SAPMT has reviewed the subject submittal dated August 04, 2014 and has no objection with the following comments:
1.	Ensure all manhole hardware and accessories comply with all the dimensions and specifications as per SAES-T-911, Paragraph 5.2.8.7 and Aramco Standard drawing SASD AA-036794.
2.	All manhole hardware must be non-corrosive type such as hop dipped galvanized or better.
3.	Ensure to provide plastic inserts.
4.	Method Statement shall be provided for the fabrication process of the manhole with compliance to SASD AA-036794.
5.	Submit grounding material required for the manhole with compliance to SAES-T-911, Paragraph 5.2.8.8.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.
