INSERT INTO `submittal` VALUES(1495, 1531, 43, 'SAPMT has reviewed the subject submittal dated September 11, 2014 and has the following comment:\r\n1.	Provide connection details at the culvert and dike.\r\n2.	Provide details of erosion protection.\r\n3.	Provide a detailed rebar bending schedule with shapes and codes.\r\n4.	Provide legible drawings in color.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Box Culvert', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1116/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1496, 1532, 43, 'SAPMT has reviewed the subject submittal dated September 11, 2014 and has no objection with the following comments:\r\n1.	The samples for light poles and luminaires for KAM access road are acceptable provided all comments sent via emails are incorporated.\r\n2.	The specifications for light poles for IDAS, patrol road and parking are acceptable provided the samples are submitted for final approval.\r\n3.	The galvanizing process shall comply with ASTM standards and coatings shall be done by Saudi Aramco approved vendors.\r\n4.	Ensure that all approved lighting fixtures and associated fittings are compatible with the poles.\r\n5.	Ensure specifications are as per document VE846472, Section 2.02.\r\n6.	Ensure that lighting pole for IDAS and Patrol road lighting meet the HCIS requirements SEC-04 Para 4.6.2.3.\r\n7.	Fuse box and terminal blocks shall be heavy duty type with UL or IEC markings.\r\n8.	Ensure compliance with SAES-P-123.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.\r\n', 'Lighting Poles', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1067/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1497, 1533, 43, 'SAPMT has reviewed the subject submittal dated September 10, 2014 and has the following comments:\r\n1.	A Construction Manager has already been approved for the project and working. Explain the need for another similar position.\r\n2.	All CVs shall be submitted with proof of experience and licenses/ certifications.\r\n3.	Attach the Job description with recommendations for key positions.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.', 'Construction Manager', 'Complete', '2014-09-24', 0, 87, 0, 46, 'L-1070/14', '2014-09-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1498, 1534, 43, 'For Information Only', 'Progress Meeting', 'Complete', '2014-10-12', 0, 25, 0, -1, 'For Information Only', '2014-10-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1499, 1535, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0803 dated September 10, 2014 and has the following comments:\r\n1.	The conditional approval of Mr. Sarfraz Ahmed as “QC Inspector – Civilâ€ is extended for another three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1063/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1500, 1536, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0802 dated September 10, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4570.\r\n', 'LBE ACD Extension', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-1062/14', '2014-09-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1501, 1537, 43, 'SAPMT has reviewed the subject submittal dated September 11, 2014 and has the following comment:\r\nBI	Transmittal Type	Transmittal Ref. #	IL no.	Description	9com	Level of Inspection	Status\r\n25-00026	IAP	IAP-07	107000099905	Package Substation	NA	Two(2)	Approved  with Comments \r\n\r\n•	The component shall be from approved source.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Package Substation, Transformer', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1089/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1502, 1538, 43, 'SAPMT has reviewed the subject submittal dated September 11, 2014 and has the following comment:\r\n•	While usage of UPVC pipes is acceptable, IC is urged to ensure that for 200mm dia pipes, the manufacturer is able to provide PN-16 fittings.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'RTR Pipes, UPVC Pipes', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1084/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1503, 1539, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1504, 1540, 43, 'No Comments, For Information Only', 'Incident Report', 'Complete', '2014-09-17', 0, 25, 0, -1, 'For Information Only', '2014-09-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1505, 1557, 43, 'With reference to your letter KAUST-M&U-14-0069 dated September 15, 2014, SAPMT sent a letter L-004/12 dated October 21, 2012 mentioning that the option to upgrade existing security gates at gate 2 and 3 shall be evaluated during the detailed design phases. This has been done. The decision to build new security gates was made during the 50% design review meetings which were attended and commented by various representatives from KAUST. The project designer showed how the upgrade was not possible and SAPMT and KAUST jointly arrived at the following conclusions; 1.	The existing gates cannot be made blast proof without demolishing and reconstructing them, due to the fact that the structures had to be redesigned. 2.	Various new buildings and systems (e.g. QRT building, JFCC building, K-9 area, X-ray systems, UVIS room etc) could not be added to existing gates due to lack of space. If the location of existing gates were to be used, some buildings would be placed outside the secure area, which defeats the security requirements. 3.	KAUST security operations will be compromised heavily during the re-construction because existing facilities and roadways will not be usable. Therefore, and based on the above, SAPMT will carry on with the construction of the new gatehouses so that the schedule is not impacted. Should you have any questions, please contact Sohail Moughal, Project Engineer at (012)', 'New Security Gates', 'Complete', '2014-09-20', 0, 87, 0, 46, 'L-047/14', '2014-09-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1506, 1542, 43, 'For Information Only', 'Inspection Schedule', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1507, 1543, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0804 dated Sep. 11, 2014 and has the following comments:\r\n\r\n1.	According to SCH-B para 3.1.1, the CONTRACTOR shall provide all WORK Site analysis, soil reports, inspection, survey, detailed design, engineering, procurement support and construction support necessary for the successful performance of the WORK.\r\n2.	According to the contract para 3.1.4, SAUDI ARAMCO Representative shall be permitted at all times to check the lines, elevations, reference marks, etc., set by the CONTRACTOR, who shall correct any errors in lines, elevations, reference marks, etc., disclosed by such check. Such check shall not be construed to be an approval of the CONTRACTOR’S work and shall not relieve or diminish in any way the responsibility of the CONTRACTOR for the accurate and satisfactory construction and completion of the entire Work.\r\n\r\nBased on the above, all verification of survey work are a responsibility of IC and part of IC Scope of Work and thus any claims for survey verifications within contractor Scope of Work cannot be accepted.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Survey Verification', 'Complete', '2015-01-20', 0, 25, 0, 46, 'L-1147/15', '2015-01-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1508, 1544, 43, 'SAPMT has reviewed the subject submittal dated September 14, 2014 and has the following comment:\r\n•	Provide concurrence from the designer and UPS vendor.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Foundation Corner Marks', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1080/14', '2014-09-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1509, 1545, 43, 'For Information Only', 'Progress Report', 'Complete', '2014-10-12', 0, 25, 0, -1, 'For Information Only', '2014-10-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1510, 1546, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1511, 1547, 43, 'SAPMT has reviewed the subject submittal dated September 15, 2014 and has no objection with the following comment:\r\n•	Provide details for light pole bonding to grounding grid.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Steel Lighting Pole, Single Arm', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1078/14', '2014-09-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1512, 1548, 43, 'SAPMT has reviewed the subject submittal dated September 15, 2014 and has no objection with the following comment:\r\n•	IC shall ensure that all designs are concurred by the project designer and comply with the scope of work and Saudi Aramco standards.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Concrete Curb, Gutter', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1079/14', '2014-09-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1513, 1549, 43, 'SAPMT has reviewed the subject submittal dated September 14, 2014 and has the following comment:\r\n•	Item # 3.1, 4.1 – INSTALLATION/PRE-COMMISSIONING: By Saudi Aramco approved Third Party Inspection Agency. \r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', 'Checklist, Vessel Barrier', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1106/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1514, 1550, 43, 'SAPMT has reviewed the subject submittal dated September 14, 2014 and has the following comments:\r\n1.	Item # 1.1 – In (Task/Activity) column, write “material submittal for SACS systemsâ€. “Contractor (IC) to submit for Saudi Aramco approvalâ€ shall be written in remarks column.\r\n2.	Contractor (IC) shall issue RFI for Material Receiving, Installation and Pre-commissioning,\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Checklist, SACS', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1107/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1515, 1551, 43, 'SAPMT has reviewed the subject submittal dated September 14, 2014 and has the following comments:\r\n1.	Item # 1.1 – Document Review under (Task/Activity) column: write material submittal for CCTV Systems and add remarks ICC to submit to Saudi Aramco.\r\n2.	Item # 2.1 - Material Receiving (Task/Activity): rewrite don’t use acronym: Storage, Handling and Preservation visual inspection for CCTV System and in the remarks. Weekly inspection by contractor QC.\r\n3.	Item # 2.2, 2.3, 3.2, 3.3, 3.4, 3.5, 3.7 and 4.1: Remarks, ICC will issue RFI.\r\n4.	LEGEND: R rewrite – 100% Review of Documents and Change to R1.\r\n5.	LEGEND: add R2 – Sample Review of Documents.\r\n6.	LEGEND: RH – rewrite – 100% Review and Approval of Documents and Change to RH1\r\n7.	LEGEND: add RH2 – Sample Review and Approval of Documents.\r\n8.	Same Goes to W & H: Change to W1 + W2 and H1 + H2 and accordingly change the inspection responsibility assignments. (Subcontractor, Contractor and Saudi Aramco).\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Checklist CCTV', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1105/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1516, 1552, 43, 'SAPMT has reviewed the subject submittal dated September 15, 2014 and has no objection with the following comments:\r\n1.	Ducts and Accessories 9COM is 6000001836.\r\n2.	Saudi Air Distribution Systems Co. is limited to UL listed actuator and AMCA certified models.\r\n3.	Volume dampers shall be Opposed Blades (OB) type.\r\n4.	Supply air register shall be double deflection with adjustable blades.\r\n5.	This submittal is accepted for Motorized Volume Dampers only and IC shall provide separate submittal for fire damper, combination fire/ smoke damper and duct heater.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Air Distribution Units', 'Complete', '2014-09-28', 0, 87, 0, 46, 'L-1076/14', '2014-09-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1517, 1553, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0808 dated 15th Sep. 2014 and has the following comments:\r\n1.	The conditional approval of Mr. Sajid Akram as “QC Inspector – Civilâ€ is extended for One (1) month.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'QC Inspector', 'Complete', '2014-09-28', 0, 87, 0, 46, 'L-1073/14', '2014-09-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1518, 1554, 43, 'SAPMT has reviewed the subject submittal dated September 15, 2014 and has the following comments:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	IL no. 	Description	9com	Level Of Inspection	Status\r\n25-00026	PR	RP-024	NA	FRP Underground Tank	6000002481	Two (2)	Approved \r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Underground Storage Tanks', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1082/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1519, 1555, 43, 'SAPMT has reviewed the subject submittal dated 16 October 2014 and has the following comments:\r\n1.	Attach approved MS and Purchase Requisition Package.\r\n2.	Include leveling frame for detailed mounting of Switchgear base plate to Electrical Room flooring.\r\n3.	Ensure that the protective relays and control devices are Saudi Aramco approved manufacturer and model number according to its ANSI function as listed in Appendix A of 16-SAMSS-504.\r\n4.	Provide full catalog of all protective relays and controls and associated auxiliary relays in the NMR-602 submittal.\r\n5.	Protective relays shall be set to final relay settings upon approval of ETAP and Relay Coordination Study by PDD during commissioning.\r\n6.	Lifting devices, test cabinet, remote racking unit and portable manually operated ground and test device shall be included for Switchgear assembly as per 16-SAMSS-504.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'NMR MV Switchgear', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1130/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1520, 1556, 43, 'SAPMT has reviewed the subject submittal dated September 17, 2014 and has no objection with the following comments:\r\n1.	Include information about the loss of opportunity to emphasize the loss caused by the incident.\r\n2.	Provide an Action Plan with responsibilities and timings for implementation.\r\n3.	Submit a Job Safety and Environmental Analysis (JSEA/RAMS) in implementing the Clearing of the KAM access road as per submitted scheduled activities.\r\n4.	Include the lessons learned from the incident during Safety or Coordination Meetings.\r\n5.	Review the register of Incidences and ICC Management Safety and Health Implementation Plan and provide corrective and preventive actions to mitigate loss impacts to operation.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Incident report', 'Complete', '2014-11-03', 0, 25, 0, 46, 'L-1117/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1521, 937, 24, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1522, 1558, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0813 dated September 17, 2014 and has no objection with the following comments:\r\n1.	The work was on hold for buildings related to the gate for 3 days only, after which the work resumed normally. This gap is insignificant because work on many other buildings like the JFCC, QRT, guardhouses or UPS buildings was not affected and IC resources could be rescheduled/ redeployed to other buildings which are under construction or pending start of construction.\r\n2.	IC is urged to ensure completion of buildings by March 2015 according to the revised schedule. IC shall expedite works on all buildings by preparing pending shop drawings and deploying more resources.