SAPMT has reviewed the subject submittal dated January 01, 2014 and has the following comments: 

1.	Ensure that the Security Access Control System (SACS) software to be used are the latest and will be compatible with KAUST SACS software. 
2.	Ensure that NEMA 4X enclosure will protect outdoor card readers.
3.	Ensure to provide IP-65 rating equipment such as card reader if installed outside building in compliance to PE-000071 Section 6.14.2.
4.	Ensure that the pole/stand of proximity reader is similar to the existing stand in KAUST.
5.	Provide Bar-lock processor enclosure.
6.	Provide the technical specification of power supply.
7.	Provide the technical submittal of AXIS server.
8.	Ensure that all major system components are included in the submittal.
9.	SACS shall include all related equipment and parts such as the access controller enclosure, magnetic locks, cameras, power supply and other required deliverables with reference to PE-000071 Section 3.4
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
