SAPMT has reviewed the subject letter dated June 08, 2015 and has been rejected with the following comments:

1.	This material has inspection level zero (0).
2.	It should be procured through an approved manufacturer.
3.	The panel board name tag shall be SHELTER # 2 POWER PANEL.
4.	Panel Enclosure shall contain stainless steel drain and breather to meet the requirement of SAES P-104.
5.	Panel Enclosure access door shall be key type.
6.	Provide braided bonding jumper from the access door to the grounding bar.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.

Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