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Gate Building Hold', 'Complete', '2014-11-04', 0, 87, 0, 46, 'L-1135/14', '2014-11-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1523, 1559, 43, 'Further to our letter no. K&TPD/KRP&SFPD/SF/L-674/14 dated April 15, 2014 ICC is reminded to develop and submit for SAPMT review, quantities breakdown for Change Order Request No. 04 as per the attached scope of work.\r\n\r\nContingent upon successful review of the break-up quantities ICC will be officially requested to submit their bid proposal for this Change Order in the bid box under a separate invitation letter in line with contractual requirements and procedures.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.\r\n', 'Change Order', 'Complete', '2014-10-13', 0, 87, 0, 46, 'L-1072/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1524, 1560, 43, 'SAPMT has reviewed the subject submittal dated September 18, 2014 and has no objection with the following comment:\r\n\r\n•	Ensure that the sizes/ model of quadplex and simplex duct plugs will match with the cables and sub-ducts. \r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', 'Duct Plugs', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1095/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1525, 1561, 43, 'SAPMT has reviewed the subject submittal dated September 16, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Conduit Spacers', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1102/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1526, 1562, 43, 'SAPMT has reviewed the subject submittal dated September 16, 2014 and has the following comments:\r\n1.	Consider renaming steel box with back boxes.\r\n2.	Ensure that back boxes are UL listed or with approved equal certification.\r\n3.	EMT conduits shall not be embedded in concrete as per SAES-T-916.\r\n4.	A 4â€ box cover is not acceptable; refer to minimum standard dimensions as per SAES-T-916.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'EMT Conduits', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1114/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1527, 1563, 43, 'SAPMT has reviewed the subject submittal dated September 20, 2014 and has no objection with the following comment:\r\n\r\n•	Provide structural/ civil drawings separately for SAPMT review.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Detail of Column', 'Complete', '2014-10-08', 0, 87, 0, 46, 'L-1091/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1528, 1564, 43, '\r\nSAPMT has reviewed the subject submittal dated September 20, 2014 and has the following comment:\r\n\r\n•	Mr. Mohammad Sharif Khan is rejected as “QC Inspector – Mechanical (Plumbing & HVAC)â€ due to poor knowledge of required International and Saudi Aramco standards.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'QC Inspector', 'Complete', '2014-10-17', 0, 87, 0, 46, 'L-1097/14', '2014-10-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1529, 1565, 43, 'For Information Only', 'Progress Report', 'Complete', '2014-10-12', 0, 25, 0, -1, 'For Information Only', '2014-10-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1530, 1566, 43, 'SAPMT has reviewed the subject submittal dated September 20, 2014 and has the following comment:\r\n•	Justify as to why the new manufacturer is proposed and provide a compatibility certificate from Maxxess.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Biometric Reader', 'Complete', '2014-11-11', 0, 25, 0, 87, 'L-1115/14', '2014-11-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1531, 1567, 43, 'For Information Only', 'Progress Meeting', 'Complete', '2014-10-12', 0, 25, 0, -1, 'For Information Only', '2014-10-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1532, 1568, 43, 'SAPMT has reviewed the subject submittal dated September 20, 2014 and has no objection with the following comment:\r\n•	Include information about the loss of opportunity to emphasize the loss caused by the incident.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Incident Report', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1118/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1533, 1569, 43, 'SAPMT has reviewed the subject submittal dated September 22, 2014 and has the following comment:\r\n•	Provide heat load calculations.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Server Cabinet', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1113/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1534, 1570, 43, 'SAPMT has reviewed the subject submittal dated September 22, 2014 and has no objection with the following comments:\r\n1.	Consider laying the FOC cable parallel with the road bend near Sta. 3+500.\r\n2.	Provide A1 size drawing.\r\n3.	Proposed manhole Detail-A, showing the proposed 8 core cable for IDAS is not acceptable. This proposal should be submitted in different submittal for further review and requires KAUST concurrence.\r\n4.	Proposed manhole Detail-A is incomplete since fiber loops and splice point are not indicated.\r\n5.	SAPMT comment No. 7 still not provided and complied.\r\n6.	SAPMT Comment No. 9 was responded incorrectly.\r\n7.	Ensure to provide and submit the required drawing and document for SAPMT comment No. 8.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'FOC Route Layout', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1094/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1535, 1571, 43, 'SAPMT has reviewed the subject submittal dated September 20, 2014 and has no objection with the following comment:\r\n\r\n•	Provide structural/ civil drawings separately for SAPMT review.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Detail of Column', 'Complete', '2014-10-08', 0, 87, 0, 46, 'L-1092/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1536, 1572, 43, 'For Information Only', 'Inspection Schedule', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1537, 1573, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0820 dated September 23, 2014 and has the following comments:\r\n1.	Mr. Joseph Buban Navarro is conditionally approved as “QC Inspector – Civilâ€ for three (3) months. \r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance. \r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'QC Inspector', 'Complete', '2014-09-28', 0, 87, 0, 46, 'L-1075/14', '2014-09-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1538, 1574, 43, 'For Information Only', 'Eid Holidays', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1539, 1575, 43, 'SAPMT has reviewed the subject submittal dated September 22, 2014 and has the following comments:\r\n\r\n1.	M/s. Enersys Power / Full Solutios, Manufacturer ID 30003391 is not approved manufacturer in Saudi Aramco system.\r\n2.	Since the material has inspection level zero (0) and it shall be procured through one of the Saudi Aramco approved manufacturer.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'UPS and Batteries', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1100/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1540, 1576, 43, 'SAPMT has reviewed the subject submittal dated September 22, 2014 and has the following comment:\r\nBI	Transmittal Type	Transmittal Ref. #	IL no. 	Description	9com	Level Of Inspection	Status\r\n25-00026	PR	RP-025	NA	PIPE; NON-METALLIC; ALL SIZES; THERMOPLA	6000000031	Zero (0)	Approved \r\nwith Comments \r\n\r\n\r\n•	The manufacturer approval is limited to Pipe Sizes ½" to 10".\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Thermoplastic UPVC Pipe', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1083/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1541, 1577, 43, 'SAPMT has reviewed the subject submittal dated September 18, 2014 and has rejected with the following comment:\r\n•	Proposed coating material as per product data sheet is the protective coating for buried steel or concrete pipes and not for buried concrete foundations.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Bituminous Paint', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1086/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1542, 1578, 43, 'SAPMT has reviewed the subject submittal dated September 20, 2014 and has no objection with the following comments:\r\n\r\n•	Provide structural/ civil drawings for SAPMT review separately.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer on Tel. No. 012 422 4423.\r\n', 'Detail of Column', 'Complete', '2014-10-08', 0, 87, 0, 46, 'L-1077/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1543, 1579, 43, 'SAPMT has reviewed the subject submittal dated September 20, 2014 and has no objection with the following comment:\r\n\r\n•	Provide structural/ civil drawings for SAPMT review separately.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Details of Columns', 'Complete', '2014-10-08', 0, 87, 0, 46, 'L-1093/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1544, 1580, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0819 dated September 23, 2014 and has the following comment:\r\n•	Mr. Arman Ali is rejected as “QC Inspector – Electricalâ€ as he failed to justify his knowledge and experience during written examination and personal interview.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'QC Inspector, Arman Ali', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1085/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1545, 1581, 43, 'SAPMT has reviewed the subject submittal dated September 24, 2014 and has no objection with the following comment:\r\n\r\n•	Approved for architectural design only. Provide shop drawings for structural/ civil separately.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Detail of Footing', 'Complete', '2014-10-08', 0, 87, 0, 46, 'L-1090/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1546, 1582, 43, 'SAPMT has reviewed the subject submittal dated September 24, 2014 and has the following comments:\r\n\r\n1.	Use correct 9com # 6000014850.\r\n2.	Provide electric tin plated copper ground bar as per SAES-T-916, Section 4.4.2.10 and 4.7.6.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Bus Bar', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1099/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1547, 1583, 43, 'SAPMT has reviewed the subject submittal dated September 24, 2014 and has the following comments:\r\n\r\n1.	9com 6000000587 is not applicable and DD listed. Use 9com 6000000573.\r\n2.	The material has inspection level one (1) and shall be procured through an approved manufacturer.\r\n3.	Ensure the size mentioned in IFC is complied.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Anchor Bolt', 'Complete', '2014-10-17', 0, 87, 0, 46, 'L-1101/14', '2014-10-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1548, 1584, 43, 'With reference to KAUST request letter no. KAUST-M&U-14-0071 dated September 21, 2014 to incorporate LED lights into the KAM road design, the following points are to be considered:\r\n1.	Technically, changes with the fixture type from HPS to LED have significant impact on the electrical loads. SAES P-123 table 4 requires a minimum of 10 lux for the roadways. With a 30 meter spacing of the lighting pole to meet the existing lighting arrangement, an LED lighting fixture needs at least a minimum of 23,000 lumens to meet the illumination requirements which cannot be found in the market. To use the available lighting LED fixtures in the market, we need to increase the number of poles and decrease the spacing pattern. Additional switch racks, fixtures, and LV cables will be required.\r\n2.	The approved lighting type as per project scope of work for KAM access road is 250 watts High Pressure Sodium type and this is already delivered to site.\r\n3.	High Pressure Sodium and Metal Halide type are the only approved fixtures for street lighting/ outdoor lighting according to Saudi Aramco Standard SAES P-123.\r\nThis change at this stage of the project shall require a complete redesign of the electrical systems, cause delays in delivery of KAM road and have significant cost impact. Therefore, SAPMT will proceed in providing the lighting type as per the original project scope.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer (A) at (012) 422 4423.\r\n', 'Lighting Pole Sample', 'Complete', '2014-11-04', 0, 87, 0, 46, 'L-1149/14', '2014-11-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1549, 1585, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0832 dated September 25, 2014 and has no objection. It is contractor’s responsibility to ensure full compliance of Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Extend ACD, INCR', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1081/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1550, 1586, 43, 'SAPMT has reviewed the subject submittal dated September 25, 2014 and has no objection with the following comment:\r\n•	9com 6000000682; Manhole is non-inspectable, RP is not required.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', 'Fiberglass Manhole', 'Complete', '2014-11-02', 0, 25, 0, 46, 'L-1153/14', '2014-11-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1551, 1590, 43, 'The matter discussed through email. no need to send the letter.', '', 'Complete', '2014-09-30', 0, 25, 0, -1, 'L-1077/14 Emailed', '2014-09-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1552, 1591, 43, 'SAPMT has reviewed the subject submittal dated September 27, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specifications.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Mortar, Grout', 'Complete', '2014-09-30', 0, 87, 0, 46, 'L-1087/14', '2014-10-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1553, 1587, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0835 dated September 28, 2014 and has no objection with the following comment:\r\n\r\n•	ACD for LBE # 141 is granted a onetime extension upto 31st October 2014.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'LBE Closing', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1096/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1554, 1588, 43, 'For Information Only', 'Inspection Schedule', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1555, 1589, 43, 'SAPMT has reviewed the subject submittal dated September 25, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', 'Fence Footing Corner Marks', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1103/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1556, 1592, 43, 'SAPMT has reviewed the subject submittal dated September 25, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', 'Road Signage, Marking', 'Complete', '2014-10-17', 0, 87, 0, 46, 'L-1104/14', '2014-10-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1557, 1593, 43, 'For Information Only', 'Progress Meeting', 'Complete', '2014-10-12', 0, 25, 0, -1, 'For Information Only', '2014-10-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1558, 1594, 43, 'For Information Only', 'Progress Report', 'Complete', '2014-10-12', 0, 25, 0, -1, 'For Information Only', '2014-10-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1559, 1595, 43, 'SAPMT has reviewed the subject submittal dated September 28, 2014 and has no objection with the following comments:\r\n1.	Contractor shall follow the conduit layout for flash mounted weather proof receptacle as shown in IFC drawing VA-846676 sht-001.\r\n2.	Provide material specifications for weather proof receptacle outlet with ground fault circuit interrupter (GFCI).