SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:
1.	For material receiving, installation and commissioning of LV Power Cable, add in the “Remarksâ€ column of ITP refer to SATIP-P-104-01 and SATIP-P-111-01â€.
2.	All testing checklists should be as per the Manufacturer’s Testing Procedure.
3.	ICC ITP-T-011 Item # 3.1 (Pedestal Installation and Pre-Commissioning) – Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.
4.	ICC ITP-T-004 Item # 4.1 (Equipment Installation and Pre-Commissioning Visual Inspection) – Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.
5.	ICC ITP-T-004 Item # 4.2 (Turnstile System – Equipment Installation and Pre-Commissioning Visual Inspection) – Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.
6.	Commissioning checklist to be provided by each vendor and sequence of operation and should  include the followings:
a.	It should include the cause and effect matrix during force entry to drop arm and crash barrier.
b.	LPRS has to give a visual and alarm noise in the workstation to alert the operator in case of hot vehicle license plate.
c.	Turnstile has to be interconnected with SACS to de-magnetize the magnetic lock during a recognized access entry.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
