IC is urged to coordinate with mobily and acquire more information about the specifications of manholes, ducts and covers etc. The following points shall be considered in the design. // 1. Location A's proposed manholes 7 and P are not necessary since Gate #3 has provisions of manhole and duct banks used for communications that can be utilized for mobily cable. IC shall coordinate with the communications subcontractor in this regard. // 2. Detailed Shop drawings shall be provided to clearly locate the proposed manholes Q and R of LOcation A at the ends of the culvert and how the mobily cable will pass through the culvert. //3. Update and revise the mobily cable route at Location A according to Item 1 and 2. // 4. It is appropriate to relocate proposed manhole G between existing manhole 1d and duct bank K at Location B since the current location of manhole G is not necessary due to the distance between proposed manholes F and H are not far. // 5. Provide details for the proposed duct bank crossings for all locations. 6. Provide detailed Material Take-off List (MTO). 7. Ensure the drawings, scope and MTO will be reviewed by Mobily with their concurrence.