SAPMT has reviewed the subject submittal dated November 02, 2013 and has no objection as noted:
1.	It is contractor’s responsibility to ensure full compliance of Saudi Aramco standards and specifications.
2.	Separate method statement shall be submitted on location basis for SAPMT approval.
Should you have any questions, please contract Fahad A. Al-Balawi, Sr. Project Engineer on Tel. No. +966 12 422 4393.
