SAPMT has reviewed the subject submittal dated February 03, 2015 and has no objection with the following comments:

1.	Ensure that all copies to be provided for Non Material Requirements such as vendor drawings, catalogs and shop drawings for the package substations were readable. 
2.	Ensure the single line diagram and protection system of proposed Package Substations shall be in compliance with Project Specifications, IFC VA-846412 Sht 001, 002 and SEC standards. 
3.	Ensure to select the correct type of Trip functions from catalogue for LV Main Circuit Breaker which is to be based on IFC VA-846412 Sht 001, 002. 
4.	Ensure to select the accurate internal dimensions of CT’s which can accommodate the size of cables.

IC shall ensure that no scope change or cost/schedule implication arises from this letter.

Should you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.
