SAPMT has reviewed your subject submittal dated May 12, 2013 and has the following comments.

1)	Security Access Control System (SACS) – Correct & Re-submit
•	Submit SACS submittal in a separate Material Submittal (MS).
•	Servers for storage and Snapshot cameras must be included in SACS submittal.
•	Video Server, and related Bar Lock Processor accessories, Card reader enclosures must be included in the SACS submittal.
•	Used proposed proximity reader stand in drawing HID-2000 3d for entry and exit lanes
•	Ensure that the system requirements and deliverables will meet construction document PE-000071.
•	Ensure that the proposed software is matching with the existing SACS software used in KAUST.
•	Shall comply with the issued for construction drawing and Saudi Aramco Standards SAES 0-205.
2)	Full length Turnstile - Correct & Re-submit
•	Submit Turnstile submittal in a separate Material Submittal (MS).
•	Ensure that the proposed turnstile is the same with the existing.
•	Shall comply with the issued for construction drawing and project construction specifications.
3)	Operator Console - Correct & Re-submit
•	Submit Operator Console submittal in a separate Material Submittal (MS).
•	Ensure that the number of servers to be installed inside the console cabinet can accommodate all servers.
•	Ensure that the power outlet will match with the servers and computer plugs without using adapters.
•	Shall comply with the issued for construction drawing and project construction specifications.
4)	Video wall screens (LCD)- Correct & Re-submit
•	Submit Video wall with model SAMSUNG UD55C in a separate Material Submittal (MS).
•	Ensure that the video wall has a ultra-narrow bezels.
•	Shall comply with the issued for construction drawing and project construction specifications.
Should you have any questions, please contact Fahad A, Al Balawi, Senior Project Engineer at Tel No. +966 2 422-4393.
