SAPMT has reviewed the subject submittal dated May 11, 2015 and has no objection with the following comments:

1.	Ensure the underground 13.8kV MV cable shall be installed as per SAES-P-104.
2.	Redundant Medium Voltage Feeders shall have a clearance of 1.8 meters as per SAES P-104 para. 14.5.
3.	Ensure that switch rack numbering is accurate.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.
