1. The attached as-built drawing  VA-207593 is outdated. Update the drawing as per site condition.
2. The proposed new manhole and relocated manhole is not acceptable. This will initiate down time on exsiting IDAS System and manhole construction will take a lot of time. Propose optipeds instead in replacement of manholes if applicable.
3. Propose a vacant fiber cores on existing IDAS 96 core FOC for reservation.
4. contractor to ensure the IDAS on the relocated fence is running smoothly and satisifed KAUST operation prior to disabling the existing IDAS.