SAMPT has reviewed the subject submittal dated May 05, 2015 and has the following comments:

1.	Underground Power and Control Cable shall be installed as per SAES-P-104 para 10.
2.	Minimize the number of Splicing of Conductors for main cable from SEC SS-2 to Switchgear (SWGR 1&2) as per SAES-P-104 para 5.6.
3.	Control Cable shall not be installed directly above the Power Cable (13.8kV MV Cable) as per SAES-P-104 para 10.14.
4.	Consider to use latest revision of Electrical One Line Diagram for 13.8KV switchgear (SWGR 1 & 2).
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.
