1.	Underground LV cable shall be installed as per SAES-P-104 para 10 and in accordance with standard drawing AD-036874.
2.	Ensure LV cable will not obstruct any other underground utilities during installation.
3.	In the legend, remove the description for lighting type “similar with SLC-GEPS /5â€.
4.	Reflect the bridge in drawing at gate # 1 and ensure that the 5m pole will not be obstructed by the bridge.
5.	Ensure that SSD pole to pole clearance shall be 20m as per HCIS requirement.
