INSERT INTO `submittal` VALUES(900, 917, 43, 'SAPMT has reviewed the subject submittal dated March 23, 2014 and has no objection with the following comments:\r\n1.	While various technical departments are still reviewing the subject submittal, comments from SAPMT are attached for incorporation and feedback from IC, so that the project execution can be expedited.\r\n2.	All the attached comments shall be reflected in the shop drawings.\r\n3.	A list of proposed Shop drawings shall be submitted by IC.\r\n4.	A Material Take off List for Communications and Security System including related MEP works to be submitted for SAPMT review.\r\n5.	Provide the High Level design (HLD).\r\n6.	Provide Project Specifications for Communications, Security MEP works.\r\n7.	Provide hard copies of the complete IFC package including drawings and write-ups.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'IFC, Security, Communication', 'Complete', '2014-04-13', 0, 25, 0, 26, 'L-664/14', '2014-04-14', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(902, 931, 43, 'Reference to the subject matter, ICC shall provide a certified Medium Voltage (MV) and Fiber Optic cables splicers with valid Job Clearance Card (JCC) complying Saudi Aramco procedures and standards.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.\r\n', 'Aramco Certified, MV', 'Complete', '2014-03-30', 0, 25, 0, 27, 'L-592/14', '2014-03-29', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(903, 930, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0483 dated March 29, 2014 and has rejected due to lack of crash rating certificate by TTI.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Crash Rating', 'Complete', '2014-04-29', 0, 25, 0, 27, 'L-666/14', '2014-04-29', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(904, 934, 43, 'SAPMT has reviewed the subject submittal dated March 23, 2014 and has the following comments:\r\n\r\n•	Mr. Abdul Qadoos is rejected as “QC Inspector – Civilâ€ based on his personal interview that the candidate is incapable to prove his proficiency.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.\r\n', 'QC Inspector, Civil', 'Complete', '2014-04-02', 0, 27, 0, 26, 'L-607/14', '2014-04-03', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(905, 939, 43, 'For Information Only', 'Progress Report', 'Complete', '2014-04-06', 0, 25, 0, -1, 'For Information Only', '2014-04-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(906, 938, 43, 'SAPMT has reviewed the subject submittal dated March 30, 2014 and has the following comment:\r\n\r\n•	The submitted cable sizing calculation does not show the voltage drop calculation if the proposed size of power cable, (120 mm sq.) can carry the required ampacity for a long run of loop distribution system. As discussed during SAPMT/IC/SCEC meeting dated Feb. 9, 2014, SAPMT/IC/SCEC conference call dated March 10, 2014 and progress meeting # 28 dated March 31, 2014, IC is urged to provide 3/c x 185mm2 cable with package substations as stated in the bid package. Package Substation shall constitute an RMU, Distribution Transformer and LV Power Panel which is not possible with the pad mounted Transformer. Furthermore, 185 mm sq. Power cable is suitable for termination to the load break switch of Ring Main Unit (RMU). It is to be noted that the award of contract is based on the bid package and IC shall refrain from lowering the specifications without providing adequate technical justifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'MV, Cable, Calculation', 'Complete', '2014-04-08', 0, 25, 0, 27, 'L-642/14', '2014-04-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(907, 932, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0482 dated March 30, 2014 and has the following comment:\r\n\r\n•	Please refer to the attached SAPMT letter # K&TPD/KRP&SFPD/SF/L-674/14 dated April 15, 2014.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Elimination, Ditch', 'Complete', '2014-04-27', 0, 27, 0, 26, 'L-697/14', '2014-04-27', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(908, 933, 43, 'SAPMT has reviewed the subject submittal dated March 26, 2014 and has the following comments:\r\n\r\n1.	The piping material is acceptable but the submittal is incomplete.\r\n2.	The subject of the submittal shall be more specific. Rename the description of the submittal with "PVC CONDUITS NEMA TYPE DB and EB for ELECTRICAL AND COMMUNICATION conduits and duct banks".\r\n3.	Include in the submittal the proposed conduit spacers and conduit fittings.\r\n4.	Ensure that the PVC conduits to be used will comply with SAES P-104, IFC drawings and Project Specification.\r\n5.	Discuss with electrical and communication engineers from SAPMT to include necessary documents, summaries and drawings.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Pipe UPVC', 'Complete', '2014-04-12', 0, 25, 0, 27, 'L-654/14', '2014-04-12', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(909, 941, 43, 'SAPMT has reviewed the subject submittal dated March 31, 2014 and has the following comment:\r\n•	The candidate does not possess educational qualifications in environmental engineering nor has approved certifications in HSE.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Environmental Officer', 'Complete', '2014-04-03', 0, 25, 0, 27, 'L-630/14', '2014-04-03', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(910, 940, 43, 'SAPMT has reviewed the subject submittal dated March 30, 2014 and has no objection with the following comments:\r\n1.	Fence should be grounded as per SAES-P-III.\r\n2.	Provide concrete footings according to SAES-M-5.2.\r\n3.	The fencing fabric mesh, length of rolls, woven design and splicing shall follow HCIS standards.\r\n4.	Refer to attached Dwg. GI-AS-62037 and AB-036677-001-02 for more details.\r\n5.	When fully constructed the barbed wire, tension wire, fabric, and truss rods shall be taut.\r\n6.	Contractor should submit the shop drawing of concrete footing and beam.\r\n7.	It is contractor’s responsibility to follow all related HCIS and Aramco standards for materials and installation.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Chain Link, Fence', 'Complete', '2014-04-08', 0, 25, 0, 27, 'L-641/14', '2014-04-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(911, 936, 43, 'For Information Only', 'QA Manager', 'Complete', '2014-04-21', 0, 25, 0, -1, 'For Information Only', '2014-04-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(912, 935, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0486 dated March 30, 2014 and has the following comment:\r\n\r\n•	IC is urged to focus on the requirements put forth in the PMT letter no. K&TPD/KRP&SFPD/SF/L-601/14 dated March 27, 2014 and provide point-wise responses showing actions taken, if any, accordingly.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Ditch, Suspension Period', 'Complete', '2014-04-27', 0, 27, 0, 26, 'L-698/14', '2014-04-27', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(913, 942, 43, 'Comments given to IC verbally...', 'KAM, Realignment', 'Complete', '2014-04-09', 0, 25, 0, -1, 'For Information Only', '2014-04-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(914, 948, 43, 'As discussed during SAPMT/IC/SCEC meeting dated Feb. 9, 2014, SAPMT/IC/SCEC conference call dated March 10, 2014 and progress meeting # 28 dated March 31, the power cable feeding the Generator Building shall tie in with SEC#2 substation, whereas in the BID package the tie in was identified to be with substation #4. IC is urged to provide the details of impacts occurring with this variation, along with revised design layouts, shop drawings and material submittals as necessary.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.\r\n', 'Substation, Variation', 'Complete', '2014-04-08', 0, 27, 0, 26, 'L-649/14', '2014-04-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(915, 943, 43, 'The Document has been pulled out back to ICC.', 'KAM, Transition', 'Complete', '2014-04-09', 0, 25, 0, -1, 'For Record Only', '2014-04-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(916, 944, 43, 'For Information Only', 'Progress Meeting', 'Complete', '2014-04-09', 0, 25, 0, -1, 'For Information Only', '2014-04-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(917, 945, 43, 'For Information Only', 'Safety, Inspection Report', 'Complete', '2014-04-06', 0, 25, 0, -1, 'For Information Only', '2014-04-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(918, 946, 43, 'SAPMT has reviewed the subject submittal dated March 30, 2014 and has no objection with the following comment:\r\n•	The comments and recommendations raised during the emergency evacuation drill shall be evaluated and implemented.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570\r\n', 'Fire Fighting Drill', 'Complete', '2014-04-08', 0, 25, 0, 27, 'L-640/14', '2014-04-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(919, 947, 43, 'SAPMT has reviewed the subject submittal dated March 30, 2014 and has no objection with the following comment:\r\n•	The concerns raised during the drill shall be evaluated and implemented.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Camp, Emergency Evacuation', 'Complete', '2014-04-08', 0, 25, 0, 27, 'L-639/14', '2014-04-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(920, 949, 43, 'SAPMT has reviewed the subject submittal dated April 01, 2014 and has the following comments:\r\n\r\n1.	Drawing No. VA-846512, Sht. 001 & 002: Change the Pad Mounted Transformer to Package Substation as indicated in the legend. The correct configuration of Package Substation shall comprise of 3-way RMU, Distribution Transformer and LV Panel which shall be reflected in the drawing.\r\n2.	Drawing No. VA-846925, Sht. 005 & 006: Indicate NC in the breaker of normal power supply and tie breaker and NO in Standby Generator \r\n3.	Drawing VA-846925, Sht. 005 and 006: Clarify the rating of spare breaker if 1200A or 600A as it did not match with the Single Line Diagram, VA-846512, Sht. 001 & 002.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'IFC Drawings, Electrical, One Line Diagram, Switchgear, Generator', 'Complete', '2014-04-17', 0, 25, 0, 26, 'L-680/14', '2014-04-17', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(921, 950, 43, 'SAPMT has reviewed the subject submittal dated April 01, 2014 and has no objection with the following comments:\r\n1.	Maintained all records systematically in case required during external audits by third parties.\r\n2.	All corrective actions shall be maintained/ logged in the register.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'SCAR', 'Complete', '2014-04-08', 0, 25, 0, 27, 'L-634/14', '2014-04-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(922, 952, 43, 'SAPMT has reviewed the subject submittal dated April 01, 2014 and has the following comments:\r\n1.	Mr. Imran Khan is conditionally approved as “QC Inspector Telecommunications and securityâ€ for Two (2) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\n3.	The Saudi Aramco approval shall be renewed in June 2014.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel. No. +966 12 422 4570.\r\n', 'QC Inspector, Telecommunication, Security', 'Complete', '2014-04-12', 0, 25, 0, 27, 'L-647/14', '2014-04-12', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(923, 953, 43, 'SAPMT has reviewed the subject submittal dated April 02, 2014 and has the following comments:\r\n\r\n1.	PVC conduits and fittings shall comply with SAES P-104 para. 8.1.1 and 8.1.2.\r\n2.	EGA Honeywell is not mentioned in the recommended manufacturers list provided in construction specification document section 16110 page 2 of 10. IC is urged to consult the designer and acquire concurrence.\r\n3.	Consider segregating the submittals for PVC Conduits and Fittings, Wire way and Back boxes to avoid confusion.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'PVC Conduits, Fittings', 'Complete', '2014-04-21', 0, 25, 0, 27, 'L-692/14', '2014-04-21', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(924, 954, 43, 'With reference to the subject matter, SAPMT would like to inform you that the factory acceptance test for SONAR head, alarm management and its servers is not necessary, if IC/ESE will provide the same models installed in KAUST. However, it is the prime responsibility of the contractor to ensure the new SONAR equipments to be provided will pass the site acceptance test that will be held during the commissioning of the system.', 'FAT, SONAR', 'Complete', '2014-04-07', 0, 27, 0, 26, 'L-645/14', '2014-04-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(925, 955, 43, 'It is mandatory that IC appoints quantity surveying professionals and related technical staff which are currently not available at IC site offices, as soon as possible to provide quantities and impacts for the following activities;\r\n1.	Elimination of ditch and related impacts.\r\n2.	Narrowing of the culvert at Wadi Khulais due to elimination of the ditch.\r\n3.	Backfilling scenarios at the culvert Wadi Wesami for guard house and in between the culverts.\r\n4.	Changes to the route of the cables due to changes in power source from SS4 to SEC2.\r\n5.	Changes to the lengths of various cables crossing the ditch.\r\n6.	Removal of culverts on access roads to main gates.\r\n7.	Steel grills and bollards at the flood control channels.\r\n8.	Changes to the maintenance access roads and gates for the ditch.\r\n9.	Grade beams for the precast wall.\r\n10.	Pipelines between gates 2 and 3 and related lift stations eliminated.\r\n11.	Variations related to switchgears and generators.\r\n12.	Variations related to HVAC.\r\n13.	Variations related to all of the above including any others which IC may deem necessary shall be incorporated in a single document with quantities to be agreed upon by the two parties and sent to SAPMT for review before 30 April 2014.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Elimination, Ditch, Claim', 'Complete', '2014-04-15', 0, 25, 0, 26, 'L-674/14', '2014-04-16', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(926, 957, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(927, 958, 43, 'Replied to ICC Through SAPMT Letter # L-656/14 as attached.', 'Time Sheet', 'Complete', '2014-04-23', 0, 25, 0, -1, 'For Record Only', '2014-04-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(928, 956, 43, 'Please refer to the attached drawings for the anti-climb spikes shown on top of the precast wall which were included in the project proposal, in 50% design, in 90% design and in the IFC. It is observed that the existing spikes on top of the existing KAUST fence are different from the ones selected for the KAUST-Perimeter Security Systems project. While SAPMT believes that proposed spikes at 4m height are not visible from the ground to the intruder and thus create an element of surprise and are more feasible than the existing visible ones and have already been approved by KAUST during the detailed design phase, it is nevertheless necessary that KAUST concurs with the design of such spikes.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.\r\n', 'Anti Climb Spikes', 'Complete', '2014-09-21', 0, 25, 0, 26, 'L-669/14', '2014-06-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(929, 963, 43, 'IC is urged to refer to para 13 of the SCH-A of the contract before bringing any subcontractor to start any work on site. Subcontracts for the performance of any portion of the WORK shall be procured only after CONTRACTOR has received written authorization from SAUDI ARAMCO that CONTRACTOR may subcontract that portion of the WORK. If not accomplished prior to the effective date of this Contract, then promptly thereafter, CONTRACTOR shall prepare and submit to the Company Representative for SAUDI ARAMCO''s approval CONTRACTOR''s subcontracting plan specifically identifying those portions of the WORK which CONTRACTOR proposes to subcontract. Any changes to an approved subcontracting plan shallbe done with written approval of Saudi Aramco. In procuring subcontracts, CONTRACTOR shall select and recommend subcontractors solely on the basis of financial and technical considerations. Saudi Aramco shall evaluate subcontractors based on their past performance and resources available for the project. All subcontracts entered into by CONTRACTOR shall contain a provision whereby the subcontractor agrees and consents to the conditions of the contract between the CONTRACTOR to SAUDI ARAMCO. Nothing in this Contract shall create any contractual relation between SAUDI ARAMCO and any subcontractor unless SAUDI ARAMCO elects to exercise its rights under Paragraph 13.4 of SHC-A. SAUDI ARAMCO''s approval to subcontract any portion of the WORK and SAUDI ARAMCO''s non-objection to CONTRACTOR''s subcontractor selection shall not relieve CONTRACTOR any of its obligations under this Contract.', 'Subcontracting Plan', 'Complete', '2014-04-06', 0, 25, 0, 27, 'L-646/14', '2014-04-07', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(930, 959, 43, 'SAPMT has reviewed the subject letter dated April 16, 2014 and has the following comments:\r\n1.	SAPMT believes that IC has delayed the preliminary works required at Wadi Khulais culvert, which could have been done without waiting for completion of works by the other contractors working in the area.\r\n2.	SAPMT believes that IC has delayed all backfilling works for the project so far, especially for the areas for security buildings at gates. With such speed of progress it seems IC is in no position to claim to be ready for work on any other areas. IC is expected to resolve the interface after coordination with other contractors and not to use the interface as a reason to create delays. SAPMT has asked IC to arrange meetings with interfaces, which have not been planned by IC yet.\r\n3.	The referred slab does not affect the IC scope of work in any way. IC shall not wait for other contractors to clear the areas but coordinate to work side by side.\r\n4.	The referred backfilling does not affect IC scope of work in any way. IC shall coordinate with the interfaces to find a solution and start work by acquiring access through the laydown yards.\r\n\r\nBased on the above IC is urged to hire an effective Interface Manager who can find solutions instead of creating issues and coordinate with other contractors working in the area, according to the conditions of the contract mentioned in para 2.4, 1.1.17, 3.9 & 3.10. IC is also urged to provide shop drawings for all interfaces and acquire SAPMT approvals before starting works.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Completion Dates, Wesami, Khulais, Nasser Bin Haza', 'Complete', '2014-04-21', 0, 25, 0, 27, 'L-688/14', '2014-04-21', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(931, 960, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(932, 961, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(933, 962, 43, 'SAPMT has reviewed the subject submittal dated April 05, 2014 and has no objection with the following comment:\r\n•	ICC shall comply with project specifications, SAES-L-132, 01-SAMSS-029 (Gravity Flow) and 01-SAMSS-34 (Pressurized Flow) during installation of RTR pipes and selection of fittings/ fixtures.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570\r\n', 'Pipe & Fittings, RTR, FRP', 'Complete', '2014-04-12', 0, 25, 0, 27, 'L-660/14', '2014-04-12', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(934, 964, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2014-04-13', 0, 25, 0, -1, 'For Information Only', '2014-04-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(935, 965, 43, 'The procurement process for following materials is being delayed by IC, despite the fact that technical submittals for most of them have been approved by PMT:\r\n1.	Switch Gears\r\n2.	UPS\r\n3.	Lighting Poles\r\n4.	Panel Boards\r\n5.	Data Network System\r\n6.	Video Conference\r\n7.	IPTV\r\n8.	Work Station\r\n9.	Fiber Optic Cable\r\n10.	Sewer Pipes & Accessories\r\n11.	MIDS(APU signal processing, TX & RX, Microwave sensors, Mounts mast/pole)\r\n12.	Cameras\r\n13.	Field Equipment Cabinet\r\n14.	System control unit\r\n15.	Proximity Readers\r\n16.	Long Range Readers\r\n17.	Reader Interface\r\n18.	Badging stations\r\n19.	Operator workstations\r\n20.	Intercom Interface\r\n21.	Turnstiles\r\n22.	SACS System\r\n23.	Vessel barriers\r\n24.	Boat Identification System\r\n25.	Crash Barriers\r\n26.	Drop Arm Barriers\r\nThe following are long lead items for which IC has still to finalize technical submittals.\r\na.	Package Substation\r\nb.	MV cable\r\nc.	Switch racks\r\nd.	UPS and Batteries\r\ne.	Fire alarm control panel and notification devices.\r\nf.	LV cable /  Building wires\r\ng.	Grounding rods / grounding conductors / Lighting Protection\r\nh.	Direct Digital Controller and sensors\r\ni.	Package Air-conditioning Unit\r\nj.	Fan Coil Unit\r\nk.	Exhaust Fans\r\n\r\nIC is urged to expedite the placement of all pending purchase orders by May 29, 2014 and consider this letter with utmost urgency so that the project progress is not hindered any more.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Purchase Orders', 'Complete', '2014-04-12', 0, 25, 0, 27, 'L-652/14', '2014-04-12', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(936, 973, 43, 'Please refer to the attached drawings for the anti-climb spikes shown on top of the precast wall which were included in the project proposal, in 50% design, in 90% design and in the IFC. It is observed that the existing spikes on top of the existing KAUST fence are different from the ones selected for the KAUST-Perimeter Security Systems project. While SAPMT believes that proposed spikes at 4m height are not visible from the ground to the intruder and thus create an element of surprise and are more feasible than the existing visible ones and have already been approved by KAUST during the detailed design phase, it is nevertheless necessary that KAUST concurs with the design of such spikes.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.\r\n', 'Anti Climb, Spikes', 'Complete', '2014-04-23', 0, 27, 0, 26, 'L-669/14', '2014-04-23', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(937, 969, 43, 'With reference to the subject, we would like to inform you that the IDAS Pelco CCTV FAT will be conducted on May 19-20, 2014 at Clovis, California, USA. The FAT will cover the following:\r\n1.	The built in analytic inside the IXE10.\r\n2.	The VOD configuration and performance for IXE10.\r\n3.	The Day and night performance for the IXE10.\r\n4.	The resolution of the object ratio to object distance from the camera (Px/m) to get object detection.\r\n5.	The auto tracking functionality for the Esprit ES41E.\r\n6.	The functionality between the IXE10 once detect intruder and Esprit ES41E tracking to this intruder.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.\r\n', 'IDAS, FAT', 'Complete', '2014-04-12', 0, 27, 0, 26, 'L-661/14', '2014-04-12', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(938, 966, 43, 'Letter Withdrawn through ICC letter # KPSS/SA/B/AKR/14/0533 Dated April 20, 2014.', 'Baseline Schedule', 'Complete', '2014-04-23', 0, 25, 0, -1, 'For Record Only', '2014-04-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(939, 967, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0499 dated April 07, 2014 and has the following comments:\r\n1.	Contractor shall propose two candidates for precast plant related inspections from the pre-approved Civil Inspectors (which are still under probation).\r\n2.	Among the two candidates, one shall be assigned permanently in the precast yard, and the other shall be assigned permanently for onsite installation and erection works.\r\n3.	The candidates will be interviewed and approved by Mr. J.C. Borja from BP&CTU, before they are considered officially as a replacement of Mr. Harley G. Balance.\r\n4.	Precast Inspector is a mandatory BP&CTU requirement in the Precast Facility approval.\r\n5.	Consider revised submission through document submittal.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'QC Inspectors, Precast Facility', 'Complete', '2014-04-21', 0, 25, 0, 27, 'L-681/14', '2014-04-21', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(940, 968, 43, 'SAPMT has reviewed the subject submittal dated April 08, 2014 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Saudization, March 2014', 'Complete', '2014-05-10', 0, 27, 0, 26, 'L-719/14', '2014-05-08', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(941, 970, 43, 'In reference to your subject letter no. KAUST-M&U-14-0034 dated March 18, 2014, the point wise response to your comments is given below;\r\n1.	The architectural features have been revised as shown in the attached section of the KAM road.\r\n2.	A typical 4m shoulder has been provided on both sides. The shoulder however, might be reduced for a short distance of 10m on one inside corner of the southern side of the KAM road where the road curves closely around the mangrove. This short distance will be safeguarded by concrete or steel barriers.\r\n3.	Three lines of trees shall be provided as indicated on the attached section. Considering the low mortality rate of Date Palm trees in saline environments or Sabkha, alternative favorable species of tress shall be considered. This alternative was also discussed during 90% detailed design review meetings item 284.(attached)\r\n4.	The revised section as attached shows the street lights on both sides. If a similar design of lights as on Road 2 is not available, alternative designs shall be used after mutual approval.\r\n5.	Same as item 2 above.\r\n6.	Relocated IDAS shall follow the same principles as existing. New IDAS shall meet the principles of design in IFC.\r\n7.	The ditch has been shown as removed from the section attached and internal patrol road can be provided without interfering with the KAM road. Hence there shall be no need to install chain link gates.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Re-alignment, Mangrove Conservation', 'Complete', '2014-09-21', 0, 25, 0, 26, 'L-599/14', '2014-06-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(942, 971, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(943, 972, 43, 'SAPMT has reviewed the subject submittal dated April 07, 2014 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of Saudi Aramco applicable standards and specifications.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570\r\n', 'Video Door Station, Intercom', 'Complete', '2014-04-13', 0, 25, 0, 26, 'L-665/14', '2014-04-14', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(944, 974, 43, 'SAPMT has been requested KAUST for access through Gate # 5 so that the contractor could install a chain link fence to isolate the area on the shoreline as requested by KAUST (see attachment # 2) and also to conduct studies for realignment of the corridor after the elimination of ditch. The approval/ work has been pending for almost 3 months as KAUST is requesting to provide third party security personnel to secure the subject area, which SAPMT believes is excessive due to the following reasons;\r\n1.	The location is outside the existing KAUST wall and IDAS system (see attachment # 1).\r\n2.	The area between the existing KAUST wall and the mentioned area is otherwise accessible through the flood channel which is not protected by any chain link fence, temporary gate, or third party security company.\r\nWe would like to reiterate that this issue has become a bottleneck for the project and delaying so many activities specifically the realignment of security corridor due to the ditch elimination and the installation of chain link fence. KAUST is requested to coordinate with the Security department to reconsider and allow security and access with the help of Contractor''s owned forces instead of third party security.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.\r\n', 'Access, Southern Perimeter', 'Complete', '2014-04-23', 0, 27, 0, 26, 'L-670/14', '2014-04-23', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(945, 975, 43, 'SAPMT has reviewed the subject submittal dated April 09, 2014 and has the following comments:\r\n\r\n1.	Contractor shall use correct description i.e. Pipe Non Metallic Thermoplastic (UPVC) and 9Com number 6000000031 for UPVC Pipes.\r\n2.	Contractor shall Use Correct 9Com# 6000000216 for UPVC Fittings.\r\n3.	UPVC pipes with 9Com #6000000031 (having Inspection Level Zero) shall be procured from Aramco approved manufacturing Plant.\r\n4.	Please write correct manufacturing Plant #30000919 for SAPPCO DAMMAM FACTORY.\r\n5.	“UPVC Pipe & Fitting with dia/sizeâ€ shall be written on cover sheet of Material submittal.\r\n\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'UPVC, Pipe, Irrigation System', 'Complete', '2014-04-16', 0, 25, 0, 26, 'L-667/14', '2014-04-16', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(946, 976, 14, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(947, 977, 43, 'SAPMT has reviewed the subject submittal dated April 10, 2014 and has the following comments:\r\n\r\n1.	IC to include cross section at different intervals to show details related to the MOT, Patrol Road, Perimeter Fence, IDAS/ MIDS and Maintenance Road and also indicate the gradual slope change as per previous discussions.\r\n2.	Consider adding the expansion joints where necessary.\r\n3.	A table showing stations, approved shop drawings and pending shop drawings shall be included in subsequent submittals.\r\n4.	It is ICC’s responsibility to ensure that the precast wall is casted and installed according to SA standards and with highest level of aesthetic in workmanship and appearance.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Fence Plan, Shop Drawings', 'Complete', '2014-04-17', 0, 25, 0, 26, 'L-678/14', '2014-04-17', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(948, 978, 43, 'SAPMT has reviewed the subject submittal dated April 10, 2014 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of Saudi Aramco applicable standards and specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Shop Drawings, KAM Section, Soil Improvement, Wet Aread', 'Complete', '2014-04-17', 0, 25, 0, 26, 'L-677/14', '2014-04-17', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(949, 979, 43, 'SAPMT has reviewed the subject submittal dated April 10, 2014 and has rejected with the following comment:\r\n•	IC shall increase its procurement related efforts to overcome delays and achieve at least 24% progress by the end of April 2014.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Material Procurement', 'Complete', '2014-04-23', 0, 25, 0, 27, 'L-695/14', '2014-04-23', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(950, 980, 43, 'For Information Only', 'Progress Report', 'Complete', '2014-04-21', 0, 25, 0, -1, 'For Information Only', '2014-04-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(951, 981, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0510 dated April 10, 2014 and has no objection with the following comment:\r\n•	The headings and sub headings do not match with the areas/locations mentioned. Activities in the North are shown as a part of activities in the East. IC is urged to verify the quality of documents before submitting to SAPMT.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Inspection Schedule', 'Complete', '2014-04-23', 0, 25, 0, 27, 'L-696', '2014-04-23', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(952, 789, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(954, 982, 43, 'SAPMT has reviewed the subject submittal dated March 31, 2014 and has no objection with the following comments:\r\n\r\n1.	ICC to provide a bending schedule for the rebar and to construct accordingly.\r\n2.	Provide details for duct banks at KAM 0+000 for crossing utilities for KPSS project and KAM project after related interface coordination.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Transition, Duct Bank, Steel Bar, Shop Drawings', 'Complete', '2014-04-17', 0, 25, 0, 26, 'L-676/14', '2014-04-17', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(955, 983, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0498 dated April 12, 2014 and has the following comments:\r\n\r\n1.	Redundant server for SONAR SYSTEM is missing in the provided SONAR Purchase Order list of materials.\r\n2.	Ensure that system training and familiarization shall be included in purchase order, as per contract requirement Appendix-H section 7.0.\r\n3.	Include all material approvals and pre-requisites.\r\n4.	Ensure that delivery dates are provided.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Purchase Order, RADAR, SONAR, Vessel Barrier', 'Complete', '2014-04-23', 0, 25, 0, 27, 'L-694/14', '2014-04-23', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(956, 984, 43, 'SAPMT has reviewed the subject submittal dated April 12, 2014 and has no objection with the following comment:\r\n•	The selected geotechnical contractor shall provide the endorsement letter and once this letter is submitted, the geotechnical file number will be provided.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'SOW, Geotechnical Investigation, KAM', 'Complete', '2014-04-13', 0, 25, 0, 26, 'L-663/14', '2014-04-14', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(957, 985, 43, 'SAPMT has reviewed the subject letter KPSS/SA/B/AKR/14/0511 dated April 13, 2014 and has the following comment:\r\n\r\n•	The variation is acceptable for the following:\r\n1.	Installing 1200A breakers in place of 600A breakers for 2 x switchgears.\r\n2.	Adding a tie breaker to both the switchgears.\r\nIC is urged to start the material specification/submittals for SAPMT approval.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'MV, Switchgear, Panel, Change Order', 'Complete', '2014-04-15', 0, 25, 0, 26, 'L-671/14', '2014-04-15', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(958, 986, 43, 'SAPMT has reviewed the subject submittal dated April 13, 2014 and has rejected with the following comments:\r\n\r\n1.	Mr. Mudassar Hussain was interviewed and found not eligible for the position of “Environmental Officerâ€.\r\n2.	The candidate possess less than 5 years of experience in Environmental Management as required in SA-CSM, Volume-I, CSAR, Chapter 4.5, Contractor Site Safety Staff (applicable for environment staff).\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Environmental Officer', 'Complete', '2014-04-24', 0, 25, 0, 27, 'L-702/14', '2014-04-23', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(959, 987, 43, 'SAPMT has reviewed the subject letter KPSS/SA/B/AKR/14/0514 dated April 13, 2014 and has the following comment:\r\n\r\n•	IC is urged to revise the subcontracting plan which was approved via SAPMT letter no. K&TPD/KRP&SFPD/SF/L-252/14 dated October 21, 2013.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Subcontracting Plan', 'Complete', '2014-04-15', 0, 25, 0, 26, 'L-672/14', '2014-04-15', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(960, 988, 43, 'Please find enclosed Two (A3 Size) hard copy sets and Two (2) CD’s of IFC Design for Communications and Security of “KAUST-Perimeter Security Systemsâ€ project for your review and comments. Please provide your comments on or before May 5, 2014.\r\n\r\nShould you have any questions, please contact Fahad A, Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'IFC, Security, Communication', 'Complete', '2014-04-21', 0, 25, 0, 27, 'L-673/14', '2014-04-21', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(961, 989, 43, 'SAPMT has reviewed the subject submittal dated April 14, 2014 and has the following comments:\r\n1.	Identify the power supply of SONAR Head # 4, Power supply from Uninterruptable Power Supply (UPS) shall be different from the existing.\r\n2.	In IFB drawing and 50 percent detail design package, new SONAR servers will be installed in JFCC building server room, however in IFC drawing it was stated that existing KAUST SONAR servers located in SHQ will be used to accommodate SONAR # 4. Include a document or signed MoM to show this change.\r\n3.	In addition to this method of statement, IC/ESE has to provide concurred construction specification for work execution, showing nature and types of bolts, resins, sealants, fittings etc.\r\n4.	Sonar head tag to be changed to SONAR # 1, 2, and 3.\r\n5.	Attach approved shop drawings for foundations and columns.\r\n6.	Provide more quality related details about excavation methods, ensuring stability of formation levels, and backfilling methods.\r\n7.	Provide more details about avoiding soil erosion from water currents.\r\n8.	Include Inspection and test plans.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Diver Detection, SONAR', 'Complete', '2014-04-23', 0, 25, 0, 27, 'L-693/14', '2014-04-23', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(962, 990, 43, 'SAPMT has reviewed the subject submittal dated April 14, 2014 and has rejected with the following comments:\r\n\r\n1.	"For the Week Progress" at Level I & Level II Summary shown as 0%. It can''t be 0% for both the Plan and Actual.\r\n2.	Data date for the submitted Weekly Report No. 33 shall be April 11, 2014 whereas it is wrongly mentioned as April 04, 2014.\r\n3.	Contractor key personnel are advised to review the document before signing and submitting to SAPMT.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Progress Report, 33', 'Complete', '2014-04-17', 0, 25, 0, 26, 'L-679/14', '2014-04-17', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(963, 997, 43, 'SAPMT has reviewed the subject submittal dated April 14, 2014 and has the following comments:\r\n\r\n1.	IC shall submit missing items which are part of SACS system deliverables as per FSD document, PE 000071 section 4.4.3, section 5.1, section 5.2.5 /5.2.9 such as Badging Station, Operator workstation, Fingerprint System and door control accessories.\r\n2.	Ensure that Reader interface shall be supplied with internal DC battery backup for minimum 8 hour including power to energize door lock as per FSD document PE-000071 section 5.2.3.\r\n3.	IC is urged to provide technical data for all remaining materials stated in IFC and/ or project specifications.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'SACS, Security Access, Control System', 'Complete', '2014-04-29', 0, 27, 0, 26, 'L-705/14', '2014-04-30', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(964, 991, 43, 'SAPMT has reviewed the subject submittal dated April 14, 2014 and has no objection with the following comments:\r\n\r\n1.	Use 25mm wheel & chair spacer for slabs & joist not exposed to earth. Refer to IFC drawing VA-846497 sheet # 001, 25mm spacers are to be used as chair and wheel spacers only where 25mm is allowed for vertical clearance.\r\n2.	Use 50mm chair spacer for beams, column, buildings, walkways, stairs and equipment pads. This is in compliance with SAES Q-001 paragraph 5.8, Table # 2.\r\n3.	Use 70mm chair spacer for concrete cast exposed to earth. Refer to SAES Q-001 paragraph 5.8, Table#2.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Wheel Spacer, Chair Spacer', 'Complete', '2014-04-21', 0, 25, 0, 27, 'L-691/14', '2014-04-21', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(965, 992, 43, 'SAPMT has reviewed the subject submittal dated April 14, 2014 and has the following comments:\r\n\r\n1.	Provide the purpose or location of materials being proposed in the subject.\r\n2.	Provide correct 9Com 600000573 with correct description such as (Bolt Assembly/ Anchor etc.)\r\n3.	It shall be inspection level 1 and procured through an approved vendor/ manufacturer.\r\n4.	Use galvanized steel bolt high strength ASTM-325, nuts & washers. Refer to SAES Q-012, paragraph 5.14 Connection Material and Construction Specifications Section-01000 paragraph 15.0D Bolts, Anchor bolts & Nuts.\r\n5.	The 550MM length shall be used and zinc coating shall be done after threading.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Fixing Bolt, Galvanized', 'Complete', '2014-04-21', 0, 25, 0, 27, 'L-690/14', '2014-04-21', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(966, 993, 43, 'Payment Application # 11 for the month of March 2014 was approved, service entry sheet is attached herewith.', 'Invoice, Payment Application, 11', 'Complete', '2014-05-11', 0, 27, 0, -1, 'For Record Only', '2014-05-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(967, 994, 43, 'For Information Only', 'Progress Meeting', 'Complete', '2014-04-27', 0, 25, 0, -1, 'For Information Only', '2014-04-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(968, 995, 43, 'For Information Only', 'Progress Meeting, 29', 'Complete', '2014-04-21', 0, 25, 0, -1, 'For Information Only', '2014-04-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(969, 996, 43, 'IC is urged to provide the following information;\r\n1.	Quantity of trees according to IFB/ SOW.\r\n2.	Quantity of trees according to approved IFC.\r\n3.	Nature of trees according to the approved IFB/ SOW.\r\n4.	Nature of trees according to material approvals.\r\n5.	Number of street lights according to IFB/ SOW.\r\n6.	Number of street lights according to IFC.\r\n7.	Nature of street lights according to material approvals.\r\n8.	Nature of street lights according to IFB.\r\n9.	Quantification of any variations to irrigation and control systems according to material approvals.\r\n10.	Quantification of any variations to electrical systems according to material approvals.\r\nUpon receiving the above information, the nature of claimed variations and quantities shall be evaluated by SAPMT.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Horticulture', 'Complete', '2014-04-17', 0, 25, 0, 26, 'L-682/14', '2014-04-17', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(970, 998, 43, 'SAPMT has reviewed the subject letter dated April 16, 2014 and has rejected with the following comments:\r\n1.	IC is urged to refer to IFB where it is clearly mentioned in 1.2.1 that "This project will be designed in accordance with the respective government agencies standards including MOWE and SEC. Also, industrial standards will be used for scope elements that are not covered under the respective Government agencies standards. Only current Saudi Aramco standards for Loss Prevention, Safety and Security and Environmental Protection will be applied for this project." IC shall understand that an Aramco contract does not necessarily mean that only Aramco standards shall be followed, especially if the legal document such as a contract mentions it clearly.\r\n2.	Keeping the above-said option to waive from standards in mind as mentioned in the IFB, the MOM attached by IC shows a generalised comment for guidance and not specific to the issue at hand. A project with multiple disciplines and interfaces has to have a base for standards, which is Aramco standards. IC shall avoid from creating a confusion where none exists. It also does not mean that SAPMT did not know as to why a deviation from Aramco standards was made in IFB for package substations. PMT had acquired a formal waiver internally already. As an example KAUST has been developed with only packaged substations in the past.\r\n3.	The IFC drawings were issued by IC in parts due to lack of coordination within IC; and were partly accepted via PMT letter # K&TPD/KRP&SFPD/SF/L-433/14 dated January 21, 2014. PMT acceptance of a submittal from IC does not relieve the contractor from its contractual obligations as mentioned in the IFB. It can be ascertained that IC deliberately tried to create a confusion by providing wrong technical specifications not concurring with the requirements of the contract.