SAMPT has reviewed your subject submittal dated January 21, 2014 and has the following comments:

	Provide complete catalogue of FEC indicating the rating of the circuit breaker for power supply and DC output, specification of each components and mounting details of FEC.
	Provide stainless steel drain fittings and breather or combination as per SAES-P-104 para 7.8.1 for enclosure having an internal volume exceeding 2,000 ã€–cmã€—^3 and SAES-J-102.
	Suggest a locking mechanism with more security.
	Provide related design drawings of IDAS system showing Field Equipment Cabinet (FEC) in the submittal package for reference.
	Provide specifications/datasheets for stainless steel components like sunshades, base etc. 
Should you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.
