SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/13/0279 dated December 12, 2013 and has the following Comments:

1.	Attach as-built to prove the congestion at Gate 3.
2.	Provide details of cable tray for passing the cable through the culverts.
3.	Provide another option C with the following features;
a.	Warning tape to be placed on top of the red tiles.
b.	Provide a duct bank directly under the foundations of the ditch to avoid damages to the direct buried cable from compaction and loads from foundations.
c.	Propose passage through the concrete wall if required at STA 8+400.
Should you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.