\r\n4.	The contract clearly mentions which standards are to be followed as mentioned in line 1 and IC is obligated to follow them.\r\n5.	IC has shown lack of technical know how by using wrong gauge cables with wrong type of equipment. Even though the terminology has varied in the IFB for the desired equipment, the intention has been clear that packaged substations are required. The same term "Packaged substations" has been used in the SCH – C against which IC has provided its rates during bidding. It is clearly mentioned in the IFB that, "3.1.3 In the event of any conflict between the provisions of this Construction Scope of Work and the CONTRACTOR Obligations as set forth in the Contract Documents, the Conditions of Contract shall govern.\r\n6.	The IFB also clearly mentions that, "2.2 Promptly after this Contract''s effective date, review and evaluate the SAUDI ARAMCO-provided Preliminary Design to ensure that it does not conflict with another drawing, specification or standard referenced in this Contract. IC is advised to read Contractor’s obligations in details as mentioned in the contract, before creating such confusions.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Pad Mounted, Transformer', 'Complete', '2014-04-21', 0, 25, 0, 27, 'L-687/14', '2014-04-21', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(971, 1000, 43, '\r\nThe Saudi Aramco Quality Assessment Unit conducted a quality assessment of the “KAUST-Perimeter Security Systemsâ€ project on 9th and 10th April 2014 and three (3) CARs were issued as attached. The CARs were explained to IC during the closing meeting and also intimated to IC earlier via email. IC is urged to resolve these CARs on or before July 16, 2014.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Quality Assessment, April 2014', 'Complete', '2014-04-21', 0, 25, 0, 26, 'L-686/14', '2014-04-21', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(972, 999, 43, 'SAPMT has reviewed the subject submittal dated April 16, 2014 and has no objection with the following comments:\r\n1.	Mr. Alfredo V. Pacheco Jr. is conditionally approved for One (1) month commence on first reporting date.\r\n2.	His acceptance is based on his previous Saudi Aramco approval in BI-25-00002-0006, KAUST Lab Fit Outs Project with reference # KAUSTTRNM/T-300/2013 dated February 13, 2013.\r\n3.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance and incapability.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'QC Manager', 'Complete', '2014-04-23', 0, 27, 0, 26, 'L-689/14', '2014-04-23', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(973, 1001, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(974, 1002, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0770, 0603, 0566 & 0532 dated 27th August 2014, 27th May 2014, 10th May 2014 & 20th April 2014 respectively and has the following comments:\r\n1.	Provide detailed quantities of all work items/ activities involved in the deletion of ditch from the scope of work and reworks if any etc., for both parties to agree, after which the processes for change order/ amendment can start.\r\n2.	Contact SAPMT to understand Saudi Aramco procedures if necessary.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Ditch Elemination', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1039/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(975, 1003, 43, 'SAPMT has reviewed the subject submittal dated April 19, 2014 and has no objection with the following comments:\r\n\r\n1.	SAPPCO is limited to Pipe Sizes ½" to 10â€.\r\n2.	Contractor shall comply with project specifications, SAES-L-105 for UPVC pipes and fittings selection.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Pipe, UPVC', 'Complete', '2014-04-23', 0, 25, 0, 27, 'L-700/14', '2014-04-23', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(976, 1004, 43, 'SAPMT has reviewed the subject submittal dated September 01, 2014 and has no objection. However, IC is urged to ensure that the following activities are reflected appropriately in the plan:\r\n1.	Civil works for package substation.\r\n2.	Radio Frequency Identification (RFID) system with activity ID CSF-1050 to 1080 shall be deleted. RFID is part of SACS system and must be included under activity SDF-1010.\r\n3.	Upgrading the existing guardhouse.\r\n4.	Demolition of existing turnstile.\r\n5.	The construction schedule of IDAS system (activity ID CSF-1000) must be adjusted according to the readiness of the security corridor KPSS wall and maintenance road schedule.\r\n6.	Construction schedule of Batteries, Chargers and UPS inside JFCC building.\r\n7.	Specify which activity Fire water/Portable water lines belong to.\r\n8.	Specify if holding tanks, oily tanks were included in the buildings.\r\n9.	Pavilion is missing in the procurement plan.\r\n10.	Include the MEP commissioning schedules.\r\n11.	Provide the Procurement, and Construction Schedule of Switchrack.\r\n12.	Provide the construction schedule of Generator buildings.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', '', 'Pending', '2014-11-02', 0, 87, 0, 46, 'L-1152/14', '2014-11-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(977, 1004, 43, 'SAPMT has reviewed the subject submittal dated September 01, 2014 and has no objection. However, IC is urged to ensure that the following activities are reflected appropriately in the plan:\r\n1.	Civil works for package substation.\r\n2.	Radio Frequency Identification (RFID) system with activity ID CSF-1050 to 1080 shall be deleted. RFID is part of SACS system and must be included under activity SDF-1010.\r\n3.	Upgrading the existing guardhouse.\r\n4.	Demolition of existing turnstile.\r\n5.	The construction schedule of IDAS system (activity ID CSF-1000) must be adjusted according to the readiness of the security corridor KPSS wall and maintenance road schedule.\r\n6.	Construction schedule of Batteries, Chargers and UPS inside JFCC building.\r\n7.	Specify which activity Fire water/Portable water lines belong to.\r\n8.	Specify if holding tanks, oily tanks were included in the buildings.\r\n9.	Pavilion is missing in the procurement plan.\r\n10.	Include the MEP commissioning schedules.\r\n11.	Provide the Procurement, and Construction Schedule of Switchrack.\r\n12.	Provide the construction schedule of Generator buildings.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', '', 'Complete', '2014-11-02', 0, -1, 0, -1, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(978, 1005, 43, 'SAPMT has reviewed the subject submittal dated April 20, 2014 and has no objection with the following comment:\r\n•	It has been observed that IC is removing various action items from the MOM without closing them, despite the fact that SAPMT has highlighted such instances during the meetings more than a few times. IC shall refrain from such practices in future.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'MOM, Progress Meeting', 'Complete', '2014-05-07', 0, 25, 0, 27, 'L-722/14', '2014-05-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(979, 1006, 43, 'For Information Only', 'Revised, Baseline, Schedule, Wiothdrawl', 'Complete', '2014-04-23', 0, 25, 0, -1, 'For Information Only', '2014-04-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(980, 1007, 43, 'SAPMT has reviewed the subject submittal dated April 21, 2014 and has no objection with the following comments:\r\n1.	IC shall ensure that the proposed light poles are of exact same dimensions, diameters, lengths, shape and style as the existing ones. In case of any shape variations from existing, IC shall be responsible for replacement.\r\n2.	Consider bringing a sample on site and installing as a mockup before delivering the complete quantity for verification.\r\n3.	The galvanizing process shall comply with ASTM standards and coatings shall be done by Saudi Aramco approved vendors.\r\n4.	Ensure that approved lighting fixtures and associated fittings are compatible with the poles.\r\n5.	Consider preparing a shop drawing showing details of all attachments, fixtures, fittings, foundations, anchor bolts, etc.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Lighting Poles', 'Complete', '2014-04-24', 0, 27, 0, 26, 'L-703/14', '2014-04-24', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(981, 1008, 43, 'SAPMT has reviewed the subject submittal dated April 21, 2014 and has the following comments:\r\n1.	The following QC Personnel are permanently approved for Precast Facility of “KAUST – Perimeter Security Systemsâ€ project BI-25-00026-0001;\r\na.	Mr. Farrukh Naveed Khan\r\nb.	Mr. Shaik Abdul Hameed\r\nc.	Mr. Jerry A. Paga\r\n2.	SAPMT reserves the right to revoke this approval based on their unsatisfactory/poor performance.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393. \r\n', 'QC Inspectors, Precast Facility', 'Complete', '2014-05-10', 0, 27, 0, 26, 'L-720/14', '2014-05-08', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(982, 1009, 43, 'The L-704 was drafted and hold by Mr. Fahad Al-Balawi, to wait for suitable time to discuss this matter.', '', 'Complete', '2014-09-21', 0, 25, 0, -1, 'For Information Only', '2014-04-24', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(983, 1010, 43, 'SAPMT recommends using SEC-2 instead of Sub-Station # 4 as the source for the KPSS project power requirements for the following reasons;\r\n1.	Substation 4 is not ready and thus studies required for KPSS power design may be delayed.\r\n2.	SEC-2 is only 200 meters away from the KPSS Generator building where as SS4 is about 1600 meters away.\r\n3.	Running the power cable to SS4 shall require various road crossings and putting at risk other utilities in an already congested areas, where as connecting to SEC-2 avoids any road crossings and delays.\r\nBased on the above, feeder breakers number 8 and 19 of SEC main substation (which is under construction) shall be reserved for the KPSS project. Enclosed in this letter are Building locations of Generator Building, Substation # 4 and New SEC-2 Building, and new SEC-2 switchgear breaker assignment for your reference.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'reservation, Feeder Breaker', 'Complete', '2014-04-27', 0, 25, 0, 26, 'L-602/14', '2014-04-27', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(984, 1011, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(986, 1013, 43, 'SAPMT has reviewed the subject submittal dated April 23, 2014 and has the following comments:\r\n1.	Revise the General notes applicable to the drawing.\r\n2.	Revise the elevation ensuring the duct bank to the minimum depth requirement by Aramco standard.\r\n3.	Coordinate with the interface contractor to ensure which pipe sleeve belongs to which contractor, and mark explicitly on the drawings and acquire concurrence from all parties.\r\n4.	Show all dimensions of the ducts.\r\n5.	Provide more details and reasons for soil improvement.\r\n6.	Revise hook lengths for re-bars\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Duct Bank', 'Complete', '2014-04-29', 0, 25, 0, 27, 'L-709/14', '2014-04-29', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(987, 1014, 43, 'SAPMT has reviewed the subject submittal dated April 23, 2014 and has no objection with the following comments:\r\n1.	The correct 9com for subject material is 6000013097.\r\n2.	Contractor shall use the correct 9com with the correct description of materials.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Fiber Optic Cable, FOC, Patch Panel', 'Complete', '2014-05-01', 0, 27, 0, 26, 'L-707/14', '2014-05-01', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(988, 1015, 43, 'SAPMT has reviewed the subject submittal dated April 24, 2014 and has no objection with the following comments: \r\n\r\nB.I	Transmittal Type	Transmittal Ref. #	IL no. 	Description	9COM	Level Of Inspection	Status\r\n25-00026	IAP	IAP-002	107000096404	Fiber Optic Cable	6000001216	2	Approved with Comments \r\n1.	ITP shall be finalized during the PIM.\r\n2.	Confirm that contractor PO is JDH/104/226 prior to PIM.\r\n3.	Considering the large quantity involved, IC is urged to prepare proper handling and storage system according to Saudi Aramco standards.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'FOC, IAP, Fiber Optic Cable', 'Complete', '2014-04-29', 0, 27, 0, 26, 'L-708/14', '2014-04-30', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(989, 1016, 43, 'Cancelled by Mr. Fahad A. Al-Balawi.', 'Construction Manager', 'Complete', '2014-09-21', 0, 25, 0, -1, 'For Information Only', '2014-06-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(990, 1017, 43, 'SAPMT has reviewed the subject submittal dated April 24, 2014 and has no objection with the following comments:\r\n1.	Ensure that the lights are installed at appropriate heights and at appropriate distances maintaining the required lux according to standards and according to SAPMT Letter no. K&TPD/KRP&SFPD/SF/L-595/14 dated March 27, 2014.\r\n2.	Ensure the colour/ finish for the lighting fixture matches with the light pole.\r\n3.	While the lighting fixture is acceptable, provide a lighting fixture sample along with the pole and fixtures/ fittings to analyse the arrangement and installation.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Lighting Fixtures', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-734/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(991, 1018, 43, 'SAPMT has reviewed the subject submittal dated April 22, 2014 and has no objection with the following comments:\r\n1.	Submit specifications for the PVC cement/solvent to be used to connect the conduits.\r\n2.	Only 4â€ PVC type DB-120 TC-8 shall be used for communications. Ensure ¼â€ɸ fish-line rope to be installed on all PVC ducts.\r\n3.	Consider providing details of other materials required for duct bank installation such as warning tapes and marker system.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'PVC Conduits', 'Complete', '2014-05-07', 0, 25, 0, 27, 'L-723/14', '2014-05-07', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(992, 1019, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(993, 1020, 43, 'SAPMT has reviewed the subject submittal dated April 26, 2014 and has no objection with the following comments:\r\n1.	IC is urged to prepare shop drawings considering the constructability at site in prevailing site conditions.\r\n2.	The number of manpower and equipment to be deployed for work and the start times and finish times required to complete the work shall be mentioned in the method statement and mentioned resources shall be made available on site before the start of work.\r\n3.	The method statement shall be prepared in such a way that it is self-explanatory to the construction team on site.\r\n4.	IC is responsible for ensuring that the materials and methods chosen to fill the trial pits are adequate and do not create depressions with the passage of time on the road surface.\r\n5.	Consider using well graded crush stone (lesser than 75mm) to fill the pits.\r\n6.	Geo-grid and/or geo-textile shall be laid to match the existing geo-grid and/or geo-textile at similar depths without damaging the existing.\r\n7.	Provide the final Geo-technical Investigation report after review and approval by CSD as per SAES-A-113, Para 5.4.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Trial Pit,Backfilling', 'Complete', '2014-04-30', 0, 25, 0, 27, 'L-712/14', '2014-04-30', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(994, 1021, 43, 'For Information only', 'Boat Identification', 'Complete', '2014-05-07', 0, 25, 0, -1, 'For Information Only', '2014-05-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(995, 1022, 43, 'Para 2.4 (INTERFACE WITH OTHER PROJECTS) clearly mentions that the project has interfaces with the following projects:\r\n1.	Flood Control Channels under BI-25-00012.\r\n2.	New sub-station under BI-25-00012.\r\n3.	King Abdullah Monument under BI-25-00021-00003\r\n4.	New MOT Road IC is urged to refer to the contract para 3.9 for interfaces.\r\nSAPMT assessments are given below;\r\na.	Referring to 1.1.17, SAPMT is of the view that IC has failed to employ an interface manager, a key position, which is necessary to mark and manage the interfaces. The person designated by IC to act as Interface Coordinator does not even know the names of liaison officers for interfaces with other projects. He has not delivered interface drawings to other contractors for flood control as noticed in a site meeting with NBH coordinator on April 28, 2014. Also the said interface coordinator has been absent from site many times when SAPMT required to meet with him.\r\nb.	Referring to 3.5, CONTRACTOR shall verify, amplify and correct the preliminary design including but not limited to, investigation of “interface pointsâ€ between said preliminary design and any existing plant facilities not included in the preliminary design, complete the documents and drawings and provide all necessary materials and equipment necessary for the FACILITIES to perform in full compliance with the Job Specification. IC has failed to provide shop drawings for the interface points. IC does not have enough equipment/ materials / stock piles on site to perform the backfilling work. The delays and inspection issues arising on daily basis on KAM access road regarding shortage of materials and quality of work are a clear example of inability of IC to start any other work on any other location.\r\nc.	The excavations for precast wall work are being delayed due to lack of manpower and equipment and prompt payments to earthworks subcontractors.\r\nd.	The reports for geotechnical studies for one of the interface points are pending.\r\ne.	IC does not have enough resources to carry on simultaneous work. While concentrating on KAM road, backfilling for buildings has taken 6 months on security gates.\r\nf.	Referring to 3.9.4, 3.9.4 CONTRACTOR shall develop interface drawings in sufficient detail to define the method and location of interfaces of the WORK and the work performed by SAUDI ARAMCO and /or Other Contractors. IC has failed to provide such drawings to SAPMT or the interface contraction.\r\ng.	The interdependency schedule according to para 3.10.1 has not been provided by IC.\r\nh.	SAPMT has requested IC to convene interface meetings according to para 3.10.4 at various occasions and IC had not been able to do so, because IC is not ready to start the work as shop drawings have not been prepared yet.\r\ni.	IC is continuously delaying other contractor’s work in the area, such as utilities corridor for KAM project, due to non-payments to its subcontractors and issues with quality of work.\r\nj.	Para 3.10.5 requires the Contractor to host meetings. IC shall not breach from the requirement of the contract by saying that IC is not bound to do so.\r\nk.	Para 3.10.6 requires the Contractor communicate directly with Other Contractors to review technical issues and exchange technical data related to interfaces and to reach mutual agreement on dates for interfaces. IC shall not breach from the requirement of the contract by saying that IC is not bound to do so.\r\nContractors notice to claim has no basis and is rejected as SAPMT believes that IC is not ready to complete work on interface points, because the shop drawings and studies are not prepared by IC, adequate staff/ equipment has not been employed and interface meetings have not been conducted as required by the contract and as a matter of fact IC is delaying other contractors at some of the interface points.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Back filling, Concrete Slab', 'Complete', '2014-05-07', 0, 25, 0, 27, 'L-710/14', '2014-05-07', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(996, 1023, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0544 dated April 26, 2014 and has the following comments:\r\n\r\n1.	The following HSE Officers are permanently approved for “KAUST – Perimeter Security Systemsâ€ project BI-25-00026-0001;\r\na.	Mr. Muhammad Farook Shah\r\nb.	Mr. Smruti Prakash Mallick\r\n2.	SAPMT reserves the right to revoke this permanent approval based on misconduct or negligence in performing their duties during project tenure. \r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'HSE Officers', 'Complete', '2014-05-10', 0, 27, 0, 26, 'L-740/14', '2014-05-08', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(997, 1024, 43, 'SAPMT has reviewed the subject submittal dated April 26, 2014 and has no objection with the following comments:\r\n1.	Protective devices and controls shall comply with Appendix A of 16-SAMSS-504 for the list of approved manufacturer and model with its corresponding ANSI function number that will be used in the proposed 13.8KV Switchgear at Generator Building.\r\n2.	Comply with all the required protection for Generator as per SAES-P-114, paragraph 6.0 in the breaker compartment of Emergency Generator.\r\n3.	Provide all the required vendor drawings such as Single Line Diagram, Three Line Diagram, set up 13.8KV Switchgear with corresponding dimensions of each compartment, mounting details and accomplished Data Schedule in the NMR-601 submittal.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Switchgear', 'Complete', '2014-04-30', 0, 25, 0, 27, 'L-714/14', '2014-04-30', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(998, 1025, 43, 'SAPMT   has   reviewed the  subject submittal dated  April 27,  2014 and  has  the  following  comments:\r\n1.	IC is urged to expedite responses to SAPMT comments instead of delaying for more than a month as seen in the subject case.\r\n2.	Include all related shop drawings in the submittal including the revised lifting hook arrangement.\r\n3.	Chipping depth shall be according to the manufacturer’s recommendations.\r\n4.	Provide more details about ice blocks and shelters etc. to maintain the mixing water temperature according to manufacturer’s recommendations.\r\n5.	The compressive strength of materials for concrete repair material shall match with the compressive strength of the concrete as per SAER 5803.\r\n6.	Change the subject with Method Statement for Concrete Defects Repair of Precast Concrete Elements.\r\n7.	Include in the Method Statement the repair procedure for concrete stains of Precast Wall Panel, Column and Column Cap.\r\n8.	In Item 1 – Include footing after column cap. Change the footing neck with column pedestal.\r\n9.	Include QC Civil Supervisor’s responsibility.\r\n10.	Use approved concrete repair materials with SAPMT letter Ref. # K&TPD/KRP&SFPD/SF/L-215/13 dated September 17, 2013.\r\n11.	All sketches/exhibits must have a drawing log number and concurred by the designer.\r\n12.	Discuss the Method Statement with SAPMT before submitting again.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Concrete Repair', 'Complete', '2014-04-30', 0, 25, 0, 27, 'L-713/14', '2014-04-30', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(999, 1026, 43, 'For Information Only.', 'Progress Meeting, 31', 'Complete', '2014-04-30', 0, 25, 0, -1, 'For Information Only', '2014-04-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1000, 1027, 43, 'For Information Only', 'Progress Report, 34', 'Complete', '2014-04-30', 0, 25, 0, -1, 'For Information Only', '2014-04-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1001, 1028, 43, 'For Information Only', 'Progress Report, 33', 'Complete', '2014-04-30', 0, 25, 0, -1, 'For Information Only', '2014-04-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1002, 1029, 43, 'SAPMT has reviewed the subject submittal dated April 27, 2014 and has no objection with the following comments:\r\n1.	Provide the switch rack dimension and panel arrangement shop drawings.\r\n2.	All breakers shall pass the required testing procedure and commissioning requirements as per Saudi Aramco Pre-Commissioning form P -030 for moulded case circuit breakers.\r\n3.	Switch rack Lighting fixtures and receptacle outlets shall be outdoor type.\r\n4.	Ensure that switch rack structure will meet ANSI requirements for hot dip galvanization.\r\n5.	Ensure that all panel enclosure will meet SAES P-104 and 16-SAMSS-512\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Switch Rack', 'Complete', '2014-04-30', 0, 25, 0, 27, 'L-715/14', '2014-04-30', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1003, 1030, 43, 'SAPMT has reviewed the subject submittal dated April 27, 2014 and has no objection with the comments/ conditions given in the attached letter no. KAUPIS/L-033/2014 dated October 02, 2014.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at (012) 422-4423.\r\n', 'ICC Batching Plant, Mix Designs', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1088/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1004, 1034, 43, 'The change in the power source of the project from Substation Number 4 to SEC Substation Number 2 is a variation from the scope of work as per IFB drawing PA-000087-001. IC’s request to consider such a change as an outcome of an adequate and safe design is rejected.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Substation, Variation', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-711/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1005, 1032, 43, 'SAPMT has reviewed the subject submittal dated April 28, 2014 and has no objection.\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status	Comments\r\n25-00026	RP	RP-009	Medium Voltage Cable 	6000000797	1	Approved 	 \r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'MV, Cable', 'Complete', '2014-05-10', 0, 27, 0, 26, 'L-730/14', '2014-05-08', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(1006, 1033, 43, 'SAPMT has reviewed the subject submittal dated April 29, 2014 and has no objection with the following comments:\r\n•	Ensure that the proposed 8 core FOC fits through the cable entrance of the proposed fiber patch panel.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'FEC, Patch Panel', 'Complete', '2014-05-01', 0, 25, 0, 27, 'L-717/14', '2014-05-01', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1007, 1031, 43, 'SAPMT has reviewed the subject submittal dated April 27, 2014 and has the following comments:\r\n1.	The first subcontracting Plan was submitted by IC in April 2013, and since then at least 8 submissions have been made by IC but the current submittal still mentions that it is revision 2 with a rev code E.\r\n2.	Names and Contact details of the primary points of contact nominated from both parties for any subcontract shall be provided.\r\n3.	IC shall expedite the approval process of Subcontractor names mentioned but not approved.\r\n4.	In a separate submittal provide the list of manpower with their CVs and equipment proposed for completion of MEP works which are to be done by IC.\r\n5.	Testing and commissioning of electrical equipments such as but not limited to LV panel boards, Switch racks, Switchgears, Package Substations, HVAC Air Balancing, shall be executed by an approved third party.\r\n6.	The work order for building works shall include the names of buildings and extent of external works around the buildings.\r\n7.	Suggest name of the contractor nominated for building finishes, fenestration and hard and soft landscaping around buildings.\r\n8.	Suggest name of contractor nominated for patrol roads, chain-link fencing, metal works/ steel structures etc.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Subcontracting Plan', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-725/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1008, 1035, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0549 dated April 29, 2014 and has rejected with the following comments:\r\n1.	IC is urged to revise the quantities in light of the para 1.2.2.1.17, where it is mentioned that Scope of work includes "Provision of irrigation lines for the road median for Palm trees AND landscaped areas on BOTH SIDES of sidewalk areas. Interface shall be made with BI-25-00021-003 for exact location of non-electric utilities in the detailed design phase".\r\n2.	The items shall be measured according to the matching items and units used in SCH-C taking in to account the inclusions and exclusions.\r\n3.	Complete all the requirements mentioned in SAPMT letter no. K&TPD/KRP&SFPD/SF/L-682/14 dated April 17, 2014 especially related to the approval of nature of trees, poles and lighting fixtures.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'KAM Road, Quantity Difference', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-737/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1009, 1036, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0548 dated April 29, 2014 and has the following comment:\r\n•	Attach agreed upon quantities of work done.\r\nShould you have any questions, please contact Sohail Moughla, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Ditch Backfilling', 'Complete', '2014-05-17', 0, 25, 0, 27, 'L-501/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1010, 1037, 43, 'SAPMT has reviewed the subject submittal dated May 01, 2014 and has the following comment:\r\n1.	Attach calculations for lifting hooks.\r\n2.	Provide details about block-outs and materials to be used for creating block outs.\r\n3.	Provide a revised method statement explaining the schedule/ fixing of lifting hook re-bars, cutting of lifting hooks, grouting method, epoxy touch-ups etc.\r\n4.	The title of the shop drawing is inaccurate and should provide specific info about the shop drawing, such as "Details of Lifting Hook for K12 Footing"\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n \r\n', 'Footing, K12', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-728/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1011, 1038, 43, 'SAPMT has reviewed the subject submittal dated April 29, 2014 and has no objection with the following comments:\r\n1.	Arabian Company for Water Pipe Industry is limited to 1" - 160" for use at ambient temperatures.\r\n2.	Ensure that pipe is installed with adequate earth cover according to the manufacturer’s recommendations.\r\n3.	Installation shall be done according to the instructions provided by the manufacturer.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'FRP Pipe', 'Complete', '2014-05-01', 0, 25, 0, 27, 'L-716/14', '2014-05-01', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1012, 1039, 43, 'The approved project proposal includes trees on the median and sidewalks and landscaping on both sides of KAM access Road as shown in Dwg KA714497-001. SAPMT suggests that KAM road be enhanced as a multi-purpose scenic route by introducing dedicated bicycle and pedestrian/ jogging tracks on either side of the KAM road. 3D visualizations are attached for KAUST concurrence.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Sidewalk, Landscaping', 'Complete', '2014-05-24', 0, 25, 0, 26, 'L-718/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1013, 1040, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0552 dated April 30, 2014 and has rejected with the following comment:\r\n•	KAUST has 4 colour logo and placement of logo on the wall is shown on the drawings. Colors have their significance on a logo and without colours it cannot be considered a trademark. IC is urged to attach all related documentation/references to prove otherwise.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Paint, Precast Fence', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-736/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1014, 1041, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0551dated April 30, 2014 and has the following comments:\r\n1.	IC is urged to submit quantities using Aramco approved formats.\r\n2.	If any activities are not mentioned in Schedule-C then quantities of materials, manpower and equipment required to complete the activity shall be provided.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Concrete Ditch Quantity', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1040/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1015, 1042, 43, 'SAPMT has reviewed the subject submittal dated April 29, 2014 and has the following comments: \r\n1.	Propose the approved manufacturer for batteries for 9com # 6000000951 and 6000001075 in the submittal sheet.\r\n2.	All the inspectable items shall be procured through an approved manufacturer.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'UPS, Batteries', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-729/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1016, 1043, 43, 'SAPMT has reviewed the subject submittal dated April 28, 2014 and has rejected with the following comments:\r\n1.	York Johnson is not an approved manufacturer for ACU.\r\n2.	There is one Saudi Aramco approved manufacturer for this specific material; i.e. 30006889 PETRA ENGINEERING INDUSTRIES (Jeddah) with a condition that "units shall be certified at manufacturing facility to comply with UL-1203 & UL-1995 by an approved 3rd party".\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Air Conditioning Uint', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-739/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1017, 1044, 43, 'SAPMT has reviewed the subject submittal dated May 01, 2014 and has no objection with the following comment:\r\n•	The source has been changed from SS4 as mentioned in IFB Dwg No. PA-000087-001 to the nearer location of SECS/S2. IC is urged to provide detailed quantities of the difference in routes and associated works between IFB Dwg No. PA-000087-001 and the revised IFC Dwg No. VA-846512-002-0F2.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'IFC Electrical, One Line Diagram', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-726/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1018, 1047, 43, 'For Information Only', 'Company Representative', 'Complete', '2014-05-05', 0, 25, 0, -1, 'For Information Only', '2014-05-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1019, 1048, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0557 dated May 01, 2014 and decided to revoke the approval of Mr. Yasir Ashraf. IC shall appoint a new “QC Managerâ€ without further delay.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'QC Manager', 'Complete', '2014-05-13', 0, 27, 0, 26, 'L-731/14', '2014-05-13', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(1020, 1049, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0554 dated April 30, 2014 and has the following comments:\r\n1.	Mr. Muhammad Imran Ali is permanently approved for the position of “QC Inspector (Sub-contractor)â€ based on his performance.\r\n2.	SAPMT reserves the right to revoke this permanent approval if found to be incompetent and ineffective during project tenure.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'QC Inspector', 'Complete', '2014-05-10', 0, 27, 0, 26, 'L-733/14', '2014-05-08', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(1021, 1050, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0553 dated April 30, 2014 and has the following comments:\r\n1.	The conditional approval of Mr. Qazi Muhammad Arif as “QC Supervisor – Civilâ€ is extended for another three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval extension based on his unsatisfactory performance.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'QC Supervisor', 'Complete', '2014-05-10', 0, 27, 0, 26, 'L-732/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1022, 1051, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0555 dated April 30, 2014 and has no objection with the following comments:\r\n1.	IC shall ensure that even if a materials source is approved, the conditions under which it is approved are strictly implemented.\r\n2.	Unfiltered/ unscreened materials shall not be acceptable and shall not be delivered to site.\r\n3.	All materials entering the site shall be monitored by IC QC personnel as per design requirements and as per agreed upon delivery/ acceptance methods to control quality of work.\r\n4.	A similar violation if repeated shall be escalated as per SAEP-381.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Logbook Entry, 76', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-727/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1023, 1052, 43, 'SAPMT has reviewed the subject submittal dated May 01, 2014 and has the following comments:\r\n1.	IC is urged to find all superseded drawings and destroy them or stamp them as "superseded".\r\n2.	IC shall consider conducting a quick topographic survey between 1+900 to 4+00 for the width "from seaside to the outer edge of KAM utilties" and send to the designer to ensure that the design is done according to the prevailing conditions after removal of road surfaces and backfilling in certain previously depressed areas.\r\n3.	Provide details about the irrigation network.\r\n4.	Show all culvert crossings, conduit banks, pits, duct banks in compliance with KA-714494-001 and KA-714490-002.\r\n5.	Show valve boxes being installed by others along the KAM road, to finalise the landscaping design.\r\n6.	Ensure minimum covers are provided from the finished grade level for all utilities for traffic or non-traffic areas.\r\n7.	Provide a complete set for SAPMT review and to be shared with the proponent according to existing practices.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'IFC, KAM', 'Complete', '2014-05-17', 0, 25, 0, 27, 'L-743/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1024, 1053, 43, 'SAPMT has reviewed the subject submittal dated April 30, 2014 and has no objection with the following comment:\r\n•	Use the recommended SFP Fibre modules manufactured by the ADDER.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570\r\n', 'DVI, Converter', 'Complete', '2014-05-07', 0, 25, 0, 27, 'L-724/14', '2014-05-07', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1025, 1054, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1026, 1055, 43, 'SAPMT has reviewed the subject submittal dated May 03, 2014 and has the following comments:\r\n1.	Mr. Mohammed Izzeldeen Ajeeb Alameen is conditionally approved as “Project Coordinatorâ€ to liaison between the designer and site construction activities for three (3) months with the following specific tasks;\r\na.	Review and interpret Project Engineering drawings and specifications for scope and constructability and provide feedback to the Designer, Engineering Manager and Construction Manager for rectifications and shop drawings.\r\nb.	Ensure that Saudi Aramco standards, Engineering codes and project specifications are reflected in design drawings/ shop drawings according to the Scope of Work.\r\nc.	Coordination with other disciplines and interface coordinator.\r\nd.	Archive design/engineering related information in a professional manner and maintain drafting standards according to Saudi Aramco requirements.\r\n2.	IC shall ensure that the candidate shall be presented again for re-evaluation.\r\n3.	SAPMT reserves the right to revoke this conditional approval based on his poor/ unsatisfactory performance.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Project Coordinator', 'Complete', '2014-05-17', 0, 27, 0, 26, 'L-746/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1027, 1056, 43, 'No Comments, For Information Only', 'Progress Report, 33', 'Complete', '2014-05-11', 0, 25, 0, -1, 'For Information Only', '2014-05-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1028, 1057, 43, 'SAPMT has reviewed the subject submittal dated May 04, 2014 and has no objection with the comments given in the attached letter no. KAUPIS/L-016/2014 dated July 02, 2014.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Concrete Mix Design', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-896/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1029, 1058, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0562 dated May 05, 2014 and has the following comments:\r\n1.	IC is urged to implement the operational emergency preparedness procedures according to Aramco Safety Standards in case of hazardous working conditions during low visibility, high temperatures, high winds or hazardous gases etc.\r\n2.	It has been noticed that site workers are not being directed to safe places during hazardous working conditions. Moreover, sufficient sanitation facilities for site workers are not provided on site, despite numerous instructions during weekly meetings.\r\n3.	Only work at heights or crane operations etc. shall be stopped when wind speeds exceed the limits set by the Aramco Construction Safety Manual.\r\n4.	Relevant data like the Anemometer readings etc. shall be attached with the reports about bad weather conditions on site.\r\n5.	Reports about bad weather conditions shall include the nature and location of jobs to be stopped and number of personnel affected.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Bad Weather, Sand Storm', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-735/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1030, 1059, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1031, 1060, 43, 'Report is rectified as desired and resubmitted as acceptable by PMT.', '', 'Complete', '2014-09-21', 0, 25, 0, -1, 'For Information Only', '2014-07-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1032, 1061, 43, 'SAPMT has reviewed the subject submittal dated April 28, 2014 and has no objection with the following comment:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	RP	RP-010	RTR Pipe and Fittings	6000013160	2	Approved with Comments \r\n\r\n•	The Correct 175 Form is IR-012300.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'RTR Pipe, Fitting', 'Complete', '2014-05-17', 0, 27, 0, 26, 'L-747/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1033, 1062, 43, 'For information Only', 'Bad Weather', 'Complete', '2014-05-13', 0, 25, 0, -1, 'For Information Only', '2014-05-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1034, 1063, 43, 'For Information Only', 'Management Report, April', 'Complete', '2014-05-24', 0, 25, 0, -1, 'For Information Only', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1035, 1064, 43, 'SAPMT has reviewed the subject submittal dated May 05, 2014 and has the following comments:\r\n1.	Mr. Hafeez-Ur-Rehman Chohan is conditionally approved as “Environmental Officerâ€ for Three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his poor/ unsatisfactory performance.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Environmental Officer', 'Complete', '2014-05-17', 0, 27, 0, 26, 'L-745/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1036, 1065, 43, 'SAPMT has reviewed the subject submittal dated May 04, 2014 and has no objection with the following comments:\r\n1.	The observations mentioned in the reports shall be immediately rectified under the guidance of SAPMT Safety Engineer.\r\n2.	Weekly inspections shall be conducted by IC Safety Staff and any observations/ violations shall be entered in the register. Entries in the register shall be closed with the concurrence of SAPMT Safety Engineer.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Camp Inspection, April 2014', 'Complete', '2014-05-17', 0, 25, 0, 27, 'L-749/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1037, 1066, 43, 'SAPMT has reviewed the subject submittal dated May 05, 2014 and has no objection with the following comments:\r\n1.	Ensure that finishes and thicknesses of aluminum frame and extrusions are according to VE 846472, Section 8460 and 8810.\r\n2.	