SAPMT has reviewed the subject submittal dated May 18, 2015 and has no objection with the following comments:

1.	Underground LV cable shall be installed as per SAES-P-104 paragraph 10 and in accordance with standard drawing AD-036874.
2.	Ensure LV cable will not obstruct any other underground utilities during installation.
3.	Underground Control cable (8CX2.5sq.mm) shall be installed as per SAES-P-104 para 10.
4.	Correct the drawing of the Patrol road lighting pole, it must be a 10m pole.
5.	Contractor shall ensure that the number of cables inside the trench and related clearances are fit for the purpose of SSD lighting system.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.
