SAPMT has reviewed the subject submittal dated September 20, 2014 and has no objection with the following comments:

•	Provide structural/ civil drawings for SAPMT review separately.
Should you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer on Tel. No. 012 422 4423.
