IC is urged to coordinate with Mobily and acquire more information about the specifications of manholes, ducts and covers etc. The following points shall be considered in the design.
1.	Location A's proposed manholes 7 and P are not necessary since Gate#3 has provisions of manhole and duct banks used for communications that can be utilized for Mobily cables. IC shall coordinate with the communications subcontractor in this regard.
2.	Detailed Shop drawings shall be provided to clearly locate the proposed manholes Q and R of Location A at the ends of the culvert and how the Mobily cable will pass through the culvert.
3.	Update and revise the Mobily cable route at Location A according to Item 1 and 2.
4.	It is appropriate to relocate proposed manhole G between existing manhole 1d and duct bank K at Location B since the current location of manhole G is not necessary due to the distance between proposed manholes F and H are not far.
5.	Provide details for the proposed duct bank crossings for all locations.
6.	Provide detailed Material Take-off List (MTO).
7.	Ensure the drawings, scope and MTO will be reviewed by Mobily with their concurrence.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
