SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0470 dated March 24, 2014 and has rejected with the following comments:
1.	None of the mentioned utilities are an obstacle to the quantum of work being done by IC.
2.	IC is urged to quantify and qualify any obstacles and claims instead of sending unsupported notices and employ adequate technical and quantity surveying staff to expedite such matters.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
