident/incident reporting as per established SA procedure.\r\n2. SAPMT will expect the sibmission of the final report from the Contractor (ICC) within 48 hours after discovery of the incident.\r\n3. PMT- Safety Advisor enters the incident data into the PM Incident Reporting System as part of the monthly report.\r\n4. Final report will subject for final review by SAPMT and if approve will be maintained on SA/ICC Document Control File and CC the Department Safety Coordinator. \r\n5. All accidents/Incidents in the Project which are above a pre-determined value or standing policies follow the above guidelines.\r\n\r\n\r\nAttached Files:  \r\n', 0, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2222, 1297, 70, 'There are some areas take long path while can drain to nearest point such as visitor building is close to infiltration trench while the area drain to the MOT road. It’s so difficult to control the slop of the long path.', 2, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2223, 1297, 47, 'IC to verify the elevation provided by the topographic survey after grading and proceed accordingly or notify SAPMT if there is a major difference in elevations', 2, 'sent', '2014-06-30');
INSERT INTO `review` VALUES(2224, 1298, 72, '1. sleeve for irrigation control cable to be submitted separately. ', 2, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2225, 1298, 70, '•My recommendation to add geotextile below and above the gravel layer.\r\n•The material of the PVC sleeve should be as per Saudi Aramco Standards.\r\n•No cost impact.\r\n', 2, 'sent', '2014-06-30');
INSERT INTO `review` VALUES(2226, 1299, 47, '#Provide the vendors shop drawings as per note 2-5 on DWG: VA-846739-003-0F1 for more details.', 2, 'sent', '2014-07-01');
INSERT INTO `review` VALUES(2227, 1299, 70, 'No comment.', 1, 'sent', '2014-06-30');
INSERT INTO `review` VALUES(2228, 1300, 47, '#Provide a bending schedule indicating shapes and codes of all rebars.\r\n#Provide all opening details for sleeves or any miscellaneous items.\r\n#Provide specific notes on concrete/ compaction specifications ', 2, 'sent', '2014-07-01');
INSERT INTO `review` VALUES(2229, 1300, 70, 'The blast resistance building shall be designed as per SAES-M-009\r\n-- Gate Houses (SG 2 & 3):\r\n•The corner column has rebar  8 Φ 16 mm in the Plan detail and has 6 Φ 16 mm in section A-A of drawing VA-846582-001-0F1 & VA-846778-001-0F1. SCEC should confirm which is correct.\r\n•The column cross sections are very small. Kindly enlarge them.\r\n•The wall thickness in this submittal is 250 mm while in IFB Drawing PA-000203-001-C is 350 mm. why did SCEC reduce the walls thickness?\r\n•The roof beam thickness 350 mm as per IFB Drawing PA-000203-001-C while it is 300 mm in the IFC VA-846582-001 and VA-846778-001, but in this submittal is 250 mm only. Why did SCEC reduce the thickness?\r\n•Provide more details of roof beam (RB-01).\r\n•Provide cross sections at the two directions for roof slab to show the rebar arrangement.\r\n•Missing rebar schedule for all attachment drawings\r\n•What is the compression strength of concrete?\r\n• Concrete cover should be 75 mm for concrete expose to earth and to weather as per general note VA-846497-001. \r\n-- Operator Building (SG 2 & 3):\r\n•No approval from SAPMT for the operator building till this moment.\r\n•Concrete cover should be 75 mm for concrete expose to earth and to weather as per general note VA-846497-001. \r\n•Missing rebar schedule for all attachment drawings\r\n•What is the compression strength of concrete?\r\n', 3, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2230, 1319, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2231, 1319, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2232, 1318, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2233, 1316, 47, '#IC/SCEC to provide a comparison between the IFB and IFC and justify their choice/preferred design criteria\r\n#IC/SCEC did not respond to SAPMT letter and base their design on the issue raised already\r\n#The IFB drawing (KA 714497-001)indicate 80mm and 40mm for base and wearing course respectively whilst the IFC (KA 714498-004) indicate 70 mm and 50mm respectively and as per SAES-Q-006-Cl 5.5.3 (B) the designer chose 70 mm which is as per the standard avoiding ARAMCO justification\r\n#IC/SCEC to follow SAES-Q-006- CL.4.2 table 2 and 4.5 table 3\r\n', 3, 'sent', '2014-06-30');
