1.	Underground LV cable shall be installed as per SAES-P-104 paragraph 10 and in accordance with standard drawing AD-036874.
2.	Ensure LV cable will not obstruct any other underground utilities during installation.
3.	Underground Control cable (8CX2.5sq.mm) shall be installed as per SAES-P-104 para 10.
4.	Correct the drawing of the Patrol road lighting pole, it must be a 10m pole.
5.	Contractor shall ensure that the number of cables inside the trench and related clearances are fit for the purpose of SSD lighting system.
