1. Location A's proposed manholes 7 and P are not necessary since Gate #3 has provisions of manhole and duct banks used for communications that can be utilized for mobily cable.

2. A Shop drawing has to be provided to clearly locate the proposed manholes Q and R of LOcation A at the ends of the culvert and how the mobily cable will pass through the culvert.

3. Update and revise the mobily cable route at Location A according to Item 1 and 2.

4. It is appropriate to relocate proposed manhole G between existing manhole 1d and duct bank K at Location B since the current location of manhole G is not necessary due to the distance between proposed manholes F and H are not far.

5. Provide details for the proposed duct bank crossings for all locations.

6. Provide detailed Material Take-off List (MTO).

7. Ensure the drawings, scope and MTO will be reviewed by design consultant with their concurrence.