SAPMT has reviewed the subject submittal dated June 03, 2014 and has no objection with the following comments:
1.	The provided quantities shall meet the required grounding system ohmic value as stated in SAES P-111.
2.	The provided quantities for bus bar shall be two hole lugs as per project requirement. 
3.	Provide the correct catalog and related specifications.
4.	Provide necessary Fiberglass with 250mm dia, with angle steel plate cover as shown in IFC drawing VA-846492.
5.	Grounding rods, aerial rods and copper clamps shall be UL listed and labeled.
Should you have any questions, please contact Yaser A. Al-Johani, Project Engineer at Tel No. +966 2 422-4686.
