1. Material offered is from Saudi EGA but the name of manufacturer on front cover is EGA Honey well. Justify the relationship between the two.
2. EGA PVC conduit does not comply with SAES P-104. The following types of Electrical and Communication conduits for concrete and direct buried are acceptable;
a. PVC Conduit TYPE DB - 120 (Direct Buried) 
b. PVC Conduit TYPE EB - 35 (Concrete Encasement) 
c. PVC Conduit TYPE EPC - 40 (Direct Buried and Concrete Encasement) 
3. Correct Vendor ID for Al Abdul Karim Holding Dammam is 10011901
4. Consult with PMT for more clarification before resubmittal.