\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Power Layout', 'Complete', '2014-10-21', 0, 87, 0, 46, 'L-1108/14', '2014-10-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1560, 1596, 43, 'SAPMT has reviewed the subject submittal dated September 28, 2014 and has the following comments:\r\n\r\n1.	Provide samples of all wiring devices especially for outdoor use and for battery room use etc.\r\n2.	Ensure that utility boxes and fittings shall adapt to the proposed wiring devices during installation.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Wiring Devices', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1098/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1561, 1597, 43, 'The scope of work created by IC is rejected based on the following reasons:\r\n1.	It does not include the construction of road in the mangroves area as required by the original scope of work.\r\n2.	IC is urged to refer to the agreed upon scope of work for Change order No 1, “KAM access road IFC drawingsâ€ signed between IC and SAPMT on June 05, 2013, where it is mentioned that the missing drawings have no direct contribution in terms of cost to the construction/ procurement activities.\r\n3.	The scope of work submitted by IC incorrectly includes activities as positive changes which had to be done even if no relocation or variation had occurred, e.g. Backflow preventer and air release valves etc.\r\n4.	IC has already been awarded the work for redesign of KAM road according to change order No 1; where the IFC for KAM was declared as IFB and IC was asked to prepare detailed drawings with no cost impacts. Re-alignment of KAM to avoid mangroves was a voluntary proposal made by IC much later. Hence any works done on re-redesign or relocation cannot be considered as a variation.\r\n5.	SAPMT accepted the proposal of re-alignment of KAM road and shifting of the existing fence with no impact on costs or schedule, otherwise SAPMT would have not accepted the IC proposal and IC would have carried on with constructing the road through the mangroves.\r\n6.	The scope of work shall include only one issue and not mix various issues like changes to irrigation systems and realignment of KAM road and extras for biking track etc.\r\n7.	No details or references are attached to support the scope of work.\r\n8.	No earthworks for shoulders can be considered as a variation as the original scope includes leveling the ground between the KAM road and the internal maintenance road. The shoulder on the sea side has to accommodate utilities for KAM road and sidewalks; and the width depends on IC design; and does not have to be the same width as the other side.\r\n9.	Provide IFB and IFC drawings to show changes made to aggregates. If the road design aggregate base was changed by IC voluntarily without specific prior approval and implemented then it cannot be approved as change order. \r\n10.	The elevation of KAM road has been lowered from the elevations given in IFB to avoid the side slopes extending in to the water. The scope of work provided by IC does not include the negative variation for the reduced earthworks.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Change Order, 5', 'Complete', '2014-11-03', 0, 87, 0, 46, 'L-1127/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1562, 1598, 43, 'SAPMT has reviewed the subject submittal dated September 30, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Saudization, September 2014', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1150/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1563, 1599, 43, 'For Info Only.', 'Camp Inspection', 'Complete', '2014-10-12', 0, 25, 0, -1, 'For Information Only', '2014-10-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1564, 1600, 43, 'SAPMT has reviewed the subject submittal dated 02 October 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Waterstop', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1120/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1565, 1601, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1566, 1602, 43, 'For Information Only', 'Inspection Schedule', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1567, 1603, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0843 dated October 02, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'INCR Closing', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1110/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1568, 1605, 43, 'For Information Only', 'Inspection Schedule', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1569, 1604, 43, 'No Comments', 'Progress Report', 'Complete', '2014-11-07', 0, 25, 0, -1, 'For Information Only', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1570, 1606, 43, 'The above comments was mutually agreed between SAPMT and ICC and the subject invoice was approved and SES issued to ICC.', 'Invoice, Payment Application', 'Complete', '2014-11-10', 0, 25, 0, -1, 'For Information Only', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1571, 1614, 43, 'The revised and approved schedule for the project shows that the asphalt works are to be completed by 20th October 2014, Electrical systems to be completed by 7th November 2014 and remaining works like irrigation, landscaping, road marking etc. to be completed by 30th November 2014.\r\n\r\nLast month, in a meeting held between SAPMT and IC management, IC agreed to complete the KAM road earlier i.e. mid October 2014. The current status, speed of site works and related procurements show that IC has not been able to meet the promised targets.\r\n\r\nThe following issues require your immediate attention; \r\n1.	The curb and gutter work is slow due to insufficient number of curbing equipment, no coordination between site prep and concrete work, and irregular supply of concrete.\r\n2.	The subcontractors for lighting, landscaping and irrigation systems are not fully mobilized.\r\n3.	Works for wiring and foundations for light poles is continuously facing delays due to lack of manpower.\r\n4.	All communications works, Radar, Sonar, existing utilities at KAM road are being handled inappropriately, with huge delays, disruptions and faulty works.\r\n5.	IC has been unable to understand the scope of work and items like sidewalks have not been planned on time.\r\n6.	It is necessary that housekeeping around the KAM road is ensured and all debris removed simultaneously.\r\n7.	Panels, generators, racks for energizing KAM road are still not finalized.\r\nIC is urged to provide a detailed schedule to show as to how the targets promised by IC during the management meeting shall be achieved. \r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'KAM Construction Delays', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1119/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1572, 1607, 43, 'SAPMT has reviewed the subject submittal dated 11 October 2014 and has the following comments:\r\n1.	Rigid Steel Conduit shall comply with ANSI C80.1 and must be hot dip galvanized as SAES P-104 Para. 8.2 2.\r\n2.	Provide technical specifications and catalog for Rigid Steel Conduit Fittings.\r\n3.	Sizes of RSC conduits shall comply with Project Specifications and Saudi Aramco Standards e.g. SAES P-104 standard.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Rigid Steel Conduit', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1124/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1573, 1608, 43, 'SAPMT has reviewed the subject submittal dated 11 October 2014 and has the following comments:\r\n1.	List IFC references against each shop drawing.\r\n2.	Reflect on the key plan the concerned plan and profile.\r\n3.	Attach cross section of the maintenance road.\r\n4.	Advise design status between Sta 0 to Sta 7+500.\r\n5.	Provide final profile from Sta 13+500 to 13+900.\r\n6.	Provide complete shop drawings for geometrical features e.g. transition, vertical and horizontal curves, radii, gradients, intersection points etc.\r\n7.	Provide clear color copies.\r\n8.	Provide references to the grading plan and attach related dwgs.\r\n9.	Clarify the bottom of base course and EGL line on Dwg. 1C-SD-846503-107.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', 'Maintenance Road Plan', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1131/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1574, 1609, 43, 'SAPMT has reviewed the subject submittal dated 11 October 2014 and has the following comments:\r\n1.	Satellite controller location to be provided and integration details with existing KAUST irrigation central control system to be mentioned in the drawing.\r\n2.	Distinguish the connection line, if it is in existing KAUST PW or in Golf irrigation line. (Tapping from KAM or new Tapping).\r\n3.	Identify the valve boxes proposed and provide valve box every 500 meters.\r\n4.	Ensure to locate the Air Valve (Highest point) and Wash out valve (lowest point).\r\n5.	Valve box shall be positioned in the median and not in the road.\r\n6.	It is recommended to show the excavation plan of the trees to identify the distance between the trees and the main line.\r\n7.	Hydro test shall be flange to flange.\r\n8.	Provide in the tie in point a back flow preventer and water meter.\r\n9.	Show North Orientation.\r\n10.	Show the KEY plan and the designated area.\r\n11.	Change the drawing type from MEC to IRRI.\r\n12.	Remove the SCOPE – in the drawing title.\r\n13.	Show the proposed irrigation waterlines in BOLD lines all existing lines shall be in light line or dotted line.\r\n14.	Show notes and legends for irrigation line system and call-outs.\r\n15.	Show the tie in point from existing and new line.\r\n16.	Justify why lateral pipe size shall be 2-1/2 inches dia instead of 2-3 inches dia.\r\n17.	Provide complete irrigation layout and details in the drawings.\r\n18.	Use dewatering type for bubbler.\r\n19.	Irrigation line shall be auto system with controller. Locate an existing controller if possible.\r\n20.	Show the graphic scales in the drawing.\r\n21.	Show the solenoid valve location/ coordinates and indicate the solenoid valve number.\r\n22.	Provide air bend on the highest point of the main line.\r\n23.	Install CPVC ball valve before the solenoid valve.\r\n24.	Provide flashing ball valves at the end of each zone main pipe lateral line.\r\n25.	Provide pipe sleeves for pipes crossing the walkway, tracks or pavements.\r\n26.	The trees shall be planted every 10 m and not every 20m.\r\n27.	The height of palms shall be 5 m and not 2 m.\r\n28.	Submit the tree specifications, excavation depths and certification criteria and/ or alternatives in a separate submittal.\r\n29.	All designs shall be concurred by the Project designer.\r\n30.	Ensure that all designs and construction is adhering with Saudi Aramco standards and project specifications.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Irrigation Layout', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1123/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1575, 1610, 43, 'For Information Only', 'Incident Report', 'Complete', '2014-10-19', 0, 25, 0, -1, 'For Information Only', '2014-10-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1576, 1611, 43, 'SAPMT has reviewed the subject submittal dated 11 October 2014 and has rejected with the following comments:\r\n1.	Justify why the drawing is being re-submitted.\r\n2.	The concrete shall be 8.3 plus the two OD of the FRP pipe meter wide instead of 2.3 plus the two OD of the FRP pipe to protect the RABYA utilities. Refer to the Dwg. VA – 846479.\r\n3.	Consider using wire mesh for concrete.\r\n4.	Ensure proper drainage with slopes to avoid ponding of water.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Pipe Culvert', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1128/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1577, 1612, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0852 dated 12 October 2014 and has the following comments:\r\n1.	Mr. Ricky Flores is permanently approved as “QC Inspector – Electrical & Instrumentationâ€ for “KAUST – Perimeter Security Systemsâ€ Project.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance during project tenure.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n \r\n', 'QC Inspector', 'Complete', '2014-10-17', 0, 87, 0, 46, 'L-1121/14', '2014-10-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1578, 1613, 43, 'No Comments', 'Progress Report', 'Complete', '2014-11-07', 0, 25, 0, -1, 'For Information Only', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1579, 1615, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0853 dated 12 October 2014 and has the following comments:\r\n1.	The conditional approval of Mr. Leonardo P. Rodrigo Jr. as “QC Inspector – Electrical, Instrumentation & Telecommunicationâ€ is extended for another three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval extension based on his unsatisfactory performance.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'QC Supervisor', 'Complete', '2014-10-15', 0, 87, 0, 46, 'L-1122/14', '2014-10-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1580, 1616, 43, 'For Information Only.', '', 'Complete', '2014-10-15', 0, 25, 0, -1, 'For Information Only', '2014-10-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1581, 1617, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1582, 1618, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0857 dated October 13, 2014 and has rejected with the following comments:\r\n1.	Consider completing the construction of associated buildings on priority basis.\r\n2.	Consider providing a warehouse on site to store materials and equipment.\r\n3.	It is necessary that all materials and equipment are shipped to site for final receiving inspection, especially when more than 70% payments have been done.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'AS&E Equipments', 'Complete', '2014-11-06', 0, 87, 0, 46, 'L-1139/14', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1583, 1619, 43, 'For Information Only', 'QAQC Meetings', 'Complete', '2014-10-15', 0, 25, 0, -1, 'For Information Only', '2014-10-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1584, 1620, 43, 'SAPMT has reviewed the subject submittal dated October 12, 2014 and has the following comments:\r\n1.	Provide the battery load calculation.\r\n2.	IFC mentions APC, and thus IC is urged to make necessary changes and/or also validate the proposed manufacturer and model of the UPS.\r\n3.	Ensure to provide back-up time as per SOW and Appendix H for networking devices.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'UPS Package', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1145/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1585, 1629, 43, 'SAPMT has reviewed the subject submittal dated 14 October 2014 and has rejected with the following comments:\r\n1.	Contractor shall submit separate Material submittal for each Material Type.\r\n2.	For LV panels (6000000859), Alfanar Company has limitations to use only MB-N Model Breakers. In this submittal various other Models of breakers have been used which is not acceptable (see attached print out from Aramco SAP system).\r\n3.	Alfanar Company is not an approved manufacturer for Lighting Control Panel having 9Com# 6000002698 (see attached list of approved manufacturers for 9Com# 6000002698).\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.', 'LV Panel Board', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1129/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1586, 1631, 43, 'SAPMT has reviewed the subject submittal dated October 16, 2014 and has the following comments:\r\n1.	