1.	Use correct applicable 9Com#6000001826 with correct description as “A/C Unit, Mini-Split DE, below 5.5 Tonsâ€
2.	Use correct manufacturing Plant ID:30006251  with correct name of Plant as “ Zamil Central Air Conditioners Dammamâ€
3.	Zamil Airconditioner plant #30000313 as quoted by contractor is on hold and not approved.
4.	A/C  mini split Units are having inspection Level One(1)
5.	Approval of above manufacturer in Aramco system is valid up to Dec 31,2014, therefore PO shall be placed immediately after approval of Purchase requisition.
6. Highlight proposed model number
7. Building wise summary sheet with model number,cooling capacity are to be provided. 
8. Outdoor units shall have copper fins according to Saudi Aramco Standards.