SAMPT has reviewed the subject submittal dated April 01, 2015 and has no objection with following comment;

1.	Contractor shall mention and submit First page all the applicable Standards as part of Requisition Package after approval of this Material submittal, particularly 34-SAMSS-820 and SAEP-302.
2.	Contractor to ensure the proposed lighting contactor is magnetic type and complies with NEMA ICS2 as per VE-846472 sheet 05 off 07. 
3.	Ensure the rating and number of main poles for lighting contactor are suitable for intended application. 
4.	List the quantity required. 
5.	Lighting contractor for indoor/outdoor application shall meet the requirements as specified in SAES-P-100.