Provide complete architectural and structural drawings concurred by the Genset vendor/ switchgear vendor and project designer to ensure that all items including batteries and tanks etc. are also taken into account.\r\n2.	The concrete cover should be as mentioned in the general drawing VA-846497.\r\n3.	Provide reinforcement for sleeves.\r\n4.	Provide the hook length according to VA-846498 with min. 388mm for db=20 mm and 310mm for db=16 mm.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Generator Building', 'Complete', '2014-11-02', 0, 87, 0, 46, 'L-1143/14', '2014-11-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1587, 1621, 43, 'No Comments', 'Progress Meeting', 'Complete', '2014-11-07', 0, 25, 0, -1, 'For Information Only', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1588, 1622, 43, 'SAPMT has reviewed the subject submittal dated October 16, 2014 and has the following comments:\r\n1.	Mr. Anand Erulandi is conditionally approved as “QC Inspector – Electricalâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'QC Inspector Electrical', 'Complete', '2014-11-02', 0, 25, 0, 46, 'L-1155/14', '2014-11-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1589, 1623, 43, 'SAPMT has reviewed the subject submittal dated 15 October 2014 and has the following comment:\r\n•	Provide what steps were taken before the lifting to ensure that equipment is suitable for operations.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Incident Report', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1132/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1590, 1624, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0859 dated October 15, 2014 and has no objection with the following comment:\r\n\r\n•	ACD for LBE # 160 is granted a onetime extension upto 31st October 2014.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'LBE Closing', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1134/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1591, 1625, 43, 'No need to extend as lab tech Prince has returned already', 'LBE Closing', 'Complete', '2014-10-21', 0, 25, 0, -1, 'For Information Only', '2014-10-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1592, 1626, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0862 dated October 15, 2014 and has the following comment:\r\n•	Provide more information/ identification about how many and which IDAS Pole, camera, and Field Equipment Cabinet (FEC) will be affected and must be removed.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'IDAS Equipments', 'Complete', '2014-11-03', 0, 25, 0, 46, 'L-1144/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1593, 1627, 43, 'For Information Only', 'Material Transfer', 'Complete', '2014-11-10', 0, 25, 0, -1, 'For Information Only', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1594, 1628, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1595, 1630, 43, 'SAPMT has reviewed the subject submittal dated 18 October 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Red Tile', 'Complete', '2014-10-26', 0, 87, 0, 46, 'L-1126/14', '2014-10-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1596, 1632, 43, 'No Comments', 'Progress Meeting', 'Complete', '2014-11-07', 0, 25, 0, -1, 'For Information Only', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1597, 1633, 43, 'No Comments', 'Progress Report', 'Complete', '2014-11-07', 0, 25, 0, -1, 'For Information Only', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1598, 454, 24, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1599, 1634, 43, 'For Information Only.', 'Precast Panel Curing', 'Complete', '2014-10-21', 0, 25, 0, -1, 'For Information Only', '2014-10-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1600, 1635, 43, 'KAUST concurrence is requested for the proposed location of extra cameras on Wadis.\r\nReferring to the meeting held on 12 August 2014 for review of the revised IFC for security and communications, it was decided that the under fence penetration at the Wadi Wesami and Wadi Khulais can be controlled by installing steel grills and crash rated bollards and installing the PTZ cameras on the sides of flood channel to control/ monitor the openings on the downstream side of the culvert. Cameras shall be removed from the top of guard houses for these wadis. Live monitoring of possible intrusion through culvert cells could be done from any station on the IP based network.\r\nWhile Flood Control Channel project is handling the arrangements for Wadi Wesami; steel grills and crash rated bollards at Wadi Khulais shall be installed by the KPSS project. The above said arrangements shall be made in addition to the IDAS passing over both the culverts, keeping in view that the project security follows the following design principles;\r\n1.	Agreed upon scope of work.\r\n2.	Designed as a Class 4 facility with Category 1 fencing system, adhering with the HCIS as much as possible where local conditions permit.\r\n3.	Designed keeping in view the orders given in the royal decree.\r\n4.	The latest design also includes the changes made to the scope of work at later stages specifically the deletion of the ditch from the security corridor.\r\nA sketch of the proposed location of PTZ cameras is being attached for KAUST concurrence.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) on (012) 422 4423.\r\n', 'Under Fence Penetration', 'Complete', '2014-11-04', 0, 87, 0, 46, 'L-1151/14', '2014-11-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1601, 1636, 43, 'SAPMT has reviewed the subject submittal dated October 22, 2014 and has the following comments:\r\n1.	Provide the missing documentation such as Figure 6.4-1, Table 7.2, and the references for the equations.\r\n2.	IC shall ensure that no scope change or cost/ schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Calculation for Stresses', 'Complete', '2014-11-03', 0, 25, 0, 87, 'L-1160/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1602, 1637, 43, 'SAPMT has reviewed the subject submittal dated October 22, 2014 and has no objection with the following comments:\r\n1.	Water curing has to continue until 70% of the specified compressive strength is reached, but not less than 7 days.\r\n2.	While it is preferred that precast panels are transported after the required strength is verified by tests, nevertheless, based on the above, transporting the precast elements after curing is acceptable after 7 days, as confirmed by subcontractor calculations that panels can support lifting and transportation loads plus any other loads as per the PCI handbook and also as concurred by the project designer.\r\n3.	It is advisable to conduct a few closely monitored trials and observe for any cracks, spalls or deformities before adopting the practice.\r\n4.	It is Contractor’s responsibility to remove any panels which do not meet applicable standard requirements or aesthetics necessary for the wall, and replace with new ones, if and when rejected by Saudi Aramco.\r\n5.	IC shall ensure that no scope change or cost/ schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Calculation, Fence', 'Complete', '2014-11-03', 0, 25, 0, 87, 'L-1161/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1603, 1638, 43, 'SAPMT has reviewed the subject submittal dated October 22, 2014 and has no objection with the following comments:\r\n1.	Lighting fixtures shall be 250W,230V MH Lamp\r\n2.	Ensure that the rebar and anchor bolt details are placed in the precast molds as discussed, in order to avoid any movement during pouring and to ensure that the spacing between anchor bolts is exactly according to the holes on the base plate.\r\n3.	Revise the drawing and acquire designer’s concurrence before the foundations are released from the yard.\r\n4.	The damp proof/ water proof coating shall be done on the foundations in the yard after 70% strength is achieved.\r\n5.	Ensure that casting for pole foundations is finished before 10 November 2014 according to the tracking schedule for KAM road submitted by the contractor. This may require at least 50 molds to be poured every day in the yard, keeping in view the required curing times and timely release to the site for installation.\r\n6.	Ensure that all related fixtures like fuse boxes are procured to expedite cable terminations.\r\n7.	It is contractor’s responsibility to ensure that all works are done according to related Saudi Aramco standards.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Single Arm', 'Complete', '2014-11-09', 0, 25, 0, 87, 'L-1169/14', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1604, 1639, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1605, 1641, 43, 'SAPMT has reviewed the subject submittal dated October 21, 2014 and has the following comments:\r\n1.	Use correct 9Com# 6000000744 for Cable Trays (Aluminum or Steel).\r\n2.	Use correct 9Com# 6000014116 for Cable Tray accessories.\r\n3.	Cable tray for electrical works shall be copper free aluminum to meet Saudi Aramco Standard SAES P-104 para. 9.1.\r\n4.	Ensure electrical cable tray full compliance with Metal Cable Tray System stated in NEMA VE-1.\r\n5.	The Summary list and specifications are for Cable Tray System only. Cable Ladders/Cable Runways are not listed. Provide specification no. PA000070004 and attach data sheets which are from Chatsworth Manufacturer as per the Scope of work for ladders.\r\n6.	The proposed Supplier and Manufacturer Abahsain Cope is not approved to supply Chatsworth Products.\r\n7.	Consider submitting products separately according to the discipline and activity.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Cable Tray, Cable Ladder', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1154/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1606, 1640, 43, 'SAPMT has reviewed the subject submittal dated October 23, 2014 and has the following comments:\r\n1.	The drawings are incomplete. IC is urged to provide details for all stations.\r\n2.	IC shall ensure that the existing elevation of MOT is kept as a reference for all elevations in the security corridor.\r\n3.	IC shall ensure that proper grading/ drainage is provided.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Patrol Road', 'Complete', '2014-11-09', 0, 25, 0, 87, 'L-1176/14', '2014-11-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1607, 1642, 43, 'No Comments', 'Progress Report', 'Complete', '2014-11-07', 0, 25, 0, -1, 'For Information Only', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1608, 1643, 43, 'SAPMT has reviewed the subject submittal dated October 23, 2014 and has the following comments:\r\n1.	Use correct 9COM # 6000000752.\r\n2.	All outdoor disconnect switches shall be rated with NEMA 4X enclosure to meet SAES P-104 para 7.\r\n3.	Ensure that disconnect switches ampere rating and number of poles will meet Project requirements as per scope of work and Saudi Aramco standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Safety Switch', 'Complete', '2014-11-01', 0, 25, 0, 46, 'L-1158/14', '2014-10-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1609, 1644, 43, 'SAPMT has reviewed the subject submittal dated  October 27, 2014 and has the following comments:\r\n1.	Mr. Javed Hussain is conditionally approved as “QC Inspector – Civilâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on unsatisfactory performance.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-11-09', 0, 25, 0, 87, 'L-1168/14', '2014-11-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1610, 1645, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0885 dated October 27, 2014 and has the following comments:\r\n1.	Mr. Sajid Akram is permanently approved as “QC Inspector – Civilâ€ for “KAUST-Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke the approval based on his unsatisfactory performance during project tenure.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-11-03', 0, 25, 0, 46, 'L-1159/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1611, 1646, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0884 dated October 27, 2014 and has the following comment:\r\n•	IC is urged to arrange the approval from BP&CTU.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-11-09', 0, 25, 0, 87, 'L-1173/14', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1612, 1647, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0883 dated October 27, 2014 and has the following comments:\r\n1.	The conditional approval of Mr. Riasat Ali Khan as “QC Inspector – Telecommunication & Securityâ€ is extended for another three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Inspector', 'Complete', '2014-10-30', 0, 25, 0, 46, 'L-1156/14', '2014-10-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1613, 1648, 43, 'SAPMT has reviewed the subject submittal dated October 26, 2014 and has the following comments:\r\n1.	Fire Extinguishers shall be supplied by approved Vendors and shall be UL or FM Listed (not indicated in the Catalogue).\r\n2.	Provide a package with approved drawings which show the Type and locations of Fire Extinguisher approved for the facility. Final Approval will be subject to the consensus of Saudi Aramco Fire Protection Department.\r\n3.	Provide details of the mounting accessories as required per SAES-B-019.\r\n4.	Saudi Factory for Fire Equipment is an Aramco approved vendor and IC shall start procurement processes while other details are prepared.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Fire Extinguisher', 'Complete', '2014-11-04', 0, 25, 0, 87, 'L-1166/14', '2014-11-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1614, 1649, 43, 'SAPMT has reviewed the subject submittal dated October 29, 2014 and has no objection with the following comment:\r\n•	Contractor is urged to submit material requisition package for pipes.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Pipe UPVC', 'Complete', '2014-11-02', 0, 25, 0, 46, 'L-1157/14', '2014-11-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1615, 1650, 43, 'SAPMT has reviewed the subject submittal dated October 28, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Checklist for Lighting Accessories', 'Complete', '2014-11-04', 0, 25, 0, 87, 'L-1142/14', '2014-11-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1616, 1651, 43, 'SAPMT has reviewed the subject submittal dated October 25, 2014 and has no objection with the following comments:\r\n1.	IC is urged to procure non-inspectable materials from Aramco approved vendors only.\r\n2.	Grounding rods shall meet standard requirements of SAES P-111 para. 5.2.\r\n3.	Molds and cadweld thermite powders shall be as per Furse manufacturer recommendations.\r\n4.	Ensure that the mold sizes are checked based on grounding cables and rods diameter.\r\n5.	Observe and follow best installation practices for grounding rods and conductors, grounding bolts are only acceptable within grounding test pit, while all installations to be back-filled shall be cadwelded.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Grounding Rod', 'Complete', '2014-11-03', 0, 25, 0, 87, 'L-1163/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1617, 1652, 43, 'No Comments', 'Progress Report', 'Complete', '2014-11-07', 0, 25, 0, -1, 'For Information Only', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1618, 1653, 43, 'SAPMT has reviewed the subject submittal dated October 29, 2014 and has no objection with the following comments:\r\n1.	