While the re-routing proposal has been sent to Saudi electrical Company (SEC) via Kaust, IC is urged to coordinate with SEC to expedite SEC concurrence/ acceptance with stamp, signature, name and designation of signatory. When SEC agrees with the distribution of scope of work and the proposed route is acceptable to all concerned parties, IC shall provide a detailed design in collaboration with SEC, for both SEC and IC scope of work. IC shall be resposnible for detailed design, execution of IC own scope of work and the subcontracted work for SEC scope and SEC supervision and acceptance. Works outside of KAUST premises shall be done according to SEC standards. The following items shall be taken care of during the detailed design;

//1. Reconsider the proposed cable tray mounting plan in the existing culvert and provide more details for the cable tray routing plan. // 2. Provide shop drawing for duct bank to cable tray transition. //3. Provide cable profile for the SEC cables running across KAUST Gate 3 road.