SAPMT has reviewed the subject submittal dated November 01, 2014 and has the following comments:
1.	Material submittal for back flow preventer, isolation valve in the main valve box to be submitted separately with names of vendors/ manufacturers.
2.	Design drawing shall be stamped by SCEC and submitted to Aramco for approval.
3.	Gate valve for the solenoid shall be brass type.
4.	Identify and highlight on the submitted catalogue sheets the material type, size, model, and quantities for each item in the system for review and approval.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
