
SAMPT has reviewed the subject submittal dated March 19, 2015, and has no objection with following comment;

•	Indicate power source for PP-Gen panel in panel board schedule. Attach single line diagram showing power feeding from 300KVA package substation (PS-01A) to PPA-Gen with Power cable number.
