SAPMT has reviewed the subject submittal dated September 16, 2014 and has the following comments:
1.	Consider renaming steel box with back boxes.
2.	Ensure that back boxes are UL listed or with approved equal certification.
3.	EMT conduits shall not be embedded in concrete as per SAES-T-916.
4.	A 4â€ box cover is not acceptable; refer to minimum standard dimensions as per SAES-T-916.
Should you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.
