1. Provide more information about testing according to 17-SAMAA-518 and VE-864472 para 3.04 B.1 to 4 and compliance matrix shall be verified between contractor and supplier.
2. The layout drawing shall show the neutral grounding resistor, control panel, fuel day tank and ventilation requirements.
3. After approval of the techncial details, IC shall provide requisition package including inspection form from SA-175-170400 rev 06/22/2011 and PR sheet.