
SAMPT has reviewed the subject submittal dated April 01, 2015, and has no objection with following comment;
1.	Provide the sample of doors face metal as per VE 846472 section 1.07-D. 
2.	Use correct 9Com# 6000008995 with correct description of material as “Metallic Doors, Building, and Fire Ratedâ€. 9Com#6000001074 as mentioned in Material submittal is depleted and no more in use.
3.	Submit applicable SA-175-120400 with Requisition Package.
4.	Mention and attach First page of all the applicable standards of 9Com# 6000008995 in Requisition Package. Applicable Standards are 2006,AWS D1.1 and AWSD1.3. Also mention and attach First page of SAEP-302 in Requisition package.
5.	Doors shall be certified to UL10C for Fire Rating and UL1784 for smoke and draft control.
6.	IC shall ensure that all doors, frames and accessories are according to the door schedule mentioned in the IFC drawings and meet SA standards.