INSERT INTO `review` VALUES(2234, 1316, 70, '•IC should getting prior approval from SAPMT.\r\n•We need the references of the options A & B.\r\n', 3, 'sent', '2014-06-30');
INSERT INTO `review` VALUES(2235, 1315, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2236, 1314, 70, '•It’s better if there is possibility to relocate one of the two tanks to be in the other side of the HAMMAM building to provide far distance between the two tanks to avoid any type of pollution.\r\n•Regarding to Non – Electrical Utilities Layout drawing (VA-846996-001-0F1), maintain a distance between the sanitary main pipe and potable water pipe as per Saudi Aramco standard.\r\n•There is a conflict regarding to Pump Control Panel location, the two drawing show deferent locations (VA-847009-001-0F1 and VA-84-7018-001-0F1).\r\n•Its better if relocate the pump control panel to the nearest wall to the pump to reduce the cable length.\r\n', 2, 'sent', '2014-07-03');
INSERT INTO `review` VALUES(2237, 1314, 47, '#IC to adhere to all the specifications, functionality and the ideas behind the Guard House positioning as per KAUST requirements. \r\n#IFC Drawing for Kitchen/ toilet (VA-847024) and Guard House (VA-847023)to be included for clarity.\r\n#IC/SCEC to expedite on note 12 as indicated on DWG VA-846997-001-0F2 to finalise all the details such as openings for sleeves or any equipment fittings.\r\n#Provide more details on coordinates and elevations of all the piping,cabling, concrete and rebar details.\r\n#specify the compaction of the screened gravel materials and interfacing of the fibre glass anchor strip and cables clamps\r\n#Clarify the 100 mm thick crushed rock dimension/ rock size on top of the the valve box as the drawing is indicating 2 layers.', 2, 'sent', '2014-07-01');
INSERT INTO `review` VALUES(2238, 1313, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2239, 1312, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2240, 1310, 70, 'This area under KAUST custody and they used to remove any infected or died palm tree but this area was neglected by them and no maintenance for this area for long time. KAUAST should send their maintenance team for investigation and action.', 2, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2241, 1309, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2242, 1308, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2243, 1308, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2244, 1307, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2245, 1307, 11, 'No more further comment.', 1, 'sent', '2014-06-30');
INSERT INTO `review` VALUES(2246, 1304, 70, 'No comment', 1, 'sent', '2014-06-30');
INSERT INTO `review` VALUES(2247, 1304, 47, '#IC/SCEC to expedite on note 12 as indicated on DWG VA-847045-001-0F2 to finalise all the details.\r\n#Provide more details on elevations of all the piping, concrete rebar anchor pad.\r\n#specify the compaction of the screened gravel materials and interfacing of the fibre glass anchor strip and cables clamps\r\n#Clarify the 100 mm thick crushed rock dimension/ rock size on top of the the valve box as the drawing is indicating 2 layers.', 2, 'sent', '2014-06-30');
INSERT INTO `review` VALUES(2249, 1301, 72, '1. Subject TQ shall be approved and stamped by the designer. ', 4, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2250, 1302, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2251, 1303, 45, '1. The report is in order and compliant with the SA Incident Reporting System procedure.\r\n2. Strongly suggest that you (Operating Management and supervision) observe the religious implementation of your recommendations to prevent re-currence of similar incidents in the future.\r\n3. Contractor leadership should be more visible in demonstrating in observing accident/incident prevention initiatives rather that expecting compliance by the workers.\r\n4. Keep this report on ICC DC file for auidt and other purposes and furnish copy to the Department Safety Coordinator c/o Mr. Samuel Noah Wilson\r\n5. Disccuss this to the workers c/o the Supervisors/Foremen.', 0, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2252, 1306, 11, 'Information only. Waiting for KAUST final comment.', 2, 'sent', '2014-07-03');
