      SAPMT has reviewed the subject submittal dated May 26, 2014 and has the following comments:
1.    Quantities indicated in the Bill of quantities are incorrect. Re-verify the quantities and ensure all requirements are met for the project.
2.    The proposed manhole frame and cover is not acceptable since it conflicts with SAES-T-911 requirements.
3.    All accessories shall be non-corrosive, hot dipped galvanized and ensure compliance with SAES-T-911.
4.    Specifications of fiber marker post is included in the attachment and shall be included in the Bill of Quantities.
5.    Use correct 9com # 6000000682 for Manhole. 9com # 6000000681 is depleted and no more used in Saudi Aramco system.
