•The blast resistance building shall be designed as per SAES-M-009
•The house size is more than the IFB, if no prior approval from SAPMT then No positive change order.
•Contractor shall submit the structural shop drawing as usual in separate submittal.
•Provide blow up details for sleeves with necessary rebar such as roof drain sleeve, Electrical conduits …etc.
•There is a CMU wall in front of the Guard House door (Marine Road) VA-Q-847118 – 001 – 0F1- Section C – C, as per Architectural drawing VA-847116-001-0F2 no wall at all. Kindly confirmation from SCEC.
•Concrete cover should be 75 mm for concrete expose to earth and to weather as per general note VA-846497-001.
•Regarding Marine Guard house, as per Architectural drawing VA-847116-001-0F2 the stair case has three way to enter to the building but in this submittal VA-847118-001-0F1 show one way. Kindly confirmation from SCEC.
•Provide cross section of stair case flight for marine guard house.