INSERT INTO `review` VALUES(2253, 1305, 11, 'The letter has been transmitted to KAUST.', 2, 'sent', '2014-07-03');
INSERT INTO `review` VALUES(2254, 1320, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2255, 1320, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2256, 1321, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2257, 1321, 72, '1. calibration certificate to be provided with the material.', 2, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2258, 1322, 32, 'No Comments', 1, 'sent', '2014-06-30');
INSERT INTO `review` VALUES(2259, 1242, 47, '# a new FOC cable routing have to be re-designed because IC/ SCEC opted to change the KAM Road alignment to avoid the rehabilitation of mangroves plants/ species from CH 1850 to 3300.\r\n#IC ensure that the FOC cable construction / installation is not under the walkway before any cable pulling starts to avoid any faults on the Sonar and Radar during operations.\r\n#IC/SCEC to verify the coordinates and elevation of the FOC routing and make certain that it is outside the road shoulder.\r\n#IC to ensure that the mandrel test inside the ducts bank is conducted before cable pulling works is carried out to avoid reworks.', 2, 'sent', '2014-07-01');
INSERT INTO `review` VALUES(2260, 1329, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2261, 1323, 30, 'Provide schematic diagram or block diagram of the connectivity of the proposed server\r\nAll servers must be fully redundant as per Appendix H Section 2.3.2.3\r\nOperating System must be included.\r\nProvide calculation that the proposed server capacity is enough to accomodate the project''s requirement', 3, 'sent', '2014-07-01');
INSERT INTO `review` VALUES(2262, 1323, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2263, 1324, 11, '1. Consider submitting the other License Plate Recognition System (LPRS) that is interface with Maxess.\r\n2. Ensure that the data base for upgrading the LPRSS systems is centralized.\r\n\r\n\r\n\r\n', 2, 'sent', '2014-07-03');
INSERT INTO `review` VALUES(2264, 1325, 32, 'No Comments. For Information Only.', 1, 'sent', '2014-07-01');
INSERT INTO `review` VALUES(2265, 1326, 70, 'No comment.', 1, 'sent', '2014-07-01');
INSERT INTO `review` VALUES(2266, 1327, 70, '•The blast resistance building shall be designed as per SAES-M-009\r\n•The house size is more than the IFB, if no prior approval from SAPMT then No positive change order.\r\n•The submittal is general architectural drawing, the contractor shall submit the details architectural drawings such as tiles, paints …etc. in individual submittals also the contractor shall submit the structural drawing in another submittal.\r\n•Delete the note no. 3 which is canceled by SCEC.\r\n', 2, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2267, 1327, 11, '1. Consider reflecting the fire alarm notification devices such as horn, flasher and bell in the plan and elevation details.\r\n', 2, 'sent', '2014-07-04');
INSERT INTO `review` VALUES(2268, 1328, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2269, 1330, 45, '1. This preliminary incident report is in compliance to the Initial Notification Stage in accident/incident reporting as per established SA procedure.\r\n2. SAPMT will expect the sibmission of the final report from the Contractor (ICC) within 48 hours after discovery of the incident.\r\n3. PMT- Safety Advisor enters the incident data into the PM Incident Reporting System as part of the monthly report.\r\n4. Final report will subject for final review by SAPMT and if approve will be maintained on SA/ICC Document Control File and CC the Department Safety Coordinator.', 0, 'sent', '2014-07-02');
INSERT INTO `review` VALUES(2270, 1331, 32, 'No Comments. For Information only.', 1, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2271, 1332, 28, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2272, 1332, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2273, 1333, 47, '#Provide a clear color readable copy of drawing; VA-847118-0F1.\r\n#IC to consider submitting an A1 or A0 drawing to highlight all important information on the drawing.\r\n#Kaust deed line to be clearly shown on the drawing and all the designs to be based on that as a guideline.', 3, 'sent', '2014-07-09');
