SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/14/0360 dated February 08, 2014 and has no objection with the following comments:
•	IC is urged to refer to SAPMT letter no. K&TPD/KRP&SFPD/SF/L-437/14 dated January 15, 2014 and provide a final mock-up for SAPMT and KAUST approval as mentioned in the said letter.
Should you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.
