SAPMT has reviewed the subject submittal dated April 21, 2014 and has no objection with the following comments:
1.	IC shall ensure that the proposed light poles are of exact same dimensions, diameters, lengths, shape and style as the existing ones. In case of any shape variations from existing, IC shall be responsible for replacement.
2.	Consider bringing a sample on site and installing as a mockup before delivering the complete quantity for verification.
3.	The galvanizing process shall comply with ASTM standards and coatings shall be done by Saudi Aramco approved vendors.
4.	Ensure that approved lighting fixtures and associated fittings are compatible with the poles.
5.	Consider preparing a shop drawing showing details of all attachments, fixtures, fittings, foundations, anchor bolts, etc.
Should you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.
