SAPMT has reviewed the subject submittal dated May 18, 2015 and has no objection with the following comments:

1.	Ensure to have safety and quality personal available during the splicing of MV cable.
2.	Ensure that all the MV Cable splicing tools shall have calibration certificates.
3.	Ensure correct cables shall be identified and marked prior to splicing of the cables.
4.	Compression type connectors shall be used for splicing of MV cable as per SAES-P-104 para 6.0.
5.	Aramco approved splicing kit shall be used for splicing of MV cables.
6.	Ensure Vendor installation manual shall be available on site during splicing.
7.	MV cable splicing schedule shall be submitted to ARAMCO at least one week prior to start of activity.
8.	Splicing of cable shall be avoided at the bending of the cable.
9.	Ensure that qualified MV Cable splicers shall conduct splicing.
10.	Splicer shall obtain a valid Saudi Aramco Job Clearance Card.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.
