Contractor (IC) proposed Switch Socket Outlet based on KAUST Technical Bulletin issued on Sept 12, 2012 in regards to the “implementation of SASO 2203 for 220V Plugs and Socket outlets which is UK 3-Pin and in compliance with BS-1363â€. However the IFC VA-846899 Sht 001 and Construction Specification shows non UK pin which is to be red line or corrected as stated in KAUST Technical Bulletin. 