1. Provide the dimensions of the crash barriers.
2. Provide the dimensions of the remote control panel and Isometric view.
3. Ensure the local power available will match with the proposed crash barrier, the proposed is 208 volts, 3phase, 4Wire, while the available power as per schedule is 400 volts 3 phase 4 Wire, 230 line to neutral.
