SAPMT has reviewed the subject submittal dated April 14, 2014 and has the following comments:

1.	Provide the purpose or location of materials being proposed in the subject.
2.	Provide correct 9Com 600000573 with correct description such as (Bolt Assembly/ Anchor etc.)
3.	It shall be inspection level 1 and procured through an approved vendor/ manufacturer.
4.	Use galvanized steel bolt high strength ASTM-325, nuts & washers. Refer to SAES Q-012, paragraph 5.14 Connection Material and Construction Specifications Section-01000 paragraph 15.0D Bolts, Anchor bolts & Nuts.
5.	The 550MM length shall be used and zinc coating shall be done after threading.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
