SAPMT has reviewed the subject submittal dated June 01, 2014 and has no objection with the following comments:
1.	WESCOSA has limitations to use only Cutler Hammer Model breakers under license from Cutler Hammer.
2.	Submit requisition package at the earliest ande use special SA-175 form as per the inspection test plan (ITP) produced by WESCOSA for these Package substations.
3.	Ensure that the fuse rating of Ring Main Unit (RMU) for tee-off circuit is rated according to the rating of transformers of different sizes as indicated in the Single Line Diagrams.
4.	The enclosure of the Package shall be adequately protected against corrosion and painted according to relevant clauses of SEC standard 01-SDMS-01.
5.	Provide Datasheet for each Package Substation concurred by the designer and manufacturer.
6.	LV Panel Board shall be according to the Panel Schedule drawings of the project.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
