1. Provide the CV/resume of the personnels that will be relocating the IDAS.
2. The submitted method of statement needs to be signed by the QA manager and not by QC manager.
3. Downtime for IDAS relocation was not included.
4. Include the breakdown and quantity of PTZ, Fixed, Poles and FEC that will relocated.
5. Since it was already highlighted that existing FOC cable cannot be removed, ICC/ESE to highlight the proposal to route new FOC cables.
6. ICC/ESE must nominate interface coordinator to start accumulating the required documents to KAUST IDAS O&M.
7. This method of statement does not mention any single word for the existing lights and its panelboards. Provide the plan for this lighting system for this is part of relocation.
8. Provide detail sequence of events from removal of IDAS to storage handling and preservation, and vice versa from storage to erection.