INSERT INTO `review` VALUES(2274, 1333, 11, 'Consider removing the word DITCH from the title "Overall Fence and Ditch layout" as shown in VA-846501 sht 001 rev. 0F1', 2, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2275, 1333, 70, '•The submittal title and drawing VA-846501-001-0F1 are wrong because they demonstrate the area without Ditch, while the title saying “overall fence and Ditch layout new securityâ€.\r\n•Provide the cross sections as mentioned in the drawing VA-846502-001-0F2 to show the new alignment of the security fence and the distances between the other utilities. \r\n', 3, 'sent', '2014-07-10');
INSERT INTO `review` VALUES(2276, 1334, 47, '#IC to provide full set of drawing; SAPMT will not allow any further delays in terms of issuing the outstanding shop drawings since the IFC were ridiculously delayed because IC management are still searching for out of scope items.\r\n#Provide all relevant vendor shop drawings together with this submittal and avoid using Note 4-6 as a scapegoat/ incomplete submittal; Note 7 is not valid since the drawing mentioned (VA-846799-001) does not show any specific details other than that shown on VA-847106-0F1.\r\n#Based on the Auxiliary Gate Elevation Section on VA-847105-0F1 there is a big level difference between the sliding gate and the precast foundation footing; provide cross section indicating the interface between the two.', 3, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2277, 1334, 70, '•The footing section/plan in drawing VA-847106-001-0F1 without reference.\r\n•The contractor shall submit the precast concrete column fixation details/shop drawing.\r\n', 3, 'sent', '2014-07-11');
INSERT INTO `review` VALUES(2278, 1334, 11, '1. Identify the position of conduit stub-up for power supply and grounding cables.\r\n2. Ensure that the location of motor and necessary controls are coordinated with the motorized gate vendor.\r\n', 2, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2279, 1335, 47, '#The quality of drawings is deteriorating for each submittal.\r\n#Provide a color copy drawing and indicate the enlarged fence, the fence concerned is not visible on the drawing; \r\n#Information/ dimensions are crossing too many lines which makes it difficult to relate to the detailing.\r\n#Provide/ Align your chainages/ stations outside the lines for a clear defined reference point.\r\n#IC to consider providing an A1 or A0 for this kind of submittals.', 3, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2280, 1335, 70, '•Additional round about in National Guard Petrol Road as per drawing VA-846506-001-0F1 and the additional drain pipe in the same drawing which are not included in the original IFC ( VA-846506-001) are accepted without positive change order.\r\n•Attach the detail drawing of the drain pipe as mentioned drawing VA-846506-001-0F1\r\n•Gravel trenches and slope protection of maintenance road which are not included in the original drawing IFC are accepted without positive change order.\r\n•There is another road joint the maintenance road at St. 9+300 (VA-846506-005-0F1) which is not mentioned in the original drawing IFC VA-846506-005.  IC should have a prior approval from SAPMT first and No positive change order.\r\n•Why the Station numbering of brick wall (inset) in drawing VA-846506-006-0F1 change and started by 0+000 instead of continue the numbering as per the original drawing IFC VA-846506-006?\r\n•Additional round about in National Guard Petrol Road as per drawing VA-846506-006-0F1 is not included in the original IFC (VA-846506-006) is accepted without positive change order.\r\n•Connecting the Maintenance road with Security patrol road and extending the maintenance road started at Station 14+400 which are not mentioned in the original drawing IFC VA-846506-006 needs a prior approval from SAPMT and No positive change order. \r\n•In this submittal (VA-846506-006-0F1) the shore line protection reduced 50 linear meter compared by original IFC VA-846506-006. It needs a prior approval from SAPMT and negative change order if SAPMT accepted.\r\n', 2, 'sent', '2014-07-11');
