SAPMT has reviewed the subject submittal dated March 18, 2014 and has the following comments:
1.	IC is urged to include the calculation for sizing of the generator in the submittal.
2.	Ensure that the proposed Generator will run efficiently for at least 30 percent of its rating as confirmed by the designer SCEC in meeting held on February 09, 2104.
3.	The dimensions of the proposed Diesel Generator and its accessories shall conform to the size of the Generator Room according to the IFC drawing. Shop drawing is required to verify the set-up of the equipment, foundations, cable routes/trays, fuel lines, maintenance options showing the layout drawing and elevation of the Generator Room.
4.	Contractor is required to coordinate with the Switchgear manufacturer for the interconnection of control and protection that auto transfer scheme between both equipment complies with the IFC drawing Single Line Diagram and 13.8KV Relay One Line Diagram, VA-846512, Sht. 01 & 02 and VA-846925, Sht. 05 & 06 respectively
5.	After technical approval the contractor is required to submit Purchase Requisition Package (RP) and NMR documents for SAPMT review and approval as the equipment is under Inspection Level 2 with Pre-Inspection Meeting (PIM) prior to start of fabrication
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
