SAPMT has reviewed the subject submittal dated May 26, 2015 and has no objection with the following comments:

1.	MEP IFC drawings, submittals and shop drawings shall also be reviewed and signed by ICC MEP Manager.
2.	This approval is only for the materials (only for double flanged fittings and not for FW/PW tie-in).
3.	Shop drawings shall be submitted separately with tie-in procedures.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
