1. There are differences and conflicts observed between differet drawings which can not be approved for construction. IC is urged to consult with SAPMT to clear such conflicts.
2. Te buildings shall be designed according to SAES-M-009.
3. At this stage of project all drawings shall be complete in all respects showing all diciplines and shall be ready for construction without the need for shop drawings.
4. Concrete covers shall be 75 mm for concrete exposed to earth and to weather as per general note VA-846497-001.
5. Justify why the Architectural drawing VA-847116-001-0F2 for Marine Guard house, the staircase has three ways to enter the building but this submittal VA-847118-001-0F1 shows one way only. Provide cross section of stair case flight for marine guard house.
6. Sleeve details shall be zoomed in with necessary rebars.