SAPMT has reviewed the subject submittal dated March 30, 2014 and has no objection with the following comments:
1.	Fence should be grounded as per SAES-P-III.
2.	Provide concrete footings according to SAES-M-5.2.
3.	The fencing fabric mesh, length of rolls, woven design and splicing shall follow HCIS standards.
4.	Refer to attached Dwg. GI-AS-62037 and AB-036677-001-02 for more details.
5.	When fully constructed the barbed wire, tension wire, fabric, and truss rods shall be taut.
6.	Contractor should submit the shop drawing of concrete footing and beam.
7.	It is contractor’s responsibility to follow all related HCIS and Aramco standards for materials and installation.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
