SAPMT has reviewed the subject submittal dated May 06, 2015 and has no objection with the following comments:

1.	Card Reader shall incorporate key pads to meet High Commission in Industrial Security (HCIS) para. 4.3.2.1 as minimum requirements.
2.	Biometric Card readers will be used for all vital doors as stated in project document PE-00002 para. 1.2.2.1.5.7. L.
3.	Controllers enclosures were not included in the submittal, however it shall be NEMA type 1 for Indoor and NEMA type 4X for outdoor as stated in SAES J-902 and SAES P-104.

IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.
