1. All drawings/ designs shall be concurred by the project designer.
2. Install feeder breakers in LV Panel according to feeder assignment of IFC drawing. Take note that Package Substations are not supplying power to street lighting only.
3. Ensure to follow standard frequency of 60 hz. The SFRMU shows 50 Hz, correct it, and use only 60 Hz.
4. Consider the sizing of fuses in the RMU according to Vendor recommendations.

Alaa Please show the draft to mark and Jun and ask what will we do with SCEC comments. 