SAPMT has reviewed the subject submittal dated March 09, 2014 and has no objection with the following comments:
1.	Ensure that energy efficient electronic ballasts having less than 10% THD (voltage total harmonic distortion) shall be used for fixtures with type T8 fluorescent fixtures.
2.	Ensure that the luminaire efficiency of fluorescent fixtures shall meet the minimum requirements of SAES P-123 table 2.
3.	Ensure that Efficacy of Compact fluorescent lights (CFL) shall not be less than 80 Lumen / Watt.
4.	Model NLC MHD2/232.E6 type C is not approved, project requirements is High Pressure Sodium type with 110 watts as per IFC drawing VA846993.
5.	Ensure that luminaires installed outdoor shall be approved as weather proof and dust tight.
6.	Clarify and correct the catalog provided for model NLC490/70W.MH.220IP65, the project requirements is 150 watts High Pressure Sodium (HPS) and not 70 Watts Metal Halide.
7.	For JFCC control room and in Generator buildings the emergency lighting back up requirements shall meet SAES P-123 Para. 5.6.3.
8.	Ensure that proposed model NLC650HP/218.E2.A.M31 Illuminated exit signs shall be manufactured in accordance with NFPA 101 requirements.
9.	Lighting fixture for King Abdullah Monument (KAM) access road shall match with the existing fixtures in road # 2 as discussed by SAPMT.
10.	All lighting fixtures and accessories shall meet Project specification, IFC drawing, SAES P-123 and SAES 0-204.
11.	Consider submitting products for specific locations as separate submittals.
Should you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.
