a. IC and the manufacturer shall ensure that the proposed Genset shall run efficiently at 30% of its rating as was discussed and confirmed by IC during the meeting held on Feb 09, 2014.//b. IC shall ensure that the size and elevation of the Genset building shall be adequate to accomodate the Genset and associated accessories/ panels etc., and also for maintenance and repairs in the future.//c. A shop drawing shall be provided to show in or around the room the orientation and location of genset, fuel tanks, fuel pipes, cable routes, foundations, cable trays, panels, door sizes according to the genset dimensions, exhaust mechanisms/ openings, drainage system, sleeves etc.//d. IC is urged to coordinate with the Switchgear manufacturer to ensure that the auto transfer scheme complies with the approved single line diagrams and 13.8kV relay diagrams.//e. Consider provision of an I-Beam rail aligned with the length of the genset, on top of the genset for maintenance purposes, after consultation with the manufacturer. //f. This item has an inspection level 2. IC shall submit an RP and an NMR. A Pre-inspection meeting is also required prior to start of fabrication.