1. Provide letter of Compliance from Design Consultant, SCEC that all the comments on the 90% review has been complied and incorporated in the IFC for all discipline.
2. Provide certification letter or stamp with design consultant concurrence to all Communications and Security drawings. Certification shall indicate that the OSP and SCS design has been reviewed by a certified BICSI/RCDD Engineer.
3. Cross section details of duct banks and direct buried cables installed in trenches are incorrect due to violation to Saudi Aramco Standards SAES-T-624 and SAES-T-911.
4. In gate house #2 and #3 area, all fiber optic cables shall be placed inside the duct banks provided with the cable pulling tension calculations. Orientation of telecom manholes has to be corrected in accordance to the standard. Also provide all the coordinates, stations and curves of duct banks and manholes.
5. Fiber cabling assigned to SHQ and BDC shall be installed inside duct banks. Correct the type of fiber cable used inside duct banks and direct buried.
6. High level Design (HLD) shall be revised in accordance to SAPMT/KAUST comments.
7. Drawing for Emergency Notification System (ENS) shall be corrected in accordance to SAPMT comments.
8. Service Manhole Construction details violates Saudi Aramco Standard Drawing.
9. Fiber Optic Cable Budget Link Loss Calculation shall be provided.
10. All rack mounted UPS to be provided and installed for all new buildings shall be under this project scope of work. UPS sizing calculation shall be provided.
11. Grounding Bus Bar shall be provided to all communication room.
12. Most of the comments of SAPMT during the 90% review has yet not complied.
 