1. Ensure that all MV cable running under roads were protected by Ductbanks.
2. Ductbanks for MV cable shall SAES P-104.
3. Ensure that MV cable clearance with other utilities are within the minimum requirements of 300 mm as stipulated in Saudi Aramco standards.
4. Provide detail shop drawing for all underground electrical and non-electrical utilities that will pass through box culverts 3 & 4 and Wadi Khulais Culvert.