SAPMT has reviewed the subject submittal dated 16 October 2014 and has the following comments:
1.	Attach approved MS and Purchase Requisition Package.
2.	Include leveling frame for detailed mounting of Switchgear base plate to Electrical Room flooring.
3.	Ensure that the protective relays and control devices are Saudi Aramco approved manufacturer and model number according to its ANSI function as listed in Appendix A of 16-SAMSS-504.
4.	Provide full catalog of all protective relays and controls and associated auxiliary relays in the NMR-602 submittal.
5.	Protective relays shall be set to final relay settings upon approval of ETAP and Relay Coordination Study by PDD during commissioning.
6.	Lifting devices, test cabinet, remote racking unit and portable manually operated ground and test device shall be included for Switchgear assembly as per 16-SAMSS-504.
Should you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.