Powder coated finishes are specified and Wall thickness shall be 3mm as per specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Automatic Sliding Door', 'Complete', '2014-05-10', 0, 25, 0, 27, 'L-741/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1038, 1067, 43, 'SAPMT has reviewed the subject submittal dated May 03, 2014 and has no objection with the following comments:\r\n1.	Work shall be done according to Scope of work document PE000002 section 1.2.2.1.17.1 para f and g, where irrigation lines are to be provided at the median and both sides of the KAM Access Road.\r\n2.	Detailed design for the irrigation systems for KAM access Road shall be submitted by 15 May 2014.\r\n3.	The flow lines, branch lines, power cables, control cables, inspection pits, valve boxes  shall be marked on ground by 20 May 2014.\r\n4.	A list of resources available for the subcontract shall be provided by 15 May 2014.\r\n5.	A schedule of works in accordance with the KAM tracking sheets being followed by IC shall be provided by 15 May 2014.\r\n6.	New irrigation control system shall be compatible with existing KAUST irrigation system (which isâ€ Rain Birdâ€ make).\r\n7.	Provide details of connecting new system with existing Irrigation central control station.\r\n8.	Provide all technical submittals before 20 May 2014.\r\n9.	CVs of contractor’s key/ technical personnel shall be submitted for SAPMT approval by 15 May 2014.\r\n10.	A copy of the unpriced subcontract showing the agreed upon scope of work in the subcontract shall be provided by 10 May 2014.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Landscaping, Saudi Leelas', 'Complete', '2014-05-10', 0, 27, 0, 26, 'L-738/14', '2014-05-08', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1039, 1068, 43, 'For Information Only', 'Progress Report, 09, April', 'Complete', '2014-05-24', 0, 25, 0, -1, 'For Information Only', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1040, 1069, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0560 dated May 08, 2014 and has no objection with the following comment:\r\n•	The report from TTI has been reviewed by SAPMT for reference only, and IC is urged to prepare the site, backfill, cast concrete and install precast members exactly according to the method followed by TTI.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Crash Test Final Report', 'Complete', '2014-05-24', 0, 27, 0, 26, 'L-769/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1041, 1070, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0561 dated May 08, 2014 and has the following comments:\r\n1.	IC can use the steel reinforcements brought to site only after it has been inspected and approved by Saudi Aramco according to applicable standards.\r\n2.	Steel shall be stored, handled, fabricated or re-fabricated in such a way that the epoxy coating is not damaged. Any damages to epoxy shall be retouched with approved coatings.\r\n3.	According to SCH-C, steel is included in the unit prices for the reinforced concrete and can be considered as work done only when the reinforced concrete has been poured according to specifications.\r\n4.	Nevertheless accepting the fact that IC procured pre-cut or pre-bent steel in order to meet the schedule requirements and to expedite work, re-fabrication of steel might ensue some wastage. IC shall provide details of the following for SAPMT review;\r\na.	Complete verified documentation of steel procured and brought to site.\r\nb.	Quantity of Steel that has been poured with reinforced concrete.\r\nc.	Quantity of steel that has been installed but not poured.\r\nd.	Physical Site verification of weight of available steel as compared to calculations based on invoices and estimates.\r\ne.	Agreed upon percentage of wastage for re-fabricating available steel.\r\nf.	Areas/buildings where the steel will be used with required quantities.\r\nShould you have any questions, please contract Sohail Moughal, Project Engineer on Tel. No. +966 12 422 4570.\r\n', 'Ditch Steel', 'Complete', '2014-05-17', 0, 25, 0, 27, 'L-405/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1042, 1071, 43, 'For Information Only', 'Progress Meeting', 'Complete', '2014-05-24', 0, 25, 0, -1, 'For Information Only', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1043, 1072, 43, 'SAPMT has reviewed the subject submittal dated May 08, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Saudization, April 2014', 'Complete', '2014-05-17', 0, 27, 0, 26, 'L-748/14', '2014-05-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1044, 1073, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1045, 1074, 43, 'SAMPT has reviewed your subject Invoice No. 12 dated May 8, 2014 and has the following comments:\r\n1.	Item 1.2.4-20, 60, 70 and 90 - Purchase Orders for MV cables, UPS, lighting poles and Fibre Optic Cables, without any quantities stated, are not considered as valid Purchase Orders. ICC’s claims for these items are therefore rejected.\r\n2.	Item 1.2.4-80 - “Miscellaneous Electrical Itemsâ€ is not considered as Major Material and hence does not qualify for the 10% material advance payment.\r\nICC is required to revise the invoice based on the above comments and re-submit immediately for approval.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n \r\n', 'Payment Application, 12', 'Complete', '2014-05-17', 0, 25, 0, 27, 'L-750/14', '2014-05-17', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1046, 1075, 43, 'SAPMT has reviewed the subject submittal dated May 10, 2014 and has the following comments:\r\n1.	Attach data sheets for all approved materials like grouts/ curing compounds etc., manufacturer’s recommendations specific to the application and calculations to show desired results.\r\n2.	Attach concrete repair matrix showing types of deformities, repair procedure, products to be used, acceptable level of deformities and location where repairs shall be done.\r\n3.	Provide more details about grouting between the column and foundations at the pocket joint and acquire concurrence from the project designer, ensuring that no changes are made to the design or methods as were followed by the crash testing agency.\r\n4.	Show/ attach relevant references to IFC and Shop drawings if any.\r\n5.	The approved Texas A&M Transportation Institute conducted the tests as per ASTM F2656-07 and the methods followed by the crash testing agency to construct the precast wall shall be strictly followed.\r\n6.	Consider amending the construction specifications to show the desired stripping/ de-moulding times and procedures.\r\n7.	Consider merging all scattered information about precast concrete wall into one submittal e.g. backfilling, erection, repair etc.\r\n8.	Work can carry on if the above comments are fulfilled.\r\n9.	Consider revising the Method statement by adding required information.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n \r\n', 'Fence, ITP, Checklist', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-764/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1047, 1076, 43, '', '', 'Complete', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1048, 1077, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0770, 0603, 0566 & 0532 dated 27th August 2014, 27th May 2014, 10th May 2014 & 20th April 2014 respectively and has the following comments:\r\n1.	Provide detailed quantities of all work items/ activities involved in the deletion of ditch from the scope of work and reworks if any etc., for both parties to agree, after which the processes for change order/ amendment can start.\r\n2.	Contact SAPMT to understand Saudi Aramco procedures if necessary.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Ditch Elemination', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1039/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1049, 1085, 43, 'ICC is urged to accelerate the production of precast elements by implementing appropriate means and methods as the rate of production and installation is falling behind the desired rate. IC is requested to reply with steps that shall be taken by IC to expedite the above said works.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Precast Elements, Production', 'Complete', '2014-05-17', 0, 25, 0, 27, 'L-485/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1050, 1095, 43, 'KAUST is urged to review the revised location of Guard House at Wadi Wesami. Flood Control Project’ has objected to the IFC location of Guard House as it causes obstruction to the flow. The IFC and a sketch for the revised location is attached for KAUST concurrence.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.\r\n', 'Wadi Wesami, Guard House, Location', 'Complete', '2014-05-17', 0, 27, 0, 26, 'L-751/14', '2014-05-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1051, 1089, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0577 dated May 12, 2014 and has the following comments:\r\n1.	SAPMT is agreed for Mr. Abdul Rasheed to act as QC Manager temporarily.\r\n2.	IC shall provide agreed actual date of new “QC Managerâ€ appointment according to Schedule-Q attachment-I and SAEP-381 respectively.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'QA/QC Manager', 'Complete', '2014-05-24', 0, 27, 0, 26, 'L-757/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1052, 1093, 43, 'SAPMT has reviewed the subject submittal dated May 11, 2014 and has the following comments:\r\n1.	Mr. Yasir Ashraf is approved for the position of “Mechanical QC Supervisorâ€.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory/ poor performance.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n \r\n', 'Mechanical QC Supervisor', 'Complete', '2014-05-25', 0, 27, 0, 26, 'L-758/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1053, 1078, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1054, 1079, 43, 'SAPMT has reviewed the subject submittal dated May 06, 2014 and has no objection with the following comments:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	RP	RP-012	FRP Pipe & Fittings	6000000020	0	Approved with Comments \r\n\r\n1.	9com 6000000020; sizes between 1"- 160" are approved for use at ambient temperature. Other sizes are not approved.\r\n2.	The Level is reduced to zero as the low severity of application.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'FRP Pipe, Fitting', 'Complete', '2014-05-17', 0, 27, 0, 26, 'L-753/14', '2014-05-17', 0, '', '', '', '', 'R-19');
INSERT INTO `submittal` VALUES(1055, 1080, 43, 'SAPMT has reviewed the subject submittal dated May 10, 2014 and has the following comments:\r\n1.	Use the correct 9com 6000000031 for UPVC Pipes.\r\n2.	It has inspection level 0 (zero) and shall be procured through Saudi Aramco approved manufacturer.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'UPVC Pipes', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-760/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1056, 1081, 43, 'For Information Only', '3D Side Walk', 'Complete', '2014-05-17', 0, 25, 0, -1, 'For Information Only', '2014-05-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1057, 1082, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0569 dated May 11, 2014 and has the following comments:\r\n1.	SAPMT has already sent a letter to NAVY (copy attached) to request an expedited solution.\r\n2.	IC is urged to coordinate for this interface and keep all parties informed about the status, as it has been observed that the transformer and the main Naval gate has already been decommissioned.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Removal Existing Utilities', 'Complete', '2014-07-15', 0, 25, 0, 46, 'L-930/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1058, 1083, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0573 dated May 11, 2014 and has rejected with the following comments:\r\n1.	The change order notification is rejected and IC is urged to refer to document PE-000002 para. 1.2.2.1.3 and drawing number PA-000231 - 001.\r\n2.	A document may not be entertained by SAPMT if IC forwards a subcontractors letter without evaluating it first and without providing a detailed justification with references to contractual clauses in the scope of work, technical specifications and drawings.\r\n3.	All claims or notices shall be accompanied with quantities involved.\r\n4.	A complete updated list of all claims by IC shall be attached with every notice to claim, instead of sending incomplete and scattered information.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Security Work', 'Complete', '2014-05-24', 0, 25, 0, 26, 'L-780/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1059, 1084, 43, 'For Information Only', 'Progress Report, 37', 'Complete', '2014-05-24', 0, 25, 0, -1, 'For Information Only', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1060, 1087, 43, 'SAPMT has reviewed the subject submittal dated May 11, 2014 and has no objection with the following comment:\r\n\r\n•	Provide a detailed incident report with;\r\na.	Brief description of the incident.\r\nb.	Flow of events leading to the Incident.\r\nc.	Facts, Findings and/or Observations.\r\nd.	Causal Analysis; immediate and basic causes.\r\ne.	Remedial Actions to be implemented by IC to prevent recurrence.\r\nf.	Picture attachments, illustrations of the incident.\r\ng.	Sign-offs.\r\nh.	Safety Advisory should be posted on Safety Notice Boards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Preliminary Incident Report', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-541/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1061, 1086, 43, 'SAPMT has reviewed the subject submittal dated May 08, 2014 and has no objection with the following comments:\r\n1.	Battery calculation and Specification shall comply with IFC drawings, SAES P-103, and Project Specifications.\r\n2.	Provide shop drawings showing the layout of the Battery Charger in the Electrical Room including mounting details and cable/ conduit home run to the equipment.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Battery Charger, Rectifier', 'Complete', '2014-05-26', 0, 25, 0, 26, 'L-787/14', '2014-05-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1062, 1088, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0576 dated May 11, 2014 and has the following comments:\r\n1.	Mr. Jul-Anni Abdullah Marrack is permanently approved as “Project Nurseâ€ for KAUST-Perimeter Security Ssytems BI-25-00026-0001.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory/poor performance. \r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Nurse', 'Complete', '2014-05-17', 0, 27, 0, 26, 'L-752/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1063, 1090, 43, 'SAPMT has reviewed the subject submittal dated May 12, 2014 and has the following comments:\r\n\r\n1.	Procedure shall include the cut-over of current fiber optic connection of SONAR/RADAR to the new proposed fiber optic cable line.\r\n2.	Attached the schematic diagram of the Existing IDAS Fiber Cabling System highlighting the splicing points for the new proposed FOC.\r\n3.	Include all splicing, termination and testing equipment to be used and attach calibration certificates.\r\n4.	Shall include the CV or certificate of the fiber optic cable splicer(s) valid Job Clearance Card (JCC) from Saudi Aramco.\r\n5.	Shall include the cross section details of the road where the duct bank will cross. Identify and reflect all utilities that will pass on this area and ensure that there are no conflicts and provided with minimum clearances as per Saudi Aramco standard.\r\n6.	Manual excavation must be done to avoid any damage to existing utilities.\r\n7.	Fiber optic cable shall be reel tested prior to installation.\r\n8.	Provide complete list of communication passive materials and ensure all are available at site prior to any execution of works.\r\n9.	Concrete red tile has to be provided in bullets 9 and 10.\r\n10.	Wood marker poles are to be shown with correct arrows.\r\n11.	Show the procedure to change over from existing to new showing risk factors.\r\n12.	Provides details of terminations.\r\n13.	Provide documentation such as test results, red line drawings and coordinates of UG FOC, and inspection checklists.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'FOC Installation', 'Complete', '2014-05-24', 0, 25, 0, 26, 'L-776/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1064, 1091, 43, 'SAPMT has reviewed the subject submittal dated May 11, 2014 and has no objection with the following comments:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	RP	RP-008	Outdoor LV Switch Rack	6000000886	2	Approved with Comments \r\n\r\n1.	The ITP shall be finalized during PIM.\r\n2.	This approval is conditional & contractor shall place the purchase order with one of listed approved vendors within two weeks period from MR review date provided that there is no deviation from Saudi Aramco applicable standards and project specifications. It is contractor’s responsibility to re-confirm the manufacturer’s approval status prior to purchase order placement. \r\n', 'LV Switchrack', 'Complete', '2014-05-24', 0, 27, 0, 26, 'L-755/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1065, 1092, 43, 'SAPMT has reviewed the subject submittal dated May 06, 2014 and has no objection with the following comments:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	RP	RP-011	MV Switchgear	6000000878	2	Approved with Comments \r\n\r\n•	The ITP shall be finalized during the PIM.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'MV, Switchgear', 'Complete', '2014-05-17', 0, 27, 0, 26, 'L-754/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1066, 1094, 43, 'SAPMT has reviewed the subject submittal dated May 12, 2014 and has no objection with the following comments:\r\n•	The work can start in case the following details are incorporated during execution;\r\na.	Confirm if the Note 1 in sheet 601 shall refer to LV or MV.\r\nb.	Confirm if soil improvement is necessary as mentioned in Note 4.\r\nc.	Consider using mm or m, i.e. same system of units on the drawing.\r\nd.	Show the length of concrete for the duct bank and concrete end details. i.e bell ends etc.\r\ne.	Used PVC solvent cement in connecting the conduits as per SAES P-104 10.5.5 2.\r\nf.	The top layer of the concrete shall be mixed with red dye as per Saudi Aramco standards.\r\ng.	Consider reducing the length of hooks.\r\nh.	Consider revising the shop drawings.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Duct Bank', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-765/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1067, 1096, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1068, 1097, 43, 'SAPMT has reviewed the subject submittal dated May 13, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco Standards and specifications.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'KAM, Duct Bank', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-762/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1069, 1098, 43, 'SAPMT has reviewed the subject submittal dated May 10, 2014 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'UPS, Battery', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-520/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1070, 1099, 43, 'SAPMT has reviewed the subject submittal dated May 12, 2014 and has the following comments:\r\n1.	A list of coordinates shall be attached.\r\n2.	Drawings are not readable, provide larger format printouts to see all details.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Shop Drawing, Fence', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-766/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1071, 1100, 43, 'SAPMT has reviewed the subject submittal dated May 12, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'IP Telephone', 'Complete', '2014-05-24', 0, 25, 0, 26, 'L-782/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1072, 1101, 43, 'SAPMT has reviewed the subject submittal dated May 12, 2014 and has the following comments:\r\n1.	Detailed structural analysis are required to prove that filling with dune sand will not affect the crash rating of the pre-cast wall.\r\n2.	More details about packing the excavated space with dune sand, flooding durations with water and steps for quality control are required.\r\n3.	According to SAES-A-114, other fill materials may be used with the approval of the Supervisor, Civil Engineering Unit of Consulting Services Department (CSD).\r\n4.	IC shall not deviate from the backfill type used during the crash test.\r\n5.	Consider consolidating all issues related to the precast wall in one single submittal.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Footing Backfill', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-767/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1073, 1102, 43, 'No Comments, For Information Only', 'Progress Meeting, 33', 'Complete', '2014-07-12', 0, 25, 0, -1, 'For Information Only', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1074, 1103, 43, 'SAPMT has reviewed the subject submittal dated May 13, 2014 and has no objection with the following comments:\r\n1.	Badging station shall comply with FSD document PE-000071, also ensuring that during the installation, badging station is the latest version.\r\n2.	Ensure that the badging machine shall be integrated to the SACS to allow exchange information’s (As per PE-000071 section 5.2.4).\r\n3.	Password security shall be available to control user access (As per PE-000071 section 5.2.4).\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Badging Machine', 'Complete', '2014-05-26', 0, 25, 0, 26, 'L-786/14', '2014-05-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1075, 1104, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0583 dated May 17, 2014 and has no objection with the following comment:\r\n•	It is IC and project designer''s responsibility to ensure that the south culvert is designed according to the hydrological data and IFC drawings provided by interfacing projects like the Flood Control Channel at the culvert in addition to approved project specifications and Saudi Aramco Standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Hydrology Study', 'Complete', '2014-05-26', 0, 25, 0, 26, 'L-788/14', '2014-05-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1076, 1105, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/14/0581 dated May 13, 2014 and has rejected with the following comment:\r\n•	Based on the fact that all resources, i.e. manpower, equipment and materials could be used on other activates in the project, which IC failed to plan and start on time, any claims on this issue are rejected by SAPMT.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Time Sheet, Fatayerji', 'Complete', '2014-05-17', 0, 25, 0, 27, 'L-513/14', '2014-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1077, 1106, 43, 'In reference to the subject, IC request is rejected and can only be evaluated if there are no cost implications to Saudi Aramco for already agreed scope of work.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Time Extension', 'Complete', '2014-05-24', 0, 25, 0, 26, 'L-759/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1078, 1107, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0582 dated May 13, 2014 and has the following comments:\r\n1.	There are various anomalies and deficiencies in the revised drawings as compared to IFC such as changes to stations, dike lining, thickness of lean concrete, details of base slab, cement screed, membranes, cell spaces, welded wire mesh etc. IC is urged to discuss these issues with SAPMT before submission.\r\n2.	The drafting quality needs improvement.\r\n3.	Provide the Geo-technical Study for SAPMT approval.\r\n4.	Provide a complete bar bending schedule.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Box Culvert', 'Complete', '2014-05-26', 0, 25, 0, 26, 'L-789/14', '2014-05-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1079, 1108, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1080, 1109, 43, 'SAPMT has reviewed the subject submittal dated May 12, 2014 and has the following comments:\r\n1.	Vendor Bahra Cables (9COM 6000000797) is an Aramco approved vendor.\r\n2.	Use 15-SAMSS-502 dated December 4, 2012 for compliance statement.\r\n3.	Use inspection form SA-175-150200 while submitting Purchase Requisition.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Medium Voltage Cable', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-763/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1081, 1110, 43, 'SAPMT has reviewed the subject submittal dated May 13, 2014 and has no objection with the following comments:\r\n1.	Ensure to choose the correct regulatory domain applicable to Saudi Arabia.\r\n2.	Include the installation kit and patch cord required.\r\n3.	Include the Smartnet services applicable to the proposed model.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Wireless Access', 'Complete', '2014-05-24', 0, 25, 0, 26, 'L-783/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1082, 1111, 43, 'SAPMT has reviewed the subject submittal dated May 13, 2014 and has the following comments:\r\n1.	Relevant IFC Drawings shall be attached.\r\n2.	Shop drawings shall elaborate on IFC and not make changes to IFC. Note 2 on SD-FCC-846521-111 is not in accordance with IFC.\r\n3.	Fill material other than dune sand shall be used between the foundations and below the panel.\r\n4.	Provide an enlarged section of the pocket joint without hashing for more clarity.\r\n5.	Work can start in case the above points are taken into account on site.\r\n6.	Consider revising the submittal.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Erection Detail', 'Complete', '2014-05-24', 0, 25, 0, 26, 'L-779/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1083, 1112, 43, 'SAPMT has reviewed the subject submittal dated May 14, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco Standards and specifications.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Incident Report', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-761/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1084, 1116, 43, 'In reference to the above subject, IC is urged to submit officially the IT Applications (software) with necessary patch & key as per Schedule-B, Attachment-V, Exhibit II, Para 2 as soon as possible.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n \r\n', 'Software, IT Applications', 'Complete', '2014-05-17', 0, 25, 0, 27, 'L-744/14', '2014-05-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1085, 1114, 43, 'SAPMT has reviewed the subject submittal dated May 15, 2014 and has no objection with the following comment:\r\n•	LV cables and building wires shall comply with construction specifications, SAES-P-104 para. 5.1 and IFC drawings.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'LV Cable, Wire', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-768/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1086, 1113, 43, 'SAPMT has reviewed the subject submittal dated May 14, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards & specifications. \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'RTR, Thermoplastic Piping', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-774/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1087, 1115, 43, 'SAPMT has reviewed the subject submittal dated May 15, 2014 and has the following comments:\r\n1.	Provide more details about the expansion joints, fillers and connections between concrete, asphalt and rock.\r\n2.	Notes shall be provided to show the applicable standards, concrete strengths, steel grades etc.\r\n3.	The shop drawing shall also be concurred by the X-Ray machine vendor for interfaces, conduits, anchoring etc.\r\n4.	Show concrete cover suitable for equipment foundations.\r\n5.	Vendor recommendations for steel, maintenance space etc. shall be strictly followed and attached with the submittal.\r\n6.	Bar bending schedule shall show hook length.\r\n7.	Provide more information about drainage.\r\n8.	IC is urged to discuss the submittal with SAPMT before resubmitting.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Z Portal', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-770/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1088, 1117, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1089, 1118, 43, 'SAPMT has reviewed the subject submittal dated May 17, 2014 and has the following comments: \r\n1.	The comments provided in letter no. K&TPD/KRP&SFPD/SF/L-713/14 dated April 30, 2014 have not been completely incorporated, i.e Item No. 5 regarding the compressive strength of repair material.\r\n2.	Attach a repair matrix showing the type of deformity, type of repair, material to be used, acceptable deformity with frequency/ percentage of surface area, and location where the repair shall be done.\r\n3.	The precast wall in addition to being a crash barrier, also has to be aesthetically acceptable and IC shall take utmost care in providing an excellent finish without any deformities in the fair face concrete.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Concrete Defects Repair', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-772/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1090, 1119, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1091, 1120, 43, 'SAPMT has reviewed the subject submittal dated May 17, 2014 and has no objection with the following comments:\r\n1.	IC shall provide detailed quantities and plans of relocation for SAPMT approval.\r\n2.	Provide shop drawings and data/load schedule for lighting and IDAS Power Panels.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Patrol Road Lighting', 'Complete', '2014-05-24', 0, 25, 0, 26, 'L-778/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1092, 1121, 43, 'SAPMT has reviewed the subject submittal dated May 17, 2014 and has no objection with the following comment:\r\n•	All coordinates shall fall on the alignment of the perimeter provided with the IFB and shall be inspected by SAPMT Surveying team on site before construction.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'BM Align, General Notes', 'Complete', '2014-06-03', 0, 25, 0, 26, 'L-809/14', '2014-06-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1093, 1122, 43, 'SAPMT has reviewed the subject submittal dated May 18, 2014 and has the following comments:\r\n1.	SAPMT has already approved a vendor for this material via MS-0080.\r\n2.	While Alfanar Cables and Wires is an approved Aramco vendor, the submittal needs to be revised with the same material submittal number as MS-0080-Alt.\r\n3.	Adequate reason shall be provided for providing an alternative vendor.\r\n4.	LV cables and building wires shall comply with construction specifications, SAES-P-104 para. 5.1, and IFC drawings.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'LV Cable, Wire', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-771/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1094, 1123, 43, 'SAPMT has reviewed the subject submittal dated May 17, 2014 and has the following comments:\r\n1.	Material offered is from Saudi EGA but the name of manufacturer on front cover is EGA Honey well. Justify the relationship between the two.\r\n2.	EGA PVC conduit does not comply with SAES P-104. The following types of Electrical and Communication conduits for concrete and direct buried are acceptable;\r\na.	PVC Conduit TYPE DB - 120 (Direct Buried).\r\nb.	PVC Conduit TYPE EB - 35 (Concrete Encasement).\r\nc.	PVC Conduit TYPE EPC - 40 (Direct Buried and Concrete Encasement).\r\n3.	Correct Vendor ID for Al Abdul Karim Holding Dammam is 10011901.\r\n4.	Consult with SAPMT for more clarification before re-submission.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'PVC Conduits', 'Complete', '2014-05-29', 0, 25, 0, 26, 'L-792/14', '2014-05-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1095, 1124, 43, '', '', 'Complete', '2014-06-04', 0, -1, 0, -1, 'For Information Only', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1096, 1127, 43, 'SAPMT has reviewed the subject submittal dated May 18, 2014 and has the following comments: \r\n1.	Fixture for Earthling System comes under 9Com # 6000000773 and not under the 9Com#6000000983 as quoted by Contractor.\r\n2.	Wrong Vendor number is given for Abdul Karim Holding Co. Correct vendor ID is 10011901.\r\n3.	Correct Vendor ID for A.N.Wallis & Co is 10032321.\r\n4.	Material list given by the Contractor is for Lighting Fixtures and not for the Lighting Protection Accessories.\r\n5.	Contractor is advised to prepare a complete list of Lighting Protection and Fixture for Earthling Systems under this submittal with quantities and Catalogue number mentioned therein.\r\n6.	Contractor is advised to responsibly submit only relevant pages of the catalog clearly highlighting the product codes/ material offered.\r\n7.	Only test reports and Certificates of the selected items may be submitted.\r\n8.	Unnecessary Prequalification documents already approved vendor AL-Abdul Karim Holding are provided in Section 7 of the submittal which is not required.\r\n9.	It has been noted that Contractor has typed the compliance statement on the Project specification documents which is not correct. Separate compliance statement shall be submitted as part of the material submittal and not overwrite, copy and paste clauses from Project specifications.\r\n10.	Contractor is advised to assign the task of Preparing and reviewing the material submittals to technically competent staff and improve the quality of submittals.\r\n11.	Consider replacing the title of submittal to "Grounding and Lightning System Accessories"\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Lighting Protection System', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-773/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1097, 1125, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1098, 1126, 43, 'With reference to Royal Decree No. M/9, November 18, 1987 Article No. 6, which regulates the protection of Marine Life in Saudi Territorial Waters, forbids any one to cut tree or other plants growing in Saudi coasts or islands without the prior approval of Ministry of Agriculture and Water. Hence, in conformance with the Royal decree, the construction of KAM Access Road will be shifted North-wards to avoid mangroves area; and the following security measures will be provided upon project completion:\r\n1.	Current KAUST Security Fence will be relocated to the shifted area.\r\n2.	IDAS and Lighting System will be maintained at the shifted area.\r\n3.	Internal Patrol Road will be maintained at the shifted area. \r\n4.	Chain Link Fence shall be installed to isolate KAM Access Road from Internal Patrol Road. Multiple manually open-able Chain Link Type gates will be installed for access to IDAS zone according to KAUST Security requirements.\r\n5.	The new KAM Access Road will have architectural features similar to Road 2.\r\n\r\nThe above design optimization will yield the following positive outcomes:\r\n1.	The Project will comply with Royal Decree No, M/9 article No 6.\r\n2.	The Project will preserve approximately 1000m long and 30m wide strip of mangroves.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.', 'Mangrove Conservation', 'Complete', '2014-09-21', 0, 25, 0, -1, 'L-548/14', '2014-05-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1099, 1128, 43, 'SAPMT has reviewed the subject submittal dated May 18, 2014 and has rejected with the following comment:\r\n•	The submitted report is incomplete and Procurement Progress % is not matching with detailed report. \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Progress Report', 'Complete', '2014-05-24', 0, 25, 0, 27, 'L-784/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1100, 1129, 43, 'DONE, through PManywhere initiation # 1170 & 1169, for Security & Communication respectively.', 'IFC Security ', 'Complete', '2014-05-29', 0, -1, 0, -1, 'For Information Only', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1101, 1137, 43, 'The work on the substructure of the buildings in front of gate 2 and gate 3 has started but the superstructure construction shall be soon stopped due to the overhead lines above. \r\n\r\nAs the ditch has been removed from the scope of work, there is no need to run cable duct banks and relocation works can be performed without any further delay. KAUST is urged to coordinate with the Saudi Electrical Company (SEC) to start the works for removal of these overhead lines.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Overhead Lines', 'Complete', '2014-05-24', 0, 25, 0, 26, 'L-781/14', '2014-05-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1102, 1136, 43, 'SAPMT has reviewed the subject submittal dated May 21, 2014 and has no objection with the following comments:\r\n1.	Ensure that no-standard sizes of panels are minimum and on non-obvious locations.\r\n2.	Ensure that any requirement of providing expansion joints is taken into account.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Footing Corner Coordinates', 'Complete', '2014-05-29', 0, 25, 0, 26, 'L-796/14', '2014-05-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1103, 1130, 43, 'SAPMT has reviewed the subject submittal dated May 19, 2014 and has rejected with the following comment:\r\n•	Vendor ID: 10026091 is wrongly associated with Saudi K. Span Factory in the document submittal. This Vendor ID was issued to USKAN SPACE CONSTRUCTION TURKEY in 2002, which is also no more a valid contractor in Saudi Aramco System. \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570\r\n', 'Space Frame, Shades', 'Complete', '2014-05-26', 0, 25, 0, 26, 'L-785/14', '2014-05-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1104, 1135, 43, 'SAPMT has reviewed the subject submittal dated May 20, 2014 and has the following comments:\r\n1.	Explain how the gap between the wall panel top and column cap shall be filled.\r\n2.	Correct the description of item 2 and 4.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Top View, Column Detail', 'Complete', '2014-05-29', 0, 25, 0, 26, 'L-793/14', '2014-05-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1105, 1139, 43, 'SAPMT has reviewed the subject submittal dated May 21, 2014 and has the following comments:\r\n1.	Provide more information about testing according to 17-SAMAA-518 and VE-864472 Para 3.04 B.1 to 4 and compliance matrix shall be verified between contractor and supplier.\r\n2.	The layout drawing shall show the neutral grounding resistor, control panel, fuel day tank and ventilation requirements.\r\n3.	After approval of the technical details, IC shall provide requisition package including inspection form SA-175-170400 rev 06/22/2011 and PR sheet.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Diesel Generator', 'Complete', '2014-06-01', 0, 25, 0, 26, 'L-804/14', '2014-06-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1106, 1131, 43, 'SAPMT has reviewed the subject submittal dated May 20, 2014 and has the following comments:\r\n1.	Mr. Mohammed Thanzeer Khan is conditionally approved as “QC Inspector (Civil) for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory/ poor performance.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-05-31', 0, 25, 0, 26, 'L-777/14', '2014-05-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1107, 1133, 43, 'SAPMT has reviewed the subject submittal dated May 21, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n \r\n', 'Concrete Fence Coordinates', 'Complete', '2014-05-29', 0, 25, 0, 26, 'L-795/14', '2014-05-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1108, 1134, 43, 'FOR INFORMATION ONLY', 'Heat Stress', 'Complete', '2014-05-27', 0, 25, 0, -1, 'For Information Only', '2014-05-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1109, 1142, 43, 'SAPMT has reviewed the subject submittal dated May 21, 2014 and has the following comments:\r\n1.	Provide connection details at the area where soil improvement ends and show coordinates.\r\n2.	Revise road sections showing site conditions after the revised Topography and Geo-technical Investigation.\r\n3.	Provide a composite drawing showing details/ sections of all utilities (electrical, communication, irrigation, valve boxes and pipe culvert) including utilities for KAM project with elevations.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'KAM, Plan & Profile', 'Complete', '2014-05-29', 0, 25, 0, 26, 'L-794/14', '2014-05-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1110, 1141, 43, 'For Information Only', 'Progress Meeting, 34', 'Complete', '2014-05-26', 0, 25, 0, -1, 'For Information Only', '2014-05-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1111, 1140, 43, 'SAPMT has reviewed the subject submittal dated May 19, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Saudi German, Aluminium Products', 'Complete', '2014-05-29', 0, 25, 0, 26, 'L-791/14', '2014-05-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1112, 1132, 43, 'SAPMT has reviewed the subject submittal dated May 20, 2014 and has the following comments:\r\n1.	Mr. Abdul Nisar is conditionally approved as “QC Inspector (Civil) for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory/ poor performance.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'QC Inspector - Civil', 'Complete', '2014-05-31', 0, 25, 0, 26, 'L-797/14', '2014-05-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1113, 1138, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1114, 1144, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0584 dated May 22, 2014 and has rejected with the following comments:\r\n1.	The pre-cast wall panels and columns shall be fabricated fair face with required texture and irrespective of the fact that the wall is to be painted or not.\r\n2.	IC is urged to refer to Appendix-B of IFB for the following;\r\na.	The "Architectural design brief/ basis", in para 1.4 for Materials and Finishes for the project as included in the IFB mentions that all exterior walls shall be Light coloring, heat reflecting, thermal insulating qualities and low maintenance shall be the major considerations in the selection of all exterior finishes.\r\nb.	Appropriate jointing and backing systems shall be incorporated into the design of all exterior finish system.\r\nc.	Painting of exterior walls shall be with acrylic emulsion paint on primer/sealer.\r\nd.	Special attention shall be given to the selection of appropriate coating for the finishing of exterior surfaces. Metals in particular require high quality coatings as a protection against corrosion and heat absorption.\r\ne.	All elevation treatments shall follow the common architectural design theme as closely as possible.\r\n3.	Based on the above IC has already presented samples out of which SAPMT has already approved one sample and conveyed to IC.\r\n4.	All IFB drawings are in black and white which does not mean that no painting or colors are required on any facility of the project.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Paint, Precast Wall', 'Complete', '2014-05-27', 0, 25, 0, 26, 'L-790/14', '2014-05-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1115, 1143, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1116, 1145, 43, 'For Information Only', '', 'Complete', '2014-06-08', 0, 25, 0, -1, 'For Information Only', '2014-06-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1117, 1146, 43, 'SAPMT has reviewed the subject submittal dated May 24, 2014 and has the following comments:\r\n1.	