SAPMT has reviewed the subject letter no. KPSS/SA/B/MUN/13/0143 dated October 26, 2013 and has the following comments:

1.	Provide a detailed drawing showing the coordinates and structural design according to SA standards and concurred by the project designer.
2.	Attach the site layout/ interface drawings.
3.	The top of the duct bank shall have red oxide cement for utility identification and in addition a yellow electrical marker tape must be laid prior to final backfilling.
4.	Specify the material to be used.
5.	Provide cross section profile of the duct bank showing the ditch and the underground IDAS, Transformers, and Perimeter lighting cables.
6.	The installation and construction of duct bank shall be in accordance with Saudi Electric Company Standard, SAES P-104 and NFPA-70.
7.	SAPMT will share your submittal with KAUST & SEC and revert back to ICC if a change order is applicable.
Should you have any questions, please contract Sohail Moughal, Project Engineer on Tel. No. +966 12 422 4570.
