As per General Note VA-846497 – all elements expose to earth or weather should have 75 mm cover; this is applicable for underground and above the ground elements. The drawing shows the cover less than 75 mm. IC should revise the drawings and comply with the General Notes.
Regarding to Drawing: FOUNDATION & GROUND BEAM DETAIL:
1-Missing Staircase Rebar at Bent Rebar Schedule and No details or Section. 2-check the number of column ties.
Regarding to Drawing: ROOF, BEAM, ELE AND COLUMN DETAILS & PLAN:
1-Parapet wall steel details show the length of the vertical rebar L=4.6 which is wrong. 2- Rebar No. 8 is repeated at two locations, one for roof rebar and the other at stirrup of beam. 3- Rebar No. 11 mentioned in Rebar schedule but it isn’t show in the drawing.  
