SAPMT has reviewed the subject submittal dated August 18, 2013 and has the following comments:

1.	Mention the correct Manufacturing Plant ID # 30000448 for BRC industrial Jeddah.
2.	Please mention the Vendor ID of M/s. Fatayerji Contracting Co. if acting as supplier.
3.	Use Inspection form SA-175-092000 (for Coating, shop applied) while submitting Purchase Requisition.
4.	Furnish test results (mechanical properties) for the following Debars 16mm, 18mm, 20mm and 25mm and submit a readable copy of the test certificates Ref. TR105.
5.	Use minimum of 422 MPa yield strength for the steel reinforcement. Refer to Construction Specifications Section-03200, paragraph 2.01.A.a Reinforcing Bars.
Should you have any questions, please contract Fahad A. Al-Balawi, Sr. Project Engineer on Tel. No. +966 12 422 4393.
