SAPMT has reviewed the subject letter no. KPSS/SA/B/MUN/13/0125 dated October 05, 2013 and rejected with the following comments:

1.	Drawing # 1019-1.PSS-SF.3008 shall include detailed dimensions of the logo and relative location of leaves.
2.	Precast panel samples for inspection and acceptance shall be in conformance with SAES Q-012, Clause 6.1.
3.	Architectural shop drawings shall be concurred by the approved project designer after which the proponent approval shall be acquired.
4.	Consider also related comments if any, provided after the 90% technical review meetings.
Should you have any questions, please contract Fahad A. Al-Balawi, Sr. Project Engineer on Tel. No. +966 12 422 4393.
