SAPMT has reviewed the subject submittal (MS-0004) and advices IC to resubmit due to the following comments
1.	IC shall submit missing items which are part of SACS system deliverables as per FSD document, PE 000071 section 4.4.3, section 5.1, section 5.2.5 /5.2.9 such as Badging Station, Operator workstation, Fingerprint System and door control accessories.
2.	Ensure that Reader interface shall be supplied with internal DC battery backup for minimum 8 hour including power to energize door lock as per FSD document PE 000071 section 5.2.3.
3.	IC is urged  to provide techncial data for all remaining materials stated in IFC and/ or project specifications.

