SAPMT has reviewed the subject submittal dated April 27, 2014 and has no objection with the following comments:
1.	Provide the switch rack dimension and panel arrangement shop drawings.
2.	All breakers shall pass the required testing procedure and commissioning requirements as per Saudi Aramco Pre-Commissioning form P -030 for moulded case circuit breakers.
3.	Switch rack Lighting fixtures and receptacle outlets shall be outdoor type.
4.	Ensure that switch rack structure will meet ANSI requirements for hot dip galvanization.
5.	Ensure that all panel enclosure will meet SAES P-104 and 16-SAMSS-512
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
