1. Contract addendum 01 has been shared with all bidders reflecting 6 package substations and 449 lighting poles in National Patrol Road. Reference drawings # PA-00095 sht 001 to 018.
2. The rating and quantity of the lighting fixtures were specified in the IFB, it is the obligation of the LSTK contractor to provide sound estimation for the cable sizing and panel schedule.
3. There is no impact in any transformer capacities the minimum KVA rating for the package substation is 75 KVA, and this is also the size that were provided in IFC. 
4. The location of the package substations were determine during the released of contract addendum 01 (PA-00095 sht 003, 006, 009, 012, 014 017) the single line diagram has been provided already before the release of contract addendum, it is the obligation of LSTK contractor to incorporate information from the BID Package and reflect in detail design.
5. In the IFC an additional of 37 lighting poles, and few meters of LV cable only are subject for variation, this additional lighting poles were added due to detail positioning to meet project requirements.