1. The piping material is acceptable but the submittal is incomplete. 2. The subject of the submittal shall be more specific. Rename the description of the submittal with "PVC CONDUITS NEMA TYPE DB and EB for ELECTRICAL AND COMMUNICATION conduits and duct banks". 3. Include in the submittal the proposed conduit spacers and conduit fittings. 4. Ensure that the PVC conduits to be used will comply with SAES P-104, IFC drawings and Project Specification.