1. For MoM item number 15, 16 & 17, The power requirements for the vehicle x-ray machine was not included in the 50% and 90% detail design. Contractor must resolve the voltage conflict from 230 volts line to neutral into 230 volts line to line.
2. Vehicle x-ray contractor must share the power requirements of their machine not only the voltage requirement but also the power rating and amperage.
3. For MoM item number 22, Contractor must ensure that sharing the UPS system for both UVIS and Vehicle X-ray machine is sufficient and calculation must be provided.
4. In any case that the permanent power is not yet available for the vehicle x-ray, it is the responsibility of the contractor to ensure that temporary power is available to operate the vehicle x-ray for testing and commissioning.
5. The human interface machine shall be installed as per manufacturer recommendation.
6. All electrical and civil works, must be reviewed comprehensively by SCEC designer to ensure that the vehicle x-ray machine installation requirements will be met.