SAPMT has reviewed your subject submittal dated May 11, 2013 and has the following comments.
1.	CCTV – Correct and Re-submit
a)	Submit in a separate Material Submittal (MS) the SACS and Parking CCTV cameras.
b)	Specify the proposed model for Fixed and PTZ cameras in the technical data sheets.
c)	Ensure that the camera voltage rating is compatible with the source voltage.
d)	Ensure that the system requirements and deliverables will meet Functional Specification Document (FSD) PE-000072..
e)	Shall comply with the issued for construction drawings and Saudi Aramco Standards SAES T-555
2.	Video Management Software – Correct and Re-submit
a)	Include the technical specification and related hardware’s and software’s for Alarm Management System
b)	Ensure that the system requirements and deliverables will meet Functional Specification Document (FSD) PE-000072.
c)	Shall comply with the issued for construction drawings and Saudi Aramco Standards
3.	Microwave Intrusion Detection System (MIDS)- Approved as Noted
a)	Used the proposed CIAS for the IDAS MIDS.
b)	Ensure that the system requirements and deliverables will meet Functional Specification Document (FSD) PE-000072.
c)	Shall comply with the issued for construction drawing and Saudi Aramco Standards
4.	Led lights- Correct and Re-submit
a)	Provide the illumination levels for AXIS T90A illuminators and Raymax 100.
b)	Clarify if the LED lights will replace all lighting pole with HPS lighting bulbs.
Should you have any questions, please contact Fahad A, Al Balawi, Senior Project Engineer at Tel No. +966 2 422-4393.