INSERT INTO `review` VALUES(2281, 1336, 47, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2282, 1336, 70, '•The blast resistance building shall be designed as per SAES-M-009\r\n•The house size is more than the IFB, if no prior approval from SAPMT then No positive change order.\r\n•Contractor shall submit the structural shop drawing as usual in separate submittal.\r\n•Provide blow up details for sleeves with necessary rebar such as roof drain sleeve, Electrical conduits …etc.\r\n•There is a CMU wall in front of the Guard House door (Marine Road) VA-Q-847118 – 001 – 0F1- Section C – C, as per Architectural drawing VA-847116-001-0F2 no wall at all. Kindly confirmation from SCEC.\r\n•Concrete cover should be 75 mm for concrete expose to earth and to weather as per general note VA-846497-001.\r\n•Regarding Marine Guard house, as per Architectural drawing VA-847116-001-0F2 the stair case has three way to enter to the building but in this submittal VA-847118-001-0F1 show one way. Kindly confirmation from SCEC.\r\n•Provide cross section of stair case flight for marine guard house.\r\n', 3, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2283, 1336, 11, 'No technical comment. Forwarded to civil team, Mr. Easy and Sami.', 2, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2284, 1337, 47, '#Provide a readable color copy so we may be able to relate to your drawing and provide a proper review.\r\n#Drawing too congested and all the lines looks similar with no reference point like a specific chainage\r\n#Provide the agreed/ initial demolition plan and the revised after the re-alignment of KAM Road.', 3, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2285, 1337, 70, 'No positive change order due to the additional demolition and realignment of KAM Access Road.', 2, 'sent', '2014-07-10');
INSERT INTO `review` VALUES(2286, 1338, 47, '#With each security Gate only 11 m wide , IC/ SCEC to make sure that the Guard House is positioned or located at a point where there will be clear visibility to the all the 23 cells of the Box Culvert as per Aramco requirement.\r\n#Provide all coordinates of tie-in points as PI reference during construction.\r\n#IC/ Scec to provide color drawing copies in all their submittals, in a black an white copy nothing stands out since all the lines look similar and difficult to indentify during submittal review.\r\n\r\n', 2, 'sent', '2014-07-09');
INSERT INTO `review` VALUES(2287, 1338, 70, 'No Comment.', 1, 'sent', '2014-07-07');
INSERT INTO `review` VALUES(2288, 1338, 11, 'No technical comment. Forwarded to civil team, Mr. Easy and Sami.', 2, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2289, 1339, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2290, 1340, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2291, 1341, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2292, 1341, 47, 'No Comment', 1, 'sent', '2014-07-07');
INSERT INTO `review` VALUES(2293, 1341, 70, 'IC should add Asphalt activity in KAM Access Road', 3, 'sent', '2014-07-10');
INSERT INTO `review` VALUES(2294, 1343, 84, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2295, 1343, 11, '1. Aluminum fins is not allowed for outdoor unit, only copper fins for outdoor unit shall be used as per project specifications and Saudi Aramco Standard.\r\n', 3, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2296, 1343, 72, '1. Propposed model number to be highlighted or included in the summary sheet.\r\n2. Building wise summary sheet with model number,cooling capacity are to be provided.\r\n3. Indoor unit shall be WMX -18 and out door unit shall be KXC-18 as per IFC.\r\n4. Outdoor unit shall be constructed of galvanized steel or aluminium bonderized and coated with powder coat paint as per VE 846472 section 2.01.\r\n5. TER Room back up split unit shall be libert DX type units. ', 3, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2297, 1344, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2298, 1345, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2299, 1345, 11, '1. It is the responsibility of the contractor to impose extra care while working in the nearby Mobily Fiber Optic Cables.\r\n2. Apply manual exploration to the suspected locations of Fiber Optics, and protect the fiber optic cables using sleeves or ductbanks in case it will be exposed.\r\n\r\n\r\n\r\n\r\nFor Saudi Aramco:\r\n\r\n1. SAPMT has to finalize with KAUST the extra works for relocation of Mobily FOC.\r\n', 2, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2300, 1345, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2301, 1346, 70, '1.Sulfur mortar capping compound shall be as per ASTM C 617 recommendation.\r\n2.Safety Caution: The primary hazard in handling powdered Sulfur is that Sulfur DUST suspended in air ignites easily and produce explosive forces in confined areas. Ignition sources can be heat, friction, pyrophoric Sulfur and internally generated static electricity. An initial small explosion can create subsequent large explosion if the building area contains dusty powder residue on overhead surfaces such as rafters or trusses. A Sulfur dust will produce Sulfur Dioxide, a TOXIC gas. I prefer to use another material with less dangerous.\r\n', 2, 'sent', '2014-07-07');
