SAPMT has reviewed the subject submittal dated August 17, 2014 and has the following comments:
1.	Ensure that all SONAR heads are monitored from JFCC Building control room and SHQ Building control room as per project requirements and scope of work.
2.	Ensure that New SONAR system is same as existing.
3.	Provide a separate power system for the new SONAR # 4 equipment in Shelter # 2 by providing an approved UPS system and back-up batteries.
4.	Since the new SONAR # 4 will use existing SONAR System servers and Alarm Management System, Provide a signed scope of work and quantities for all servers that will not be used, to process a negative change order.
5.	Consider providing shop drawings showing the equipment arrangements in Shelter # 2 cabinet rack, New UPS and related batteries and electrical single line diagram.
6.	Ensure full compliance with scope of work and approved Project Specifications and approved IFC drawings.
Should you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.
