1. The proposed route of FOC cable is required due to the fact that IC has voluntarily chosen to build the KAM access road on a route which is different from IFB between ST 1850 to ST 3300, so that construction works in the sea water are avoided and timelines can be improved. While SAPMT has agreed to IC proposal of rerouting KAM road between ST 1850 to ST 3300, IC shall ensure that it is done with no cost and time impacts to the project.
2. Resubmit the re-routing plans by superimposing the proposed routing layout with new KAM access road/ corridor and King Abdullah Monument drawing plans. 
3. Provide the coordinates for corners and curves of the propose fiber optic cable layout and distances desired from the edge of the road. 
4. Ensure that the propose layout is coordinated with the existing underground FOC, and electrical cables running for King Abdullah Monument Project.
5. Show locations of markers/ posts.
6. Provide fold out details of manholes
7. Provide details and schematic diagram and splicing details of the proposed 24 core fiber cable to the existing IDAS cable. 
8. Provide plan and splicing details of the existing primary and redundant 96 core fiber cable of IDAS
9. Explain how existing optipeds and service manhole shall be removed
10. IC/SCEC to verify the coordinates and elevation of the FOC routing and make certain that it is outside the road shoulder and cover is provided according to the standrads.