INSERT INTO `review` VALUES(2302, 1346, 47, 'No Comment for info only.', 1, 'sent', '2014-07-07');
INSERT INTO `review` VALUES(2303, 1346, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2304, 1347, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2305, 1347, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2306, 1348, 32, 'No comments. For Information only.', 1, 'sent', '2014-07-08');
INSERT INTO `review` VALUES(2307, 1349, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2308, 1352, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2309, 1353, 12, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2310, 1352, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2311, 1356, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2312, 1357, 45, 'The case is a community car incident which happened at the border of Zone B worksite. The details were not known until the vehicle was removed from site by the authorities as per information gathered by ICC Safety Department.\r\nThe incident is for SAPMTs information which brings to mind the previous suggestion of installing concrete roadside barriers along work areas  adjacent the MOT roads. This will reduce direct contact to the workers when a malfunctioning vehicle crashes against these structures.', 0, 'sent', '2014-07-13');
INSERT INTO `review` VALUES(2313, 1358, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2314, 1361, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2315, 1361, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2316, 1362, 70, 'No comment.', 1, 'sent', '2014-07-12');
INSERT INTO `review` VALUES(2317, 1362, 47, '#IC to submit a method statement and ITP for SAPMT/ PID approval before any work can be executed.\r\n#The material applications and timing to be as per manufatures technical data recommendation\r\n#Since all the building are single storey we recommend the use of Spatter Dash SB which has more compressive strength after 28 days and its application thickness of 4-6 mm and aggregate size of 2.8 mm max.\r\n#Plaster shall not be retempered as per SAES-M-100, Sudi Aramco Building Code ;Chapter 25- plaster; Sec.2511.1\r\n#Water to be used must have a TDS of around 10,000ppm or exposure 2 or 3 as defined on SAES-Q-001 table 1; IC to maintain the mixing temperature as per manufactures recommendations', 2, 'sent', '2014-07-13');
INSERT INTO `review` VALUES(2318, 1363, 47, '#IC to submit a method statement and ITP for SAPMT/ PID approval before any work can be executed.\r\n#IC to submit all concrete masonry unit block sample to SAPMT/ PID for visual inspection and approval\r\n#The compressive strength of mortar shall not be less than 12.4 Mpa(1800 psi) and mortar shall not be retempered as per SAES-M-100, Chapter 21- Masonry; Sec.2103.8\r\n#Grout shall not be retempered as per SAES-M-100, Chapter 21- Masonry; Sec.2103.12\r\n#Water to be used must have a TDS of around 10,000ppm or exposure 2 or 3 as defined on SAES-Q-001 table 1; IC to maintain the mixing temperature as per manufactures recommendations\r\n#Correct the typing error or confirm the casting date on ''Al Hoty Test Report Ref: RD-00110/2 dated 29 January 2013 for vetonit masonry mortar.\r\n', 2, 'sent', '2014-07-13');
INSERT INTO `review` VALUES(2319, 1363, 70, '•The grout filler C GP compressive strength must exceed the CMU compressive strength and not less than 2000 psi as per the vendor data sheet. Provide the compressive strength of all  CMU type which contractor will use them in this project.\r\n•The contractor should follow the vendor recommendations.\r\n•The Test reports which are attached in this submittal are one year old. They should submit new test of these production.\r\n', 3, 'sent', '2014-07-12');
