SAPMT has reviewed the subject submittal dated February 01, 2015 and has no objection with the following comments:

1.	The spikes should be sharper at the top ends to cause considerable damage to the intruder.
2.	The galvanizing shall be done according to SA standards and according to corrosive environment on site.
3.	The fasteners and their spacing shall be coordinated with precast subcontractor.
4.	A 15m long mockup to be installed for proponent inspection before February 08, 2015.
5.	Ensure there is no deviation from the preliminary designs provided in the IFB.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.

Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
