SAPMT has reviewed the subject submittal dated July 23, 2014 and has the following comments:
1.	Consider relocating the fire alarm panel, the lighting panel and other electrical panels away from the indoor A/C unit.
2.	The subcontractor for communications shall provide concurrence in addition to the project designer.
3.	Reflect the changes made to the diameter of sleeves from 1.25 to 1.5 as per site conditions.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 12 422-4570.
