SAPMT has reviewed the subject submittal dated September 01, 2014 and has the following comments:
1.	The proposed exhaust fans don't have the provision of back draft damper which is a non-compliance of project specifications, IFC drawing, and SAES K-001 Para. 4.8.9 requirements.
2.	Consider adding the project specifications and Saudi Aramco standard requirements for exhaust fans in the compliance sheet provided.
3.	Ensure full compliance with IFC drawings, Project Specifications, and Saudi Aramco Standard SAES K-001, K-002 and K-003.
Should you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.
