SAPMT has reviewed the subject submittal dated December 04, 2014 and has the following comments:

1.	ICC-IC-T-101: Add item no. A2. Verify that storage area of the CCTV equipments and accessories is in accordance with detailed instructions issued by the manufacturer; all applicable specifications and Saudi Aramco standards (Refer to Schedule-Q, Att. IV, Sec. 6).
2.	ICC-IC-T-101: Add item no. A3. Verify that the storage area is well secure and provided with environments control for the protection of the equipment’s (Refer to Schedule-Q, Att. IV, Sec.6).
3.	ICC-IC-T-101: Add item no. A4. Verify that the storage area provided is not located near water sources nor flammable materials (Refer to Schedule-Q, Att. IV, Sec.6).
4.	ICC-IC-T-102: Add item no. A4. Verify received CCTV Camera power supply is 220V AC (Input), 24V AC (Output), 60 Hz in compliance with the approved Project Specification & Scope of Work.
5.	ICC-IC-T-102: Add item no. A5. Verify that received CCTV Camera has a high finish tamper resistant camera enclosure and shall have an adjustable swivel/tilt head in compliance with approved Project Specification & Scope of Work.
6.	ICC-IC-T-102: Add item no. A6. Verify that the CCTV camera shall incorporate a color CCD Camera, 8 X or 10 X zoom lens, an integral receiver/ driver unit, and an integral pan/ tilt drive in to a low profile 250mm diameter (minimum) dome. In compliance with the approved Project Specification & Scope of Work.
7.	Item 2.6/3.3/3.8 for inspection responsibility assignment shall be deleted and refer it to SATIP-P-104-01.
8.	Add one (1) item for pre-commissioning of cables/ wires and refer it to SATIP-P-104-01 and SATIP-P-111-01.
9.	All testing checklists should be as per the Manufacturer’s Testing Procedure.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.

Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
