1. Ensure that all MV cable running under roads were protected by duct banks.
2. Duct banks for MV cable shall comply with SAES P-104.
3. Ensure that MV cable clearance with other utilities is within the minimum requirement of 300 mm as stipulated in Saudi Aramco standards.
4. Provide detail shop drawing for all underground electrical and non-electrical utilities that will pass through box culverts 3 & 4 and Wadi Khulais Culvert.
5. Cable routing of main power cable in drawing no. VA-845614-006, PC-001 & 003 shall be connected to new SEC-2.
6. Reflect the routes proposed for the relocation of existing SEC MV cables from existing SEC substation.