SAPMT has reviewed the subject submittal dated March 26, 2014 and has no objection with the following comments:
1.	Ensure that battery back-up time meets the requirement of 4 hours as per 4.3.5 of SEC 07 HCIS.
2.	Ensure that the VRLA type battery has the service life greater than 10 years as per SAES P-103.
3.	Provide Data Schedule 1 & 2 for UPS and Battery Unit duly accomplished by the designer and manufacturer respectively to verify full compliance as per project specification and 17-SAMSS-516.
4.	Provide shop drawing submittal showing the layout of the UPS unit and batteries in the UPS Bldg. and JFCC UPS / Battery Room.
5.	This submittal includes 80KVA UPS unit which is inspect-able item as per 17-SAMSS-516, submit Purchase Requisition Package (RP) and NMR documents for SAPMT and VID review and approval including Pre-Inspection Meeting (PIM) prior to fabrication of the unit.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
