SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/14/0432 dated March 04, 2014 and has the following comments:
1.	Submit shop drawings of the single line diagram that incorporates all the decisions made in the meetings dated February 09, 2014 and March 10, 2014.
2.	The Switchgear BUS is considered as a single ended bus with only one spare, one space and one tie breaker. This decision is made due to the reason that a capable energy generator shall be used instead of a secondary power source from Saudi Electric Company (SEC).
3.	Shop drawings shall be concurred by the designer.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
