1.Regarding to NOTE 1: it is LV cable not MV cable.
2.Regarding to NOTE 4: delete the Soil Improvement sentence because no more soil improvement above the duct bank.
3.Regarding to the top and bottom rebar hooks should be 230 mm not 300 mm.
4.The contractor  has to apply red dye as per SAES-P-104 Para 10.3.
