SAPMT has reviewed the subject submittal dated May 31, 2014 and has no objection with the following comments:
1.	Contractor shall identify the enclosure rating of the proposed panel boards.
2.	Contractor shall identify the cable entry (Top or Bottom) for each of the panel boards.
3.	Provide vendor shop drawing for each of the panel board showing Main Circuit Breakers and its branches.
4.	Dry type transformer enclosure shall comply with SAES P-104 para. 7.
5.	Provide vendor shop drawing for dry type transformer to verify the ventilation details.
6.	Submit purchase requisition for LV panel and Lighting Control Panel.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