Host a toolbox talk with relevant personnel regarding safe work procedures.\r\n2.	Ensure that a spotter is always present and diligently assisting the operators in excavation activities.\r\n3.	Always follow permit requirements.\r\n4.	Submit the detailed report as when required.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Incident Report', 'Complete', '2014-11-03', 0, 25, 0, 87, 'L-1164/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1619, 1654, 43, 'SAPMT has reviewed the subject submittal dated October 28, 2014 and has no objection with the following comments:\r\n1.	Proposed Mix Design is a pre-approved mix design for Cast-in-Situ Structural Concrete by BP&CTU with Saudi Aramco Mix ID # SRM(1)-THUW(2)-351SF-06 dated October 16, 2014.\r\n2.	It is to be utilized by Fatayerji Contracting Co. (FCC) for the production of Precast Concrete elements and to be supplied and delivered by SRMCC, Thuwal branch.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Concrete Mix Design', 'Complete', '2014-11-03', 0, 25, 0, 87, 'L-1165/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1620, 1655, 43, 'SAPMT has reviewed the subject submittal dated October 27, 2014 and has no objection with the following comments:\r\n1.	IC is urged to procure non-inspectable materials from Aramco approved vendors only.\r\n2.	It is IC responsibility to ensure that all materials adhere with Saudi Aramco standards.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Copper Conductor', 'Complete', '2014-11-03', 0, 25, 0, 87, 'L-1162/14', '2014-11-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1621, 1656, 43, 'SAPMT has reviewed the subject submittal dated November 27, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Saudization Report', 'Complete', '2014-12-27', 0, 70, 0, 87, 'L-1240/14', '2014-12-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1622, 1657, 43, 'Approved', 'Invoice', 'Complete', '2014-12-27', 0, 25, 0, 87, 'For Record Only', '2014-12-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1623, 1659, 43, 'SAPMT has reviewed the subject submittal dated October 29, 2014 and has the following comments:\r\n1.	ICC is urged include all related drawings in the submittal to refer to on this submittal like drawing BA-846649-001.\r\n2.	Most cross sectional drawing does not mention the use of vapor barrier and 2 coats of bituminous paint, which should be mentioned in the notes section.\r\n3.	Provide column, wall, roof beam and roof slab connection refers to IC-SD-846843-104 and 105.\r\n4.	Provide detail section at the beginning of the ramp.\r\n5.	The blast resistance building shall be designed as per SAES-M-009.\r\n6.	Provide blow up details for sleeves with necessary rebar such as roof drain sleeve, Electrical conduits …etc. \r\n7.	Concrete cover should be 75 mm for concrete expose to earth or to weather as per general note VA-846497-001. Revise the NOTE 02.\r\n8.	Ensure that the roof slab of machine gun room on cantilever beams is safe for the usage requirements.\r\n9.	The External, staircase and ramp walls are Reinforcement Concrete as per IFB K55-R-PA-000264-001-C.\r\n10.	The wall on axis B is Reinforcement Concrete as per IFC VA-846837-001.\r\n11.	IC shall ensure that all shop drawings are submitted according to the agreed scope of work and Saudi Aramco Standards without any cost or schedule implications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Pavilion', 'Complete', '2014-11-09', 0, 25, 0, 87, 'L-1170/14', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1624, 1661, 43, 'SAPMT has reviewed the subject submittal dated October 23, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Road Marking System', 'Complete', '2014-11-10', 0, 25, 0, 87, 'L-1177/14', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1625, 1660, 43, 'SAPMT has reviewed the subject submittal dated October 25, 2014 and has no objection with the following comments:\r\n1.	Cable glands shall meet the specified requirement of SAES P-104 para. 6.8, 6.9 and 6.14.\r\n2.	Ensure that Cable Glands has provision for armored cables and for unarmored cables.\r\n3.	It is the Contractors responsibility to ensure the correct sizing of cable glands.\r\n4.	Terminal Lugs number of holes shall be determined using SAES P-104 para. 6.1.\r\n5.	Ensure that terminal lugs are tinned copper and has Underwriters Laboratories "UL" markings.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Cable Gland, Lugs', 'Complete', '2014-11-09', 0, 25, 0, 87, 'L-1175/14', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1626, 1658, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1627, 1665, 43, 'SAPMT has reviewed the subject submittal dated November 02, 2014 and has been rejected with the following comment:\r\n•	This submittal shall be a revision of DS-308, (approved with comments previously), and shall have all the SAPMT comments incorporated, especially about mentioning approved products for repairs like RENDEROC-LA. It is advisable to discuss all related issues with SAPMT before resubmitting.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'Precast Repair Matrix', 'Complete', '2014-11-09', 0, 25, 0, 87, 'L-1172/14', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1628, 1666, 43, 'IC is urged to submit a Fabrication Plan and Schedule for all Concrete Structures as listed below which should have started much earlier according to the approved schedule;\r\n1.	Communication Manholes.\r\n2.	Field Equipment Cabinet (FEC) Foundations.\r\n3.	IDAS Camera Pole Foundations.\r\n4.	Microwave Foundations.\r\n5.	Lighting Pole Foundations.\r\n6.	Foundations pads for equipment’s/ machines.\r\nThese concrete works should start immediately and should be given priority since the fabrication process and concrete curing will take time and will affect the completion of IDAS. Also include in your plan the status of all the embedded materials needed with their delivery date to site.\r\nIt is also noted that no procurements related to security works e.g. VESSEL BARRIER, SONAR, RADAR, CAMERAS have been done so far and no specialty resources/ subcontractors have been employed for completion of OSP works and MEP works. IC is urged to provide a detailed plan of action to ensure that the project shall be delivered according to the approved schedule by the end of the week.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'Delayed Communication, Security Works', 'Complete', '2014-11-04', 0, 25, 0, 87, 'L-1167/14', '2014-11-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1629, 1675, 43, 'Emailed to Ahmed Karar', 'Amendment, Ditch Deletion', 'Complete', '2014-11-09', 0, 25, 0, -1, 'For Information Only', '2014-11-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1630, 1674, 43, 'SAPMT has reviewed the subject submittal dated November 04, 2014 and has the following comments:\r\n1.	Provide Catalog from A.O Smith for Comparison of Equivalent.\r\n2.	Select the Correct Type in Catalog as referred to in the Summary.\r\n3.	Ensure and highlight that power requirements such as voltage rating, number of poles of breaker and breaker rating are all conducive with the related power panel.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Water Heater', 'Complete', '2014-11-12', 0, 25, 0, 87, 'L-1179/14', '2014-11-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1631, 1673, 43, 'SAPMT has reviewed the subject submittal dated November 04, 2014 and has the following comment:\r\n•	Provide the correct model and specifications in compliance with IFC Drawing i.e. VA-847173 and Saudi Aramco standard SAES-T-795 and SAES-T-916.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Grounding Bus Bar', 'Complete', '2014-11-17', 0, 25, 0, 87, 'L-1183/14', '2014-11-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1632, 1670, 43, 'SAPMT has reviewed the subject submittal dated November 01, 2014 and has the following comments:\r\n1.	Material submittal for back flow preventer, isolation valve in the main valve box to be submitted separately with names of vendors/ manufacturers.\r\n2.	Design drawing shall be stamped by SCEC and submitted to Aramco for approval.\r\n3.	Gate valve for the solenoid shall be brass type.\r\n4.	Identify and highlight on the submitted catalogue sheets the material type, size, model, and quantities for each item in the system for review and approval.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Irrigation System', 'Complete', '2014-11-09', 0, 25, 0, 87, 'L-1174/14', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1633, 1669, 43, 'SAPMT has reviewed the subject submittal dated November 02, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'UPS, Battery', 'Complete', '2014-11-09', 0, 25, 0, 87, 'L-1171/14', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1634, 1672, 43, 'SAPMT has reviewed the subject submittal dated November 06, 2014 and has the following comments:\r\n1.	Provide Lighting Control Panel shop drawing that shows the dimension of the enclosure, wiring and devices arrangements.\r\n2.	Provide the catalog and specification for the control transformer and pilot lamps.\r\n3.	Indoor Lighting Control Panel shall be type NEMA 1, while Outdoor Lighting Control Panel shall be type NEMA 4X to meet enclosure requirements specified in SAES P-104.\r\n4.	Include dedicated LCP tagging identification, for indoors which shall be phenolic type; for outdoors it shall be stainless steel.\r\n5.	Consider submitting indoor and outdoor separately.\r\n6.	Ensure that dimensions are provided so that installation on the wall with other panels is not an issue.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'Lighting Control System', 'Complete', '2014-11-11', 0, 25, 0, 87, 'L-1148/14', '2014-11-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1635, 1671, 43, 'No Comments, For Information Only', 'MQMR', 'Complete', '2014-11-10', 0, 25, 0, -1, 'For Information Only', '2014-11-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1636, 1662, 43, 'No Comments', 'Incident Report', 'Complete', '2014-11-12', 0, 25, 0, -1, 'For Information Only', '2014-11-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1637, 1663, 43, 'No Comments', 'Incident Report', 'Complete', '2014-11-12', 0, 25, 0, -1, 'For Information Only', '2014-11-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1638, 1664, 43, 'No Comments', 'Progress Report', 'Complete', '2014-11-07', 0, 25, 0, -1, 'For Information Only', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1639, 1667, 43, 'No Comments', 'Progress Report', 'Complete', '2014-11-07', 0, 25, 0, -1, 'For Information Only', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1640, 1668, 43, 'No Comments', 'QAQC Meeting', 'Complete', '2014-11-07', 0, 25, 0, -1, 'For Information Only', '2014-11-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1641, 1676, 43, 'No Comments', 'Near Miss Report', 'Complete', '2014-11-25', 0, 25, 0, -1, 'For Information Only', '2014-11-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1642, 1677, 43, 'SAPMT has reviewed the subject submittal dated November 05, 2014 and has no objection with the following comment:\r\n•	While the revised curb design is acceptable, nevertheless, referring to KA-714497, IC is urged to provide the differences in quantities of concrete works.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'Curb & Gutter', 'Complete', '2014-11-17', 0, 25, 0, 87, 'L-1181/14', '2014-11-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1643, 1680, 43, 'Emailed PID response to IC.', 'LBE Closing', 'Complete', '2014-11-12', 0, 25, 0, -1, 'For Information Only', '2014-11-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1644, 1678, 43, 'No Comments', 'Progress Report', 'Complete', '2014-11-12', 0, 25, 0, -1, 'For Information Only', '2014-11-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1645, 1679, 43, 'No Comments', 'Inspection Schedule', 'Complete', '2014-11-16', 0, 25, 0, -1, 'For Information Only', '2014-11-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1646, 1681, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1647, 1682, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1648, 1685, 43, 'SAPMT has reviewed the subject submittal dated November 11, 2014 and has no objection with the following comment:\r\n•	Submit Requisition Package for Cable Trays/ Ladders with correct 9com 6000000744.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n \r\n', 'Cable Tray, Ladder', 'Complete', '2014-11-12', 0, 25, 0, 87, 'L-1178/14', '2014-11-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1649, 1683, 43, 'No Comments', 'Incident Report', 'Complete', '2014-11-25', 0, 25, 0, -1, 'For Information Only', '2014-11-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1650, 1684, 43, 'SAPMT has reviewed the subject submittal dated November 09, 2014 and has the following comments:\r\n1.	The drawings are not readable.\r\n2.	Consider the shifted coordinates of curb and gutter in the revised alignment of the road.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Street Lighting Layout', 'Complete', '2014-11-17', 0, 25, 0, 87, 'L-1182/14', '2014-11-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1651, 1686, 43, 'SAPMT has reviewed the subject submittal dated November 11, 2014 and has been rejected with the following comments:\r\n1.	SHERWIN WILLIAMS COMPANY is not an approved Manufacturer/ Vendor for Paint.\r\n2.	Following are the approved paint companies;\r\n•	Hempel Paints Saudi Arabia W.L.L. Riyadh. Vendor ID: 10012821.\r\n•	Saudi Industrial Paint Company Ltd. Dammam. V.ID: 10013791.\r\n•	Saudi Chemical Industries Company. Jeddah. V.ID: 10013759.\r\n3.	Paint shall be Purchased from Saudi Aramco approved Vendors/ Manufacturers.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Paint', 'Complete', '2014-11-13', 0, 25, 0, 87, 'L-1180/14', '2014-11-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1652, 1687, 43, 'SAPMT has reviewed the subject submittal dated November 12, 2014 and has the following comments:\r\n1.	Include new Communication Tower (6 M) to be erected near Water Sports for mounting RADAR (DOME & PTZ Camera).\r\n2.	Include Camera Poles (3 M) – one each at roof top of Building # 2 and 5 to mount PTZ Cameras.\r\n3.	ICC ITP-T-007 Item No. 4.1 & 4.2 (PRECOMMISSIONING) – INSPECTION RESPONSIBILITY ASSIGNMENTS: Change W1 to H for Saudi Aramco & Proponent.\r\n4.	Pre-commissioning and Commissioning of the equipment’s shall be a hold point and not a witness point.\r\n5.	Include RADAR Tower and Long Range Camera poles for the material receiving inspection.\r\n6.	Provide the manufacturer’s recommended testing procedures and has to be included in the commissioning documentation checklist.\r\n7.	Include the inspection checklist plan for the Uninterruptable Power Supply (UPS).\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'ITP & Checklist, LRDAS', 'Complete', '2014-11-17', 0, 25, 0, 87, 'L-1185/14', '2014-11-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1653, 1688, 43, 'SAPMT has reviewed the subject submittal dated November 11, 2014 and has no objection with the following comment:\r\n•	Submit Requisition Package for Cable Trays.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Cable Trays', 'Complete', '2014-11-17', 0, 25, 0, 87, 'L-1184/14', '2014-11-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1654, 1689, 43, 'SAPMT has reviewed the subject submittal dated November 11, 2014 and has no objection with the following comment:\r\n•	Delivery date for the cable is not acceptable and shall be improved.