1.	Ensure that the single and double arm bracket of the lighting pole will suit for the lighting fixture.
2.	Submit lighting pole foundation in compliance with SAES-P-123, paragraph 4.1.14.4 which states that “Poles and foundations shall be designed to withstand wind loading due to a basic wind speed value stated in SAES-A-112 and a gust factor of 1.3 acting on the effective projected area of the pole, bracket, and lighting fixtureâ€.
3.	Accessories for the lighting pole (fuse/terminal box with split bolt grounding connector as per IFC) should be included in the submittal.
4.	Include the tapping point handhole connection details which include the terminal blocks, fuses and nonconductive metallic plate.
