SAPMT has reviewed the subject submittal dated May 27, 2014 and has no objection with the following comments:
1.	Use AVK high pressure wet barrel hydrant series-2490 in compliance with SAES B-017 para. 7.2.1, Hydrant selection & Design; states “hydrant should have three connections; One-5â€ stores connection and 2½â€ fire hose compatible threads.
2.	Submit shop drawing for fire hydrant. Show piping components, thrust block support and direct buried valve. (refer to IFC drawing VA-846559-001).
3.	Fire hydrant shall be manufactured by Saudi Valves Manufacturing Company (30000959). 
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
