
SAPMT has reviewed your subject submittal dated March 01, 2015 and has no objection with the following comments;

1.	Provide the installation detail of the aerial rod and the down conductor.
2.	Locate the tie in point of the lightning system into the existing roof lightning system.
3.	500 mm rod lenght is too short for equipment coverage zone protection, provide technical justification if necessary, or Use 1000 mm aerial rod to ensure good coverage.
4.	Ensure that down conductor will match with the saddle.