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Fire Resistance Cable', 'Complete', '2014-11-20', 0, 25, 0, 87, 'L-1189/14', '2014-11-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1655, 1690, 43, 'SAPMT has reviewed the subject submittal dated November 12, 2014 and has no objection with the following comments:\r\n1.	Provide Recorder for 24hours Hydro-test for extra tool in Manifold.(Show in Manifold Drawing)\r\n2.	Flushing and Opening of Branches from Highest to Lowest.\r\n3.	Describe how to discharge the Water of Flushing water and after completion of Hydro-test if there is no drain nearby.\r\n4.	Potable water piping systems shall be hydro tested with fresh potable water.\r\n5.	The test manifold shall be approved by the SAPID head before being utilized in system pressure testing.\r\n6.	Add drain valve and pipe branch with isolation valve to connect temperature and pressure recorder if needed in the test manifold. \r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'Hydrostatic Pressure', 'Complete', '2014-11-20', 0, 25, 0, 87, 'L-1186/14', '2014-11-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1656, 1691, 43, 'SAPMT has reviewed the subject submittal dated November 13, 2014 and has no objection with the following comment:\r\n•	It has been observed that the safety violations have increased and IC is urged to take necessary measures to avoid such practices. The following steps shall be taken on urgent bases.\r\n1.	Housekeeping shall be improved and conducted on daily basis even for ongoing activities and not only for completed activities.\r\n2.	No demolished materials shall be left or stockpiled on site and removed instantly.\r\n3.	All lifting operations shall be observed by designated representatives from IC.\r\n4.	All operations involving heavy machinery shall be observed by designated representatives from IC.\r\n5.	All excavations shall be planned with work permit systems to ensure any damages to existing utilities.\r\n6.	Workers shall be protected from dehydration, fatigue and exposure according to Saudi Aramco Safety standards.\r\n7.	Residential facilities for IC employees or subcontractor employees shall be improved to meet the required standards.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Incident Report', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1206/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1657, 1692, 43, 'In light of the weekly meetings with IC and as emailed on November 18, 2014; it is suggested that IC shall propose ways where the precast panels can be slid in place sideways using rails or forklifts instead of cast-in-situ or sliding from top with cranes.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Panel under Bridge Gate # 1', 'Complete', '2015-01-01', 0, 25, 0, 89, 'L-1282/14', '2014-12-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1658, 1693, 43, 'No Comments', 'Inspection Schedule', 'Complete', '2014-11-16', 0, 25, 0, -1, 'For Information Only', '2014-11-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1659, 1694, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0903 dated November 12, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n \r\n', 'QC Inspector', 'Complete', '2014-11-23', 0, 25, 0, 87, 'L-1188/14', '2014-11-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1660, 1695, 43, 'No Comments', 'Progress Report', 'Complete', '2014-11-27', 0, 25, 0, 87, 'For Information Only', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1661, 1696, 43, 'SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:\r\n1.	It is about hydro-testing a 4â€ PVC water line. Remove all the irrelevant Hydro-Carbon documents from the submittal.\r\n2.	The test manifold approval shall be provided prior of proceeding with the system hydro testing.\r\n3.	Attach the approved procedure along with the approval.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Hydrotest', 'Complete', '2014-12-02', 0, 25, 0, 87, 'L-1212/14', '2014-12-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1662, 1697, 43, 'SAPMT has reviewed the subject submittal dated November 12, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'NMR, MV Switchgear', 'Complete', '2014-11-20', 0, 25, 0, 87, 'L-1187/14', '2014-11-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1663, 1698, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1664, 1701, 43, 'SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:\r\n1.	All testing checklists should be as per the manufacturer’s Testing Procedure.\r\n2.	ICC-T-603, Item B; include all applicable items of the attached checklist (SAIC-T-919).\r\n3.	Under installation; include the following items:\r\na.	Route survey shall be performed prior to cable placing to select the cable route and means of cable protection (light weight protection, armor, and burial or combination methods). The route survey shall be also determine and address the sea bottom environmental sensitivity and ecological integrity. Refer to Appendix-I for all applicable surveys needed prior to the installation (refer to SAES-919, Para 5.1.2).\r\nb.	Cable placing is normally performed using a recognized cable-ship after any necessary route clearance in shallow water has been carried out. Placing is normally undertaken only when weather and sea conditions do not create severe risk of damage to the submarine portion, cable ship and laying equipment, or of injury to the personnel. Cable ships shall be equipped with dynamic positioning and dynamic tracking systems. Cable laying and trenching equipment, Remote Operated Vehicles (ROV), shallow water barge, shore-end jack-up barge, cable storage barge and work boats shall be required for laying and repair operation (refer to SAWS-919, Para 5.2).\r\nc.	Cable pulling tensions and bending radii shall be monitored and maintained within the limits specified by the manufacturer (Refer to SAED-919 Para 6.3).\r\n4.	For material receiving, installation and pre-commissioning of LV Power Cable. For column “Quality Procedure & Recordâ€ change to “See Remarksâ€. Add in the remarks column of ITP to “Refer to SATIP-P-104-01 and SATIP-P-111-01â€.\r\n5.	Provide checklist for under water dredging and Method Statement for all discipline activities related to submarine cables installation.\r\n6.	Commissioning checklist has to include structured and unstructured checklist of SONAR System which has to be provided by vendor SONARDYNE and has to incorporate in ITP.\r\n7.	Provide installation checklist for submarine power cable to be installed in the sea bed and in the corals. Use method statement and has to be incorporated with the ITP.\r\n8.	Use available related Saudi Aramco ITP for SONAR power system such as UPS and power supply.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'UWIDS Sonar', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1201/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1665, 1699, 43, 'SAPMT has reviewed the subject submittal dated November 15, 2014 and has no objection with the following comment:\r\n•	All UPS shall have network management card and must be integrated to KAUST existing system.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'UPS', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1197/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1666, 1700, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1667, 1702, 43, 'SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:\r\n1.	For “Material Receiving, Installation and Commissioning of LV Power Cableâ€ add in the remarks column of ITP to “Refer to SATIP-P-101-01â€.\r\n2.	Commissioning of ENS shall be a hold point for Saudi Aramco and KAUST.\r\n3.	Commissioning checklist of ENS during the site acceptance test shall be as per manufacturer’s recommendation.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'ENS', 'Complete', '2014-12-02', 0, 25, 0, 87, 'L-1200/14', '2014-12-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1668, 1703, 43, 'SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:\r\n1.	All testing checklists should be as per Manufacturer’s Testing Procedure.\r\n2.	ICC ITP-T-005 Item # 3.3 (Cable Pulling, Identification, Termination Visual Inspection Low Voltage Copper Cable). Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.\r\n3.	ICC ITP-T-005 Item # 4.1 “Baggage X-Ray Machine System – Installation and Identification Visual Inspectionâ€. Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.\r\n4.	For “Material Receiving, Installation and Pre-Commissioning of LV Power Cableâ€ for column “Quality Procedure & Recordâ€ change to “See Remarksâ€. Add in the remarks column of ITP to “Refer to SATIP-P-104-01 and SATIP-P-111-01â€.\r\n5.	Pre-commissioning and Commissioning of Baggage X-ray Machine shall be a hold point to Saudi Aramco and KAUST Proponent. Change W to H in the ITP.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Baggage X-Ray', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1202/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1669, 1704, 43, 'SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:\r\n1.	For material receiving, installation and commissioning of LV Power Cable, add in the “Remarksâ€ column of ITP refer to SATIP-P-104-01 and SATIP-P-111-01â€.\r\n2.	All testing checklists should be as per the Manufacturer’s Testing Procedure.\r\n3.	ICC ITP-T-011 Item # 3.1 (Pedestal Installation and Pre-Commissioning) – Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.\r\n4.	ICC ITP-T-004 Item # 4.1 (Equipment Installation and Pre-Commissioning Visual Inspection) – Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.\r\n5.	ICC ITP-T-004 Item # 4.2 (Turnstile System – Equipment Installation and Pre-Commissioning Visual Inspection) – Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.\r\n6.	Commissioning checklist to be provided by each vendor and sequence of operation and should  include the followings:\r\na.	It should include the cause and effect matrix during force entry to drop arm and crash barrier.\r\nb.	LPRS has to give a visual and alarm noise in the workstation to alert the operator in case of hot vehicle license plate.\r\nc.	Turnstile has to be interconnected with SACS to de-magnetize the magnetic lock during a recognized access entry.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Gate Security System', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1193/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1670, 1705, 43, 'SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:\r\n1.	All testing checklist should be as per the Manufacturer’s Testing Procedure.\r\n2.	ICC ITP-T-004, Item # 3.1 (Z-Portal System Installation and Pre-Commissioning Visual Inspection) – Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.\r\n3.	ICC ITP-T-004, Item # 4.1 (Pedestal Installation and Pre-Commissioning) – Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.\r\n4.	Material receiving inspection item no. 2.5: For Quality procedure and records; change “SA-IC-P-3202â€ to “See Remarksâ€. For remarks, change to “See SATIP-P-104-01â€.\r\n5.	Add one (1) item for installation and pre-commissioning task/activity of low voltage cables.\r\n6.	Quality procedure and records include “See Remarksâ€. For remarks, indicate “See SATIP-P-104-01 and SATIP-P-111-01.\r\n7.	Consider providing a commissioning checklist and procedure for the X-ray machine that shows the commissioning expectations with heavy and small vehicles to be used and objects that will be using for detection, ex-ammunition, or suspicious type contraband.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Z-Portal System', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1194/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1671, 1706, 43, 'SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:\r\n1.	For “Material Receiving, Installation and Commissioning of LV Power Cableâ€ add in the remarks column of ITP to “Refer to SATIP-P-104-01â€.\r\n2.	This ITP shall not be used for IDAS system. Provide a separate ITP for CCTV of IDAS system which includes the Microwave Intrusion Detection System (MIDS), and Alarm Management System.\r\n3.	This ITP only shows cabling and conduiting inspection procedure, commissioning checklist is not included.\r\n4.	Pre-Commissioning and Commissioning of CCTV cameras shall be done in Security Control Station, Provide Vendor proposed checklist and guidelines for commissioning and include it in ITP.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'CCTV System', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1203/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1672, 1707, 43, 'No Comments, For Information Only', 'Lagoon Fence Arrangement', 'Complete', '2015-02-01', 0, 25, 0, -1, 'For Information Only', '2015-01-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1673, 1714, 43, 'SAPMT has reviewed the subject submittal dated November 18, 2014 and has no objection with the following comment:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	IL no.	Description	9com	Level Of Inspection	Status	Manufacturer\r\n25-00026	PR	RP-023	N/A	Package Air Conditioning Unit	6000001881	Two (2)	Approved with Comments 	Petra Engineering Industries\r\nID no. 30006889\r\n\r\n•	Units shall be certified at Manufacturing Facility to comply with UL-1203 & UL-1995 by an approved 3rd Party and all other inspection requirements.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Air Conditioning', 'Complete', '2014-11-23', 0, 25, 0, 87, 'L-1192/14', '2014-11-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1674, 1708, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1675, 1709, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0909 dated November 18, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'LBE Closing', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1195/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1676, 1710, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0910 dated November 18, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'INCR Closing', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1196/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1677, 1711, 43, 'SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:\r\n1.	For Material Receiving, Installation and Pre-Commissioning of LV Power Cable; for column “Quality Procedure & Recordsâ€ change to “See Remarksâ€. Add in remarks column of ITP to “Refer to SATIP-P-104-01 and SATIP-P-111-01â€.\r\n2.	ITP does not contain any installation procedure of Card Access Reader, Push Button and CCTV Camera.\r\n3.	Include installation checklist for the SACS server and SACS panel.\r\n4.	Commissioning checklist and the cause and effect matrix sequence has to be included in the ITP.\r\n5.	Pre-commissioning and commissioning is a hold point to Saudi Aramco and KAUST proponent.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'SACS', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1198/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1678, 1712, 43, 'SAPMT has reviewed the subject submittal dated November 17, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'Pipe PVC Sch.80', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1204/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1679, 1713, 43, 'SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:\r\n1.	All testing checklists should be as per the manufacturer’s Testing Procedure & Manual.\r\n2.	Installation and Pre-Commissioning should be by Saudi Aramco approved Third Party Inspection Agency.