1.	For “Material Receiving, Installation and Commissioning of LV Power Cableâ€ add in the remarks column of ITP to “Refer to SATIP-P-104-01â€.
2.	This ITP shall not be used for IDAS system. Provide a separate ITP for CCTV of IDAS system which includes the Microwave Intrusion Detection System (MIDS), and Alarm Management System.
3.	This ITP only shows cabling and conduiting inspection procedure, commissioning checklist is not included.
4.	Pre-Commissioning and Commissioning of CCTV cameras shall be done in Security Control Station, Provide Vendor proposed checklist and guidelines for commissioning and include it in ITP.