Mr. Emadudden M. Macadato is conditionally approved as “QC Inspector (Civil) for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory/ poor performance.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'QC Inspector - Civil', 'Complete', '2014-05-31', 0, 25, 0, 26, 'L-798', '2014-05-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1118, 1147, 43, '', '', 'Complete', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1119, 1148, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0602 dated May 24, 2014 and has rejected with the following comments:\r\n1.	The claim is not acceptable because IFB package requires a sub-base and a base course of the same thicknesses as shown in IFC. Determining a class for these materials depends on the geo-technical findings during the detailed design phase. IC is urged to provide design details showing why using a certain class of material was necessary along with the findings from geo-technical studies. It is also urged that a change shall not be made to the requirements/ specifications of the contract without acquiring prior technical and administrative approval from SAPMT.\r\n2.	The calculations for the quantities are also not acceptable because they are not based on the design width of the base course material for KAM road.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Aggregate Base Course', 'Complete', '2014-06-01', 0, 25, 0, 26, 'L-803/14', '2014-06-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1120, 1149, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0600 dated May 25, 2014 and has rejected with the following comment:\r\n•	IC is urged to refer to Para 12 of SCH-A, where the specifications created by IC and approved by SAPMT if not negating any standards shall take precedence.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Bituminous Paint', 'Complete', '2014-06-02', 0, 25, 0, 26, 'L-806/14', '2014-06-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1121, 1153, 43, 'SAPMT has reviewed the subject submittal dated May 25, 2014 and has no objection with the following comments:\r\n1.	Mention in the subject whether the shop drawing for structural or architectural works.\r\n2.	Provide rebar schedule for masonry.\r\n3.	Provide more details about the texture of CMU, finishes at ramps etc.\r\n4.	Provide more details about lintel beams.\r\n5.	Provide more details about bituminous coatings under the NGL.\r\n6.	Provide interface details between silicone sealants and bitumen sealants.\r\n7.	Provide details for adjustable hanger rods, fixtures, supports for acoustic ceilings, roof access cage etc.\r\n8.	Provide more details about the wall insulation.\r\n9.	Provide drawings for doors and windows.\r\n10.	Dowel spacing in IC-SD-846859-102 (Block Wall Plan) and IC-SD-846860-102 (Block Wall Plan) are different.\r\n11.	Explain why the width of groove is 32mm in conflict with IFC VA-846861-001.\r\n12.	Consult with SAPMT to discuss all conflicts between IFC and shop drawings before revised submittal.\r\n13.	Structural works can start but the revised submittal conforming to the above comments shall be provided within 3 days.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Turnstile, X-Ray Building', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-825/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1122, 1154, 43, 'SAPMT has reviewed the subject submittal dated May 26, 2014 and has the following comments:\r\n1.	Quantities indicated under the Bill of quantities are all wrong. Re-verify the quantities and ensure all requirements shall be provided and installed in this project.\r\n2.	The proposed manhole frame and cover is not acceptable since it conflicts to SAES-T-911 requirements.\r\n3.	All manholes inside accessories shall be non-corrosive, hot dipped galvanized and ensure all have specifications and dimensions in compliance to SAES-T-911.\r\n4.	Specification of fiber marker post is included in the attachment; please clarify since it is not included in the Bill of Quantities.\r\n5.	Use correct 9com # 6000000682 for Manhole. 9com # 6000000681 is depleted and no more used in Saudi Aramco system.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Communication Manholes', 'Complete', '2014-06-09', 0, 25, 0, 26, 'L-818/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1123, 1157, 43, 'SAPMT has reviewed the subject submittal dated May 25, 2014 and has no objection with the following comments:\r\n1.	Mention in the subject whether the shop drawing for structural or architectural works.\r\n2.	Provide rebar schedule for masonry.\r\n3.	Provide more details about the texture of CMU, finishes at ramps etc.\r\n4.	Provide more details about lintel beams.\r\n5.	Provide more details about bituminous coatings under the NGL.\r\n6.	Provide interface details between silicone sealants and bitumen sealants.\r\n7.	Provide details for adjustable hanger rods, fixtures, supports for acoustic ceilings, roof access cage etc.\r\n8.	Provide more details about the wall insulation.\r\n9.	Provide drawings for doors and windows.\r\n10.	Dowel spacing in IC-SD-846859-102 (Block Wall Plan) and IC-SD-846860-102 (Block Wall Plan) are different.\r\n11.	Explain why the width of groove is 32mm in conflict with IFC VA-846861-001.\r\n12.	Consult with SAPMT to discuss all conflicts between IFC and shop drawings before revised submittal.\r\n13.	Structural works can start but the revised submittal conforming to the above comments shall be provided within 3 days.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Turnstile, X-Ray Building', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-826/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1124, 1150, 43, 'SAPMT has reviewed the subject submittal dated May 25, 2014 and has the following comments:\r\n1.	Mr. Sajid Akram is conditionally approved as “QC Inspector (Civil)â€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory/ poor performance.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-06-09', 0, 25, 0, 26, 'L-820/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1125, 1151, 43, 'SAPMT has reviewed the subject submittal dated May 25, 2014 and has no objection with the following comment:\r\n•	IC is urged to submit clear copies of drawings.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Duct Bank', 'Complete', '2014-06-01', 0, 25, 0, 26, 'L-802/14', '2014-06-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1126, 1152, 43, 'For Information Only', 'Progress Report', 'Complete', '2014-05-27', 0, 25, 0, -1, 'For Information Only', '2014-05-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1127, 1155, 43, 'This CV was pulled out and sent back to ICC due to not availability of candidate for his personal test and interview.', '', 'Complete', '2014-07-12', 0, 25, 0, -1, 'For Information Only', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1128, 1156, 43, 'SAPMT has reviewed the subject submittal dated May 26, 2014 and has the following comment:\r\n•	Mr. Hamid Nasir is not acceptable for the post of “QC Inspector (Civil)â€ based on the facts observed during personal interview.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-06-09', 0, 25, 0, 26, 'L-819/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1129, 1160, 43, 'Accepted, Service Entry Sheet attached herewith.', 'Payment Application', 'Complete', '2014-09-21', 0, 25, 0, -1, 'For Information Only', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1130, 1158, 43, 'SAPMT has reviewed the subject submittal dated June 01, 2014 and has no objection with the following comment:\r\n•	Reference to compliance statement 15-SAMSS-502 para. 8.4, Contractor has to comply for cable additional protection in all areas to meet project specification and validation from designer (SCEC) through email dated March 10, 2014. (email attached).\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'MV Cable', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-815/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1131, 1159, 43, 'SAPMT has reviewed the subject submittal dated May 25, 2014 and has no objection with the following comment:\r\n•	Contractor shall comply with SAES P-104 para. 8.4, 8.6 and 8.11.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'EMT Conduit, Steel Box', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-816/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1132, 1170, 43, 'Please find attached two copies of SAPMT feedback to KAUST review comments on IFC drawings for Security systems for the KPSS project. KAUST is requested to concur by returning one copy to SAPMT with initials.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'IFC Security', 'Complete', '2014-05-29', 0, 25, 0, 26, 'L-775/14', '2014-05-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1133, 1171, 43, 'Please find attached two copies of SAPMT feedback to KAUST review comments on IFC drawings for Communications systems for the KPSS project. KAUST is requested to concur by returning one copy to SAPMT with initials.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'IFC, Communication, Comment', 'Complete', '2014-05-31', 0, 25, 0, 26, 'L-799/14', '2014-06-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1134, 1161, 43, 'SAPMT has reviewed the subject submittal dated May 26, 2014 and has the following comments:\r\n1.	Provide and submit UPS Battery Load Calculation per building equipment’s requirement to ensure 30 minutes back-up time will be provided for edge or access switches and 2 hours back-up time for Routers as per Appendix H prior review and SAPMT approval.\r\n2.	Once the Load Calculation has been approved by SAPMT, it shall be attached to this revised Material Submittal.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'UPS', 'Complete', '2014-06-03', 0, 25, 0, 26, 'L-811/14', '2014-06-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1135, 1162, 43, 'SAPMT has reviewed the subject submittal dated May 27, 2014 and has the following comments:\r\n1.	Mr. Muhammad Ameen. V is accepted as “Alternate Internal Auditorâ€.\r\n2.	SAPMT reserves the right to revoke this approval for any noncompliance with Saudi Aramco standards and requirements, during the contractor and its representative’s involvement in the project.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Alternate Internal Auditor', 'Complete', '2014-06-03', 0, 25, 0, 26, 'L-808/14', '2014-06-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1136, 1163, 43, 'SAPMT has reviewed the subject submittal dated May 26, 2014 and has no objection with the following comments:\r\n1.	Use correct 9Com#6000000682 for Manhole.\r\n2.	The Title of Submittal is for 1200mm dia, but the Catalogue shows 1800mm dia also. Only 1200mm dia is approved as requested.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Fiber Glass, Manhole', 'Complete', '2014-06-01', 0, 25, 0, 26, 'L-801/14', '2014-06-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1137, 1164, 43, 'SAPMT has reviewed the subject submittal dated June 01, 2014 and has the following comments:\r\n1.	Refer to AB-036255-001-04 and comply with the requirements.\r\n2.	Provide details as to how the compaction for road works with heavy machinery shall be done on top of the concrete protection slab.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Pipe Culvert Protection', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-830/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1138, 1165, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0600 dated May 25, 2014 and has rejected with the following comment:\r\n•	IC is urged to refer to Para 12 of SCH-A, where the specifications created by IC and approved by SAPMT if not negating any standards shall take precedence.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Pocket Joint', 'Complete', '2014-06-01', 0, 25, 0, 26, 'L-805/14', '2014-06-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1139, 1166, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0770, 0603, 0566 & 0532 dated 27th August 2014, 27th May 2014, 10th May 2014 & 20th April 2014 respectively and has the following comments:\r\n1.	Provide detailed quantities of all work items/ activities involved in the deletion of ditch from the scope of work and reworks if any etc., for both parties to agree, after which the processes for change order/ amendment can start.\r\n2.	Contact SAPMT to understand Saudi Aramco procedures if necessary.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Ditch Elemination', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1039/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1140, 1167, 43, 'SAPMT has reviewed the subject submittal dated May 26, 2014 and has no objection with the following comments:\r\n1.	SAPPCO approval is limited to pipe sizes ½ inch to 10 inch.\r\n2.	For Gravity Pipes & Fittings – use minimum Class 3 or equivalent.\r\n3.	For Force-Main Pipes & Fittings – use minimum Class 5 (Solvent Joints) or equivalent.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'UPVC', 'Complete', '2014-06-03', 0, 25, 0, 26, 'L-813/14', '2014-06-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1141, 1168, 43, 'SAPMT has reviewed the subject submittal dated May 31, 2014 and has no objection with the following comments:\r\n1.	Contractor shall identify the enclosure rating of the proposed panel boards.\r\n2.	Contractor shall identify the cable entry (Top or Bottom) for each of the panel boards.\r\n3.	Provide vendor shop drawing for each of the panel board showing Main Circuit Breakers and its branches.\r\n4.	Dry type transformer enclosure shall comply with SAES P-104 para. 7.\r\n5.	Provide vendor shop drawing for dry type transformer to verify the ventilation details.\r\n6.	Submit purchase requisition for LV panel and Lighting Control Panel.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'LV Panel Board', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-823/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1142, 1169, 43, 'SAPMT has reviewed the subject submittal dated May 27, 2014 and has the following comment:\r\n•	Progress percentage at Progress Summary has to be revised as per Approved Project Schedule (rev-01).\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'MOM, 35', 'Complete', '2014-06-01', 0, 25, 0, 26, 'L-800/14', '2014-06-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1143, 1172, 43, 'SAPMT has reviewed the subject submittal dated May 27, 2014 and has the following comments:\r\n1.	The work can continue according to standards and SAPMT approved repair matrix.\r\n2.	Consider using corner mesh etc. for spalled edges.\r\n3.	Revise the matrix as required in DS-308.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Concrete Defects Repair', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-828/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1144, 1173, 43, 'SAPMT has reviewed the subject submittal dated May 28, 2014 and has no objection with the following comment:\r\n•	Use correct 9Com# 6000000754 with correct description as “Tape Electricalâ€.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Warning Tape, Electrical Tape', 'Complete', '2014-06-03', 0, 25, 0, 26, 'L-812/14', '2014-06-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1145, 1174, 43, 'SAPMT has reviewed the subject submittal dated May 28, 2014 and has no objection with the comments given in the attached letter no. KAUPIS/L-016/2014 dated July 02, 2014.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Saudi Readymix', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-895/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1146, 1175, 43, 'SAPMT has reviewed the subject submittal dated May 29, 2014 and has no objection with the following comments:\r\n1.	Mention the location or purpose where the material is to be used in your description/ subject/ title.\r\n2.	Attach the standard drawing AD-036874 and not the same IFC drawing twice.\r\n3.	The work can continue but this document has to be submitted again with all required information. \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Backfilling Dry Sand', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-817/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1147, 1176, 43, 'SAPMT has reviewed the subject submittal dated May 29, 2014 and has no objection with the following comment:\r\n•	Use correct 9Com# 6000000499 with Correct description as “ Floor Tiles (Red concrete)â€\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Red Tile', 'Complete', '2014-06-03', 0, 25, 0, 26, 'L-810/14', '2014-06-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1148, 1177, 43, 'SAPMT has reviewed the subject submittal dated May 27, 2014 and has no objection with the following comments:\r\n1.	Use AVK high pressure wet barrel hydrant series-2490 in compliance with SAES B-017 para. 7.2.1, Hydrant selection & Design; states “hydrant should have three connections; One-5â€ stores connection and 2½â€ fire hose compatible threads.\r\n2.	Submit shop drawing for fire hydrant. Show piping components, thrust block support and direct buried valve. (refer to IFC drawing VA-846559-001).\r\n3.	Fire hydrant shall be manufactured by Saudi Valves Manufacturing Company (30000959). \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Fire Hydrant', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-831/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1149, 1178, 43, 'Approved with no Comments', 'Payment Application, May, 13', 'Complete', '2014-07-01', 0, 25, 0, 26, 'L-865/14', '2014-06-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1150, 1179, 43, 'SAPMT has reviewed the subject submittal dated May 29, 2014 and has the following comments:\r\n1.	Add a column showing the materials/ products to be used for repairs according to SAPMT approvals.\r\n2.	The work can continue according to the standards.\r\n3.	All defects can be reduced to minimum with cautious concrete pouring practices. IC and its subcontractors are urged to ensure that all precast members are produced with best fair face finishes irrespective of the fact that they are painted later on or not.\r\n4.	Prepare a complete mock up with all precast members in place including the spiked grill on top for SAPMT approval.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Repair Matrix', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-827/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1151, 1180, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1152, 1181, 43, 'SAPMT has reviewed the subject submittal dated May 29, 2014 and has no objection. The approval was conveyed earlier via email on June 29, 2014 and CSD approval form is attached. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specifications.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer (012) 422-4570.\r\n', 'Geotechnical Investigation, Wadi Khulais', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1018/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1153, 1182, 43, 'SAPMT has reviewed the subject submittal dated May 29, 2014 and has the comments shown in document attached. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Geo-technical Investigation, KAM Riad', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-946/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1154, 1183, 43, 'SAPMT has reviewed your letter no. KPSS/SA/B/AKR/14/0623 on May 31st 2014 and believes that there were many other open areas for work such as;\r\na.	Construction of Precast Fence.\r\nb.	Relocation of existing KAUST fence at KAM Access Road.\r\nc.	Construction of buildings at gate # 2 & 3 and south culvert.\r\nd.	Earth works.\r\nHowever, ICC has no right to claim standby time.\r\n\r\nShould you have any questions, please contact Fahad Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Time Sheet', 'Complete', '2014-06-24', 0, 12, 0, 26, 'L-839/14', '2014-06-16', 0, '', '', '', '', 'R-17');
INSERT INTO `submittal` VALUES(1155, 1184, 43, 'For Information Only', 'Clerical Error', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1156, 1185, 43, '\r\nSAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0618 dated May 29, 2014 and has rejected with the following comment:\r\n•	The letter by ICC shows gross negligence in meeting with contractual obligations.\r\n1.	Only proofs of licenses for two software are attached with the letter whereas the list shows many more software.\r\n2.	List does not include CAD software.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'IT Application', 'Complete', '2014-06-10', 0, 12, 0, 26, 'L-841/14', '2014-06-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1157, 1186, 43, 'IC shall manage the documents with its subcontractors without involving SAPMT or disrupting the document control procedures set forth in the contract.', 'Box Culvert', 'Complete', '2014-09-15', 0, -1, 0, -1, 'For Information Only', '2014-07-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1158, 1193, 43, 'SAPMT has reviewed the subject submittal dated June 01, 2014 and has no objection with the following comments:\r\n1.	WESCOSA has limitations to use only Cutler Hammer Model breakers under license from Cutler Hammer.\r\n2.	Submit requisition package at the earliest ande use special SA-175 form as per the inspection test plan (ITP) produced by WESCOSA for these Package substations.\r\n3.	Ensure that the fuse rating of Ring Main Unit (RMU) for tee-off circuit is rated according to the rating of transformers of different sizes as indicated in the Single Line Diagrams.\r\n4.	The enclosure of the Package shall be adequately protected against corrosion and painted according to relevant clauses of SEC standard 01-SDMS-01.\r\n5.	Provide Datasheet for each Package Substation concurred by the designer and manufacturer.\r\n6.	LV Panel Board shall be according to the Panel Schedule drawings of the project.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Package Substation, Transformer', 'Complete', '2014-06-02', 0, 25, 0, 26, 'L-807/14', '2014-06-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1159, 1187, 43, 'SAPMT has reviewed the subject submittal dated May 31, 2014 and has no objection with the following comment:\r\n•	Ensure that queue number indicator display required in each counter and the controller should have capability to connect all required displays.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Queuing System', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-814/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1160, 1189, 43, 'SAPMT has reviewed the subject submittal dated May 27, 2014 and has no objection with the following comments:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	RP	RP-013	Battery Charger/  Battery 	6000000947/ 6000000951	2	Approved \r\n\r\n1.	The approval is conditional and contractor shall place the order with one of the approved vendors within two weeks from MR review date; provided there is no deviation from standards and specifications.\r\n2.	It is contractor’s responsibility to re-confirm the approval status of the vendor/ manufacturer at the time of placing the Purchase Order.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Battery Charger, Rectifier', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-821/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1161, 1192, 43, 'SAPMT has reviewed the subject submittal dated May 31, 2014 and has no objection with the following comment:\r\n•	Ensure that the low voltage cable and wires comply with SAES P-104 Para. 5, project Specifications and IFC drawings.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'LV Cable', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-824/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1162, 1188, 43, 'For Information Only', 'Camp Inspection', 'Complete', '2014-06-08', 0, 25, 0, -1, 'For Information Only', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1163, 1190, 43, 'For Information Only', '', 'Complete', '2014-07-01', 0, 25, 0, -1, 'For Information Only', '2014-07-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1164, 1191, 43, 'For Information Only', '', 'Complete', '2014-07-01', 0, 25, 0, -1, 'For Information Only', '2014-07-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1165, 1194, 43, 'SAPMT has reviewed the subject submittal dated June 01, 2014 and has the following comments:\r\n1.	Explain why the sleeve diameter has been reduced to 40mm, in conflict with SDS 008 and 009. Have the previous shop drawings been revised and approved. Attach as necessary.\r\n2.	Attach approvals for bolts.\r\n3.	It is IC’s responsibility to keep track of revisions and changes to approved shop drawings.\r\n4.	Provide all related documents and justifications before making changes to previous approved drawings.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Column Cap Detail', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-822/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1166, 1202, 43, 'SAPMT has reviewed the subject submittal dated June 02, 2014 and has no objection with the following comment:\r\n•	UPVC pipes shall be of Class 5.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'UPVC Pipe Sleeve', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-837/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1167, 1195, 43, 'SAPMT has reviewed the subject submittal dated June 02, 2014 and has no objection with the following comments:\r\n1.	Ensure to include all fiber closure accessories upon placement of purchase order.\r\n2.	Air valve shall be installed on all outdoor type closures.\r\n3.	Ensure all models selected can accommodate all splicing requirement as per the IFC drawings.\r\n4.	Use the correct 9com # 6000001114 with correct description as “Accessory: Fitting for Fiber Optic Cableâ€. 9com # 6000001174 is depleted and not in use anymore. \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'FOC, Splice Closure', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-832/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1168, 1196, 43, 'SAPMT has reviewed the subject submittal dated May 31, 2014 and has rejected with the following comments:\r\n1.	Petra Engineering Jeddah (30006889) is an SA approved manufacturing Plant with a condition that units shall be certified at manufacturing facility to comply with UL-1203 and UL-1995 by an approved third party inspection agency.\r\n2.	PAC Unit shall have pre-filter with 30% dust spot efficiency and a final filter with 95% dust spot efficiency.\r\n3.	Summary sheet shall be required with model number.\r\n4.	All the accessories including mixing box, differential pressure switches for filter, motorized dampers shall also be included.\r\n5.	According to IFC, PACU shall have top duct connections and not side duct connections.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Air Conditioning Unit', 'Complete', '2014-07-15', 0, 25, 0, 46, 'L-934/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1169, 1197, 43, 'SAPMT has reviewed the subject submittal dated June 02, 2014 and has no objection with the following comments:\r\n1.	Ensure that Monitors, CPU and servers to be positioned in the console fit with sufficient clearance for cabling, and has sufficient ventilation to avoid accumulation of heat.\r\n2.	Ensure that the power strip for computers and servers ware compatible and oriented properly.\r\n3.	Provide more details in shop drawing and submit separately for SAPMT approval.\r\n4.	Ensure that the Monitor and CPU are of latest model.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Operator Console', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-833/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1170, 1198, 43, 'SAPMT has reviewed the subject submittal dated June 01, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Environmental Management', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-829/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1171, 1199, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0617 dated June 03, 2014 and has the following comments:\r\n\r\n1.	Mr. Robert V. Bandalan is permanently approved for the position of “HSE Officerâ€ for “KAUST-Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke this permanent approval based on his unsatisfactory/ poor performance during project tenure.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'HSE Officer', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-842/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1172, 1200, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2014-07-12', 0, 25, 0, -1, 'For Information Only', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1173, 1201, 43, 'SAPMT has reviewed the subject submittal dated June 02, 2014 and has no objection with the following comments:\r\n1.	Ensure that the proposed camera is suitable for outdoor environment.\r\n2.	Provide details about manufacturer recommended enclosure/housing for the camera.\r\n3.	Ensure to submit the details of required server for SACS and with capacity calculations in a separate submittal for SAPMT approval.\r\n4.	The quantity of Proximity readers, Bio-metric readers and cameras shall meet the project specification requirements and SACS Functional Specification Document PE-000071.\r\n5.	Ensure that the fingerprint system will comply to FSD document PE-000071 para. 4.8 & 5.2.8.\r\n6.	The pole for proximity readers located in gate # 2 & 3 inbound and outbound, shall be capable for small and big cars.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'SACS', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-835/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1174, 1203, 43, 'SAPMT has reviewed the subject submittal dated June 03, 2014 and has no objection with the following comments:\r\n1.	Ensure that pipe is cut neatly along the length as demonstrated on site to the construction team.\r\n2.	Use cable ties, insulation tape and plastic sheet wrapped as an extra precaution to avoid any sand moving inside the pipe for future maintenance purposes.\r\n3.	The electrician, permit receiver and site engineer shall be available on the location during the excavation, installation of sleeves and backfilling around the pipe.\r\n4.	Consider replacing the title to "Proposed protection for Existing 13.8 kV cable for Sonar".\r\n5.	A shop drawing should not have options but direct instruction to implement.\r\n6.	Delete the FOC cable shown in option 2 and replace with 1-3C-35mm2 13.8 KV Power Cable.\r\n7.	Work can start but a re-submission is necessary showing these comments.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'MV Cable, Duct Bank', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-836/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1175, 1204, 43, 'SAPMT has reviewed the subject submittal dated June 04, 2014 and has the following comments:\r\n1.	Referring to SDS 028, IC is urged to provide the details of transition at the end of soil improvement.\r\n2.	Revise the alignment according to these sections and resubmit.\r\n3.	Work can start based on the sections in this submittal and IC is urged to provide the above mentioned information within 3 days.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'KAM Road Section', 'Complete', '2014-06-10', 0, 25, 0, 26, 'L-840/14', '2014-06-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1176, 1207, 43, 'Please find attached a CD containing the final report of crash rating test (M30/M50) conducted by Texas A & M Transportation Institute (TTI) according to ASTM F2656-07 for the precast wall of KAUST-Perimeter Security Systems project.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'TTI, Crash Test, Final Report', 'Complete', '2014-06-08', 0, 25, 0, 26, 'L-834/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1177, 1205, 43, 'SAPMT has reviewed the subject submittal dated June 04, 2014 and has the following comments:\r\n1.	Regarding HVAC Sleeves Schedule - XB-S7, XB-S8, XB-S9, XB-S10, XB-S11 & XB-S12 in all drawings are 230 mm from Grid C and not from Grid B.\r\n2.	Locations of HVAC sleeves XB-S3, XB-S4, XB-S9 and XB-S10 in all drawings shall be revised as per IFC drawings.\r\n3.	It is preferable that the SPU-05-IU is not mounted above the Power Panel and Lighting Contactor Panel. (Refer to VA-846676-01 and VA-846685-01).\r\n4.	It is preferable that the SPU-01-IU is not mounted above the Fire Alarm Control Panel. (Refer to BA-846682-01 and VA-846685-01).\r\n5.	Sleeves penetrating structural concrete shall meet the requirements of the ACI 318 for reinforced concrete, chapter 6 section 6.3.\r\n6.	Unless the codes specify, maintain consistency in usage of units of measurement.\r\n7.	Provide the related standards in the notes.\r\n8.	Provide sections to show elevations and also to show enough concrete cover.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Location of Sleeves', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-880/14', '2014-07-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1178, 1206, 43, 'SAPMT has reviewed the subject submittal dated June 04, 2014 and has the following comments:\r\n1.	It is preferable not to mount an air conditioner above the electrical panels.\r\n2.	Improve the drafting quality of submittals by maintaining consistency in line thicknesses, units of measurements and colors etc.\r\n3.	Correct the wrongly written title block on DWG IC-SD-846730-101-00.\r\n4.	Sleeves penetrating structural concrete shall meet the ACI 318 for reinforced concrete, chapter 6 section 6.3.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Location of Sleeves', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-881/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1179, 1208, 43, 'Referring to the meeting held between KAUST, SEC, SAPMT and ICC on site for relocation of SEC poles/ conductors and affects to the old layouts after the removal of the ditch from the scope of KAUST-Perimeter Security Systems project, a revised layout is attached for coordination by KAUST with SEC.\r\n\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.\r\n', 'Relocation, SEC Poles', 'Complete', '2014-06-07', 0, 25, 0, 26, 'L-838/14', '2014-06-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1180, 1209, 43, 'SAPMT has reviewed the subject submittal dated June 03, 2014 and has no objection with the following comments:\r\n1.	The provided quantities shall meet the required grounding system ohmic value as stated in SAES P-111.\r\n2.	The provided quantities for bus bar shall be two hole lugs as per project requirement. \r\n3.	Provide the correct catalog and related specifications.\r\n4.	Provide necessary Fiberglass with 250mm dia, with angle steel plate cover as shown in IFC drawing VA-846492.\r\n5.	Grounding rods, aerial rods and copper clamps shall be UL listed and labeled.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Grounding, Lighting System', 'Complete', '2014-06-30', 0, 12, 0, 26, 'L-843/14', '2014-06-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1181, 1216, 43, 'SAPMT has reviewed the subject submittal dated June 07, 2014 and has no objection with the following comments:\r\n1.	Ensure that all fire alarm devices are UL listed.\r\n2.	Ensure that Fire alarm Control Panel and Notification devices will meet SAES B-014 Para. 7 and IFC drawings.\r\n3.	Programming software and dongle key (If required) to be included in the BOQ.\r\n\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Fire Detection, Fire Alarm', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-854/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1182, 1215, 43, 'SAPMT has reviewed the subject submittal dated June 07, 2014 and has no objection with the following comment:\r\n•	ICC is urged to include the quality personnel’s contact numbers in QA/QC Organizational Chart in MQMR of June 2014.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Quality Management Report', 'Complete', '2014-06-30', 0, 12, 0, 26, 'L-846/14', '2014-06-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1183, 1214, 43, 'SAPMT has reviewed the subject submittal dated June 07, 2014 and has no objection with the following comments:\r\n1.	Ensure appropriate drainage for water condensation from HVAC units is done.\r\n2.	Provide rebar fixing details around the sleeves to avoid cracking.\r\n3.	Consider including equipment layouts in the shop drawing to visualize the sleeve placements.\r\n4.	It is IC’s responsibility to ensure that all designs and construction are done according to applicable standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Location of Sleeves', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-879/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1184, 1218, 43, 'SAPMT has reviewed the subject submittal dated June 08, 2014 and has no objection with the following comment:\r\n•	Use Cicobitumen WB-60.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Bituminous Paint', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-845/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1185, 1217, 43, 'SAPMT has reviewed the subject submittal dated June 08, 2014 and has the following comment:\r\n•	Mr. Marcos P. Taloza Jr. is not acceptable for the position of “QC Inspector – Multi Discipline (Civil, Plumbing & HVAC)â€ based on observations during his personal test/ interview.  \r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'QC Inspector', 'Complete', '2014-06-30', 0, 12, 0, 26, 'L-849/14', '2014-06-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1186, 1210, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0632 dated June 04, 2014 and has rejected with the following comment:\r\n•	IC is urged to study the Para 1.3.1 in Appendix-B “Architectural Design Criteriaâ€ which states that the architectural design basis covers new buildings and fence requirements. Additionally, in common industry practice, and for the purposes of the architectural design the fence/ boundary wall is considered as a part of the building.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Paint', 'Complete', '2014-07-11', 0, 25, 0, 26, 'L-917/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1187, 1211, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0630 dated June 05, 2014 and has rejected with the following comments:\r\n1.	Bid drawing PA-000103 shows the clearance between Microwaves Transmitter and Receiver for about 20 meters to 160 meters distance, this clearance is within the range of manufacturer recommendations (see CIAS letter dated May 29, 2014).\r\n2.	High Commission on Industrial Security (HCIS) does not mention distance requirements between Fence to MIDS, contractor has to position the MIDS between camera pole and Fence that will meet Bid Drawing PA-000103 and Manufacturer recommendation without extra cost to Saudi Aramco.\r\n3.	Contractor has to ensure 100% compliance to IDAS Functional Specification Document (FSD) PE-000072.\r\n4.	The claim is invalid since the ditch removal has no technical impact in the IDAS System, however changing the locations of the microwave devices to ensure system performance is under the responsibility of the contractor and part of the scope.\r\n5.	Both IDAS FSD and HCIS requirement do not limit the distance between two microwaves at exact 160 meters and it’s mentioned that there will be an option to adjust the detection plus/minus 150m or better (see note no. 1 of PA-000103).\r\n6.	IC is urged to consider the fact that the scope of work has two options for arrangement of security layers, one with IDAS next to wall and one with IDAS away from wall, and it is anticipated that IC has taken both options into account before the award of contract.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'IDAS Impact, Ditch Removal', 'Complete', '2014-11-06', 0, 87, 0, 46, 'L-1041/14', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1188, 1212, 43, 'The claims being made by IC were rejected in SAPMT letter No L-666/14 because they did not have any base and it does not mean that all previous correspondence becomes null and void. Refer to letter no. K&TPD/KRP&SFPD/SF/L-400/14, 315/13 & 289/13 on the subject. SAPMT shall not accept any materials on site if they do not meet the standards given in the scope and IC has the responsibility to prove that such standards have been achieved with appropriate testing according to the quality requirements of the project. K-rating is not a standard that can be proven merely by design, because the ratings are derived from a standard which requires testing.\r\nIt is further stated that all other materials for the project which require quality to be met to certain standards or ratings shall not be accepted on site unless they carry test certifications to prove adherence with standards. Design calculations alone shall not be accepted when products require crash rating or fire rating etc. according to industry norms.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Crash Rating Test', 'Complete', '2014-11-06', 0, 87, 0, 46, 'L-967/14', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1189, 1213, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1190, 1219, 43, 'SAPMT has reviewed the subject submittal dated June 09, 2014 and has rejected with the following comments:\r\n1.	Use 9com # 6000000686 for "Building; Space Frame; Steelâ€.\r\n2.	Use Inspection Level Two (2) for space frame structure.\r\n3.	M/s. USKON Space Frame Turkey with manufacturing ID: 3003091 have been put on hold and cannot be used.\r\n4.	IC is urged to contact Saudi Aramco to acquire an up-to-date list of approved manufacturers.\r\n', 'USKON Space Frame', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-882/14', '2014-07-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1191, 1220, 43, 'For Information Only', '', 'Complete', '2014-07-01', 0, 12, 0, -1, 'For Information Only', '2014-07-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1192, 1221, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1193, 1222, 43, 'SAPMT has reviewed the subject submittal dated June 07, 2014 and has the following comment:\r\nBI	Transmittal Type	Transmittal Ref. #	IL no.	Description	9com	Level of Inspection	Status\r\n25-00026	IAP	IAP-03	107000097718	FBEC\r\nRe-Bar	6000000684	1	Approved \r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'FBEC Reinforcing Bar', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-863/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1194, 1223, 43, 'SAPMT has reviewed the subject submittal dated June 08, 2014 and has the following comment:\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	RP	RP-014	MV Cable	6000000797	1	Approved \r\n\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'MV Cable', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-850/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1195, 1224, 43, 'SAPMT has reviewed the subject submittal dated June 09, 2014 and has the following comments:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	RP	RP-015	UPVC Pipe and Fittings	6000000031/ 6000000216	0	Approved with Comments \r\n\r\n1.	This manufacturer SAPPCO is not approved for 9COM: 6000000216.\r\n2.	SAPPCO is approved for only the 9COM 6000000031 which is limited to Pipe Sizes ½" to 10".