SAPMT has reviewed the subject submittal dated December 09, 2014 and has the following comments:

1.	I/O points are not matching with IFC. All I/O’s to be include in the list with 20% spare.
2.	IFC drawing for HVAC control to be attached with the submittal.
3.	Exhaust fan, Duct Heater and Supply Fans power panel to be include in the submittal or shall be submit separately. 

IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.
