1.	For Material Receiving, Installation and Pre-Commissioning of LV Power Cable; for column “Quality Procedure & Recordsâ€ change to “See Remarksâ€. Add in remarks column of ITP to “Refer to SATIP-P-104-01 and SATIP-P-111-01â€.
2.	ITP does not contain any installation procedure of Card Access Reader, Push Button and CCTV Camera.
3.	Include installation checklist for the SACS server and SACS panel.
4.	Commissioning checklist and the cause and effect matrix sequence has to be included in the ITP.
5.	Pre-commissioning and commissioning is a hold point to Saudi Aramco and KAUST proponent.
