SAPMT has reviewed the subject submittal dated May 18, 2015 and has no objection with the following comments:

1.	Underground LV cable shall be installed as per SAES-P-104 para 10 and in accordance with standard drawing AD-036874.
2.	Ensure LV cable will not obstruct any other underground utilities during installation.
3.	In the legend, remove the description for lighting type “similar with SLC-GEPS /5â€.
4.	Reflect the bridge in drawing at gate # 1 and ensure that the 5m pole will not be obstructed by the bridge.
5.	Ensure that SSD pole to pole clearance shall be 20m as per HCIS requirement.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686