\r\n3.	Provide Method Statement for all discipline activities related to Vessel Barrier installation.\r\n4.	Attach the manufacturer’s product data sheet, drawings and installation & operation manual.\r\n5.	In the ITP, the level of inspection for the main contractor for Material Receiving of Vessel Barrier and accessories shall be Hold Point Inspection.\r\n6.	All pre-commissioning and commissioning activities shall be a hold point to Saudi Aramco and KAUST proponent. Change W to H.\r\n7.	Provide commissioning checklist requirements to be provided by the vendor, showing the type of water vehicle to be used and related testing procedure during Site Acceptance Test. SAT procedure needs to be incorporated with the ITP.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Vessel Barrier', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1199/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1680, 1715, 43, 'Further to SAPMT letter no. K&TPD/KRP&SFPD/SF/L-353/13 dated December 04, 2013, the SOW for relocation of public utilities like STC, Mobiliy and SWCC are attached for concurrence. The estimates from STC and Mobily are also attached for verification. The estimate for water line has not been provided by SWCC; and KAUST has shown inability to get an estimate from SWCC. PMT shall execute the work through available contractors according to STC/ Mobily/ MOWE standards.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Senior Project Engineer (A) on (012) 422 4423.\r\n', 'Utilities Relocation', 'Complete', '2014-12-04', 0, 87, 0, 46, 'L-1191/14', '2014-12-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1681, 1716, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1682, 1717, 43, 'SAPMT has reviewed the subject submittal dated November 17, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'RGS PVC Coated', 'Complete', '2014-12-02', 0, 25, 0, 87, 'L-1211/14', '2014-12-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1683, 1718, 43, 'SAPMT has reviewed the subject submittal dated November 20, 2014 and has no objection with the following comments:\r\n•	Refer to Letter K&TPD/KRP&SFPD/SF/L-215/13 and use the following as recommended earlier;\r\n1.	Use Renderoc TG for patch repair in concrete and masonry for voids greater than 10mm depth.\r\n2.	Use Renderoc FC for repairing minor imperfections in concrete surfaces.\r\n3.	Use Renderoc LA Xtra for structural repair from 50 mm to 200 mm depth.\r\n4.	Use CEBOND as a bonding agent.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Repair Matrix', 'Complete', '2014-12-11', 0, 25, 0, 87, 'L-1231/14', '2014-12-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1684, 1719, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1685, 1721, 43, 'IC request for consideration cannot be entertained based on the following reasons;\r\n\r\n1.	The importance of KAM road has been stated to IC all along the project and as early as the detailed design phase, and that’s why IC submitted and SAPMT approved a baseline schedule with KAM road to be completed in March 2014, IC could not complete and requested a time extension.\r\n2.	According to the revised schedule the wearing course for KAM road was to complete on 20th October 2014 and was still delayed by more than a month.\r\n3.	SAPMT has the right to request the contractor to expedite activities and add more resources to recover from delays.\r\n4.	Contractually SAPMT has the right to ask IC to revise the Project Execution Plan as required throughout the execution of work. (Refer to para 5.3 of Schedule-B)\r\n Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Work Acceleration at KAM', 'Complete', '2015-01-06', 0, 89, 0, 46, 'L-1210/15', '2015-01-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1686, 1724, 43, 'SAPMT has reviewed the subject submittal dated November 19, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Fire Retardant Tape', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1207/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1687, 1723, 43, 'SAPMT has reviewed the subject submittal dated November 19, 2014 and has no objection with the following comment:\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	PR	RP-027	Pipe Non-Metallic Thermoplastic (UPVC) Dia/Size: 20, 63mm OD	6000000031	Zero (0)	Approved \r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'UPVC Pipe', 'Complete', '2014-12-08', 0, 70, 0, 87, 'L-1223/14', '2014-12-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1688, 1720, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0912 dated November 20, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'LBE Closing', 'Complete', '2014-11-27', 0, 25, 0, 87, 'L-1205/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1689, 1722, 43, 'No Comments', 'Progress Report', 'Complete', '2014-11-27', 0, 25, 0, -1, 'For Information Only', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1690, 1725, 43, 'SAPMT has reviewed the subject submittal dated November 25, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Irrigation System', 'Complete', '2014-12-27', 0, 25, 0, 87, 'L-1209/14', '2014-11-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1691, 1726, 43, 'No Comments, For Information Only', 'Progress Meeting', 'Complete', '2014-12-22', 0, 25, 0, -1, 'For Information Only', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1692, 1728, 43, 'SAPMT has reviewed the subject submittal dated November 25, 2014 and has no objection with the following comments:\r\n1.	All drawings/ designs shall be concurred by the project designer.\r\n2.	Install feeder breakers in LV Panel according to feeder assignment of IFC drawing. Take note that Package Substations are not supplying power to street lighting only.\r\n3.	Ensure to follow standard frequency of 60 Hz. The SFRMU shows 50 Hz, correct it, and use only 60 Hz.\r\n4.	Consider the sizing of fuses in the RMU according to Vendor recommendations.\r\n5.	Apply standard rating for Circuit Breakers such as the following:\r\na.	Instead of 1050 AT, use 1200 Ampere Trip AT with 1200 Ampere Frame AF.\r\nb.	Instead of 700 AT, use 800 AT with 800 AF.\r\nc.	Instead of 200 AT, use 250 AT with 250 AF.\r\nd.	Instead of 100 AT, use 125 AT with 150 AF.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'NMR Package Substation', 'Complete', '2014-12-04', 0, 25, 0, 87, 'L-1216/14', '2014-12-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1693, 1727, 43, 'SAPMT has reviewed the subject submittal dated November 24, 2014 and has no objection with the following comment:\r\n•	Ensure that all bus bars are TIN electro-plated as per SAES-T-916.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Grounding Bus Bar', 'Complete', '2014-12-05', 0, 25, 0, 87, 'L-1221/14', '2014-12-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1694, 1729, 43, 'SAPMT has reviewed the subject submittal dated November 24, 2014 and has no objection with the following comment:\r\n\r\n•	Ensure that the colors and patterns are similar to existing KAUST security buildings.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Ceramic Tiles', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1333/15', '2015-01-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1695, 1733, 43, 'In view of the attached Scope of Work for the change order to the contract for “Painting the crash rated precast wallâ€ ICC is requested to submit its proposal on the attached form by Wednesday the 17th of December 2014; ICC must ensure that all applicable quantities and units included in the proposal are correct and conclusive for the works required. The proposal should be enclosed in a sealed envelope clearly marked with all necessary information such as;\r\n\r\n1.	The Contract Number and Title\r\n2.	The Amendment number and Title\r\n\r\nThe envelope shall be deposited at the following location:\r\n\r\n1.	If C.O. value is over SR 3,750,000:		Central Bid Box Contracting R-A162,\r\n                                                                		Wing A, Building 3301 North Park II,\r\n                                                                		Dhahran, 31311 KSA\r\n\r\n2.	If C.O. value is below SR 3,750,000:	KAUST Project Management\r\nRm. 07, Building 100\r\nSAPMT Site Office, (Thuwal)\r\nSaudi Aramco, Jeddah\r\nAll cost and expenses incurred in preparing the proposal shall be borne solely by the contractor. For all items/ activities given in the attached bid form, the contractor shall provide prices according to the agreed scope of work for the change order. The actual award of the work is contingent upon the execution of a formal Purchase Order by both parties and the work should not commence until this aspect has been completed. \r\n\r\nPlease confirm receipt of this letter by a return Fax to the number 012-422-4178.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4423.\r\n', 'Wall Paint', 'Complete', '2014-12-04', 0, 87, 0, 46, 'L-1215/14', '2014-12-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1696, 1730, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1697, 1731, 43, 'SAPMT has reviewed the subject submittal dated November 24, 2014 and has no objection with the following comment:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	PR	RP-028	Cable Trays & Cable Ladders (Electrical)	6000000744	Zero (0)	Approved\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Cable Trays', 'Complete', '2014-12-02', 0, 25, 0, 87, 'L-1213/14', '2014-12-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1698, 1732, 43, 'SAPMT has reviewed the subject submittal dated November 24, 2014 and has no objection with the following comment:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	Description	9com	Level Of Inspection	Status\r\n25-00026	PR	RP-029	Cable Trays (Communication)	6000000744	Zero (0)	Approved\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Cable Tray', 'Complete', '2014-12-02', 0, 25, 0, 87, 'L-1214/14', '2014-12-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1699, 1736, 43, 'Find attached a copy of the minutes of meeting held on 04 NOV 14. Repeated requests were made by PMT to provide updates to show any progress on issues discussed, none received.\r\n\r\nIC is urged to refer to Para 11 of SCH-H for schedule recovery where it is explained what IC shall do in case it falls behind the approved schedule. The Para 11 also explains the option ARAMCO may exercise to ensure schedule recovery.\r\n\r\nIn light of the above and in addition to various emails and verbal requests to IC from PMT to take immediate steps to recover from delays, absolutely nothing has been achieved by IC on the issues discussed as listed below;\r\n\r\n1.	All MEP including power cables shall completely procured by December 14 according to the approved schedule and cable laying activities shall start in September 2014. Cables have not arrived yet and related activities are on hold.\r\n2.	The patrol road and maintenance shall start by October 2014 according to the approved schedule. No activity on site.\r\n3.	The construction of onshore security systems shall start by October 2014 and installation of IDAS systems shall start by December 2104 according to the approved schedule. No activity or materials on site.\r\n4.	The construction of south culvert shall start by November 14 according to the approved schedule. No activity on site.\r\n5.	Civil works for QRT and JFCC building must start by September 14 and completed by November 2014 according to the approved schedule, but it has not started yet.\r\n6.	Sun shades and bus shelters must start in October 14 but the steel structures are not here yet.\r\n7.	OSP works must start by October 2014 according to the approved schedule. There is no activity on site as appropriate resources/ subcontractor have not been engaged by IC yet.\r\n8.	Reinstallation of existing wall must start by Feb 2014 according to the approved schedule.\r\n9.	Procurements for security systems are incomplete and delayed.\r\n10.	Procurements for HVAC systems are incomplete and delayed.\r\n11.	Material submittals, shop drawings etc. for many building activities are still not submitted by IC.\r\n12.	Lighting poles for 15 km road shall start in Sep 14, no activity / materials on site.\r\n13.	UPS buildings shall start in October 2014 but there is no activity / materials on site.\r\nIC is requested to provide written explanation for the following in the shape of a delay analysis and provide an updated schedule and a recovery schedule before 03 December 2014, and show that significant efforts are being made to recover from delays. \r\nFailing which PMT shall exercise its obligations as mentioned in the contract to ensure timely delivery of project.\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4423.\r\n', 'Schedule Recovery', 'Complete', '2014-12-05', 0, 87, 0, 46, 'L-1219/14', '2014-12-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1700, 1734, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0915 dated November 30, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'LBE Closing', 'Complete', '2014-12-04', 0, 25, 0, 87, 'L-1217/14', '2014-12-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1701, 1735, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2014-12-22', 0, 25, 0, -1, 'For Information Only', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1702, 1737, 43, 'IC is urged to adhere to the approved schedule and whenever delays are detected, CONTRACTOR shall report such delays to Saudi Aramco or Company Representative/s explaining its causes, its effects to Project, and the proposed CONTRACTOR’s remedial measures. It is observed that the following activities are bound to be delayed from the approved schedule due to reasons like non-availability of resources, materials or shop drawings;\r\n1.	Sunshades construction at Gate#2 and Gate#3\r\n2.	Installation of IDAS\r\n3.	Installation of License Plate Recognition system\r\n4.	Completion of Building Civil Works  \r\n5.	Installation of Package Substations\r\n\r\nCONTRACTOR‘s failure to update the schedule and forecast the delays shall entitle Saudi Aramco to withhold progress payments until IC’s complies with Schedule A, Paragraph 8, of the Contract.\r\n\r\nShould you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4423.\r\n', 'Remedial Measures', 'Complete', '2014-12-05', 0, 87, 0, 46, 'L-1218/14', '2014-12-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1703, 1746, 43, 'Letter was cancelled, Matter resolved through emails as per direction of TAU.', 'Ceramic Tiles', 'Complete', '2014-12-27', 0, 25, 0, 46, 'For Record Only', '2014-12-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1704, 1740, 43, 'SAPMT has reviewed the subject submittal dated December 01, 2014 and has no objection with the following comment:\r\n•	Ensure that the bracket has a corrosion resistant coating and shall be bonded nearest grounding system to buildings.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Camera Bracket', 'Complete', '2014-12-08', 0, 70, 0, 87, 'L-1225/14', '2014-12-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1705, 1738, 43, 'SAPMT has reviewed the subject submittal dated November 27, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'LRDAS', 'Complete', '2014-12-27', 0, 70, 0, 87, 'L-1229/14', '2014-12-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1706, 1745, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0921 dated December 02, 2014 and has the following comments:\r\n1.	