a. Drawing IC-SD-846864-101-OF1 the section B-B of Footing 2 shows C2 while the Foundations plan shows C1 on F2. //b. The rebar details of detail - 1 (Footing F1) shows 8 bars in each direction while the correct number shall be 9 bars in each direction. //c. The rebar details of detail - 2 (Footing F2) shows 11 bars in each direction while the correct number shall be 14 bars in each direction. //d. The total numbers of bars in the rebar schedules are not correct such as total rebar of F1 is 108 instead of 64 …etc. //e. The exterior corner of two way slab needs additional reinforcement as per ACI 318-08 code section 13.3.6.//f. IC is urged to counter check shop drawings with the construction team, before submitting to avoid mistakes and rework. The names of engineers and drafters working on the shop drawings shall be mentioned on the drawings.