SAPMT has reviewed the subject submittal dated May 26, 2014 and has the following comments:
1.	Quantities indicated under the Bill of quantities are all wrong. Re-verify the quantities and ensure all requirements shall be provided and installed in this project.
2.	The proposed manhole frame and cover is not acceptable since it conflicts to SAES-T-911 requirements.
3.	All manholes inside accessories shall be non-corrosive, hot dipped galvanized and ensure all have specifications and dimensions in compliance to SAES-T-911.
4.	Specification of fiber marker post is included in the attachment; please clarify since it is not included in the Bill of Quantities.
5.	Use correct 9com # 6000000682 for Manhole. 9com # 6000000681 is depleted and no more used in Saudi Aramco system.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