\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'UPVC Pipe', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-851/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1196, 1225, 43, 'SAPMT has reviewed the subject submittal dated June 07, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'UTP', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-866/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1197, 1226, 43, 'For Information Only', '', 'Complete', '2014-07-01', 0, 12, 0, -1, 'For Information Only', '2014-07-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1198, 1227, 43, 'SAPMT has reviewed the subject submittal dated June 08, 2014 and has no objection with the technical aspects of the submission. IC is urged to provide a scope of work for including the 2500KW generators in the contract and excluding the 1000KW generators mentioning the reasons and justifications for the variation. The revised scope with Qty shall include all supply, installation, commissioning and coordination of machinery, panels, parts, fixtures, equipment, accessories, ancillaries required to fulfill the needs of the project. \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Diesel Generator', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-844/14', '2014-07-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1199, 1228, 43, 'SAPMT has reviewed the subject submittal dated June 08, 2014 and has the following comments:\r\n1.	Mr. Ricky Flores is conditionally approved as “QC Inspector – Electrical & Instrumentationâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory/ poor performance. \r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'QC Inspector', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-848/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1200, 1229, 43, 'SAPMT has reviewed the subject submittal dated June 08, 2014 and has the following comments:\r\n1.	Mr. Riasat Ali Khan is conditionally approved as “QC Inspector – Telecommunicationâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory/ poor performance. \r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'QC Inspector', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-847/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1201, 1230, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1202, 1231, 43, 'SAPMT has reviewed the subject submittal dated June 09, 2014 and has the following comments:\r\n1.	Mr. Sarfraz Ahmed is conditionally approved as “QC Inspector - (Civil)â€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his poor/ unsatisfactory performance.  \r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'QC Inspector', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-852/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1203, 1232, 43, 'SAPMT has reviewed the subject submittal dated June 09, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Fire Rated Sealant', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-861/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1204, 1233, 43, 'SAPMT has reviewed the subject submittal dated June 10, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Polywater, FOC Lubricant', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-858/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1205, 1234, 43, 'SAPMT has reviewed the subject submittal dated June 10, 2014 and has the following comments:\r\n1.	Manufacturer is not approved for 9com # 6000001075.\r\n2.	Vented Lead Acid and Valve Regulated Lead Acid (VRLA) shall meet the requirements of SAES P-103 and project specification.\r\n3.	Provide shop drawing for the equipment layout inside the room.\r\n4.	UPS and Batteries inside the rooms shall meet the required maintenance clearance.\r\n5.	Provide Battery Racks and Maintenance Cabinet as per SAES P-103 para. 6.2.12.\r\n6.	Provide the summary sheet of each building.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Battery', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-859/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1206, 1235, 43, 'Activities mentioned by IC are not causing any delays to the project activities at KAM road and at the fence. IC is urged to deal with interfaces according to Clause 1.1.17, 3.9 and 3.10 of SCH-B.\r\n\r\nIn case IC requires, a meeting can be arranged with SAPMT to close this matter as soon as possible.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Existing Utilities', 'Complete', '2015-01-07', 0, 89, 0, 46, 'L-1288/15', '2015-01-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1207, 1236, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1208, 1237, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1209, 1238, 43, 'For Information Only', 'Inspection Schedule', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1210, 1239, 43, 'The Payment Application was approved and SES issued to ICC.', 'Invoice, Payment Application', 'Complete', '2014-10-20', 0, 25, 0, -1, 'For Record Only', '2014-10-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1211, 1240, 43, 'For Information Only', 'LRSS Cameras', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1212, 1241, 43, 'SAPMT has reviewed the subject submittal dated June 10, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Communication Marker', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-860/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1213, 1242, 43, 'SAPMT has reviewed the subject submittal dated June 12, 2014 and has the following comments:\r\n1.	The proposed route of FOC cable is required due to the fact that IC has voluntarily chosen to build the KAM access road on a route which is different from IFB between ST 1850 to ST 3300, so that construction works in the sea water are avoided and timelines can be improved. While SAPMT has agreed to IC proposal of rerouting KAM road between ST 1850 to ST 3300, IC shall ensure that it is done with no cost and time impacts to the project.\r\n2.	Resubmit the re-routing plans by superimposing the proposed routing layout with new KAM access road/ corridor and King Abdullah Monument drawing plans.\r\n3.	Provide the coordinates for corners and curves of the propose fiber optic cable layout and distances desired from the edge of the road.\r\n4.	Ensure that the propose layout is coordinated with the existing underground FOC, and electrical cables running for King Abdullah Monument Project.\r\n5.	Show locations of markers/ posts.\r\n6.	Provide fold out details of manholes.\r\n7.	Provide details and schematic diagram and splicing details of the proposed 24 core fiber cable to the existing IDAS cable.\r\n8.	Provide plan and splicing details of the existing primary and redundant 96 core fiber cable of IDAS.\r\n9.	Explain how existing optipeds and service manhole shall be removed.\r\n10.	IC/SCEC to verify the coordinates and elevation of the FOC routing and make certain that it is outside the road shoulder and cover is provided according to the standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'FOC Route', 'Complete', '2014-07-15', 0, 25, 0, 46, 'L-929/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1214, 1243, 43, 'SAPMT has reviewed the subject submittal dated June 12, 2014 and has rejected with the following comment:\r\n•	The contractor’s response to SAPMT comments is not acceptable and requires more details.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Security Systems', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-910/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1215, 1244, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0659 dated June 14, 2014 and has rejected it with the following comments:\r\n•	It is IC responsibility to familiarize itself of all site conditions before bidding for an LSTK contract. It is common knowledge that areas close to the sea might require soil improvement or stabilization. IC shall propose designs/ ways to avoid the communication cables.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', 'Soil Improvement, Services Protection', 'Complete', '2014-11-11', 0, 87, 0, 46, 'L-1140/14', '2014-11-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1216, 1245, 43, 'SAPMT has already replied to this request with letter no. K&TPD/KRP&SFPD/SF/L-925/14 dated July 10, 2014 and work shall carry on according to the approved IFC.\r\n\r\nIn case IC requires, a meeting can be arranged with SAPMT to close this matter as soon as possible.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'Operator Rooms', 'Complete', '2015-01-06', 0, 89, 0, 46, 'L-1289/15', '2015-01-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1217, 1246, 43, 'Reference to KAUST letter No. KAUST-M&U-14-0058, we would like to inform you that the precast wall will have logo colors as agreed earlier between KAUST and SAPMT. Painting of KAUST logo will take place upon the completion of panel’s erection.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel. No. 012 422 4393\r\n', 'Logo Color', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-871/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1218, 1247, 43, 'Reference to KAUST letter no. KAUST-M&U-0056 dated June 12, 2014 (copy attached), the following is SAPMT responses to each point:\r\n\r\n1-	The scope of work approved by KAUST for the subject project calls for ordinary palm trees, whereas the “Barhiâ€ types are three times more expensive. KAUST is required to seek FPD approval on “Barhiâ€ plantation. \r\n\r\n2-	The Required safety measures to avoid any potential injuries will be provided according to SA Standards.\r\n\r\n3-	The scope of work approved by KAUST shows single arm street lights on both sides of the road, which also matches with the existing pattern on the Road No. 2. The lux calculations can be provided if necessary to prove that enough light according to applicable standards shall be available. The double arm street light on the median cannot be provided as it is not a part of the agreed scope of work.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel. No. 012 422 4393.\r\n', 'Side Walks, Landscaping', 'Complete', '2014-07-22', 0, 25, 0, 26, 'L-872/14', '2014-07-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1219, 1248, 43, 'SAPMT has reviewed the subject submittal dated June 14, 2014 and has the following comment:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	IL no.	Description	9com	Level of Inspection	Status\r\n25-00026	IAP	IAP-04	107000097717	Out Door LV Switch Rack	6000000886	2	Approved with Comment\r\n\r\n•	ITP will be finalized at PIM.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Outdoor LV Switchrack', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-862/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1220, 1249, 43, 'SAPMT has reviewed the subject submittal dated June 15, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Protection, 13.8KV Cable, Sonar', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-857/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1221, 1250, 43, 'SAPMT has reviewed the subject submittal dated June 14, 2014 and has the following comments:\r\n1.	The samples are rusted on the sample board and shall be replaced with better quality of submission.\r\n2.	The sample boards shall show titles.\r\n3.	Submit two samples, 400 x 400 mm in size illustrating finish color and texture as per project specification section 09220 Para 1.05.\r\n4.	Specify exactly which material shall be used in which area.\r\n5.	All previously approved and new shop drawings shall be revised or created to reflect the approved materials.\r\n6.	Avoid cutting the samples for galvanized accessories.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Plastering, Block Accessories', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-887/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1222, 1251, 43, 'For Information Only', '', 'Complete', '2014-07-01', 0, 12, 0, -1, 'For Information Only', '2014-07-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1223, 1252, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0663 dated June 15, 2014 and the proposal made by IC is not acceptable.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Subcontractor QC Inspector', 'Complete', '2014-11-02', 0, 25, 0, 46, 'L-1141/14', '2014-11-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1224, 1253, 43, 'SAPMT has reviewed the subject submittal dated June 15, 2014 and has no objection with the following comments:\r\n1.	Ensure that all MV cable running under roads were protected by duct banks.\r\n2.	Duct banks for MV cable shall comply with SAES P-104.\r\n3.	Ensure that MV cable clearance with other utilities is within the minimum requirement of 300 mm as stipulated in Saudi Aramco standards.\r\n4.	Provide detail shop drawing for all underground electrical and non-electrical utilities that will pass through box culverts 3 & 4 and Wadi Khulais Culvert.\r\n5.	Cable routing of main power cable in drawing no. VA-845614-006, PC-001 & 003 shall be connected to new SEC-2.\r\n6.	Reflect the routes proposed for the relocation of existing SEC MV cables from existing SEC substation.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', '13.8KV Cable Layout, IFC', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-867/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1225, 1254, 43, 'SAPMT has reviewed the subject submittal dated June 16, 2014 and has rejected with the following comments:\r\n1.	The proposed vendor is not approved by Saudi Aramco for the services mentioned.\r\n2.	IC is urged to finalize this resource requirement before 10 July 2014.\r\n3.	According to the Schedule A, the pre-qualification documents shall include the list/ quantities of manpower, equipment and testing agencies designated to complete the scope of work.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Rawabina, Landscaping & Irrigation', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-892/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1226, 1255, 43, 'SAPMT has reviewed the subject submittal dated June 15, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Section Soil Improvement', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-856/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1227, 1256, 43, 'SAPMT has reviewed the subject submittal dated June 14, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'MV Cable', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-868/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1228, 1257, 43, 'SAPMT has reviewed the subject submittal dated June 12, 2014 and has no objection with the following comments:\r\n1.	Referring to SASD: AA-036374-001, The SS locking bolts shall have a pentagonal head, 5/8" dia and 3-1/4" long.\r\n2.	Contractor shall ensure the full compliance of applicable Saudi Aramco standards and specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Communication Manhoels', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-875/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1229, 1258, 43, 'SAPMT has reviewed the subject submittal dated June 16, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'Heat Stress', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-855/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1230, 1259, 43, 'SAPMT has reviewed the subject submittal dated June 15, 2014 and has no objection with the following comments:\r\n1.	Use the applicable 9com # 6000000644 for Steel Plate.\r\n2.	Contractor shall proceed as per designer’s recommendation.\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Fixing Bolt, Steel Plate', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-869/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1231, 1260, 43, 'SAPMT has reviewed the subject submittal dated June 10, 2014 and has the following comments:\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level of Inspection	Status\r\n25-00026	RP	RP-016	Package Substation 	NA	2	Approved with Comments \r\n\r\n1.	ITP shall be finalized during PIM.\r\n2.	All components shall be procured from approved source.\r\n3.	RMU test certificate from manufacturer shall be submitted and reviewed by TPI. \r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Package Substation', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-878/14', '2014-07-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1232, 1261, 43, 'SAPMT has reviewed the subject submittal dated June 17, 2014 and has the following comments:\r\n1.	Include details/ coordinates of the tie-in point, existing irrigation lines etc.\r\n2.	The attached prints are not legible.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Irrigation', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1029/14', '2014-09-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1233, 1262, 43, 'SAPMT has reviewed the subject submittal dated June 17, 2014 and has no objection with the following comments:\r\n1.	It is advisable to cover the gravel with geotextile.\r\n2.	Ensure that the elevation of the cable does not interfere with other utilities & provide enough cover/ clearance as per applicable Saudi Aramco standards.     \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'LV Cable, Irrigation', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-897/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1234, 1263, 43, 'SAPMT has reviewed the subject submittal dated June 18, 2014 and has no objection with the following comments:\r\n1.	Use the applicable 9com # 6000010380 for Sign.\r\n2.	Ensure that surface marker will be provided for electrical sign post area of MV and LV cables as per standard drawing AB-036273-001.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Electrical Sign Post', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-870/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1235, 1264, 43, 'For Information Only', 'Ramadan Timing', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1236, 1265, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0661 dated June 18, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.\r\n', 'Internal Audit, 15%', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-864/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1237, 1266, 43, 'SAPMT has reviewed the subject submittal dated June 18, 2014 and has the following comments:\r\n1.	Exhaust fans shall comply with all the notes stated on the Schedule of Exhaust fans in each drawing.\r\n2.	Exhaust fans on drawings # VA- 846 541/001 & VA-846 934/001 shall be of Explosion proof type.\r\n3.	Attach copies of the missing relevant drawings of the exhaust fans given in the Bulk Material Take-off list which are as the following: VA- 846 630/001, VA-846 631/001, VA-846 636/001, VA-846 909/001, VA-846 910/001, VA- 846 969/001, VA- 846 970/001.\r\n4.	The Exhaust fans specifications on the drawing VA-846 934/001 & VA-846941/001 are not included in the MTO-List. It shall be included.\r\n5.	Contractor should select and highlight the different Exhaust fans with the Model number on the Vendor Catalogue cut sheets according to the specification stated on the respective drawing.\r\n6.	Arrange the submittal is a systematic order where unnecessary information is not included and approvals required are enlisted explicitly.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Exhaust Fans', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-894/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1238, 1267, 43, 'SAPMT has reviewed the subject submittal dated June 17, 2014 and has the following comment:\r\nBI	Transmittal Type	Transmittal Ref. #	IL no. 	Description	9com	Level of Inspection	Status\r\n25-00026	IAP	IAP-005	107000098111	MV Switchgear	6000000878	2	Approved with Comments \r\n\r\n•	ITP shall be finalized during PIM.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'MV Switchgear', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-877/14', '2014-07-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1239, 1268, 43, 'SAPMT has reviewed the subject submittal dated June 19, 2014 and has no objection with the following comment:\r\n•	Flexible conduits shall be liquid tight, UV resistant and only be used as stipulated in SAES P- Series and National Electrical Code.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Metallic Flexible Conduits', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-890/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1240, 1269, 43, 'SAPMT has reviewed the subject submittal dated June 21, 2014 and has no objection with the following comments:\r\n1.	Ensure that traffic signal and controller are heavy duty type.\r\n2.	Provide the shop drawings for mounting of signal lights, conduiting and location of the controller.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Traffic Signal', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-873/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1241, 1270, 43, 'SAPMT has reviewed the subject submittal dated June 19, 2014 and has no objection with the following comments:\r\n1.	Referring to ACI 308R, ACI 308R and ACI 308.1-98 recommendations and SAIC – Q – 1028, steam curing is acceptable and curing compound shall not be used for curing of precast and pre-stressed concrete elements. Hence, Clause 6.2 shall be deleted from the method statement.\r\n2.	Repairs of defects in concrete shall be done according to specific Aramco approvals and applicable standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'ITP, Checklist', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-876/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1242, 1271, 43, 'SAPMT has reviewed the subject submittal dated June 19, 2014 and has the following comments:\r\n1.	Use correct 9com# as 60000001880.\r\n2.	The Vendor ID 10035430 provided is for Honey Well USA and not for suggested vendor.\r\n3.	Ajib ltd. is not an Aramco approved vendor.\r\n4.	The subject of the submittal is not clear and may be changed to "DDC panel for Package HVAC unit".\r\n5.	Attach HVAC control design and Data for DDC panels.\r\n6.	Suggest the DDC controller model for each building according to the design drawings and number of I/Os.\r\n7.	Ensure that DDC controller is provided wherever necessary.\r\n8.	Provide enclosure dimensions.\r\n9.	Provide shop drawings showing the selector switch, pilot lamps, and push buttons etc. Provide internal wiring arrangement, showing the transformer and circuit breaker position, wire trunking and relay arrangements\r\n10.	Include necessary catalogs for all related electrical and control devices to be used for the DDC.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'DDC', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-919/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1243, 1272, 43, 'No Comments, For Information only', 'Inspection Schedule', 'Complete', '2014-07-20', 0, 25, 0, -1, 'For Information Only', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1244, 1273, 43, 'SAPMT has reviewed the subject submittal dated June 17, 2014 and has the following comments:\r\n1.	M/s. GAC has already been approved and M/s. Dar Al Manajim Asphalt & Contracting (DARMCO) can be used as an alternative, but the work according to the approved plan shall not be affected/ delayed.\r\n2.	The following documents shall be included (one time base approval);\r\na.	Signed copy of Contractor’s initial QC Survey Checklist Appendix A3.\r\nb.	Proposed asphalt mix design as per project requirements including copies of the internal trial batches.\r\nc.	Trial batch of the proposed asphalt mix design to be conducted by Saudi Aramco approved third party civil testing agency and to be witnessed by SAPID representative.\r\nd.	CV of proposed QA/QC personnel and safety officer (including training certificates and seminars) for review and prequalification purposes, as a minimum requirements One (1) QC Engineer, One (1) Lab Technician and One (1) Field Technician. Prequalification of proposed QA/QC personnel will be conducted upon receipt and acceptance of the CV’s.\r\ne.	Copy of ISO Certification, if available.\r\nf.	Batch Plant Serial Number of the central mixer.\r\ng.	Controlled copy of list of generator sets (Brand Name, Model, Capacity, Serail Number).\r\nh.	Emergency evacuation plan.\r\ni.	Tracking mixture of fire extinguishers and first aid kit.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'DARMCO', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-883/14', '2014-07-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1245, 1274, 43, 'For Information Only', '', 'Complete', '2014-07-01', 0, 12, 0, -1, 'For Information Only', '2014-07-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1246, 1275, 43, 'No Comments, For Information Only', '', 'Complete', '2014-07-08', 0, 25, 0, -1, 'For Information Only', '2014-07-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1247, 1276, 43, 'SAPMT has reviewed the subject submittal dated June 22, 2014 and has no objection the following comment:\r\n•	IC is to ensure that all road crossings for existing utilities and project infrastructure utilities are done according to Saudi Aramco Standards with no charge to Saudi Aramco.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'KAM Pipe Culvert', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-884/14', '2014-07-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1248, 1277, 43, 'SAPMT has reviewed the subject submittal dated June 22, 2014 and has no objection with the following comments:\r\n1.	Ensure that the LED Picture sign display is heavy duty type and its weight and other external conditions are appropriately accounted for before installing on the structure of the shed.\r\n2.	Ensure that shop drawings for mounting the sign display and conduiting will be provided before installation starts.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Picture Sign Display', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-891/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1249, 1278, 43, 'For Information Only', '', 'Complete', '2014-07-01', 0, 12, 0, -1, 'For Information Only', '2014-07-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1250, 1279, 43, 'For Information Only', 'QC Inspector Replacement', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1251, 1280, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0667 dated June 21, 2014 and has rejected with the following comments:\r\n1.	IC is urged to understand the nature of LSTK contracts where CONTRACTOR assumes all risks associated with the provision and fulfillment of its obligations under this Contract to the extent they require.\r\n2.	IC is urged to study contract documents before sending any letters to SAPMT and making any claims. The following para 6.1 from SCH-A shall be self-explanatory; "CONTRACTOR acknowledges that it has thoroughly investigated, or has had the opportunity to do so, and satisfied itself as to all general and local conditions affecting the WORK, including, but not limited to: transportation and access to the WORK Site, including the availability and conditions of roads; topography and ground surface conditions at the WORK Site, including the nature and quantity of surface and subsurface conditions, materials or obstacles to be encountered to the extent such conditions are not latent or concealed; disposal, handling and storage of materials; availability and quality of labor, water and electric power, climatic conditions, tides and ground water; and equipment, machinery and materials required by CONTRACTOR prior to and during performance of the WORK. The failure of CONTRACTOR to acquaint itself with these conditions will not entitle CONTRACTOR to any additional compensation and will not relieve it from the responsibility for meeting the Scheduled Completion Date or the Critical Milestone Dates".\r\n3.	The para 10 quoted by IC in its letter provides a way of administration of changes in general and not the technical requirements of the issue at hand.\r\n4.	The specifications section 02110 requires that all unwanted materials shall be removed to a depth not less than 0.45m below the original surface level OR to the natural rock elevation.\r\n5.	There is no reason to believe that the soil conditions require an improvement and thus the design provided by IC is not acceptable. Backfilling can be done with fill material in horizontal layers according to Saudi Aramco Standards and any other alternatives proposed by IC shall be considered voluntary and shall bear no extra costs to Saudi Aramco.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Soil Improvement, Garbage Area', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-918/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1252, 1281, 43, 'SAPMT has reviewed the subject submittal dated June 22, 2014 and has the following comments:\r\n1.	Mr. Rolando L. Relleja is conditionally approved as “QC Inspector – Civilâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his poor / unsatisfactory performance.\r\n', 'QC Inspector', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-886/14', '2014-07-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1253, 1282, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/14/0668 dated June 22, 2014 and has the following comment:\r\n•	A revised organization chart shall be submitted every time a change is made to the key personnel.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422 4423.\r\n             \r\n', 'Organization Chart', 'Complete', '2014-11-03', 0, 25, 0, 46, 'L-570/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1254, 1283, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0670 dated June 22, 2014 and is rejected on the following grounds.\r\n1.	The prices are meant to be confidential and not to be submitted in open letters.\r\n2.	The prices are submitted upon invitation after both parties have agreed upon quantities.\r\n3.	IC is urged to refer to the signed contract between both parties and follow the conditions of the contract.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Demolition Work', 'Complete', '2014-08-13', 0, 25, 0, 46, 'L-975/14', '2014-08-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1255, 1284, 43, 'For Information Only', '', 'Complete', '2014-07-01', 0, 12, 0, -1, 'For Information Only', '2014-07-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1256, 1285, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1257, 1286, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1258, 1287, 43, 'SAPMT has reviewed the subject submittal dated June 22, 2014 and has the following comments:\r\n1.	Provide and attach Heat Load Calculations of rack/cabinet where the results must show that the heat generated by the installed server can be accommodated by the proposed rack or cabinet.\r\n2.	Ensure that the proposed model is appropriate to use for high density servers.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Server Cabinet', 'Complete', '2014-07-07', 0, 25, 0, 26, 'L-900/14', '2014-07-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1259, 1288, 43, 'SAPMT has reviewed the subject submittal dated June 22, 2014 and has the following comments:\r\n1.	Buried garbage/ contaminated soils shall be removed from the entire width of the security corridor, including the IDAS zone and internal and external interface layers/ roads.\r\n2.	IC shall excavate the areas to the depth where undisturbed soil is seen for observation by Saudi Aramco.\r\n3.	IC proposal for excavating 300mm more after the undisturbed soil is reached is acceptable, to ensure no contact with contaminated soils.\r\n4.	Work on excavations can start but the shop drawing shall be revised providing acceptable grain sizes and compaction requirements for the backfill materials/ layers under the foundations.\r\n5.	The revised shop drawing shall also provide elevations after the excavation depths are finalized by Saudi Aramco.\r\n6.	Excavation and Backfilling works shall be done according to SAES-A-114.\r\n7.	Waste disposal and soil improvement/ reclamation shall be done according to the Environmental standards of the Kingdom with no extra costs to Saudi Aramco.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Soil Replacement', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-885/14', '2014-07-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1260, 1289, 43, 'SAPMT has reviewed the subject submittal dated June 22, 2014 and has the following comments:\r\n1.	A shop drawing to show the designated areas shall be developed with proper annotations as necessary, in coordination with the equipment manufacturer.\r\n2.	Ensure to meet the enclosure requirements of SAES-P-104 and SAES-P-100 para 8, and mention in the notes section.\r\n3.	Consider classifying the area between the two buildings as Zone 2 (Class 2, Div.2)\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Area Classification, Fuel Tank', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-893/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1261, 1290, 43, 'SAPMT has reviewed the subject submittal dated June 23, 2014 and has the following comment:\r\n•	More details are required showing the exact routes with coordinates, entry points into the buildings and zoomed in details etc.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Interface, SEC Substation', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-889/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1262, 1291, 43, 'For Information Only', 'Progress Meeting, 39', 'Complete', '2014-07-12', 0, 25, 0, -1, 'For Information Only', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1263, 1292, 43, 'SAPMT would like to reiterate that contractor''s claims for any variations are not acceptable, in relation with the relocation of existing security systems in the Northern and Southern boundaries of KAUST, if caused by making voluntary changes to routes or elements of the KPSS project to facilitate ongoing works. Such changes to routes can be acceptable and approved only if time can be saved and/or constructability can be improved without making any changes to the new perimeter/ legal boundaries. The estimates for claims being submitted by IC are also incorrect as many items are missed and all works are not depicted correctly e.g. dewatering involved if road was to be built on the mangroves. Additionally unsupported variations for outside plant system (OSP) cabling works for Sonar and Radar are invalid and found not acceptable, because IC could not salvage the existing cable for re-use due to lack of skilled workers. According to contract para 1.2.2.1.1.1 and KE-714475 para 10.1.4, Contractor should restore or replace to its original condition any property damaged by the contractor. IC is advised to revise the quantities given in its letter no. KPSS/SA/B/AKR/14/0672 in light of the above and avoid from time wasting correspondence.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Quantities, Take off, KAM', 'Complete', '2014-07-22', 0, 25, 0, 26, 'L-964/14', '2014-07-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1264, 1293, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1265, 1294, 43, 'No Comments, For Information Only', 'QC Supervisor', 'Complete', '2014-07-12', 0, 25, 0, -1, 'For Information Only', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1266, 1296, 43, 'No Comments, For Information Only', 'Camp Inspection', 'Complete', '2014-07-22', 0, 25, 0, -1, 'For Information Only', '2014-07-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1267, 1297, 43, 'SAPMT has reviewed the subject submittal dated June 24, 2014 and has no objection with the following comments:\r\n1.	Consider creating slopes towards the nearest disposal/ soakage points instead of providing slopes for longer distances as seems in the case of visitor building drainage sloping towards the MOT.\r\n2.	It is IC’s responsibility to ensure that all storm water drainage or drainage of any occasional water is kept away from the buildings and not allow any long term ponding/ stagnation.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Grading & Drainage', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-914/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1268, 1298, 43, 'SAPMT has reviewed the subject submittal dated June 24, 2014 and has the following comments:\r\n1.	It is advisable to reinforce the gravel layer with geotextile.\r\n2.	The material for the sleeve for irrigation water pipe shall be submitted for approval and installed according to Saudi Aramco Standards.\r\n3.	The material and sleeve for control cable for irrigation shall be submitted for approval.\r\n4.	Control cables shall be shown in the section.\r\n5.	Justify why sleeve is to be installed instead of direct buried pipe.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n\r\n', 'Irrigation Sleeves', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-912/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1269, 1299, 43, 'SAPMT has reviewed the subject submittal dated June 24, 2014 and has the following comment:\r\n•	IC is urged to attach vendors shop drawings.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'IFC Z Portal', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-907/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1270, 1300, 43, 'SAPMT has reviewed the subject submittal dated June 24, 2014 and has the following comments:\r\n1.	Verify that the building has been designed according to the blast resistance requirements given in IFB and also according to SAES-M-009.\r\n2.	The scale of column sections is very small. Corner column has rebar 8 Φ 16 mm in the Plan detail and has 6 Φ 16 mm in section A-A of drawing VA-846582-001-0F1 & VA-846778-001-0F1, creating a conflict between drawings.\r\n3.	The wall thickness is 350mm in IFB and shall not be reduced without prior approval of justification.\r\n4.	More details of the Roof Beam RB-01 are required.\r\n5.	Provide rebar schedules.\r\n6.	The concrete cover shall be according to general notes in VA-846497-001.\r\n7.	Provide the compression strength of concrete in drawing notes.\r\n8.	While gatehouses can be constructed as shown in the drawings the operator buildings can only be constructed if approved by Saudi Aramco. IC is urged to provide justifications as to why the operator building cannot be merged with the x-ray building.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Guard House, Operator Building', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-915/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1271, 1319, 43, 'Please be noted that the submittal was revised afterward and approved by VID Rep. Now consider the submittal status "No Objection (A)" as follows: \r\n\r\nSAPMT has reviewed the subject submittal dated June 25, 2014 and has the following comments:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level of Inspection	Status\r\n25-00026	PR	RP-017	Fire Detection and \r\nFire Alarm System	6000001301	Zero(0)	Approved \r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Fire Detection, Fire Alarm System.', 'Complete', '2014-07-11', 0, 25, 0, 26, 'L-921/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1272, 1318, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1273, 1317, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0679 dated June 26, 2014 and has the following comments:\r\n1.	IC missed all the project milestones especially the mobilization(Precast works scheduled to commence on October 20, 2013 as per approved schedule, whereas the molds were received only at third week of March 2014 and the yard was ready for inspection at first week of April 2014) and that’s why the factory was not ready when it should have been.\r\n2.	Idling means no work at all. The agreement from IC proves that there were other works to be done on the project at the time SAPMT requested to suspend a part of work and thus claims for idling are baseless. Workers and equipment’s should have been rescheduled to other activates promptly but as a matter of fact were rescheduled un-diligently. Despite various SAPAMT requests, other activates were not started, were slow, being done unprofessionally, damaging KAUST property and causing unnecessary delays. Various pictures were sent to IC to suggest hiring specialized skills. SAPMT agrees to compensate the contractor only for the significant resources which were acquired specifically for a single activity and could never be used anywhere else on the project.\r\n3.	There are more than 20 buildings of various sizes in the project requiring 82340 man-hours according to the approved schedule. It roughly means 1000 man-hours for 82 days or 125 workers for 82 days. At the moment there is hardly any work being done on the buildings (Plan is 40.8% whereas Actual is 5.8%). The shop drawings are still not completed. None of the buildings have come out of the ground yet. The delayed shop drawings, the speed of work on buildings and culverts and quality of submittals depicts the inadequate site and resource planning being done by IC.\r\n4.	Please refer to the daily tracking schedule for KAM road where the earthworks have been extremely behind schedule and have never been ahead of schedule since the start of the project, showing that not enough resources have ever been deployed by the contractor on any activity so far.\r\n5.	IC failed to comply with paragraph 14.4 of Schedule-A where IC is required to submit daily time sheet to SAPMT for confirmation “no later than the following scheduled work dayâ€. None of the time sheets were submitted on the following scheduled work day and verified by SAPMT.\r\n6.	This closes the discussion about claims for idling of manpower when a part of the project scope was suspended by SAPMT. If IC disagrees with SAPMT comments, IC may appeal to Saudi Aramco Contracting Department as provided for in Schedule-A Para 19. \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Time Sheet, Fatayerji', 'Complete', '2014-07-12', 0, 25, 0, 26, 'L-923/14', '2014-07-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1274, 1316, 43, '', '', 'Complete', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1275, 1315, 43, 'The notice to claim is rejected as the existing utilities are not causing delays to the project. There is more than 9km of wall to be constructed, many buildings are yet to be started and work on south culvert is on hold by IC because of technical issues to be resolved by IC.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Existing Utilities', 'Complete', '2015-01-12', 0, 25, 0, 46, 'L-1283/15', '2015-01-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1276, 1314, 43, 'SAPMT has reviewed the subject submittal dated June 26, 2014 and has the following comments:\r\n1.	Consider placing the water and sewage holding tanks further away from each other.\r\n2.	VA-846996-001-0F1 shows sewage lines going into the potable water tank, which is not acceptable.\r\n3.	The pump control panel is shifting locations between different drawings, which are not acceptable. It is advisable to place the panel on the nearest wall.\r\n4.	The manhole covers and frames shall be designed to resist corrosion due to vicinity near sea, gases from sewage and must meet with KAUST existing practices.\r\n5.	Separate shop drawings shall be submitted by IC to show sleeves through the walls/ foundations as necessary.\r\n6.	Specify the grain sizes and compaction requirements of all back fill materials.\r\n7.	Include all drawings showing details of guardhouse, kitchens and toilets.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Guard House, Wadi Wesami', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-916/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1277, 1313, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0671 dated June 28, 2014 and has the following comments:\r\n1.	