SAMPT has reviewed the subject submittal dated May 05, 2015 and has no objection with the following comments:

1.	Underground 13.8KV Power Cable shall be installed as per SAES-P-104 para 10.
2.	Ensure a minimum separation between redundant direct buried power cables, power cable and control cable shall be maintained as per SAES-P-104 para 14.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.
