SAPMT has reviewed the subject submittal dated April 22, 2014 and has no objection with the following comments:
1.	Submit specifications for the PVC cement/solvent to be used to connect the conduits.
2.	Only 4â€ PVC type DB-120 TC-8 shall be used for communications. Ensure ¼â€ɸ fish-line rope to be installed on all PVC ducts.
3.	Consider providing details of other materials required for duct bank installation such as warning tapes and marker system.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
