SAPMT has reviewed the subject submittal dated June 26, 2014 and has rejected with the following comments:
1.	Sanitary drain, waste and vent pipes for buildings shall be ASTM D 2665 with line class 80PV0D1 as per SAES-L-105.
2.	Indicate clearly which pipe and size shall be used for which application/ location.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.
