SAPMT has reviewed the subject submittal dated October 26, 2014 and has the following comments:
1.	Fire Extinguishers shall be supplied by approved Vendors and shall be UL or FM Listed (not indicated in the Catalogue).
2.	Provide a package with approved drawings which show the Type and locations of Fire Extinguisher approved for the facility. Final Approval will be subject to the consensus of Saudi Aramco Fire Protection Department.
3.	Provide details of the mounting accessories as required per SAES-B-019.
4.	Saudi Factory for Fire Equipment is an Aramco approved vendor and IC shall start procurement processes while other details are prepared.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
