SAPMT has reviewed the subject submittal dated October 25, 2014 and has no objection with the following comments:
1.	IC is urged to procure non-inspectable materials from Aramco approved vendors only.
2.	Grounding rods shall meet standard requirements of SAES P-111 para. 5.2.
3.	Molds and cadweld thermite powders shall be as per Furse manufacturer recommendations.
4.	Ensure that the mold sizes are checked based on grounding cables and rods diameter.
5.	Observe and follow best installation practices for grounding rods and conductors, grounding bolts are only acceptable within grounding test pit, while all installations to be back-filled shall be cadwelded.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
