SAPMT has reviewed the subject submittal dated October 25, 2014 and has no objection with the following comments:
1.	Cable glands shall meet the specified requirement of SAES P-104 para. 6.8, 6.9 and 6.14.
2.	Ensure that Cable Glands has provision for armored cables and for unarmored cables.
3.	It is the Contractors responsibility to ensure the correct sizing of cable glands.
4.	Terminal Lugs number of holes shall be determined using SAES P-104 para. 6.1.
5.	Ensure that terminal lugs are tinned copper and has Underwriters Laboratories "UL" markings.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
