SAMPT has reviewed your subject submittal dated March 13, 2014 and has no objection with the following comments:
1.	In drawing IC-SD-846532-01-00 ( Roof Framing Plan ) the exterior corner of two way slab needs additional reinforcement as per ACI 318-08 code, section 13.3.6 to resist the bending moment at the corners.
2.	The annotations for Rebar of Roof Framing Plan (e.g. 14á´“12@200) require correction.
3.	In drawing IC-SD-846532-02-00 (Plan) show the distance between GB-01 and the face of the column or the distance between GB-01 Center line and the axis.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
