1. Provide detail for the lighting pole bonding to the grounding grid conductor. 
2. Extend the PVC pipe with at least 150 mm stub up, till the top of the pole foundation grade level. 
3. Base plate material in the shop drawing is different from the sample provided. Sample has steel plate where as the drawing mentions die cast aluminum.
4. The brand name of the sample of lighting fixture is differnt from the one mentioned in the drawing. Consider mentioning the required fixture specifications only without the brand name. 
5. Consider re-writing the type of the pole with "Hot Dipped Galvanized steel with finish powder coating"

