SAPMT has reviewed the subject submittal dated July 02, 2014 and has rejected with the following comments:
1.	The submittal and the drawings are incomplete, without referenced information attached, and not enough to start construction works.
2.	The footing section/plan in drawing VA-847106-001-0F1 is without reference.
3.	Provide precast concrete column fixation details/shop drawing.
4.	Identify the position of conduit stub-up for power supply and grounding cables.
5.	Ensure that the location of motor and necessary controls is coordinated with the motorized gate vendor. Provide details as necessary.
6.	Based on the Auxiliary Gate Elevation Section on VA-847105-0F1 the difference in levels between the sliding gate and the precast foundation footing shall be reconsidered. Provide cross section indicating the interface between the two.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.
