SAPMT has reviewed the subject submittal dated November 06, 2014 and has the following comments:
1.	Provide Lighting Control Panel shop drawing that shows the dimension of the enclosure, wiring and devices arrangements.
2.	Provide the catalog and specification for the control transformer and pilot lamps.
3.	Indoor Lighting Control Panel shall be type NEMA 1, while Outdoor Lighting Control Panel shall be type NEMA 4X to meet enclosure requirements specified in SAES P-104.
4.	Include dedicated LCP tagging identification, for indoors which shall be phenolic type; for outdoors it shall be stainless steel.
5.	Consider submitting indoor and outdoor separately.
6.	Ensure that dimensions are provided so that installation on the wall with other panels is not an issue.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.