•It’s better if there is possibility to relocate one of the two tanks to be in the other side of the HAMMAM building to provide far distance between the two tanks to avoid any type of pollution.
•Regarding to Non – Electrical Utilities Layout drawing (VA-846996-001-0F1), maintain a distance between the sanitary main pipe and potable water pipe as per Saudi Aramco standard.
•There is a conflict regarding to Pump Control Panel location, the two drawing show deferent locations (VA-847009-001-0F1 and VA-84-7018-001-0F1).
•Its better if relocate the pump control panel to the nearest wall to the pump to reduce the cable length.
