1. The attached reference standard SAES-O-123 is no longer applicable. Ensure the proposed crash barrier will comply with SAES-O-206 Paragraph 4.4.3.//2. Use 220 VAC power supply instead of 208 VAC //3. Dimensions and measurements shall be provided in the shape of a shop drawing according to IFC drawing VA-847162 007 to indicate the required minimum distance of the barriers to other security elements such as drop arms with reference to SAES-O-203, Paragraph 4.14//4. Provide more information, preferrably a 3D view, for dimensions and orientation of the remote control panel.