SAPMT has reviewed the subject submittal dated March 29, 2014 and has rejected with the following comments:
1.	All cast-in-situ concrete members exposed to elements should have a 75 mm cover.
2.	The details and bar bending schedule for staircase is missing.
3.	The numbers and lengths of re-bars for column ties, parapet walls, roof and beam stirrups are miscalculated, not shown or duplicated at several places.
4.	IC is urged to discuss the mistakes with PMT discipline engineer. 
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
