SAPMT has reviewed the subject submittal dated October 21, 2014 and has the following comments:
1.	Use correct 9Com# 6000000744 for Cable Trays (Aluminum or Steel).
2.	Use correct 9Com# 6000014116 for Cable Tray accessories.
3.	Cable tray for electrical works shall be copper free aluminum to meet Saudi Aramco Standard SAES P-104 para. 9.1.
4.	Ensure electrical cable tray full compliance with Metal Cable Tray System stated in NEMA VE-1.
5.	The Summary list and specifications are for Cable Tray System only. Cable Ladders/Cable Runways are not listed. Provide specification no. PA000070004 and attach data sheets which are from Chatsworth Manufacturer as per the Scope of work for ladders.
6.	The proposed Supplier and Manufacturer Abahsain Cope is not approved to supply Chatsworth Products.
7.	Consider submitting products separately according to the discipline and activity.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
