SAPMT has reviewed the subject submittal dated November 25, 2014 and has no objection with the following comments:
1.	All drawings/ designs shall be concurred by the project designer.
2.	Install feeder breakers in LV Panel according to feeder assignment of IFC drawing. Take note that Package Substations are not supplying power to street lighting only.
3.	Ensure to follow standard frequency of 60 Hz. The SFRMU shows 50 Hz, correct it, and use only 60 Hz.
4.	Consider the sizing of fuses in the RMU according to Vendor recommendations.
5.	Apply standard rating for Circuit Breakers such as the following:
a.	Instead of 1050 AT, use 1200 Ampere Trip AT with 1200 Ampere Frame AF.
b.	Instead of 700 AT, use 800 AT with 800 AF.
c.	Instead of 200 AT, use 250 AT with 250 AF.
d.	Instead of 100 AT, use 125 AT with 150 AF.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
