SAPMT has reviewed the subject submittal dated February 08, 2015 and has the following comments:

•	The procedure shall be revised in compliance to KAUST comments dated February 16, 2015 as per below additional requirements: 
1.	The FAT is for complete system testing and not by components.
2.	The test shall include the viewing, recording and alarm management, masking in and masking out of alarms, and GUI/mapping.
3.	The algorithm of detection shall be done during day, day to evening and evening to night with flash lights and considering camera resolution and stabilization.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.

Should you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.