SAPMT has reviewed the subject submittal dated August 13, 2014 and has the following comments:
1.	While preliminary civil works can start, it is IC responsibility to ensure that the Z-portal manufacturer agrees with the shop drawings for civil, electrical, communications and security being created by IC or its subcontractors.
2.	All stub-up conduits shall be coordinated with Electrical, Communication and Security drawings.
3.	Proper routing direction of the underground conduits has to be reflected.
4.	Provide additional details for system disconnect enclosure, stating the rating of the disconnect switch and identify if it is fusible or non-fusible switch.
5.	Provide more details for the condensate drain pit.
6.	Consider to include the Grounding details, Power Supply source, and wiring diagrams of the Vehicle X-ray machine.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.
