SAPMT has reviewed the subject submittal dated December 22, 2014 and has no objection with the following comments:
1.	Ensure that outdoor receptacles are weather proof with Ingress Protection rating of IP 66 as per SAES P-104.
2.	Ensure that receptacle outlets to be installed outdoor and/ or which are subject to wet and damp locations shall contain a Ground Fault Circuit Interrupter (GFCI) as specified in IFC drawings VA846646 sht.002.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.

Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
