SAPMT has reviewed the subject submittal dated July 10, 2014 and has the following comments:
1.	Provide readable colored copies of the drawings.
2.	At this stage of the project, all new drawings shall be submitted complete without the need of any shop drawings.
3.	Provide a detailed section for the beginning of the ramp.
4.	The blast resistance building shall be designed as per SAES-M-009.
5.	Provide blow up details for sleeves with necessary rebar such as roof drain sleeve, Electrical conduits …etc.
6.	Concrete cover should be 75mm for concrete expose to earth and to weather as per general note VA-846497-001.
7.	The roof slab of machine gun room is setting on cantilever beams; we need design details/ confirmation from SCEC to see that the design of this portion is safe.
8.	Any design works which deviate from the scope of work or might trigger a claim shall be sent to SAPMT for prior approval, before incorporating in to construction drawings.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.
