Reference to the revised IFC drawing VA-846512 sht 001 for KPSS main cable feeding Generator Building, the new tie connection will be in new SEC#2 substation. This changes is deviating with the BID package PA - 000087 sht 001 wherein the tie connection was identified to be in substation #4. 

With this modification, there is a huge quantity reduction for the MV cable routing in addition to the civil works such as excavation, trenching and back filling and construction duct banks.

This changes has a cost and time impact in favor to Saudi Aramco, and will be taken as a negative change order for IC