INSERT INTO `review` VALUES(2320, 1363, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2321, 1374, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2322, 1371, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2323, 1371, 47, '#Rabya has been involved in a number of completed Aramco projects however the submittal received is incomplete;\r\n- This submittal should include a detailed organizational chart with all the list of resources, equipments and  manpower to be involved on this project;\r\n- a list of all the proposed personnel by name, qualification and CV''s to be included for Aramco''s approval\r\n- a detailed schedule from IFC design, construction and commissioning to be included as well in the submittal', 3, 'sent', '2014-07-13');
INSERT INTO `review` VALUES(2324, 1371, 70, 'Rabya has a shortage of manpower and there quality not high. I prefer if there is another subcontractor ', 4, 'sent', '2014-07-13');
INSERT INTO `review` VALUES(2325, 1372, 47, '#IC to submit a readable color copies on all their submittal for a proper review.\r\n#The initial IFC submittal was in November 2013 and IC is still submitting the IFC drawings 8 months later without the detailed SHOP drawing; \r\n#IC is urged to submit a detailed IFC with the bending schedule since the work is already in progress ', 3, 'sent', '2014-07-13');
INSERT INTO `review` VALUES(2326, 1372, 70, '•Provide detail section at the beginning of the ramp.\r\n•No positive change order.\r\n•The blast resistance building shall be designed as per SAES-M-009\r\n•Provide blow up details for sleeves with necessary rebar such as roof drain sleeve, Electrical conduits …etc.\r\n•Concrete cover should be 75 mm for concrete expose to earth and to weather as per general note VA-846497-001.\r\n•The roof slab of machine gun room is setting on cantilever beams; we need design confirmation from SCEC that the design of this portion is safe.\r\n', 2, 'sent', '2014-07-14');
INSERT INTO `review` VALUES(2327, 1373, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2328, 1373, 70, 'No comment.', 1, 'sent', '2014-07-16');
INSERT INTO `review` VALUES(2333, 1370, 23, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2336, 1370, 10, 'ex', 1, 'sent', '2014-09-11');
INSERT INTO `review` VALUES(2337, 1370, 44, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2338, 220, 41, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2339, 220, 10, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2340, 220, 44, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2341, 220, 23, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2342, 1376, 11, 'Sir,\r\n\r\nTo be fair with contractor, due to verbal agreement with Fahad to expedite the delivery of this long lead item, we can received the material, the letter says that ICC/ESE take the responsibility during the storing and shipping to the site.\r\n\r\nDocumentation for P.O and shipping documents are valid we can settle few percentage for their invoice.\r\n\r\n', 2, 'sent', '2014-07-19');
INSERT INTO `review` VALUES(2343, 1376, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2344, 1376, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2345, 1376, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2346, 1377, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2347, 1379, 49, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2348, 1380, 11, 'Sir,\r\n\r\nNo more further comment.', 2, 'sent', '2014-07-15');
INSERT INTO `review` VALUES(2349, 1378, 70, 'The coordination is IC responsibility as per the project scope of work. SAPMT (Mr. Mark) following up with IC to complete the excavation and preparing the area for Saudi Electrical Company to lay down their new cables but IC shows slow progress. IC delay many activities without any reasons. SAPMT is requesting IC to stop delay the activities as well as the SEC requirement.', 4, 'sent', '2014-07-16');
INSERT INTO `review` VALUES(2350, 1378, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2351, 1378, 45, 'The claim is valid from the point of view of Safety!\r\n\r\n1. Removal of the hazard as suggested during past meetings is a long overdue issue.\r\n2. Implement the recommendation so the Sub-Contractor can proceed.', 0, 'sent', '2014-07-16');
INSERT INTO `review` VALUES(2352, 1381, 30, 'approved with no comment', 2, 'sent', '2014-07-16');
