SAPMT has reviewed the subject submittal dated September 11, 2014 and has no objection with the following comments:
1.	The samples for light poles and luminaires for KAM access road are acceptable provided all comments sent via emails are incorporated.
2.	The specifications for light poles for IDAS, patrol road and parking are acceptable provided the samples are submitted for final approval.
3.	The galvanizing process shall comply with ASTM standards and coatings shall be done by Saudi Aramco approved vendors.
4.	Ensure that all approved lighting fixtures and associated fittings are compatible with the poles.
5.	Ensure specifications are as per document VE846472, Section 2.02.
6.	Ensure that lighting pole for IDAS and Patrol road lighting meet the HCIS requirements SEC-04 Para 4.6.2.3.
7.	Fuse box and terminal blocks shall be heavy duty type with UL or IEC markings.
8.	Ensure compliance with SAES-P-123.
Should you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.
