SAPMT has reviewed the subject submittal dated April 02, 2014 and has the following comments:

1.	PVC conduits and fittings shall comply with SAES P-104 para. 8.1.1 and 8.1.2.
2.	EGA Honeywell is not mentioned in the recommended manufacturers list provided in construction specification document section 16110 page 2 of 10. IC is urged to consult the designer and acquire concurrence.
3.	Consider segregating the submittals for PVC Conduits and Fittings, Wire way and Back boxes to avoid confusion.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