INSERT INTO `review` VALUES(2353, 1381, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2354, 1382, 11, 'The submittal is only for information, rev. 0F2 has no big impact only few adjustment of transformer and switchrack position due to KAM access road reallignment.', 1, 'sent', '2014-07-19');
INSERT INTO `review` VALUES(2355, 1383, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2356, 1384, 70, 'no comment.', 1, 'sent', '2014-07-21');
INSERT INTO `review` VALUES(2357, 1384, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2358, 1385, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2359, 1386, 70, '•The base coarse and sub base should continue under the median as per IFB drawing KA-714497-001-C or SAPMT will call for negative change order with confirmation from SCEC the design is save to transfer the road load.\r\n•If SAPMT accepted that the median will be general fill then the slope of base coarse and sub base should by 1:3 as per the IFB drawing KA-714497-001-C on the other hand, the subcontractor will consume more time to do this proposal that mean more of wasting time.\r\n•The curb shape in this submittal is not like in the IFB. The contractor saving around 300 cubic meters. This negative change order.\r\n', 3, 'sent', '2014-07-21');
INSERT INTO `review` VALUES(2360, 1387, 72, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2361, 1387, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2362, 1387, 70, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2363, 1387, 30, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2364, 1387, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2365, 1388, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2366, 1388, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2367, 1389, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2368, 1389, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2369, 1389, 30, 'All FOCs must be undergone reel testing once delivered to site. ', 2, 'sent', '2014-07-22');
INSERT INTO `review` VALUES(2370, 1396, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2371, 1391, 58, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2372, 1391, 59, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2373, 1392, 20, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2374, 1393, 11, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2375, 1393, 30, 'No comment.Please have Hanipah give his comments.', 2, 'sent', '2014-07-22');
INSERT INTO `review` VALUES(2376, 1394, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2377, 1395, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2378, 1397, 30, 'Approved as long as it meet project requirements.', 2, 'sent', '2014-08-09');
INSERT INTO `review` VALUES(2379, 1398, 52, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2380, 1398, 32, '', 0, 'Pending', '');
INSERT INTO `review` VALUES(2381, 1399, 45, '1. The Corrective Action Report is in order. The Contractor is duty-bound to effect the corrective or prevetive actions to the hazards, aspects and/or threats identified in the operations as per SBOIs, Focus and Major inspections as to the the schedule committed. This record shall be maintained in the record of Contractor compliance.\r\n2. Future SHE issues of this nature shall require the same action from the Contractor and shall be maintained on file ready for verification anytime PMOD requires it.\r\n3. Except for the regulatory and other SA Standard compliances such as Opearators certifications, all the others issues in the report has been verified and showed compliance.\r\n4. This inputs shall be entered into the PSI system c/o Safety Advisor.', 0, 'sent', '2014-08-08');
INSERT INTO `review` VALUES(2382, 1400, 45, '1. The Corrective Action Report is in order. The Contractor is duty-bound to effect the corrective or prevetive actions  to the hazards, aspects and/or threats identified in the operations as per SBOIs, Focus and Major inspections as to the the schedule committed. This record shall be maintained in the record of Contractor compliance.\r\n2. Future SHE issues of this nature shall require the same action from the Contractor and shall be maintained on file ready for verification anytime PMOD requires it.\r\n3. Except for the regulatory and other SA Standard compliances such as Opearators certifications, all the others issues in the report has been verified and showed compliance.', 0, 'sent', '2014-08-08');