Mr. Mohammed Mushtaque Ahmed is conditionally approved as “QC Inspector for Precast Facilityâ€ for One (1) month.\r\n2.	SAPMT reserves the right to revoke this conditional approval base on unsatisfactory performance.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'QC Inspector, Precast Facility', 'Complete', '2014-07-15', 0, 25, 0, 46, 'L-940/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1278, 1312, 43, 'No Comments, For information Only', 'Inspection Schedule', 'Complete', '2014-07-20', 0, 25, 0, -1, 'For Information Only', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1279, 1311, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1280, 1310, 43, '', '', 'Complete', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1281, 1309, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1282, 1308, 43, 'SAPMT has reviewed the subject submittal dated June 26, 2014 and has rejected with the following comments:\r\n1.	Sanitary drain, waste and vent pipes for buildings shall be ASTM D 2665 with line class 80PV0D1 as per SAES-L-105.\r\n2.	Indicate clearly which pipe and size shall be used for which application/ location.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'UPVC Pipe Sch.40', 'Complete', '2014-07-15', 0, 25, 0, 46, 'L-933/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1283, 1307, 43, 'SAPMT has reviewed the subject submittal dated June 25, 2014 and has no objection. However, it is contractor’s responsibility to ensure the full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'PVC Conduits', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-904/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1284, 1304, 43, 'SAPMT has reviewed the subject submittal dated June 24, 2014 and has rejected with the following comments:\r\n1.	At this stage of construction drawings submitted for acceptance shall be complete in all respect, instead of providing notes like No 12 in VA-847045-001-0F2.\r\n2.	Provide a complete set of drawings.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'IFC Guard House, Wadi Khulais', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-913/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1286, 1301, 43, 'SAPMT has reviewed the subject submittal dated June 25, 2014 and has rejected with the following comments:\r\n1.	All designs shall be concurred by the project designer, especially if any deviations are made from project proposal and project specifications.\r\n2.	Copper pipes are easily available in local market and is non-inspectable item and can be purchased from any reputed manufacturer. Copper pipes are not difficult to install and are a common practice in the plumbing industry.\r\n3.	Provide details of where these pipes have been specified in drawings and/ or in specifications.\r\n4.	Provide details of where these pipes shall be used, mentioning locations and references to drawings.\r\n5.	Provide a list of drawings which shall be amended.\r\n6.	Provide a general estimate of cost differences.\r\n7.	Note that CPVC pipes can be allowed only if the water temperature is less than 71C.\r\n8.	Provide proposed piping material specifications.\r\n9.	IC can resubmit if necessary by completing the basic requirements of a technical query.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Copper Pipe, CPVC Pipe', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-937/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1287, 1302, 43, 'SAPMT has reviewed the subject submittal dated June 25, 2014 and has the following comment:\r\n•	Mr. Ashat-ul-Haq is unacceptable due to not meeting the minimum inspection specialty requirements of Project Schedule Q, Attachment I, Item 3.3 for the position of “QC Inspector – Plumbing & HVACâ€.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-07-07', 0, 25, 0, 26, 'L-899/14', '2014-07-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1288, 1303, 43, 'SAPMT has reviewed the subject submittal dated June 24, 2014 and has no objection with the following comments:\r\n1.	IC is urged to use lessons learnt during these incidences as topics for safety orientations and training to the workers.\r\n2.	All such incident reports shall be archived for safety audits and copies also sent to the Safety Coordinator.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Incident Report', 'Complete', '2014-07-22', 0, 25, 0, 26, 'L-963/14', '2014-07-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1289, 1305, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1290, 1306, 43, 'With reference to the subject matter, the hard and soft copies of Communication and Security Systems HLD and specification documents are enclosed for your reference. Kindly provide your feedback on or before July 13, 2014.', 'HLD, Write-up', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-874/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1291, 1320, 43, 'SAPMT has reviewed the subject submittal dated June 28, 2014 and has the following comments:\r\n1.	The 9com and level of inspection are acceptable.\r\n2.	Provide test report for 1800mm dia manhole instead of the wrongly attached report.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Fiber Glass Manholes, Dia 1800mm', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-920/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1292, 1321, 43, 'SAPMT has reviewed the subject submittal dated June 29, 2014 and has no objection with the following comment:\r\n•	Up-to-date Calibration certificate valid for the maximum duration shall be provided with the material.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Temperature Sensor', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-909/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1293, 1322, 43, 'No Comments, For Information Only', 'Progress Meeting, 40', 'Complete', '2014-07-12', 0, 25, 0, -1, 'For Information Only', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1294, 1329, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0700 dated June 30, 2014 and has the following comments:\r\n1.	Mr. Yasir Ashraf is conditionally approved as “QC Managerâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on unsatisfactory performance.\r\n3.	ICC is urged to fill his current position of “QC Supervisor – Mechanicalâ€ within two (2) weeks.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'QC Manager', 'Complete', '2014-07-06', 0, 25, 0, 26, 'L-888/14', '2014-07-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1295, 1323, 43, 'SAPMT has reviewed the subject submittal dated June 24, 2014 and has the following comments:\r\n1.	Provide schematic diagram or block diagram of the connectivity of the proposed server.\r\n2.	All servers must have redundancy as per Appendix H Section 2.3.2.3 and Operating System must be included.\r\n3.	Provide calculation that the proposed server capacity is enough to accommodate the project''s requirement.\r\n4.	All accessories to be included in the submittal such as monitor, keyboard, mouse, UPS etc.\r\n5.	All quantities to be mentioned in the summary sheet.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Server, Workstation', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-911/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1296, 1324, 43, 'SAPMT has reviewed the subject submittal dated June 24, 2014 and has the following comments:\r\n1.	Include the other LPRS that interfaces with Maxess. \r\n2.	Ensure that the databases for the LPR systems are centralized.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'LPRS', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-906/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1297, 1325, 43, 'No Comments, For Information Only', 'Progress Report, 44', 'Complete', '2014-07-12', 0, 25, 0, -1, 'For Information Only', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1298, 1326, 43, 'SAPMT has reviewed the subject submittal dated June 30, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Visitor Building', 'Complete', '2014-07-15', 0, 25, 0, 46, 'L-931/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1299, 1327, 43, 'SAPMT has reviewed the subject submittal dated June 30, 2014 and has the following comments:\r\n1.	Building shall be designed according to SAES-M-009 and strength requirements given in the IFB.\r\n2.	Confirm that the building size is according to IFB requirements.\r\n3.	Furnish complete set of architectural and structural drawings showing finishes also.\r\n4.	All irrelevant notes shall be removed from the drawings.\r\n5.	Consider reflecting the fire alarm notification devices such as horn, flasher and bell in the plan and elevation details.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'IFC Guard Houses', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-908/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1300, 1328, 43, 'SAPMT has reviewed the subject submittal dated June 29, 2014 and has the following comment:\r\n•	Mr. Arman Ali is unacceptable for the position of “QC Inspector – Electricalâ€ based on observations during his personal test and interview.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-07-07', 0, 25, 0, 26, 'L-898/14', '2014-07-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1301, 1330, 43, 'SAPMT has reviewed the subject submittal dated July 02, 2014 and has no objection with the following comment:\r\n•	The final report shall be submitted by IC within 48 hours of the incident.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Incident Report, 006', 'Complete', '2014-07-07', 0, 25, 0, 26, 'L-901/14', '2014-07-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1302, 1331, 43, 'No Comments, For Information Only', 'Progress Report, 11', 'Complete', '2014-07-09', 0, 25, 0, -1, 'For Information Only', '2014-07-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1303, 1332, 43, 'Replacement of RTR pipes to UPVC Pipes for Underground Network of Fire and Potable Water Line is acceptable under following conditions:\r\n1.	All pipes, fittings and connections shall be pressure rated at PN16.\r\n2.	Material specification 12PV0U shall be followed from SAES-L-105.\r\n3.	Class 5 UPVC glue shall be used for pipe sizes less than 200mm.\r\n4.	The change will be affective only after all related dwgs/ specs are resubmitted for approval.\r\n5.	The change is considered a voluntary suggestion from IC and acceptable only if no extra cost and time impacts are added to the project, even if market rates of UPVC are higher than RTR.\r\n6.	As mentioned in the TQ, IC is proposing to save time by this replacement. The exact amount of time saving shall be given. IC had enough time to procure the items earlier and any delays cannot be associated to RTR pipes or approvals for replacements.\r\n7.	SAPMT has the right to claim any cost savings if found that the UPVC pipes are of lesser value than the RTR pipes.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'RTR pipe, UPVC pipe', 'Complete', '2014-07-09', 0, 25, 0, 26, 'L-905/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1304, 1333, 43, 'SAPMT has reviewed the subject submittal dated July 01, 2014 and has the following comments:\r\n1.	The title mentions ditch whereas the submittal shows a security corridor without a ditch.\r\n2.	The submission is unclear and shall be made on a larger sheet size in color.\r\n3.	Provide the cross sections as mentioned in the drawing VA-846502-001-0F2 to show the new alignment of the security fence and the distances between other utilities.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'IFC, Ditch Layout, Dimension Plan', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-950/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1305, 1334, 43, 'SAPMT has reviewed the subject submittal dated July 02, 2014 and has rejected with the following comments:\r\n1.	The submittal and the drawings are incomplete, without referenced information attached, and not enough to start construction works.\r\n2.	The footing section/plan in drawing VA-847106-001-0F1 is without reference.\r\n3.	Provide precast concrete column fixation details/shop drawing.\r\n4.	Identify the position of conduit stub-up for power supply and grounding cables.\r\n5.	Ensure that the location of motor and necessary controls is coordinated with the motorized gate vendor. Provide details as necessary.\r\n6.	Based on the Auxiliary Gate Elevation Section on VA-847105-0F1 the difference in levels between the sliding gate and the precast foundation footing shall be reconsidered. Provide cross section indicating the interface between the two.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'IFC, Guard House, Marine Road', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-951/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1306, 1335, 43, 'SAPMT has reviewed the subject submittal dated July 02, 2014 and has the following comments:\r\n1.	The drawings shall be in color and show the details clearly without overwritten annotations.\r\n2.	Consider using larger sheet sizes for effective presentation.\r\n3.	Attach the detail drawing of the drain pipe as mentioned in drawing VA-846506-001-0F1.\r\n4.	Explain why the Station numbering of brick wall (inset) in drawing VA-846506-006-0F1 changed and started from 0+000 instead of continuing the numbering as per the original drawing IFC VA-846506-006.\r\n5.	The internal patrol road and the external patrol roads cannot be connected.\r\n6.	Provide shoreline protection at all areas where there is a possibility of water damage considering high and low currents.\r\n7.	IC shall ensure that the design and drawings provided adhere with the requirements of the scope of work and any variations and/or deviations from applicable standards shall be explicitly submitted for prior approval with details of variations or deviations.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Enlarged Fence Layout', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-948/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1307, 1336, 43, 'SAPMT has reviewed the subject submittal dated July 01, 2014 and has the following comments:\r\n1.	There are differences and conflicts observed between different drawings which cannot be approved for construction. IC is urged to consult with SAPMT to clear such conflicts.\r\n2.	Buildings shall be designed according to SAES-M-009.\r\n3.	At this stage of project all drawings shall be complete in all respects showing all disciplines and shall be ready for construction without the need for shop drawings.\r\n4.	Concrete covers shall be 75mm for concrete exposed to earth and to weather as per general note VA-846497-001.\r\n5.	Justify why the Architectural drawing VA-847116-001-0F2 for Marine Guard house, the staircase has three ways to enter the building but this submittal VA-847118-001-0F1 shows one way only. Provide cross section of staircase flight for Marine Guard house.\r\n6.	Sleeve details shall be zoomed in with necessary re-bars.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'IFC, Guard House', 'Complete', '2014-07-15', 0, 25, 0, 46, 'L-932/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1308, 1337, 43, 'SAPMT has reviewed the subject submittal dated July 02, 2014 and has the following comments:\r\n1.	The prints provided are unclear. Provide legible printouts of drawings in color. Consider bigger sheet size if necessary.\r\n2.	The initial demolition plan shall be attached with a descriptive comparison with the proposed.\r\n3.	Any steps or voluntary changes made to the scope of work to facilitate the constructability of the project or to reduce the effort required to complete the works, cannot be considered as a variation from the scope of work to claim additional time and costs.\r\n4.	Any changes made to existing facilities to complete the agreed scope of work shall be restored by the contractor to their original shape and functionality.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Existing Condition, Demolition Plan', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-947/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1309, 1338, 43, 'SAPMT has reviewed the subject submittal dated July 02, 2014 and has the following comments:\r\n1.	Provide colored drawings as black & white copies do not reflect the plans clearly.\r\n2.	Justify/ ensure that the position of guard house is established to provide a clear view of all 23 cells of the box culvert.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'IFC, Guard Houses', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-949/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1310, 1339, 43, 'For Information Only', 'Meeting, QAQC', 'Complete', '2014-08-04', 0, 25, 0, -1, 'For Information Only', '2014-08-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1311, 1340, 43, 'No Comments, For Information Only', 'QAQC Meeting', 'Complete', '2014-08-31', 0, 25, 0, -1, 'For Information Only', '2014-08-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1312, 1341, 43, 'For Information Only, the above comment will be complied in next coming Inspection Schedule.', 'Inspection Schedule', 'Complete', '2014-07-20', 0, 25, 0, -1, 'For Information Only', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1313, 1342, 43, 'The above comments have been included in the SAPMT letter No.903 in reply to ICC letter No. 672 (KAM Road Take-Off Quantities)', '', 'Complete', '2014-07-07', 0, 25, 0, -1, 'For Record Only', '2014-07-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1314, 1343, 43, 'SAPMT has reviewed the subject submittal dated July 03, 2014 and has the following comments:\r\n1.	Use correct applicable 9Com#6000001826 with correct description as “A/C Unit, Mini-Split DE, below 5.5 Tonsâ€.\r\n2.	Use correct manufacturing Plant ID: 30006251 with correct name of Plant as “Zamil Central Air Conditioners Dammamâ€.\r\n3.	Zamil Air Conditioner plant # 30000313 as quoted by contractor is on hold and not approved.\r\n4.	A/C mini split Units are having inspection Level One (1).\r\n5.	Approval of above manufacturer in Aramco system is valid up to Dec 31, 2014; therefore PO shall be placed immediately after approval of Purchase requisition.\r\n6.	Highlight proposed model number.\r\n7.	Building wise summary sheet with model numbers, cooling capacity are to be provided.\r\n8.	Outdoor units shall have copper fins according to Saudi Aramco Standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Air Conditioning Unit', 'Complete', '2014-07-12', 0, 25, 0, 26, 'L-926/14', '2014-07-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1315, 1344, 43, 'No Comments, For Information Only', 'Project Manager', 'Complete', '2014-07-19', 0, 25, 0, -1, 'For Information Only', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1316, 1345, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0711 dated July 06, 2014 and has the following comments:\r\n1.	It is the responsibility of the contractor to take extra care while working in areas where underground cables exist. Follow the markers and signs and also coordinate with the service provider to locate the route.\r\n2.	Manual excavations shall be done in presence of experienced discipline engineers.\r\n3.	Protect the fiber optic cables using sleeves or duct banks as per standards.\r\n4.	“Except as may be otherwise provided in Schedule "B", CONTRACTOR shall protect from damage all existing structures, improvements or utilities at or near the WORK Site, and shall repair and restore any damage thereto resulting from CONTRACTOR''s failure to exercise reasonable care in protecting the same during CONTRACTOR''s performance of the WORK. If CONTRACTOR fails or refuses to promptly repair any such damage, SAUDI ARAMCO may perform such repairs, or have them performed by others. Paragraph 15.2 shall control with respect to CONTRACTOR''s financial liability arising from or related to such damage.â€\r\n5.	IC is urged to plan the work around cables in coordination with Mobily and create layout drawings for SAPMT approval.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Mobily Warning Letter', 'Complete', '2014-07-22', 0, 25, 0, 26, 'L-961/14', '2014-07-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1317, 1346, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0712 dated July 06, 2014 and has no objection with the following comments:\r\n\r\n1.	The subject of the submittal does not precisely reflect the contents of the submittal. Consider renaming the subject to "Sulfur mortar capping compression strength test report".\r\n2.	Consider using un-bonded caps as an effective alternative to sulfur mortar for capping concrete cylinders.\r\n3.	IC is urged to take all precautions while dealing with and storage /handling of flammable materials.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Compression Strength', 'Complete', '2014-07-11', 0, 25, 0, 26, 'L-924/14', '2014-07-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1318, 1347, 43, 'With reference to IC request dated 06th July 2014 to extend the completion date (Final system acceptance) of the subject project, SAPMT has no objection to extend the contract completion & demobilization from site to 31st August 2015, while MCC shall be accomplished by 30th June 2015. The following conditions apply;\r\n1.	The completion date is extended on contractors request to complete the scope of work as agreed at contract signing and thus shall not add any extra cost to Saudi Aramco.\r\n2.	No further extension shall be allowed.\r\n3.	A revised baseline schedule shall be submitted by IC for SAPMT acceptance.\r\n4.	A revised milestones chart shall be submitted by IC for SAPMT acceptance.\r\n5.	An extension status report shall be provided by IC every two months to show the variances between planned/ actual activities and invoice payments, proving IC adherence with the revised schedule.\r\n6.	IC is advised to acquire or re-allocate as necessary its resources to meet with the new deadlines and milestones and not to postpone or slow down on-going activities.\r\n7.	It is IC responsibility to deliver the lump sum project on turn-key basis according to the agreed scope of work and Saudi Aramco Standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Time Extension', 'Complete', '2014-08-31', 0, 87, 0, 46, 'L-999/14', '2014-08-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1319, 1348, 43, 'For Information only', 'Progress Report, 45', 'Complete', '2014-07-09', 0, 25, 0, -1, 'For Information Only', '2014-07-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1320, 1349, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0648 dated June 11, 2014 and has the following comments:\r\n1.	Mr. Sajid Akram is conditionally approved as “QC Inspector – ICC/FCC Precast Facilityâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his poor/ unsatisfactory performance.  \r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.\r\n', 'QC Inspector', 'Complete', '2014-07-07', 0, 25, 0, 26, 'L-853/14', '2014-07-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1321, 1350, 43, 'Later on the subject initiated letter was CANCELLED by Mr. Sohail Moughal.', 'Slow Production', 'Complete', '2014-09-02', 0, 25, 0, -1, 'For Information Only', '2014-09-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1322, 1352, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0714 dated July 07, 2014 and has rejected with the following comments:\r\n1.	IC has to reconsider the notices for claim when the current progress on buildings is only 5% as compared to the planned 48% according the current schedule.\r\n2.	IC shall provide an alternative/ solution being the designer of this LSTK contract and fulfill the requirements of the IFB.\r\n3.	The IFB says that, "Drawing PA-000104 sheet 002 shows just the conceptual connectivity of the proposed systems at the vehicle inspection center. With due justification and with PMT approval, the detailed engineering design may elect to establish a separate security control shelter dedicated to functions related to the vehicle inspection center. It means that IFB includes the construction of a Vehicle inspection center and if not constructed shall be considered as a negative change order.\r\n4.	The detailed design of a gatehouse was an integrated effort between shape, form, mobility, strategy, security and functions, where during the design phase decisions were made by shuffling the buildings left, right and center, security systems were re-arranged to acquire the best possible result and get an economically viable design. Some roads, walls, pathways, parking spaces, signs, lights, barriers, alignments, walls, bollards and related security infrastructure etc. were adjusted and shifted to gain the ultimate result and thus the subject room was added as a part of the integrated design. The other option was to totally automate the intersection after the subject operator room by adding features that would direct the visitors where to go, without the operator and such option was not included during the review by team consisting of IC, SAPMT and KAUST. Thus the operator room cannot be considered as in isolated instance for a change order.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'UVIS, Operator Room', 'Complete', '2014-07-12', 0, 25, 0, 26, 'L-925/14', '2014-07-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1323, 1353, 43, 'SAPMT has reviewed the subject submittal dated July 07, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Saudization Report, June 2014', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-941/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1324, 1355, 43, 'In view of the agreed and attached scope of work for the subject change order, please submit your proposal as per attached agreed upon quantities by/ before 21 July 2014, 11:00AM. The proposal shall be submitted in a sealed envelope with the following information printed on the envelope;\r\na.	Number and Title of the Project/ Contract.\r\nb.	Number and Title of Change order\r\nThe envelop shall be deposited at the following location;\r\n\r\nSaudi Aramco Project Management Team KAUST Office,\r\nRoom No. 08, Building 100, KAUST, Thuwal.\r\n\r\nIt is your responsibility that all the applicable quantities and units included in the Pricing attachment are correct. All costs and expenses incurred by you in preparing your proposal shall be borne solely by you. Your price shall include all resources required to complete the scope of work in all respects to fit the purpose according to applicable standards. It is your responsibility to familiarize yourself with the site conditions. Award of work is contingent upon execution of a formal purchase order by both parties and work shall not commence before a Purchase Order has been issued. Please confirm receipt of this letter by a return fax to +966 12 422 4178.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Change Order, 3', 'Complete', '2014-07-16', 0, 25, 0, 26, 'L-922/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1325, 1356, 43, 'SAPMT has reviewed the subject submittal dated July 07, 2014 and has no objection with the comments given in the attached letter no. KAUPIS/L-028/2014 dated September 20, 2014.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Asphalt Subcontractor', 'Complete', '2014-09-28', 0, 87, 0, 46, 'L-1014/14', '2014-09-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1326, 1357, 43, 'SAPMT has reviewed the subject submittal dated July 07, 2014 and has no objection with the following comment:\r\n•	IC shall ensure that all construction sites are safeguarded from probable and sudden crashes from passing by vehicles for safety of its workers and works according to Saudi Aramco Safety standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Incident Report', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-952/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1327, 1358, 43, 'SAPMT has reviewed the subject submittal dated July 07, 2014 and has no objection with the following comments:\r\n1.	Revise the QA/QC organizational chart to show the new QC Manager in the next monthly report.\r\n2.	Show the joining date of proposed Mechanical QC Supervisor in the next monthly report.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'MQMR, June 2014', 'Complete', '2014-07-15', 0, 25, 0, 46, 'L-935/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1328, 1359, 43, 'No Comments, For Information Only.', 'Eid, Holidays', 'Complete', '2014-07-21', 0, 25, 0, -1, 'For Information Only', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1329, 1361, 43, 'SAPMT has reviewed the subject submittal dated July 03, 2014 and has the following comment:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	RP	RP-018	LV Panel Board and Lighting Control Panel NEMA-4X 	6000000589/ 6000002698	0	 Approved \r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'LV Panel Board', 'Complete', '2014-07-20', 0, 25, 0, 26, 'L-954/14', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1330, 1362, 43, 'SAPMT has reviewed the subject submittal dated July 09, 2014 and has no objection with the following comments:\r\n1.	Provide method statements wherever non-typical plaster works are to be done and how to avoid cracks in plasterworks at transitions.\r\n2.	Consider using Spatter Dash SB. 2.\r\n3.	It is IC responsibility that all works are performed according to Saudi Aramco standards and manufacturer’s recommendations.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Plaster Works', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-944/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1331, 1363, 43, 'SAPMT has reviewed the subject submittal dated July 09, 2014 and has the following comments:\r\n1.	Provide a sample of the CMU.\r\n2.	Re-Confirm the casting date on the Test report and consider providing fresh results.\r\n3.	The compressive strength of the filler must not be less than the compressive strength of CMU.\r\n4.	The compressive strengths of all types of CMUs shall be provided.\r\n5.	It is IC responsibility to perform works according to Saudi Aramco standards and manufacturers recommendations.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Mortar, Grout', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-945/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1332, 1360, 43, 'For Information Only', '', 'Complete', '2014-07-21', 0, 25, 0, -1, 'For Information Only', '2014-07-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1333, 1354, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1334, 1365, 43, 'SAPMT shows deep concerns over the speed of works being observed on KAM access road. The current rate of progress makes it obvious that IC has failed to deliver the KAM road as agreed by IC. The daily tracking sheet is attached and the following aspects need to be addressed by IC on urgent basis.\r\n1.	Delays in starting works on stations.\r\nSTATION	PLANNED START DATE	ACTUAL START DATE\r\n0+000 TO 1+900	5-May-14	4-Jun-14\r\n1+900 TO 3+000	20-May-14	30-Jun-14\r\n3+000 TO 4+066	20-May-14	15-Jun-14\r\n\r\n2.	Delays in completing Sub-Base.\r\nSTATION	PLANNED FINISH DATE	ACTUAL FINISH DATE\r\n0+000 TO 1+900	20-May-14	24-Jun-14\r\n1+900 TO 3+000	5-Jun-14	STILL WORKING\r\n3+000 TO 4+066	5-Jun-14	STILL WORKING\r\n\r\n3.	Delays in starting base course.\r\nSTATION	PLANNED START DATE	ACTUAL START DATE\r\n0+000 TO 1+900	10-May-14	18-Jun-14\r\n1+900 TO 3+000	1-Jun-14	NOT START\r\n3+000 TO 4+066	1-Jun-14	NOT START\r\n\r\nNeedless to mention that other activities like asphalting, curbs, gutters, irrigation and lighting are already due but cannot be stared due to the predecessors still not completed. IC is urged to provide reasons and solutions to recover from the above shown slippages.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'KAM Delay', 'Complete', '2014-07-12', 0, 25, 0, 26, 'L-927/14', '2014-07-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1335, 1366, 43, 'SAPMT has observed repeated delays on Communications Outside Plant (OSP) works mainly on KAM Access Road area due to various deficiencies in IC resources. Some of them are given below;\r\n1.	Lack of competent and fully qualified personnel (violates Schedule-A Para. 3.1/ 3.9). The existing staff has lack of experience in OSP works and has no ARAMCO project(s) experience resulting in very slow and unacceptable quality works. Contractor to resolve this matter as soon as possible.\r\n2.	Delayed provision of Communications Quality Inspector (violates Schedule-Q Para. 5.1). Prior to start any activities, contractor shall ensure all quality personnel are on site to monitor and maintain quality workmanship and prevent unwanted violations and damages. However, due to this delay, uncontrollable damages keep on happening such as damages to KAUST existing IDAS fiber optic cables.\r\n3.	Planning and Management (violates Schedule-A Para. 2.7); Due to delays in design process and inadequate planning, relocation of fiber optic cable for SONAR/RADAR is still not complete which had to be completed simultaneously with KAM Access Road. As works on the North perimeter have not even started yet, procurement of cables is delayed; contractor has resorted to provide a new cable instead, causing even more delays. Any means and methods or alternatives adopted by IC to deliver the scope of work shall not cause any cost or time impacts to the project.\r\n4.	Delay Analysis (violates Schedule-B Para. 5.6.3.4); Contractor has yet not provided any delay analysis report that outlines reasons of the delay and propose alternatives and solutions to complete the on-going OSP works for SONAR/RADAR.\r\n5.	Material unavailability (violates Schedule-B Para. 5.3.7.14; 5.4.7 and 6.3); Contractor has failed to meet the Procurement schedule to meet construction needs and many works are withheld due to improper tools or incomplete materials. Contractor is strongly advised to provide solutions for the above mentioned deficiencies either to replace or add required resources in shape of qualified personnel and suitable equipment to expedite the works and minimize further delays.\r\n6.	Delaying important security works: IC is urged to provide a schedule of repair works to the damaged existing IDAS fiber optic cables and understand the importance of this work as delays are causing a grave security risk since this cable serves as existing IDAS redundant link. As stated in Schedule-A Para. 5.3, rectification and restoration of this utility and any affected existing facilities will be under the full responsibility of the contractor due to lack of diligence. If the work is not started by August 01, 2014, SAPMT will take alternative measures to get the works done as per Schedule-A Para. 15.2.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Communication Works', 'Complete', '2014-07-23', 0, 25, 0, 26, 'L-942/14', '2014-07-24', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1336, 1374, 43, 'No Comments, For Information Only', 'Inspection Schedule', 'Complete', '2014-07-20', 0, 25, 0, -1, 'For Information Only', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1337, 1371, 43, 'SAPMT has reviewed the subject submittal dated July 07, 2014 and has the following comments:\r\n•	Provide the following;\r\n1.	Organization chart for the subcontract from ICC and Rabya''s teams. Exact numbers of supervisory staff with names and quantity of skilled/ unskilled workers with specialties shall be provided. IC to ensure that the subcontractor has sufficient and skilled manpower to complete the works without any delays and quality issues.\r\n2.	A detailed Time schedule for the subcontract.\r\n3.	Activities and estimation of quantities for the subcontract.\r\n4.	CV of the key person from both sides handling the subcontract and especially designated for the task shall be provided.\r\n5.	List of interfaces and responsibilities.\r\n6.	List of projects the subcontractor has completed on time mentioning the planned and actual dates with Saudi Aramco and other organizations\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Rabya, Landscaping', 'Complete', '2014-07-20', 0, 25, 0, 26, 'L-955/14', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1338, 1372, 43, 'SAPMT has reviewed the subject submittal dated July 10, 2014 and has the following comments:\r\n1.	Provide readable colored copies of the drawings.\r\n2.	At this stage of the project, all new drawings shall be submitted complete without the need of any shop drawings.\r\n3.	Provide a detailed section for the beginning of the ramp.\r\n4.	The blast resistance building shall be designed as per SAES-M-009.\r\n5.	Provide blow up details for sleeves with necessary rebar such as roof drain sleeve, Electrical conduits …etc.\r\n6.	Concrete cover should be 75mm for concrete expose to earth and to weather as per general note VA-846497-001.\r\n7.	The roof slab of machine gun room is setting on cantilever beams; we need design details/ confirmation from SCEC to see that the design of this portion is safe.\r\n8.	Any design works which deviate from the scope of work or might trigger a claim shall be sent to SAPMT for prior approval, before incorporating in to construction drawings.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Pavilion, IFC', 'Complete', '2014-07-19', 0, 25, 0, 46, 'L-943/14', '2014-07-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1339, 1373, 43, 'SAPMT has reviewed the subject submittal dated July 10, 2014 and has no objection as per attached Appendix A, B & C with Mix Design ID No.SRMC-SRAB-281-14 and Concrete Test Reports (5-pages). However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications. \r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Mix Design, Curbstone, Gutter', 'Complete', '2014-08-06', 0, 25, 0, 46, 'L-969/14', '2014-08-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1340, 1364, 43, 'Saudi Aramco raises concerns over Project Progress delays according to base line (Rev.1) schedule. The recorded progress slippage for Procurement is 60.85 % and for Construction 38.49% as of July 04, 2014. The following details show the events and associated delays.\r\n1.	Manpower mobilization was rescheduled to complete on September 26, 2013. Original date as per contract was within 30 days from the award of contract i.e. February 25, 2013. IC completed mobilization of offices and precast plant much later in April 2014 causing delays to subsequent activities and is still struggling with lack of skilled manpower and subcontractors.\r\n2.	Complete PO Placement for all bulk materials was scheduled on October 31, 2013, but till date the Contractor is not able to complete the Material submittal and Approval process. \r\n3.	PO Placement of many long lead items is still pending. The outstanding items have been highlighted by SAPMT regularly, but actions by IC have been much slower causing enormous slippages.\r\n4.	All Materials were to be delivered to Work Site by June 20, 2014; but as of date, the contactor is not in a position to deliver a single long lead item on site.\r\n5.	Fence Installation at Zone B (7+000 to 5+500) was scheduled to complete on May 28, 2014 but it was delayed by 40.88%. Zone C (7+100 to 8+800) was scheduled to complete on July 03, 2014 but it was delayed by 84.22%. Also, the overall Progress slippage on Fence installation is hard to recover since it has reached 24.18%.\r\n6.	Construction of Culvert was scheduled to commence on January 22, 2014 and should have been completed 51% by now - to date contractor is not in a position to start the work.\r\n7.	KAM Access road construction was scheduled to complete on March 19, 2014. SAPMT agreed to complete latest by July 31, 2014. The current progress trend shows that it is impossible to complete the task as extended.\r\n8.	Construction of Maintenance road and Patrol road was delayed on Zone A, B and C as well. Overall Road construction progress has slipped by 50.33% as of to-date.\r\n9.	Complete Relocation of existing fence and security system at KAM access road was scheduled on June 20, 2014 whereas the activity is yet to be completed and is contributing 45% to progress slippage.\r\n10.	Construction of Buildings was scheduled to commence on November 21, 2013 whereas at the moment there is hardly any work being done on the buildings (Plan is 40.8% whereas Actual is 5.8%). \r\n11.	Installation of Package Substations was scheduled to commence on May 06, 2014 and IC has just recently completed the material approval process.\r\n12.	Installation of UPS System was scheduled to commence on August 04, 2014, but PO was placed only on April 22, 2014 and also Building works are yet to be commenced.\r\n13.	MV Cable laying was schedule to commence on August 04 2014, but there is no positive sign from contractor to start the activity as scheduled. PO for MV cable was placed only on April 22, 2014.\r\n14.	Installation of Lighting Pole foundation at Zone A & B should have been completed at this moment (Scheduled completion date was June 16, 2014). But till date the contractor has not prepared for pre casting of foundations. Also Lighting Poles installation should have been commenced on June 17, 2014 whereas PO was placed only on April 22, 2014, and materials have not arrived yet.\r\n15.	Communication duct bank works are delayed by 64.20% at all the stations.\r\n16.	Installation of Vessel Barriers and Sonar System was schedule to commence on May 19, 2014. Also, commencement of Boat Automatic Identification system and Radar System installation was scheduled on June 21, 2014 and June 22, 2014 respectively, but these items have still not been delivered to site. Similarly contractor has completely delayed the installation of Onshore Security Systems such as Intrusion detection and assessment system, Security Access Control System, Dropped arm crash barrier, all closed circuit system and cargo screening system. It is important to note that, the contractor was not in a position to produce a copy of PO’s for most of the Items mentioned above. Construction Progress slippage of Security systems has reached to 39.40% as of July 04, 2014.\r\n17.	The trend curve for monthly progress shows the significant progress made by the contractor during the Month of June 14 which was accomplished due to the commencement for Fence Erection. The progress is likely to be disturbed again as IC and its subcontractors have fallen behind in the fabrication and erection of precast wall, since then.\r\n \r\n\r\n18.	Contractor has proposed a revision in schedule which is still under review by SAPMT but the Procurement Progress slippage even in the proposed schedule (Rev.2) has reached to 12.45%. \r\nIC is urged to provide concrete steps to meet the project milestones and schedule deadlines.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Progress Delays', 'Complete', '2014-07-15', 0, 25, 0, 46, 'L-928/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1341, 1367, 43, 'IC has delayed the works related to Street lights and Irrigation for KAM road without any regard for the promise IC made to deliver KAM road by the end of July 2014. As a matter of fact, no works have been started despite several reminders in meetings dated 31/03, 14/04 and 05/05. Due to lack of experienced staff/ resources related to the discipline the design and procurement have still not been finalized. The curb and gutter works, soft landscaping, hard landscaping are also behind schedule and IC has shown no urgency in completing these tasks and delayed these matters for more than 3 months.