Include power cable for relocation of security system (IDAS/MIDS), also attach as-built drawing and cable specification details. 
5 KV insulation tester is not required for testing of LV cable,remove from the list of equipment shown in paragraph 5.3.1 
Contractor to make sure that there will not be any damages to existing utilities during the removal and relocating of existing fence, light poles and security systems (IDAS/MIDS) 
Consider only applicable points from the description of sequence of U/G cable pulling shown in paragraph 5.3.4 for LV cable installation work. 
Prior the removal of IDAS system and Perimeter lighting in the affected area, ICC is urged to provide the plan to install IDAS system and Lighting System in the designated corridor using the available cameras, MIDS and lighting poles. 
The plan shall include the point of connection to the existing KAUST utilities/network to provide power and connection for Lighting system and IDAS system. 
ICC is urged to provide accurate documentation, red line and as-built.
The attached as-built drawing VA-207593 is outdated. Update the drawing as per site conditions. 
The proposed new manhole and relocated manhole is not acceptable. This will initiate down time on exsiting IDAS System and manhole construction will take a lot of time. Propose optipeds instead in replacement of manholes if applicable. 
Propose vacant fiber cores on existing IDAS 96 core FOC for reservation. 
Contractor to ensure the IDAS on the relocated fence is running smoothly and satisifed KAUST operation prior to disabling the existing IDAS.