1. Consider renaming MV Switchgear - RMU Installation in document checklist E-001, into Package Substation.
2. Ensure that Ring Main Unit installation is part of the package substation and will be assembled in the approved vendor plant.  
3. Document Checklist E-001 and E-002 shall be revised, pre-commissioning activities stated in E-001 shall be moved to E-002 
4. Low voltage Molded Case circuit breakers shall be tested using Saudi Aramco inspection Form/Checklist.
5. Step Down Transformer shall be tested using Saudi Aramco inspection Form/Checklist.
6. Ring Main Unit (RMU) shall be tested using Saudi Electric Company (SEC) and or Vendor Checklist.
7. Ensure that document checklist contains only the required activity as per the document title.                         Ex. Package Substation installation in foundation, the activity must be purely in relation with the erection and installation of the unit within the foundation and must not contain any commissioning checklist.