1.	Drawing No. VA-846512, Sht. 001 & 002: Change the Pad Mounted Transformer to Package Substation as indicated in the legend. The correct configuration of Package Substation shall comprise of 3-way RMU, Distribution Transformer and LV Panel which shall be reflected in the drawing.
2.	Drawing No. VA-846925, Sht. 005 & 006: Indicate NC in the breaker of normal power supply and tie breaker and NO in Standby Generator 
3.	Drawing VA-846925, Sht. 005 and 006: Clarify the rating of spare breaker if 1200A or 600A as it did not match with the Single Line Diagram, VA-846512, Sht. 001 & 002.
