SAMPT has reviewed the subject submittal dated April 23, 2015 and has no objection with following comments;

1.	Provide the Conduit for communication cable to TER room.
2.	Location of FDAS sensor shall be away from A/C indoor unit.
3.	Fire Alarm Drawings shall be stamped by approved Fire Engineer.
4.	Work may proceed under the supervision of IC MEP engineers and any conflicts on site may be corrected with red lines on drawings.
5.	It is IC responsibility to ensure that all required cables, conduits, pipes, panels, appliances, equipments, furniture, fixtures, fasteners and fittings in buildings are installed without any conflicts or obstacles according to SA standards.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
