SAPMT has reviewed the subject submittal dated May 12, 2014 and has no objection with the following comments:
•	The work can start in case the following details are incorporated during execution;
a.	Confirm if the Note 1 in sheet 601 shall refer to LV or MV.
b.	Confirm if soil improvement is necessary as mentioned in Note 4.
c.	Consider using mm or m, i.e. same system of units on the drawing.
d.	Show the length of concrete for the duct bank and concrete end details. i.e bell ends etc.
e.	Used PVC solvent cement in connecting the conduits as per SAES P-104 10.5.5 2.
f.	The top layer of the concrete shall be mixed with red dye as per Saudi Aramco standards.
g.	Consider reducing the length of hooks.
h.	Consider revising the shop drawings.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
