SAPMT has reviewed the subject submittal dated October 16, 2014 and has the following comments:
1.	Provide complete architectural and structural drawings concurred by the Genset vendor/ switchgear vendor and project designer to ensure that all items including batteries and tanks etc. are also taken into account.
2.	The concrete cover should be as mentioned in the general drawing VA-846497.
3.	Provide reinforcement for sleeves.
4.	Provide the hook length according to VA-846498 with min. 388mm for db=20 mm and 310mm for db=16 mm.
Should you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.