\r\n\r\nIC is urged to provide a schedule showing the start and completion dates of the above mentioned activities and provide reasons for delays.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Irrigation System', 'Complete', '2014-07-22', 0, 25, 0, 26, 'L-960/14', '2014-07-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1342, 1370, 24, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1343, 1375, 43, 'Referring to the scope of work para 1.2.2.1.1.1 and the demolition plan VA846500 sheet 003; IC shall start the demolition works at the abandoned gate by NAVY as soon as possible. The IC interface manager/ coordinator shall coordinate the activities as necessary and inform SAPMT with a detailed demolition and cleanup schedule.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Demolition, Naval Base Facilities', 'Complete', '2014-07-15', 0, 25, 0, 46, 'L-939/14', '2014-07-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1344, 220, 24, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1345, 1376, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0725 dated July 15, 2014 and has rejected with the following comments:\r\n•	These material can only be inspected when they arrive on site and thus remaining payments cannot be released for which more than 70% have already been paid according to the conditions of the contract and schedule C, para 3.3. IC is urged to expedite delivery of long lead materials to site.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'AS&E Equipments', 'Complete', '2014-11-06', 0, 87, 0, 46, 'L-1138/14', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1346, 1377, 43, 'No Comments, For Information Only', 'Procurement Manager', 'Complete', '2014-08-04', 0, 25, 0, -1, 'For Information Only', '2014-08-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1347, 1378, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0724 dated July 13, 2014 and has rejected with the reasons mentioned below:\r\n1.	It is not necessary to use a concrete pump for small buildings.\r\n2.	A stationary pump, a concrete lift and/or wheel barrows can be used to place concrete at the roof of single story building.\r\n3.	SEC in the meeting for relocation of poles dated June 2, 2014 had allowed work at height less than 3 meter from the conductors.\r\n4.	IC had suggested providing insulating sleeves on conductors which IC never did or even explored.\r\n5.	The work on all building has stopped for no obvious reason, where progress should have been 58% but is frozen at 5%. The attached list and sketches shows IC has no reason to stop work due to overhead lines and only 5 out of 29 buildings are affected which could be resolved by using alternative means and methods.\r\nIC is urged to start work as soon as possible and provide a schedule to show expedited delivery.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Pouring Hindrances', 'Complete', '2014-07-20', 0, 25, 0, 26, 'L-953/14', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1348, 1379, 43, 'This Payment Application was revised which approved later.', 'Invoice, Payment Application', 'Complete', '2014-10-20', 0, 25, 0, -1, 'For Information Only', '2014-10-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1349, 1380, 43, 'KAUST is urged to coordinate with SEC to start works for lying of new power cables and remove the existing overhead lines with immediate effect. The overhead lines have become an obstruction to the construction of security buildings at gates 2 and 3. While the contractor has completed the surveys and marked the route of the proposed SEC cable at road crossings, SEC can start laying direct buried cables without waiting for the concrete duct banks. The roads have not been constructed yet and SAPMT shall ensure that the laid cables are protected by the concrete duct banks according to SEC standards, whenever roads are constructed.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer on Tel. No. 012 422 4570.\r\n                                                                   \r\n', 'Rerouting SEC Cables', 'Complete', '2014-07-20', 0, 25, 0, 26, 'L-956/14', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1350, 1381, 43, 'SAPMT has reviewed the subject submittal dated July 07, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Orange Warning Tape', 'Complete', '2014-07-20', 0, 25, 0, 26, 'L-957/14', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1351, 1382, 43, 'SAPMT has reviewed the subject submittal dated July 12, 2014 and has no objection with the following comment:\r\n•	It is IC responsibility to deliver the project according to applicable standards and approved scope of work/ specifications. Any changes made to the scope of work shall be highlighted for separate approval.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Cable, Lighting Layout', 'Complete', '2014-07-22', 0, 25, 0, 26, 'L-959/14', '2014-07-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1352, 1383, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2014-07-22', 0, 25, 0, -1, 'For Information Only', '2014-07-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1353, 1384, 43, 'The Arabic document received from Naval Authority regarding Demolition of Naval Gate Facilities being an attachment of SAPMT letter # L-939/14 dated July 15, 2014 forwarded through email to ICC for coordination and further action.\r\n\r\nDocument archived for information only.', '', 'Complete', '2014-08-04', 0, 25, 0, -1, 'For Information Only', '2014-08-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1354, 1385, 43, 'For Information Only', 'Inspection Schedule', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1355, 1386, 43, 'SAPMT has reviewed the subject submittal dated July 17, 2014 and has the following comments:\r\n1.	The base coarse and sub base should continue under the median as per IFB drawing KA-714497-001-C unless the project designer concurs to prove that the design is safe.\r\n2.	In case the project designer provides no base coarse and sub base under the median, a slope of 1:3 for the base coarse and sub base shall be maintained.\r\n3.	The curb shape shall be same as IFB.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'KAM Road Section', 'Complete', '2014-08-19', 0, 25, 0, 46, 'L-996/14', '2014-08-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1356, 1387, 43, 'SAPMT has reviewed the subject submittal dated July 19, 2014 and has rejected with the following comments:\r\n1.	Contractor has submitted just a General site Layout and not a Site Storage Plan.\r\n2.	Contractor is advised to submit a separate detailed Site Storage Plan (apart from site layout plan) mentioning the details of equipment and their location in the storage area with desired areas.\r\n3.	The location for all materials and equipment shall also show the desired temperatures according to manufacturer’s recommendations.\r\n4.	Contractor shall meet the dust proof requirements for all equipment.\r\n5.	IC is urged to understand the importance of storage area on site and take appropriate actions by installing adequate structures as soon as possible.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Site Facility Storage Plan', 'Complete', '2014-07-22', 0, 25, 0, 26, 'L-958/14', '2014-07-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1357, 1388, 43, 'SAPMT has reviewed the subject submittal dated July 16, 2014 and has the following comment:\r\n\r\nBI	Transmittal Type	Transmittal No.	Description  	9COM	Level of Inspection 	 Status \r\n25-00026	RP	RP-019	Wet Barrel Fire Hydrant 6â€ Dia 	6000001310	0	approved \r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Fire Hydrant', 'Complete', '2014-07-22', 0, 25, 0, 26, 'L-962/14', '2014-07-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1358, 1389, 43, 'SAPMT has reviewed the subject submittal dated July 12, 2014 and has no objection with the following comments:\r\n1.	Subject IDR for Fiber Optic Cable has been reviewed by Saudi Aramco and Contractor is advised to submit Final Inspection Disposition Report (Two hard and two soft copies) at the time of handing over of Project in hard binders approved by KAUST, samples of which are available in our office for reference.\r\n2.	Final IDR should also include copy of review by VID.\r\n3.	In future all FIDR (Soft copy) shall be sent for review by Contractor directly to VID with a copy to SAPMT.\r\n4.	Ensure that reel testing is performed.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'FOC', 'Complete', '2014-08-11', 0, 25, 0, 46, 'L-971/14', '2014-08-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1359, 1396, 43, 'The subject LSTK contract was awarded to International Center for Contracting Co. (IC) on January 21, 2013 with a completion date of December 26, 2014. Please extend the subject contract expiration sate in SAP to August 31, 2015 which will allow the Contractor to complete remaining scope of work. This contract time extension will not add any extra cost to Saudi Aramco.', 'Date Extension, Completion Date', 'Complete', '2014-07-22', 0, 32, 0, 26, 'L-035/14', '2014-07-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1360, 1391, 43, 'SAPMT has reviewed the subject submittal dated July 15, 2014 and has the following comment:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	IL no. 	Description	9com	Level of Inspection	Status\r\n25-00026	IAP	IAP-06	107000098471	MV Cable	6000000797	1	Approved\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'IAP, MV Cable', 'Complete', '2014-08-11', 0, 25, 0, 46, 'L-972/14', '2014-08-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1361, 1392, 43, 'SAPMT has reviewed the subject submittal dated July 19, 2014 and has the following comment:\r\n•	Mr. Udiyambath Subran Ratheesh is approved for the position of “Procurement Managerâ€ as replacement of Mr. Muhammad Ilyas during his vacation for one month starting from August 02, 2014 to September 04, 2014. \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Procurement Manager', 'Complete', '2014-07-23', 0, 25, 0, 26, 'L-966/14', '2014-07-24', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1362, 1393, 43, 'SAPMT has reviewed the subject submittal dated July 19, 2014 and has no objection with the following comments:\r\n1.	Ensure that the openings for incoming and outgoing pipes are not obstructed by the Step Ladder.\r\n2.	Prepare the manhole and connections for Leak Test.\r\n3.	It is IC responsibility to ensure that all works are performed according to the agreed scope of work and applicable standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Manholes, 1800mm', 'Complete', '2014-08-06', 0, 25, 0, 46, 'L-970/14', '2014-08-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1363, 1394, 43, 'With reference to IC request for extension in time for submission of proposal for Change Order No. 3. SAPMT agrees to extend the date to August 06, 2014, 11:00AM. The proposal shall be submitted in a sealed envelope with the following information printed on the envelope;\r\na.	Number and Title of the Project/ Contract.\r\nb.	Number and Title of Change order\r\nThe envelop shall be deposited at the following location by hand;\r\nCENTRAL BID BOX CONTARCTING R-A162 WING A,\r\nBUILDING 3301 NORTH PARK II,\r\nDHAHRAN, 31311 KSA.\r\nIt is contractor’s responsibility to be familiarized with the site conditions and all costs and expenses incurred in preparing the proposal shall be borne solely by the contractor. It is assumed that all the quantities and units have been confirmed by the contractor and no further changes are necessary to complete the scope of work that is included in this change order. The price shall include all resources, arrangements and coordination required to complete the scope of work in all respects to fit the purpose according to applicable standards. All other conditions shall stay the same as mentioned in the existing contract. Award of work is contingent upon execution of a formal purchase order by both parties and work shall not commence before a Purchase Order has been issued.\r\nPlease confirm receipt of this letter by a return fax to +966 12 422 4178.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.\r\n', 'Time Extension, Bid Submission', 'Complete', '2014-07-22', 0, 25, 0, 26, 'L-965/14', '2014-07-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1364, 1395, 43, 'No Comments, For Information Only', 'Progress Report, 47', 'Complete', '2014-07-23', 0, 25, 0, -1, 'For Information Only', '2014-07-24', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1365, 1397, 43, 'SAPMT has reviewed the subject submittal dated July 21, 2014 and has no objection. However, it is contractor’s responsibility to ensure that all materials are supplied according to the requirements of the scope of the project and Saudi Aramco specifications while ensuring that the materials are compatible with existing systems.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'UTP Patch Panel', 'Complete', '2014-08-13', 0, 25, 0, 46, 'L-978/14', '2014-08-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1366, 1398, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1367, 1399, 43, 'No Comments, For Information Only', '', 'Complete', '2014-08-12', 0, 25, 0, -1, 'For Information Only', '2014-08-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1368, 1400, 43, 'No Comments, For Information Only', 'SCAR', 'Complete', '2014-08-12', 0, 25, 0, -1, 'For Information Only', '2014-08-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1369, 1401, 43, 'SAPMT has reviewed the subject submittal dated July 23, 2014 and has the following comments:\r\n1.	Consider relocating the fire alarm panel, the lighting panel and other electrical panels away from the indoor A/C unit.\r\n2.	The subcontractor for communications shall provide concurrence in addition to the project designer.\r\n3.	Reflect the changes made to the diameter of sleeves from 1.25 to 1.5 as per site conditions.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Sleeves, Turnstile, X-Ray Building', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1007/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1370, 1402, 43, 'SAPMT has reviewed the subject submittal dated July 24, 2014 and has no objection with the following comment:\r\n•	It is IC responsibility to adhere with the scope of work of the project and Saudi Aramco standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Security Systems', 'Complete', '2014-08-17', 0, 25, 0, 46, 'L-985/14', '2014-08-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1371, 1403, 43, 'SAPMT has reviewed the subject submittal dated July 19, 2014 and has the following comments:\r\n1.	Note that Battery - Valve regulated Lead Acid with 9Com# 6000001075 has an Inspection Level One (1).\r\n2.	Enersys Power with Plant ID: 30003391 as offered by Contractor is located in ARRAS FRANCE. So the Valve REGULATED Battery of 10-KVA (6000001075) as per the submittal shall be procured only from their approved Plant in France.\r\n3.	C&D Technology with Plant ID: 30003138 as offered by Contractor is located in Dunlap USA. So the Vented Lead Acid Battery of 80-KVA (6000000951) as per the submittal shall be Procured only from their approved plant in USA.\r\n4.	All materials shall be procured only from approved manufacturing plant location and Inspection shall be carried out only at the approved manufacturing plant location.\r\n5.	Vented type battery for 80 KVA UPS Unit complies with Saudi Aramco Standard, SAES-P-103, paragraph 5.3.7 for 60 minutes back up time for each battery bank, however, project specifications require 120 minutes back-up time for each battery bank. Please provide justification.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Battery', 'Complete', '2014-08-11', 0, 25, 0, 46, 'L-973/14', '2014-08-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1372, 1404, 43, 'Payment Application approved and SES issued to ICC.', 'Invoice, Payment Application', 'Complete', '2014-10-20', 0, 25, 0, -1, 'For Record Only', '2014-10-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1373, 1406, 43, 'IC is urged to provide a time schedule before 7th August 2014, as to when the damaged cable shall be replaced/ fixed, failing which SAPMT shall invoke the clause no 5.3 & 30.8 of Schedule-A where, "In the event CONTRACTOR fails to perform any of its obligations under this Contract, SAUDI ARAMCO may, upon fourteen (14) days prior written notice, and without prejudice to any other remedies permitted by law or this Contract, perform the CONTRACTOR''s obligations, or cause them to be performed, at CONTRACTOR''s expense".\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'FOC Damage', 'Complete', '2014-08-06', 0, 25, 0, 46, 'L-968/14', '2014-08-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1374, 1407, 43, 'SAPMT has reviewed the subject submittal dated July 24, 2014 and has no comments. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Saudization, July 2014', 'Complete', '2014-08-11', 0, 25, 0, 46, 'L-974/14', '2014-08-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1375, 1408, 43, 'For Information Only', 'Inspection Schedule', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1376, 1409, 43, 'SAPMT has reviewed the subject submittal dated August 05, 2014 and has no objection with the following comments:\r\n1.	According to Aramco standard SAES-A-114, Clause 6.2.3, the TDS for Water to be used for compaction shall be less than 10,000 ppm.\r\n2.	According to Aramco standard SAES-A-114, Clause 6.2.3, Water with more than 10,000 ppm can be used if: (Both of the following apply);\r\na.	There is no other water source within 20 km. (Joint Investigation by BOTH parties is required. Determine distance, quality, quantity)\r\nb.	Adjacent concrete works are Exposure type II and III (Our foundations concrete is exposure type III; except Curbs, medians, pole foundations and gutters).\r\nIn light of the above the following can be adopted:\r\n1.	The sources of water found in the vicinity of 20km are not enough/ reliable to provide a continuous supply of water for 35km of road works to be done for the KPSS project. Using potable water for any earthworks is an overkill/ unethical.\r\n2.	Use water with 10,000 to 35,000 mg/L TDS for all types of backfilling, sub-grade, base course and sub-base where there is no adjacent concrete.\r\n3.	Use water with 10,000 to 35,000 mg/L TDS for all types of backfilling, sub-grade, base course and sub-base where the adjacent concrete is Exposure type II or III.\r\n4.	Use water with 1000 to 10,000 mg/L TDS for all types of backfilling, sub-grade, base course and sub-base where the adjacent concrete is Exposure type I.\r\nIt is IC’s responsibility to ensure that all works are done according to the agreed scope of work and Saudi Aramco Standards.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Water with TDS', 'Complete', '2014-08-17', 0, 25, 0, 46, 'L-986/14', '2014-08-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1377, 1410, 43, '\r\nSAPMT has reviewed the subject submittal dated August 02, 2014 and has no objection with the following comment:\r\n•	It is IC responsibility to adhere with the scope of work of the project and Saudi Aramco standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'LPRS', 'Complete', '2014-08-17', 0, 25, 0, 46, 'L-984/14', '2014-08-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1378, 1411, 43, 'SAPMT has reviewed the subject submittal dated August 02, 2014 and has the following comments:\r\n1.	SAPMT comment no. 1 still not complied since the attached IFC drawing only applies to SACS. Attach other drawings applicable to other systems with servers.\r\n2.	SAPMT comment no. 2 also not complied due to incomplete attached drawings. The redundancy and OS requirement must be indicated in the High level Document.\r\n3.	SAPMT comment no. 3 still not complied since calculation or technical justification or compliance certificate/recommendation from manufacturer is not provided.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Server, Workstation', 'Complete', '2014-08-17', 0, 25, 0, 46, 'L-980/14', '2014-08-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1379, 1412, 43, 'SAPMT has reviewed the subject submittal dated August 02, 2014 and has no objection with the following comments:\r\n1.	Ensure that the size and dimensions of sub-ducts and duct plugs are chosen correctly and fitted as per project requirements.\r\n2.	Ensure the Fiber cable simplex plug shall fit to all fiber optic cable sizes for 8 cores, 24 cores and 96 cores.\r\n3.	Sub-duct type/specification and color code must comply with SAES-T-624, Para 4.3.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Communication Subduct', 'Complete', '2014-08-17', 0, 25, 0, 46, 'L-988/14', '2014-08-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1380, 1413, 43, 'SAPMT has reviewed the subject submittal dated July 24, 2014 and has the following comments:\r\n1.	Design Basis and manufacturers standard specifications shall be concurred by the Project Designer.\r\n2.	Provide more details about the scope of work included in the subcontract.\r\n3.	Provide a schedule showing start and completion dates.\r\n4.	Provide CVs of subcontractor’s staff working on the KPSS project.\r\n5.	Provide CV of the Contractors staff responsible for this subcontract.\r\n6.	M/s Yamamah Space Structures is an acceptable vendor for space frames but more information is required in shape of material submittal to ensure that scope of work is handled appropriately.\r\n7.	Provide separate technical data for approval of associated items like cladding etc.\r\n8.	9Com # 6000000686 has an inspection level two (2).\r\n9.	Provide information about building and location.\r\n10.	Provide information about metal types materials to be used for the project.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Yamamah Space Structure', 'Complete', '2014-08-17', 0, 25, 0, 46, 'L-989/14', '2014-08-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1381, 1414, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2014-08-12', 0, 25, 0, -1, 'For Information Only', '2014-08-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1382, 1415, 43, 'No Comments, For Information Only', 'Propress Report', 'Complete', '2014-08-12', 0, 25, 0, -1, 'For Information Only', '2014-08-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1383, 1416, 43, 'SAPMT has reviewed the subject submittal dated August 04, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications. \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Communication Marker Post', 'Complete', '2014-08-13', 0, 25, 0, 46, 'L-979/14', '2014-08-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1384, 1417, 43, 'SAPMT has reviewed the subject submittal dated August 04, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications. \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Electrical Sign Post', 'Complete', '2014-08-13', 0, 25, 0, 46, 'L-977/14', '2014-08-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1385, 1418, 43, 'SAPMT has reviewed the subject submittal dated July 27, 2014 and has the following comments:\r\n1.	Mr. Ayaman Ahmad Alkasem is conditionally accepted as “Scaffold Supervisorâ€ for three (3) months within which period Saudi Aramco accreditation shall be acquired by the candidate.\r\n2.	SAPMT has the right to revoke the approval in case the Saudi Aramco accreditation is not acquired or any violations are observed during these three months.\r\n3.	IC shall ensure that all workers subjected to prolonged work at heights or working with important/ sensitive equipment maintain good health and are proved medically fit.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer at (012) 422-4423.\r\n', 'Scaffold Supervisor', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1010/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1386, 1419, 43, 'SAPMT has reviewed the subject submittal dated July 22, 2014 and has no objection with the following comment:\r\n•	It is IC responsibility to deliver the project according to the scope of work and Saudi Aramco standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Thermoplastic UPVC', 'Complete', '2014-08-19', 0, 25, 0, 46, 'L-995/14', '2014-08-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1387, 1420, 43, 'SAPMT has reviewed the subject submittal dated August 04, 2014 and has the following comments:\r\n1.	Method Statement shall be provided for both the cut sections of the IDAS FOC.\r\n2.	The new 96 core FOC shall be reel tested prior to installation.\r\n3.	Only approved, experienced and ARAMCO certified splicers and testers are allowed to conduct the splicing and testing of the FOC and information about their names and certificates shall be included in the Method statement.\r\n4.	OTDR (Optical Time Domain Reflectometer) shall be conducted; however Light Source Power Meter testing, Chromatic Dispersion (CD) and Polarization Mode Dispersion (PMD) must be conducted if required by client in compliance to SAES-T-634.\r\n5.	Locate and reflect the fiber marker post. Material shall be provided by KAUST.\r\n6.	Ensure all required materials and equipment are available to site prior rectification such as the splicing van, splice closures, manhole, sub-ducts and duct plugs.\r\n7.	Test Reports must be documented and submitted for acceptance.\r\n8.	Manual excavation is highly recommended at areas where other utilities are installed to avoid any damage.\r\n9.	Consider and attach Planned Schedule with the duration of all Works/Activities.\r\n10.	MS shall be reviewed and approved by QA Manager.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'MS, Redundant FOC', 'Complete', '2014-08-17', 0, 25, 0, 46, 'L-981/14', '2014-08-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1388, 1421, 43, 'SAPMT has reviewed the subject submittal dated August 04, 2014 and has no objection with the following comments:\r\n1.	Ensure all manhole hardware and accessories comply with all the dimensions and specifications as per SAES-T-911, Paragraph 5.2.8.7 and Aramco Standard drawing SASD AA-036794.\r\n2.	All manhole hardware must be non-corrosive type such as hop dipped galvanized or better.\r\n3.	Ensure to provide plastic inserts.\r\n4.	Method Statement shall be provided for the fabrication process of the manhole with compliance to SASD AA-036794.\r\n5.	Submit grounding material required for the manhole with compliance to SAES-T-911, Paragraph 5.2.8.8.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Communication Manholes', 'Complete', '2014-08-13', 0, 25, 0, 46, 'L-976/14', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1389, 1422, 43, 'For Information Only', 'PQP', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1390, 1423, 43, 'SAPMT has reviewed the subject submittal dated August 04, 2014 and has the following comment:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9COM	Level Of Inspection	Status\r\n25-00026	RP	RP-020	Diesel Generator 2500KW	6000000964	2	Approved \r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.  \r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at (012) 422-4570.\r\n', 'Generator', 'Complete', '2015-06-14', 0, 25, 0, 87, 'L-1055/15', '2015-06-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1391, 1424, 43, 'SAPMT has reviewed the subject submittal dated August 06, 2014 and has no objection with the following comments:\r\n1.	It is IC responsibility to adhere with the KAUST boundary coordinates provided with the bid package.\r\n2.	The 23/23 sheets for coordinates shall be concurred/ signed by the Project designer, before implementation on site.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Shop Drawing, Fence Coordinates', 'Complete', '2014-08-17', 0, 25, 0, 46, 'L-983/14', '2014-08-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1392, 1425, 43, 'SAPMT has reviewed the subject submittal dated August 06, 2014 and has no objection with the following comments:\r\n1.	It is IC responsibility to adhere with the KAUST boundary coordinates provided with the bid package.\r\n2.	The 23/23 sheets for coordinates shall be concurred/ signed by the Project designer, before implementation on site.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Shop Drawings, Fence Coordinates', 'Complete', '2014-08-17', 0, 25, 0, 46, 'L-982/14', '2014-08-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1393, 1426, 43, 'SAPMT has reviewed the subject submittal dated August 05, 2014 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Thermoplastic UPVC', 'Complete', '2014-08-19', 0, 25, 0, 46, 'L-994/14', '2014-08-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1394, 1427, 43, 'SAPMT has reviewed the subject submittal dated August 06, 2014 and has no objection with the following comments:\r\n1.	Contractor to submit a Corrective Action Report (CAR) specifying the actions taken and the date/s committed actions are implemented for SAPMT’s verification and close-out.\r\n2.	Contractor shall maintain a register to monitor status of concerns until all are closed-out.\r\n3.	Consult with PMT for reporting formats and report distribution.\r\n4.	All issues shall be closed-out before the next inspection schedule.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Camp Inspection', 'Complete', '2014-08-19', 0, 25, 0, 46, 'L-991/14', '2014-08-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1395, 1431, 43, 'The POC testing was done at 1430PM on August 13, 2014 and 2030PM on August 12, 2014 and the following was observed;\r\n1.	PELCO and SONY cameras did not provide the desired results.\r\n2.	The results from AXIS camera were found acceptable.\r\n3.	Subcontractor agreed to re-conduct the test with another camera model from BOSCH and compare it with AXIS.\r\n4.	IC is urged to arrange the test before August 21, 2014.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'IDAS, VOD Camera', 'Complete', '2014-08-19', 0, 25, 0, 46, 'L-992/14', '2014-08-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1396, 1428, 43, 'SAPMT has reviewed the subject submittal dated July 27, 2014 and has the following comments:\r\n1.	Mr. Saad Jamil Siddiqui is accepted as “QC Inspector – Mechanical (Plumbing & HVAC)â€ for “KAUST – Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke this approval at any time based on his unsatisfactory performance during project tenure.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'QC Inspector', 'Complete', '2014-08-30', 0, 87, 0, 46, 'L-1012/14', '2014-08-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1397, 1429, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0735 dated August 07, 2014 and has the following comments:\r\n1.	IC is urged to provide information in its correspondence which is based on facts. The attached SAPMT letter no. K&TPD/KRP&SFPD/RPI/L-072/13 and K&TPD/KRP& SFPD/RPI/L-052/13 and IC letter no. ICC/SA/KPSF/KD/0002/2013 shall show that IC was unable to provide a mobilization schedule and subsequent mobilization according to the requirements of the contract on time even though the mobilization had to be completed in February 2013. The letters attached shall also show that IC was allowed to start mobilization works under the supervision of SAPMT even though the approvals for schedules and plans were still undergoing revisions. The camp, the precast plant, mobilization on site, mobilization of human resources and the IFC were all delayed. Hence IC claim that IC could not start works before August 21, 2013 are rejected. IC is urged to study the schedule B where the notice to proceed is related to actual work and not mobilization. Mobilization works or design works can be completed before the notice to proceed. All long lead items have been delayed which have no relationship with the notice to proceed. CONTRACTOR''s failure to comply, unless otherwise excused pursuant to this Contract, constitutes a substantial breach of this Contract. Please also refer to SAPMT letter no. K&TPD/KRP&SFPD/SF/L-928/14 and 927/14 where various issues regarding progress delays have been highlighted.\r\n2.	IC claim that delays have occurred due to revision in IFC are baseless because the first submission of IFC itself was delayed by IC by approximately 4 months. The second revision has still not been submitted and SAPMT has allowed works with partly revised IFCs to avoid any delays.\r\n3.	IC is urged to refer to the contract SCH-B para 3.5, 3.9 and 3.10, regarding interfaces, where it is IC responsibility to deal with interfaces with utility companies. Inability of IC to facilitate the project by finding solutions or alternatives for interfaces on time or carrying out prompt and effective studies to avoid issues during construction while preparing IFC has caused delays. \r\n4.	IC is urged to refer to the contract SCH-B para 3.10, regarding interfaces, where it is IC responsibility to deal with interfaces with other contractors working in the area.\r\n5.	IC shall understand that damaging exiting national utilities without coordination with the utility companies and employing an effective interface manager shall result in unforeseen dire consequences and cannot be considered as a reason for delays.\r\n6.	Changing priorities during the execution cannot be considered as a reason for delays, unless IC proves that IC has or had ample resources to start works simultaneously on each and every activity of the project. All procurements and activities have been continuously behind schedule.\r\n7.	Works at gate 2 and 3 have stopped due to IC inability to produce shop drawings on time, unavailability of IC resources to work on buildings, delays in employing a sub-contractor, inability to start works despite the work permits and traffic plans have been approved, unavailability of water and electricity on site and inability to deal with interfaces.\r\n8.	Suspension of ditch has not delayed any other activities at that time, because IC had not started any other activities on the project at that time.\r\n9.	Redesign due to ditch elimination has not delayed any works because the redesign is limited to the relocation of IDAS and removal of ditch, whereby IDAS has not yet started and the precast wall and patrol road has stayed at the same alignment as before.\r\n10.	Any reworks done after suspension of ditch shall be considered during the next amendment to the contract however SAPMT believes that suspension of ditch has not delayed any other activities and by suspending a big portion of scope of work, IC shall be able to deliver the project much earlier.\r\n\r\nAs a revised schedule submitted by IC has already been approved by SAPMT, and process to amend the contract for deletion of ditch from the contract has been initiated by SAPMT and pending with IC to agree, IC is urged to ensure that the project is delivered on time without any delays.\r\n', 'Project Progress Delays', 'Complete', '2014-11-17', 0, 25, 0, 87, 'L-987/14', '2014-11-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1398, 1430, 43, 'No Comments, For Information Only', 'Inspection Schedule', 'Complete', '2014-08-13', 0, 25, 0, -1, 'For Information Only', '2014-08-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1399, 1432, 43, 'For Information Only', 'MQMR', 'Complete', '2014-08-12', 0, 25, 0, -1, 'For Information Only', '2014-08-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1400, 1433, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2014-08-19', 0, 25, 0, -1, 'For Information Only', '2014-08-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1401, 1434, 43, 'SAPMT has reviewed the subject submittal dated August 10, 2014 and has the following comment:\r\n•	Mr. Muhammad Hashim Khan was interviewed via video conferencing and it was found that his expertise is limited to insulation resistance testing and cable terminations. SAPMT shall approve the said candidate conditionally for a period of three (3) months after which a re-interview with a written examination shall be conducted to determine the candidates overall competency as a “QC Inspector - Electrical & Instrumentationâ€. This approval can be revoked by SAPMT anytime in case of unsatisfactory performance.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1000/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1402, 1435, 43, 'SAPMT has reviewed the subject submittal dated August 10, 2014 and has the following comments:\r\n1.	After a personal interview and the written test, it has been decided that the performance of Mr. Joseph Buban Navarro may be checked on site for a period of one (1) month before making a final decision.\r\n2.	SAPMT retains the right to revoke this conditional approval at any time if the performance does not meet the requirements.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-08-19', 0, 25, 0, 46, 'L-993/14', '2014-08-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1403, 1436, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1404, 1438, 43, 'SAPMT has reviewed the subject submittal dated August 10, 2014 and has the following comments:\r\n1.	Incorporate the comments as discussed during the meeting with SAPMT.\r\n2.	The road sections shall be according to the IFB.\r\n3.	Provide readable copies of drawings in the submittal\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Shop Drawings', 'Complete', '2014-08-19', 0, 25, 0, 46, 'L-997/14', '2014-08-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1405, 1441, 43, 'SAPMT has reviewed the subject submittal dated August 12, 2014 and has no objection with the following comments:\r\n1.	Action item No.2 shall be complied with.\r\n2.	Provide colored printouts where necessary to ensure that the information is easy to review.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Shop Drawings', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1009/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1406, 1437, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0751 dated August 11, 2014 and has the following comments:\r\n1.	Provide a sketch/ shop drawing as to where the storage/ assembly area shall be on the Project key plan and ensure that the proposed area is within the new KAUST boundaries and not beyond the chain link fence that divides KAUST and NAVY.\r\n2.	Provide detailed information of persons and vehicles to be used.\r\n3.	Ensure that storage and handling is done properly according to Saudi Aramco standards and manufacturer’s written recommendations.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Vessel Barrier Assembly', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-998/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1407, 1442, 43, 'IC is hereby informed that the following changes have occurred in the SAPMT related to “KAUST – Perimeter Security Systemsâ€ project;\r\n1.	Mr. Alaa A. Ainaddin shall be acting as Project Manager in place of Mr. Saad A. Al-Ghamdi.\r\n2.	Mr. Dr. Ahmed S. Khogeer shall be acting as Senior Project Engineer in place of Mr. Fahad A. Al-Balawi\r\n3.	Mr. Sami Al-Gafri shall be acting as Project Engineer in place of Mr. Yaser A. Al-Johani.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'SAPMT Changes', 'Complete', '2014-08-17', 0, 25, 0, 46, 'L-990/14', '2014-08-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1408, 1444, 43, 'No Comments, For Information Only', 'QC Inspector', 'Complete', '2014-08-19', 0, 25, 0, -1, 'For Information Only', '2014-08-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1409, 1445, 43, 'SAPMT has reviewed the subject submittal dated August 13, 2014 and has the following comments:\r\n1.	While preliminary civil works can start, it is IC responsibility to ensure that the Z-portal manufacturer agrees with the shop drawings for civil, electrical, communications and security being created by IC or its subcontractors.\r\n2.	All stub-up conduits shall be coordinated with Electrical, Communication and Security drawings.\r\n3.	Proper routing direction of the underground conduits has to be reflected.\r\n4.	Provide additional details for system disconnect enclosure, stating the rating of the disconnect switch and identify if it is fusible or non-fusible switch.\r\n5.	Provide more details for the condensate drain pit.\r\n6.	Consider to include the Grounding details, Power Supply source, and wiring diagrams of the Vehicle X-ray machine.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Z Portal, Gate 3', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1002/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1410, 1446, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1411, 1447, 43, 'No Comments, For Information Only', 'QAQC Meetings', 'Complete', '2014-08-19', 0, 25, 0, -1, 'For Information Only', '2014-08-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1412, 1448, 43, 'No Comments, For Information Only', 'QAQC Meeting', 'Complete', '2014-08-19', 0, 25, 0, -1, 'For Information Only', '2014-08-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1413, 1449, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2014-09-01', 0, 25, 0, -1, 'For Information Only', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1414, 1450, 43, 'No Comments, For Information Only', 'Inspection Schedule', 'Complete', '2014-12-27', 0, 25, 0, -1, 'For Information Only', '2014-12-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1415, 1451, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0755 dated August 14, 2014 and has the following comments:\r\n1.	IC is urged to provide coordinates for the wall up-to which the work can carry on without hindrances at old NAVY Gate and also the coordinates from which the work can proceed after the old naval gate.\r\n2.	IC shall carry on with precast wall erection and related works after the old NAVY Gate, while keeping a small gap at the old naval gate area, which can be filled later.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer (012) 422-4423.\r\n', 'Demolition, Naval Base, Existing Facilities', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1025/14', '2014-09-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1416, 1452, 43, 'SAPMT has reviewed the subject submittal dated August 18, 2014 and has no objection with the following comments:\r\n1.	The new curb on KAM Road shall match in shape with the existing curb on road 2.\r\n2.	Minor deviation from the shape of curb in IFB is accepted and IC is urged to provide difference in the quantity of concrete works.\r\n3.	It is IC responsibility to ensure that all works on the project are completed according to the scope of work and Saudi Aramco specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Concrete Curb, Gutter Detail', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1008/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1417, 1453, 43, 'SAPMT has reviewed the subject submittal dated August 17, 2014 and has the following comments:\r\n1.	Ensure that all SONAR heads are monitored from JFCC Building control room and SHQ Building control room as per project requirements and scope of work.\r\n2.	Ensure that New SONAR system is same as existing.\r\n3.	Provide a separate power system for the new SONAR # 4 equipment in Shelter # 2 by providing an approved UPS system and back-up batteries.\r\n4.	Since the new SONAR # 4 will use existing SONAR System servers and Alarm Management System, Provide a signed scope of work and quantities for all servers that will not be used, to process a negative change order.