1.	Contractor shall submit separate Material submittal for each Material Type.
2.	For LV panels(6000000859), Alfanar Company has limitations to use only MB-N Model breakers. In this submittal various other Models of breakers have been used which is not acceptable (see attached print out from Aramco SAP system).
3.	Alfanar company is not an approved manufacturer for Lighting control panel having 9Com#6000002698. (see attached list of approved manufacturers for 9Com#6000002698.
