1. The proposed manufacturer and model of the UPS is not acceptable since it is not as per the approved IFC drawing.
2. Correct and re-submit the submittal using the correct manufacturer, APC as per the IFC.
3. Ensure to provide back-up time of 30 minutes for data switch and 2 hours for router as per SOW and Appendix H.