\r\n5.	Consider providing shop drawings showing the equipment arrangements in Shelter # 2 cabinet rack, New UPS and related batteries and electrical single line diagram.\r\n6.	Ensure full compliance with scope of work and approved Project Specifications and approved IFC drawings.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Sonar TQ', 'Complete', '2014-11-03', 0, 87, 0, 46, 'L-1071/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1418, 1454, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0760 dated August 18, 2014 and the ACD has been extended with the following conditions:\r\n1.	The LBE may be escalated to an NCR if the rectification is not completed on or before the new ACD.\r\n2.	The LBE may be escalated to an NCR if the rectification is not acceptable to SAPMT.\r\n3.	IC is urged to comply with SAER-381, paras 6.6.3, 6.6.3.1 and 6.6.3.2.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'ACD, LBE', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1001/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1419, 1455, 43, 'SAPMT has reviewed the subject submittal dated August 18, 2014 and has no objection with the following comments:\r\n1.	Ensure that the proposed G.I box is compatible with lighting switches, receptacle outlets and other similar fittings and fixtures.\r\n2.	It is IC responsibility to ensure that all works are completed according to the agreed scope of work and Saudi Aramco standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'G.I Box', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1004/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1420, 1456, 43, 'SAMPT has reviewed the subject submittal dated August 17, 2014 and has no objection with the following comments;\r\n1.	Provide more details of precast fence at Gate #2 and Gate 3 to avoid irregularity of the view.\r\n2.	Ensure that all coordinates/ elevations are inspected and approved on site before starting concrete works.\r\n3.	It is IC responsibility to ensure that all works are done according to the agreed scope of work and Saudi Aramco standards.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Shop Drawings', 'Complete', '2014-09-03', 0, 87, 0, 46, 'L-1015/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1421, 1457, 43, 'SAPMT has reviewed the subject submittal dated August 19, 2014 and has the following comments:\r\n1.	Attach the related IFC drawings.\r\n2.	Show the slopes from the highest point to the outlet.\r\n3.	Consider removable grating for maintenance purpose\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Roof Drain', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1003/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1422, 1458, 43, 'SAPMT has reviewed the subject submittal dated August 17, 2014 and has the following comment:\r\n•	Provide IC-SD-846863 which is referred to in Actions items 2, 3, 4, 7 & 8.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Turnstile, X-Ray Buildings', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1006/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1423, 1459, 43, 'SAPMT has reviewed the subject submittal dated August 17, 2014 and has the following comment:\r\n•	Action items No. 2, 3, 4, 7 & 8 are referring to drawing IC-SD-846672 which is not attached with the submittal.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.\r\n', 'Turnstile, X-Ray Building', 'Complete', '2014-08-27', 0, 87, 0, 46, 'L-1005/14', '2014-08-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1424, 1460, 43, 'SAPMT has reviewed the subject submittal dated August 17, 2014 and has no objection with the following comments:\r\n1.	Provide the connection details between the column and the block works.\r\n2.	Provide a detailed bending schedule which includes all re-bars size and shapes.\r\n3.	Provide fixing bolt details for suspended ceiling to the slab and also for the wall angle plates to the wall sides.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer (012) 422-4423.\r\n', 'Turnstile, X-Ray', 'Complete', '2014-09-03', 0, 87, 0, 46, 'L-1022/14', '2014-09-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1425, 1461, 43, 'SAPMT has reviewed the subject submittal dated August 17, 2014 and has no objection with the following comments:\r\n1.	Provide the connection details between the column and the block works.\r\n2.	Provide a detailed bending schedule which includes all re-bars size and shapes.\r\n3.	Provide fixing bolt details for suspended ceiling to the slab and also for the wall angle plates to the wall sides.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer (012) 422-4423.\r\n', 'Shop Drawing', 'Complete', '2014-09-03', 0, 87, 0, 46, 'L-1021/14', '2014-09-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1426, 1462, 43, 'SAPMT has reviewed the subject submittals dated August 19, 2014 & August 27, 2014 and has the following comments:\r\n1.	The clause referred in TQ-008 sets a time limitation for ending curing only and not allowing for transportation. Provide references to clauses from Saudi Aramco standards or inspection checklists or other applicable standards (ACI or PCI) where transportation of precast panels is allowed after 7 days or after achieving certain strength.\r\n2.	In case no such transportation limitations are mentioned in any standards, the IC proposal to move the panels from the yard at any time or at certain strength shall be supported by calculations, concurred by the designer and approved by SAPMT.\r\n3.	Provide calculations to ensure that the applied load should never exceed the nominal rating load of the anchors while transporting for a given strength of concrete earlier than 28 days. Allowable lifting and handling stresses can be determined by the degree to which cracking can be tolerated. Lifting and handling concrete flexural stress calculations may assume an impact allowance of around 50% for transport and handling.\r\n4.	IC may suggest a method to prove that 100% strength has been achieved at any time before 28 days and transport the panels.\r\n5.	In all cases any cracking, chipping, spalling of concrete members due to mishandling and during transportation shall fall within the limitations set by the "repair works matrix for precast elements" dated 19 May 2014.\r\n6.	Any damaged precast members outside the limitations set by the above said matrix shall be considered unusable.\r\n7.	TQ-007 does not present anything different from what’s already mentioned in the "repair works matrix for precast elements" dated 19 May 2014. IC is urged to comply with the agreed matrix.\r\n8.	If there is a contradiction between the agreed matrix and the approved method statement, the one approved later shall be enforced, ensuring that no standards are deviated from.\r\n9.	Any proposal for deviation from standards shall be presented with complete justification for SAPMT review.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Air Bubbles, Wall Panel Delivery', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1045/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1427, 1463, 43, 'SAMPT has reviewed the subject submittal dated August 19, 2014 and has the following comments;\r\n1.	The calculated illumination for waiting area and ID office failed to meet the Saudi Aramco requirements as stated in Table 4 of SAES P-123.\r\n2.	Provide a solution to meet the standard requirements of 500 lux for waiting area and ID office.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Lighting Layout, Visitor Building', 'Complete', '2014-09-03', 0, 87, 0, 46, 'L-1017/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1428, 1464, 43, 'SAPMT has reviewed the subject submittal dated August 25, 2014 and has no objection with the following comments:\r\n1.	Ensure that all sleeves are sealed with approved fire retardant sealant after completion of conducting works.\r\n2.	It is contractor’s responsibility to ensure, verify and validate all required sleeves in accordance to IFC drawings and Saudi Aramco standards.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer at (012) 422-4423.\r\n', 'MEP Sleeves', 'Complete', '2014-08-30', 0, 87, 0, 46, 'L-1011/14', '2014-08-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1429, 1465, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0772 dated August 21, 2014 and has the following comments:\r\n1.	The conditional approval of Mr. Imran Khan as “QC Inspector – Telecommunication & Securityâ€ is extended for another three (3) months.\r\n2.	Mr. Mohammad Mushtaque Ahmed is permanently approved as “QC Inspector for Precast Facilityâ€.\r\n3.	Contractor is urged to submit a separate request for Mr. Qazi Mohammad Arif - QC Supervisor – Civil subjected for re-evaluation.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer (012) 422-4423.\r\n', 'QC Inspector', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1020/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1430, 1466, 43, 'SAPMT has reviewed the subject submittal dated August 24, 2014 and has no objection with the following comments:\r\n1.	Ensure to comply with the HCIS standards for UPS battery requirements in accordance with SEC-07 para. 4.3.5.\r\n2.	It is Contractor’s design choice to either provide battery banks that fit in the allocated room space and still provide the required backup time OR revise the spaces/ areas to meet the requirements without any cost to Saudi Aramco.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Battery', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-902/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1431, 1467, 43, 'SAPMT has reviewed the subject submittal dated August 21, 2014 and has no objection with the comments/ conditions given in the attached letter no. KAUPIS/L-035/2014 dated October 20, 2014.\r\nIC is urged to ensure that all required concrete mix designs for the project are prepared as soon as possible.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Saudi Ready Mix, Concrete Mix Design', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1133/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1432, 1468, 43, 'SAMPT has reviewed the subject submittal dated August 20, 2014 and has the following comments;\r\n1.	All conduits penetrating inside concrete shall be PVC type as stated in SAES P-104, para. 15.4.1.\r\n2.	Support for conduits and boxes shall be through channel erector components such as unistrut as per SAES P-104 para. 8.10.1.\r\n3.	The flexible conduit for floodlight mounted outdoor shall be approved liquid type flexible conduit and not ordinary flexible conduit.\r\n4.	Provide grounding/bonding connections for the turnstile metal body, and x-ray machine body, metal detector body.\r\n5.	Replace flexible conduit with Rigid Steel PVC coated conduit connecting disconnect switch & Main power feeder.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Lighting Layout', 'Complete', '2014-09-03', 0, 87, 0, 46, 'L-1016/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1433, 1469, 43, 'SAPMT has reviewed the subject submittal dated August 20, 2014 and has the following comments:\r\n•	Cumulative engineering progress does not match with Weekly Progress Report # 50.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer (012) 422-4423.\r\n', 'Progress Meeting 41', 'Complete', '2014-09-03', 0, 87, 0, 46, 'L-1019/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1434, 1470, 43, 'SAPMT has reviewed the subject submittal dated August 20, 2014 and has the following comments:\r\n1.	Progress Summary shall have a data date of August 08, 2014 and not August 10, 2014.\r\n2.	Cumulative engineering progress does not match with the weekly progress report no. 50.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer (012) 422-4423.\r\n', 'Progress Meeting 42', 'Complete', '2014-09-03', 0, 87, 0, 46, 'L-1023/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1435, 1471, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1436, 1472, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1437, 1473, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1438, 1475, 43, 'SAPMT has reviewed the subject submittal dated August 23, 2014 and has no objection with the following comment:\r\n•	Work may proceed with the following considerations;\r\na.	Provide separately the documents for the third party FOC splicers/testers with certification/approval by Saudi Aramco for review and acceptance, complying with SAPMT comment item 3 in previous review.\r\nb.	Ensure all testing equipment’s are available and possess the features/modules to test CD/PMD to comply SAES-T-634, complying with SAPMT comment item 4 in the previous review.\r\nc.	Time Schedule shall be provided to be reviewed by SAPMT prior to execution of the works.\r\nd.	Ensure only experienced and qualified personnel are available to execute the work.\r\ne.	Ensure all materials and equipment’s needed are present during the execution of the work.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer (012) 422-4423.\r\n', 'FOC Cable', 'Complete', '2014-09-03', 0, 87, 0, 46, 'L-1024/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1439, 1474, 43, 'SAPMT has reviewed the subject submittal dated August 24, 2014 and has no objection with the following comments:\r\n1.	Units shall be certified at manufacturing facility to comply with UL-1203 and UL-1995 by an approved third party.\r\n2.	Units shall be equipped with necessary field instruments like valves/ dampers, controls, safety systems; pre-wired field interfaces, control system interfaces etc. and such details shall be included in the RP.\r\n3.	Ensure that PACU condenser coils have copper fins as per SAES-K001 para 4.8.4.9.\r\n4.	IC is responsible for delivering materials/ equipment and installation of all units and accessories according to the agreed scope of work and Saudi Aramco standards.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Package Air Conditioning, HVAC', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1034/14', '2014-09-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1440, 1476, 43, 'SAPMT has reviewed the subject submittal dated August 23, 2014 and has the following comments:\r\n1.	Mr. Ali El Sayed El Shayal is conditionally approved as “Engineering Managerâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Engineering Manager', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1027/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1441, 1478, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0736 dated August 25, 2014 and has the following comments:\r\n1.	Provide copy of a PO made to the manhole manufacturer showing vendor acceptance and delivery dates.\r\n2.	Attach the quality inspection procedures/ checklists to ensure that IC understands the scope of works involved.\r\n3.	Provide an exact start data and end date for manufacturing the manhole.\r\n4.	Provide details of manufacturer for SAPMT acceptance.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Service Communication Manhole', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1137/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1442, 1477, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2014-09-01', 0, 25, 0, -1, 'For Information Only', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1443, 1479, 43, 'SAPMT has reviewed the subject submittal dated August 25, 2014 and has the following comments:\r\n1.	Since there is a change from IFB, IC shall submit a bill of quantities to be agreed upon by both parties, even if there are no price changes.\r\n2.	Modifications to pipe specifications are acceptable. Ensure that PUOU is used according to the requirements of SAES-L-105.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Copper Pipe, UPVC Pipe', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-706/14', '2014-09-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1444, 1480, 43, 'Complying by ICC. For Information Only.', 'Preliminary, Incident Report', 'Complete', '2014-09-08', 0, 25, 0, -1, 'For Information Only', '2014-09-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1446, 1482, 43, 'SAPMT has reviewed the subject submittal dated August 25, 2014 and has the following comments:\r\n1.	Provide detail for the lighting pole bonding to the grounding grid conductor.\r\n2.	Extend the PVC pipe with at least 150mm stub-up, till the top of the pole foundation grade level.\r\n3.	Base plate material in the shop drawing is different from the sample provided. Sample has steel plate whereas the drawing mentions die cast aluminum.\r\n4.	The brand name of the sample of lighting fixture is different from the one mentioned in the drawing. Consider mentioning the required fixture specifications only without the brand name.\r\n5.	Consider re-writing the type of the pole with "Hot Dipped Galvanized steel with finish powder coating".\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Single Arm, Street Lighting', 'Complete', '2014-09-03', 0, 87, 0, 46, 'L-1026/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1447, 1483, 43, 'SAPMT has reviewed the subject submittal dated August 24, 2014 and has the following comment:\r\nBI	Transmittal Type 	Transmittal no. 	Description no. 	9COM	Level Of Inspection 	Status \r\n25-00026	MR	RP-21	PIPE; NON-METALLIC 	6000000031	Zero (0)	Approved\r\n\r\n•	The manufacturer SAPPCO DAMMAM FACTORY, BRANCH of SA is limited to Pipe Sizes ½â€ to 10â€.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'UPVC Pipes Sch. 40', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1033/14', '2014-09-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1448, 1484, 43, 'SAPMT has reviewed the subject submittal dated August 26, 2014 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Shop Drawing for Fence', 'Complete', '2014-09-13', 0, 87, 0, 46, 'L-1054/14', '2014-09-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1449, 1485, 43, 'SAPMT has reviewed the subject submittals dated August 19, 2014 & August 27, 2014 and has the following comments:\r\n1.	The clause referred in TQ-008 sets a time limitation for ending curing only and not allowing for transportation. Provide references to clauses from Saudi Aramco standards or inspection checklists or other applicable standards (ACI or PCI) where transportation of precast panels is allowed after 7 days or after achieving certain strength.\r\n2.	In case no such transportation limitations are mentioned in any standards, the IC proposal to move the panels from the yard at any time or at certain strength shall be supported by calculations, concurred by the designer and approved by SAPMT.\r\n3.	Provide calculations to ensure that the applied load should never exceed the nominal rating load of the anchors while transporting for a given strength of concrete earlier than 28 days. Allowable lifting and handling stresses can be determined by the degree to which cracking can be tolerated. Lifting and handling concrete flexural stress calculations may assume an impact allowance of around 50% for transport and handling.\r\n4.	IC may suggest a method to prove that 100% strength has been achieved at any time before 28 days and transport the panels.\r\n5.	In all cases any cracking, chipping, spalling of concrete members due to mishandling and during transportation shall fall within the limitations set by the "repair works matrix for precast elements" dated 19 May 2014.\r\n6.	Any damaged precast members outside the limitations set by the above said matrix shall be considered unusable.\r\n7.	TQ-007 does not present anything different from what’s already mentioned in the "repair works matrix for precast elements" dated 19 May 2014. IC is urged to comply with the agreed matrix.\r\n8.	If there is a contradiction between the agreed matrix and the approved method statement, the one approved later shall be enforced, ensuring that no standards are deviated from.\r\n9.	Any proposal for deviation from standards shall be presented with complete justification for SAPMT review.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Air Bubbles, Wall Panel Delivery', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1045/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1450, 1486, 43, 'SAPMT has reviewed the subject submittal dated August 26, 2014 and has no objection with the following comment:\r\n•	IC and its subcontractors shall ensure that all incidents are reported promptly.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Incident Report', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1056/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1451, 1495, 43, 'KAUST & Thuwal Projects Department (K&TPD) is requesting your support to allocate 1300 tons of bitumen 60/70 to “KAUST – Perimeter Security Systemsâ€ Contractor, “International Center for Contracting Co. (IC)â€ to complete the asphalting work for King Abdullah Monument Access Road planned for the month of August, September 2014. \r\n\r\nThis quantity shall be used by M/s. Dar Al Manajim Contracting & Asphalt (DARMCO) – Briman, Jeddah, which is one of the suppliers for the asphalt works for the KPSS project.\r\n\r\nIt is requested that the concerned bulk plants in Jeddah region be informed to issue the said quantity to Al-Jeri Establishment (Customer Account No. 400608).\r\n\r\nShould you have any inquiry, please contact Sohail Moughal, Project Engineer on (012) 422-4570.\r\n\r\nThe draft was finalized by Mr. Noor N. this draft may vary in wording.', 'Asphalt Allocation', 'Complete', '2014-09-06', 0, 87, 0, 46, 'L-045 Asphalt', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1452, 1487, 43, 'We seek your support to allocate 1300 tons of bitumen 60/70 to the subject project Contractor, International Center for Contracting Co. (IC) to expedite the asphalting work for King Abdullah Monument Access Road planned for completion by September 04, 2014. \r\n\r\nIt is requested that the concerned bulk plants in Jeddah region be informed to issue the said quantity to Al-Jeri Establishment (Customer Account No 400608).  This quantity shall, in turn, be used by M/s. Dar Al Manajim Contracting & Asphalt (DARMCO) – Briman, Jeddah, which is one of the suppliers for the asphalt works under the project.\r\n\r\nYour support and quick response will be highly appreciated as it will provide the help necessary to complete the project on time. \r\n\r\nShould you have any inquiry, please contact Sohail Moughal, Project Engineer on (012) 422-4570.\r\n', 'Asphalt Request', 'Complete', '2014-09-08', 0, 87, 0, 46, 'L-045/14', '2014-09-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1453, 1488, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0768 dated August 27, 2014 and has the following comments:\r\n1.	Provide information about the proposed asphalt subcontractor, Aramco approved vendor for bitumen, and the depot for collection.\r\n2.	Ensure that all roadways for security gates and gatehouses etc. are included.\r\n3.	Ensure that biking tracks for KAM road are also included.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Bitumen', 'Complete', '2014-11-03', 0, 25, 0, 46, 'L-1136/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1454, 1489, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0773 dated August 28, 2014 and has the following comments:\r\n1.	Mr. Sarfraz Ahmad is conditionally approved as “QC Inspector for Precast Facilityâ€ for “KAUST – Perimeter Security Systemsâ€ project only for One (1) month probationary trial period.\r\n2.	He should be assign fully in the FCC precast plant for precast elements inspection works.\r\n3.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'QC Inspector', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1032/14', '2014-09-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1455, 1490, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0770, 0603, 0566 & 0532 dated 27th August 2014, 27th May 2014, 10th May 2014 & 20th April 2014 respectively and has the following comments:\r\n1.	Provide detailed quantities of all work items/ activities involved in the deletion of ditch from the scope of work and reworks if any etc., for both parties to agree, after which the processes for change order/ amendment can start.\r\n2.	Contact SAPMT to understand Saudi Aramco procedures if necessary.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Ditch Elemination', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1039/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1456, 1491, 43, 'For Information Only', 'Inspection Schedule', 'Complete', '2014-10-21', 0, 25, 0, -1, 'For Information Only', '2014-10-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1457, 1492, 43, '\r\nSAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0775 dated September 01, 2014 and has the following comments:\r\n1.	Mr. Alfredo V Pacheco Jr. is permanently approved as “QC Manager (Sub-contractor FCC)â€ for “KAUST – Perimeter Security Systemsâ€ project only.\r\n2.	SAPMT reserves the right to revoke this permanent approval based on his unsatisfactory performance during project tenure.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'QC Manager', 'Complete', '2014-10-12', 0, 87, 0, 46, 'L-1038/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1458, 1493, 43, 'SAPMT has reviewed the subject submittal dated August 28, 2014 and has no objection with the following comment:\r\n•	IC shall provide shop drawings only if the required details are not available in the IFC. Magnifying the information from IFC and submitting it as a shop drawing is unnecessary.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Roof Drain', 'Complete', '2014-09-13', 0, 87, 0, 46, 'L-1051/14', '2014-09-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1459, 1494, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0774 dated August 28, 2014 and has the following comments:\r\n1.	The temporary replacement Mr. Jerry A. Paga as “QC Technicianâ€ is acceptable provided he will be given at least two weeks for proper transition and turn-over of works.\r\n2.	Contractor shall follow Schedule Q – General Requirements, Section 5 – Resource Management, Clause 5.14.\r\n3.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'QC Technician', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1031/14', '2014-09-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1460, 1496, 43, 'SAPMT has reviewed the subject submittal dated August 30, 2014 and has no objection with the following comment:\r\n•	Ensure that the PVC coating for Rigid Steel conduits, fittings and condulets shall have a thickness as per SAES P-104 Para 8.3.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'RGS PVC Coated Pipe', 'Complete', '2014-09-13', 0, 87, 0, 46, 'L-1050/14', '2014-09-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1461, 1497, 43, 'SAPMT has reviewed the subject submittal dated August 30, 2014 and has the following comment:\r\nBI	Transmittal Type 	Transmittal no. 	Description no. 	9COM	Level Of Inspection 	Status \r\n25-00026	MR	RP-22	PIPE; NON-METALLIC 	6000000031	Zero (0)	Approved\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'UPVC Pipe', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1028/14', '2014-09-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1462, 1499, 43, 'With reference to your letter no. KAUST-M&U-14-0067 dated August 31, 2014 the attached example/ scenario explains the limitations which are also mentioned as below;\r\n\r\n1.	There are approximately 45 angles/ kinks in the boundary wall creating approximately 45 wall segments of various sizes. \r\n2.	Every wall segment is not a perfect divisible of 3 or 4 to accommodate the 3m wide panel or to allow a logo equally after every 3 panels.\r\n3.	It is impossible to construct a panel that is smaller than 1.5m wide as the integrity of the wall and the size of logo will be compromised.\r\n4.	It is impossible to make a wall panel with a kink/ angle and test it for crash rating or create a logo with an edge.\r\n5.	Every corner must have a column, as the column is the strongest element of the wall.\r\n6.	The corners or smaller segments are the points where the logo arrangement begins as the viewer slows down at the corners and notices the anomalies if any much more, as compared to a longer straight stretch. Hence corners have been kept symmetrical and more agreeable.\r\n\r\nAfter analyzing all the limitations, the designers have symmetrically placed all anomalies in the middle of segments, which will either be un-noticeable at high speeds when the complete wall is built or will allow a symmetrical view. \r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer on Tel. No. 012 422 4423.\r\n', 'Logo Arrangement', 'Complete', '2014-09-04', 0, 87, 0, 46, 'L-1030/14', '2014-09-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1463, 1500, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0788 dated September 01, 2014 and has the following comments:\r\n1.	Mr. Milo B. Abaoag is permanently approved as “QC Inspector – Civil (Sub-contractor FCC)â€ for “KAUST – Perimeter Security Systemsâ€ project only.\r\n2.	SAPMT reserves the right to revoke this permanent approval based on his unsatisfactory performance during project tenure.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'QC Inspector', 'Complete', '2014-10-12', 0, 87, 0, 46, 'L-1037/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1464, 1501, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0790 dated September 01, 2014 and has the following comments:\r\n1.	Mr. Abdul Nisar is permanently approved as “QC Inspector – Civil (Sub-contractor FCC)â€ for “KAUST – Perimeter Security Systemsâ€ project only.\r\n2.	SAPMT reserves the right to revoke this permanent approval based on his unsatisfactory performance during project tenure.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'QC Inspector', 'Complete', '2014-10-12', 0, 87, 0, 46, 'L-1043/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1465, 1502, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0791 dated September 01, 2014 and has the following comments:\r\n1.	Mr. Emadudden M. Macadato is permanently approved as “QC Inspector – Civil (Sub-contractor FCC)â€ for “KAUST – Perimeter Security Systemsâ€ project only.\r\n2.	SAPMT reserves the right to revoke this permanent approval based on his unsatisfactory performance during project tenure.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'QC Inspector', 'Complete', '2014-10-12', 0, 87, 0, 46, 'L-1042/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1466, 1503, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0792 dated September 01, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'LBE, ACD', 'Complete', '2014-10-12', 0, 87, 0, 46, 'L-1036/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1467, 1504, 43, 'SAPMT has reviewed the subject submittal dated September 01, 2014 and has no objection with the following comment:\r\n•	IC is urged to perform one time trial mix for the grout and mortar for CMU to confirm the required compressive strength.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.\r\n', 'Concrete Hollow Blocks', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1061/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1468, 1505, 43, 'No Comments', 'Block Accessories', 'Complete', '2014-09-13', 0, 87, 0, 46, 'L-1048/14', '2014-09-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1469, 1506, 43, 'SAPMT has reviewed the subject submittal dated September 01, 2014 and has the following comments:\r\n1.	The proposed exhaust fans don''t have the provision of back draft damper which is a non-compliance of project specifications, IFC drawing, and SAES K-001 Para. 4.8.9 requirements.\r\n2.	Consider adding the project specifications and Saudi Aramco standard requirements for exhaust fans in the compliance sheet provided.\r\n3.	Ensure full compliance with IFC drawings, Project Specifications, and Saudi Aramco Standard SAES K-001, K-002 and K-003.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Exhaust Fans', 'Complete', '2014-09-13', 0, 87, 0, 46, 'L-1049/14', '2014-09-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1470, 1507, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0778 dated September 02, 2014 and has rejected with the following comments:\r\n1.	Paragraph 1.3.2.3 of Schedule-C is not relevant to the submittals as it only speaks of further breakdown and not of revision.\r\n2.	Deletion of ditch from the project scope is not a reason to revise the Schedule-C, Attachment 1.\r\n3.	The deletion of ditch was conveyed to IC much earlier and IC is urged to provide a signed scope of work and signed MTO as soon as possible, according to Saudi Aramco procedures.\r\n4.	After the change order for the ditch has been processed and the value of the ditch determined according to the unit rates provided by IC, a revision in Schedule-C can be considered, if desired by IC.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Restructuring, Contract Price', 'Complete', '2014-10-14', 0, 87, 0, 46, 'L-1057/14', '2014-10-14', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1471, 1508, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0786 dated September 02, 2014 and has rejected with the following comments:\r\n1.	The communication failure was first detected in January 2014 by KAUST and all logs and reports are available if IC communication experts want to study them and discuss with the KAUST O&M Deptt.\r\n2.	After a cut made by another contractor was fixed by the other contractor, the communication error still prevailed and the second error was located directly under the KAM road (200 m from the optiped). It is quite understandable that error in the loop cannot be resolved until all cuts are fixed.\r\n3.	No other contractor has worked on KAM road since January 2014. IC workers have been avoiding to report any damages to existing utilities at various occasions in the past.\r\n4.	The depth of the FOC cable is not a constant number. It varies depending on the existence of other underground utilities or structures.\r\n5.	From the above it seems that the cut was made while excavating or removing debris, steel re-bars, old buried demolished concrete etc. from the alignment of KAM road. This debris could have been deeper than expected or seen from the surface while heavy machinery is working.\r\n6.	IC is advised to take this matter seriously and urgently and provide scientific data specifications to the discipline of communications to prove their point of view. Failing which the cables shall be fixed, replaced/ spliced as per approved design within 15 days issuance of this letter.\r\n7.	Demolition work shall be carefully executed by the CONTRACTOR in order not to damage any existing underground utilities or other Facilities which are not part of this Project.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.\r\n', 'FOC Cut', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1060/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1472, 1509, 43, 'SAPMT has reviewed the subject submittal dated September 01, 2014 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'FRP Underground Storage Tanks', 'Complete', '2014-09-14', 0, 87, 0, 46, 'L-1047/14', '2014-09-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1473, 1510, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0794 dated September 02, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'QC Manager', 'Complete', '2014-10-12', 0, 87, 0, 46, 'L-1044/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1474, 1511, 43, 'Maxess, the vendor for SACS systems has informed that the material gate pass system stated in the functional specification document FSD-002 para. 4.9 can not be a part of SACS (Security Access Control System), and therefore the requirement stated in FSD-002 para. 4.9.1 for tracking and managing materials at existing company gates cannot be fulfilled. Vendors letter is attached for referecne. KAUST is requested to concur removal of this requirement from FSD.', 'Material Gate Pass Systems', 'Complete', '2014-11-02', 0, 25, 0, -1, 'For Record Only', '2014-11-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1475, 1512, 43, 'SAPMT has reviewed the subject submittal dated September 02, 2014 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Turnstile, X-Ray Building', 'Complete', '2014-09-13', 0, 87, 0, 46, 'L-1053/14', '2014-09-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1476, 1513, 43, 'SAPMT has reviewed the subject submittal dated September 02, 2014 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Turnstile, X-Ray Building', 'Complete', '2014-09-13', 0, 87, 0, 46, 'L-1052/14', '2014-09-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1477, 1514, 43, 'SAPMT has reviewed the subject submittal dated September 02, 2014 and has no objection with the following comment:\r\n•	IC is urged to implement the solutions for findings as per agreed timetable and monitor compliance and close-out issues during regular inspections.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Camp Inspection', 'Complete', '2014-09-13', 0, 87, 0, 46, 'L-1046/14', '2014-09-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1478, 1515, 43, 'IC is urged to show proof of compliance with Schedule B, Para 5.4.3 and 5.4.4, by providing names of key personnel working in the site office. A tabulated report with details showing current staff, unavailable staff and alternatives shall be provided before 11th September 2014.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Personnel', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1035/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1479, 1516, 43, 'SAPMT has reviewed the subject submittal dated September 02, 2014 and has the following comment:\r\n•	The fire alarm cable shall be FPLP type according to approved specifications.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.\r\n', 'Fire Resistance Cable', 'Complete', '2014-09-28', 0, 87, 0, 46, 'L-1069/14', '2014-09-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1480, 1517, 43, 'SAPMT has reviewed the subject submittal dated September 06, 2014 and has the following comment:\r\n•	IC is urged to suggest other subcontractors also for SAPMT to compare and choose from which are not already busy with other significant projects in KAUST. The selection of an irrigation subcontractor has been delayed for quite some time by IC and thus the delayed design for irrigation work for KAM access road is causing delays in procurement of pipes. A quick response from IC is necessary.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.\r\n', 'Rabya, Landscaping', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1059/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1481, 1518, 43, 'No Comments, For Information Only', 'Incident Report', 'Complete', '2014-09-09', 0, 25, 0, -1, 'For Information Only', '2014-09-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1482, 1519, 43, 'SAPMT has reviewed the subject submittal dated September 04, 2014 and has no objection with the following comments:\r\n1.	IC is urged to construct a smooth and unnoticeable transition, preferably at the first bend.\r\n2.	Ensure that the road widths, road thickness and super-elevations are maintained according the agreed scope of work and applicable standards.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.', 'Transitional Area', 'Complete', '2014-09-24', 0, 87, 0, 46, 'L-1066/14', '2014-09-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1483, 1530, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1484, 1520, 43, 'For Information Only', 'Weekly Meeting', 'Complete', '2014-10-12', 0, 25, 0, -1, 'For Information Only', '2014-10-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1485, 1521, 43, 'No Comments, For Information Only', 'MQMR', 'Complete', '2014-09-17', 0, 25, 0, -1, 'For Information Only', '2014-09-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1486, 1522, 43, 'SAPMT has reviewed the subject submittal dated September 28, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', 'Saudization', 'Complete', '2014-10-17', 0, 87, 0, 46, 'L-1109/14', '2014-10-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1487, 1523, 43, 'For Information Only', 'Inspection Schedule', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1488, 1524, 43, 'Payment Application approved and SES issued to ICC.', 'Invoice, Payment Application', 'Complete', '2014-10-20', 0, 25, 0, -1, 'For Record Only', '2014-10-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1489, 1525, 43, 'No Comments, For Information Only', 'Incident Report', 'Complete', '2014-09-16', 0, 25, 0, -1, 'For Information Only', '2014-09-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1490, 1526, 43, 'SAPMT has reviewed the subject submittal dated September 02, 2014 and has no objection with the following comments:\r\n1.	The Final Inspection Disposition Report (Two hard and two soft copies) shall be submitted to KAUST at the time of handing over of the project in hard binders approved by KAUST (sample provided).\r\n2.	FIDR shall include copy of review by VID. \r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'MV Cable, IDR', 'Complete', '2014-09-28', 0, 87, 0, 46, 'L-1074', '2014-09-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1491, 1527, 43, 'SAPMT has reviewed the subject submittal dated September 09, 2014 and has the following comments:\r\n1.	The final report shall be submitted within 3 days upon discovery of the incident using the prescribed SA Format.\r\n2.	The Safety Department of the IC shall conduct a thorough investigation and provide analysis and documentation to SAPMT.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Incident Report', 'Complete', '2014-11-02', 0, 87, 0, 46, 'L-1112/14', '2014-11-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1492, 1528, 43, 'SAPMT has reviewed the subject submittal dated September 09, 2014 and has no objection. However, IC is urged to follow the revised project schedule strictly by complying applicable Saudi Aramco standards.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.\r\n', 'Project Schedule', 'Complete', '2014-10-12', 0, 87, 0, 46, 'L-1064/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1493, 1529, 43, 'SAPMT has reviewed the subject submittal dated September 09, 2014 and has no objection with the following comment:\r\n•	While the proposal to use alternatives to copper pipes is accepted, it is IC’s responsibility to ensure the following;\r\n1.	SAES-L-105 is complied with.\r\n2.	A revised project specification is issued to reflect the alternatives.\r\n3.	The Quantities shall be provided for items, the copper pipes as negative change and the alternative pipes as positive change.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.\r\n', 'CPVC Pipes', 'Complete', '2014-09-24', 0, 87, 0, 46, 'L-1068/14', '2014-09-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1494, 1541, 43, 'With reference to the site inspection of sample for lighting poles for KAM access Road and subsequent comments received from KAUST dated 09/07/2014, a compliance sheet from the vendor is attached. KAUST concurrence is required so that PO process can be finalized. A previously agreed upon responsibility matrix is also attached for your reference.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer on Tel. No. 012 422 4423.\r\n', 'Lighting Pole Sample', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1065/14', '2014-09-18', 0, '', '', '', '', '');