The conditional approval of Mr. Imran Khan as “QC Inspector – Telecommunication & Securityâ€ is further extended for another three (3) months as the communication activities are about to commence.\r\n2.	SAPMT reserves the right to revoke this conditional approval extension based on his unsatisfactory performance.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'QC Inspector', 'Complete', '2014-12-08', 0, 70, 0, 87, 'L-1226/14', '2014-12-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1707, 1739, 43, 'SAPMT has reviewed the subject submittal dated November 27, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Safety Switch', 'Complete', '2014-12-27', 0, 70, 0, 87, 'L-1227/14', '2014-12-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1708, 1741, 43, 'SAPMT has reviewed the subject submittal dated November 26, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Steel Conduit', 'Complete', '2014-12-08', 0, 70, 0, 87, 'L-1228/14', '2014-12-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1709, 1742, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0908 dated November 30, 2014 and has no objection with the following comment:\r\n•	LBE # 200 is granted one time ACD extension upto 28th February 2015.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'LBE Closing', 'Complete', '2014-12-08', 0, 70, 0, 87, 'L-1222/14', '2014-12-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1710, 1743, 43, 'SAPMT has reviewed the subject submittal dated November 27, 2014 and has no objection with the following comments:\r\n1.	Prepare a separate IAP package for the UPS (80 KVA).\r\n2.	The Battery and the valve regulator are level zero materials and will be inspected for receiving inspection at site.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'UPS, Battery', 'Complete', '2014-12-11', 0, 25, 0, 87, 'L-1233/14', '2014-12-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1711, 1744, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0923 dated December 02, 2014 and has the following comments:\r\n1.	Mr. Rolando L. Relleja is permanently approved as “QC Inspector – Civilâ€ for the “KAUST-Perimeter Security Systemsâ€ Project. \r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'QC Inspector', 'Complete', '2014-12-08', 0, 70, 0, 87, 'L-1230/14', '2014-12-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1712, 1747, 43, 'SAPMT has reviewed the subject submittal dated December 02, 2014 and has no objection with the following comment:\r\n•	IC shall arrange a FAT on December 24, 2014 to ensure the justification made by the manufacturer. \r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'CCTV', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1257/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1713, 1748, 43, 'SAPMT has reviewed the subject submittal dated December 02, 2014 and has no objection with the following comment:\r\n•	Ensure that all carpets are according to the textures and colors already being used by KAUST in corresponding buildings.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Carpet', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1252/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1714, 1750, 43, 'No Comments, For Information Only', 'Monthly Progress Report', 'Complete', '2014-12-22', 0, 25, 0, -1, 'For Information Only', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1715, 1751, 43, 'SAPMT has reviewed the subject submittal dated December 02, 2014 and has been rejected with the following comment:\r\n•	The manpower and the equipment provided in the submittal are not sufficient to carry out the magnitude of work being assigned by IC to the subcontractor. IC shall verify the adequacy of resources before proposing to SAPMT.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Safe Track', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1260/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1716, 1749, 43, 'With reference to your letter no. KPSS/SA/B/AKR/14/0926 dated December 4, 2014, find attached the exception items list with a total of 214 items (116 YES items and 98 NO items). IC is urged to provide response with corrective actions and timelines within Three (3) working days of issuance of this letter.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'PMCC', 'Complete', '2014-12-30', 0, 25, 0, 89, 'L-1268/14', '2014-12-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1717, 1752, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1718, 1759, 43, 'SAPMT has reviewed the subject submittal dated December 06, 2014 and has no objection with the following comments:\r\n1.	IC to ensure that the subcontractor is provided with all documents related to the scope of work minimizing any interfaces or dependencies.\r\n2.	The Communication works shall be finished before the end of March 2015.\r\n3.	All civil works related to communications shall finished before the end of April 2015.\r\n4.	The buildings related to the OSP works shall be completed timely so that the OSP works are completed without hindrances.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'OSP Works', 'Complete', '2014-12-11', 0, 25, 0, 87, 'L-1232/14', '2014-12-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1719, 1757, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1720, 1754, 43, 'SAPMT has reviewed the subject submittal dated December 04, 2014 and has the following comments:\r\n1.	Provide a method statement for painting works for precast fence panels and buildings (exterior and interior surfaces).\r\n2.	Submit names of proposed qualified painter’s personnel.\r\n3.	Submit an ITP and checklist.\r\n4.	Submit fire rated paint material intended for buildings with telecom, electrical and other fire rated rooms.\r\n5.	Revise the Painting Schedule to include all proposed surfaces especially above grade precast elements.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Paint', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1259/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1721, 1755, 43, 'SAPMT has reviewed the subject submittal dated December 04, 2014 and has no objection with the following comment:\r\n•	IC shall comply with applicable Saudi Aramco standards for any adjustment made at site.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'SONAR Base', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1242/14', '2014-12-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1722, 1758, 43, 'SAPMT has reviewed the subject submittal dated December 04, 2014 and has the following comment:\r\n•	Provide documents, tests, certificates to show that the doors and windows meet the HCIS requirements and resist the blast loads etc.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Aluminum Door, Windows', 'Complete', '2014-12-15', 0, 25, 0, 87, 'L-1235/14', '2014-12-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1723, 1761, 43, 'SAPMT has reviewed the subject submittal dated November 27, 2014 and has the following comment:\r\nBI	Transmittal Type	Transmittal Ref. #	IL no. 	Description	9com	Manufacturer	Level Of Inspection	Status\r\n25-00026	IAP	IAP- 008	107000102319	Battery Charger/ Rectifier	6000000947	Gutor\r\nElectronic  LLC.\r\n30001163	Two (2)	Approved with comment\r\n\r\n•	The ITP shall be finalized during PIM.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Battery Charger, Rectifier', 'Complete', '2014-12-11', 0, 25, 0, 87, 'L-1224/14', '2014-12-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1724, 1762, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2014-12-22', 0, 25, 0, -1, 'For Information Only', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1725, 1753, 43, 'For Information Only', 'Ramp', 'Complete', '2015-02-02', 0, 25, 0, -1, 'For Information Only', '2015-02-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1726, 1756, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1727, 1760, 43, 'SAPMT has reviewed the subject no. KPSS/SA/B/AKR/14/0935 dated December 06, 2014 and has the following comments:\r\n1.	Mr. Sajid Akram is permanently approved as “QC Inspector – ICC/FCC Precast Facilityâ€ for “KAUST-Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke this permanent approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'QC Inspector Precast Facility', 'Complete', '2014-12-27', 0, 70, 0, 87, 'L-1239/14', '2014-12-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1728, 1763, 43, 'SAPMT has reviewed the subject submittal dated December 06, 2014 and has the following comment:\r\n•	Specify and highlight the selected model with summary sheet.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Ball Volves', 'Complete', '2014-12-26', 0, 70, 0, 87, 'L-1245/14', '2014-12-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1729, 1764, 43, 'SAPMT has reviewed the subject submittal dated December 07, 2014 and has no objection with the following comment:\r\n•	Use only the pre-approved Mix Design with the approved Saudi Aramco Mix Design Number intended for screed in compliance to the project specifications.\r\ni.	Non-structural	SRMC-SRAB-141SF-09 (OPC + MS) Screed\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Mix Design', 'Complete', '2014-12-26', 0, 70, 0, 87, 'L-1243/14', '2014-12-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1730, 1765, 43, 'SAPMT has reviewed the subject submittal dated December 07, 2014 and has been rejected with the following comment:\r\n•	IC is urged to not include personnel in the Organizational Chart which are not approved.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Management Report', 'Complete', '2014-12-15', 0, 25, 0, 87, 'L-1237/14', '2014-12-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1731, 1766, 43, 'SAPMT has reviewed the subject submittal dated December 06, 2014 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'EMT Conduits', 'Complete', '2014-12-15', 0, 70, 0, 87, 'L-1236/14', '2014-12-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1732, 1768, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1733, 1767, 43, 'SAPMT has reviewed the subject submittal dated December 04, 2014 and has the following comments:\r\n\r\n1.	Consider submitting the Organization Chart as well as Manpower List of proposed subcontractor.\r\n2.	Contractor shall qualify and accept the subcontractor as per Schedule-Q before submitting to SAPMT for evaluation and approval.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Red Sea Housing', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1249/14', '2014-12-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1734, 1770, 43, 'SAPMT has reviewed the subject submittal dated December 08, 2014 and has the following comments:\r\n1.	The justification letter from the vendor is not acceptable since the content does not state that the previous model Bioscrypt 4G V-station is obsolete and the new proposed model Morpho Sigma Series is the equal replacement.\r\n2.	Provide a justification letter either from Bioscypt or Morpho.\r\n3.	Justification letter from Maxxess is acceptable only for confirming the compatibility of both manufacturer’s proposed products with KAUST existing system.\r\n', 'Biometric Reader', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1265/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1735, 1771, 43, 'SAPMT has reviewed the subject submittal dated December 07, 2014 and has no objection. It is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Reinforcing Bar', 'Complete', '2014-12-26', 0, 70, 0, 87, 'L-1241/14', '2014-12-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1736, 1772, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1737, 1773, 43, 'SAPMT has reviewed the subject submittal dated December 01, 2014 and has no objection. It is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Water Heater', 'Complete', '2014-12-26', 0, 70, 0, 87, 'L-1246/14', '2014-12-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1738, 1774, 43, 'The Exception Items List with Letter attached sent to ICC.', 'PMCC', 'Complete', '2014-12-27', 0, 25, 0, 87, 'L-1268/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1739, 1769, 43, 'SAPMT has reviewed the subject submittal dated December 04, 2014 and has no objection with the following comments:\r\n1.	Submit the shop drawings for gates separately if applicable.\r\n2.	Do not include irrelevant drawings in your submittal.\r\n3.	Chainlink Fence on the northern side of KAM road shall be installed according to the Scope of Work.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Chain Link Fence', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1253/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1740, 1775, 43, 'The term "K-rating"/ "Crash rating" as mentioned in Scope of Work para 1.2.2.1.1 is derived from a specific standard which requires destructive testing. This specific standard SD-STD-02.01 does not allow "desktop design analysis" or "lab testing" only to ensure the crash rating. To prove that the materials delivered by the Contractor are according to the criteria mentioned in the scope of work, the Contractor has to conduct destructive testing to prove the crash rating as explained in the standard for K-rating, and provide certificates of conformance.\r\nSAPMT rejects IC claim for compensation and IC is encouraged to arrange a meeting with SAPMT to close this matter as soon as possible.\r\nShould you have any questions, please contact Tawfiq A. Al-Ubaidi, Sr. Project Engineer at 012 422-4368.\r\n', 'Crash Rating Test', 'Complete', '2015-01-01', 0, 25, 0, 46, 'L-1238/14', '2014-12-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1741, 1777, 43, 'Please be advised that an integrated FAT for IDAS based on the agreements made during the meeting held on December 30, 2014 will be conducted on February 10, 2015. AXIS brand camera has been selected after the POC conducted in August and September 2014 for this FAT as it meets with the approved Scope of Work, FSD and HCIS requirements.\r\n\r\nPlease confirm the attendance of your representatives and should you have any question, please contact Sohail Moughal, Project Engineer on (012) 422 4570.\r\n', 'IDAS Camera FAT', 'Complete', '2015-01-13', 0, 25, 0, 89, 'L-1234/15', '2015-01-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1742, 1776, 43, 'SAMPT has reviewed the subject submittal dated December 02, 2014 and has no objection with following comment;\r\n\r\n1.	It is IC responsibility to ensure installations are done according to Saudi Aramco Engineering Drawings and Standards.\r\n2.	IC shall adhere to all IBC, IPC and NFPA standards as applicable.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Fire Extinguishers', 'Complete', '2015-05-17', 0, 25, 0, 93, 'L-1531/15', '2015-04-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1743, 1780, 43, 'SAPMT has reviewed the subject submittal dated December 11, 2014 and has no objection with the following comment:\r\n•	Response No. 4 from IC is unacceptable, because Integration between Joint Forces Control Center (JFCC), Security Operation Center (SOC) and Building No. 17 for monitoring purposes is a contractual obligation, according to PE-000002, section 1.2.2.1.4; and ICC has to ensure that such requirements will be met without any additional cost to Saudi Aramco.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'SONAR TQ', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1261/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1744, 1781, 43, 'SAPMT has reviewed the subject submittal dated December 09, 2014 and has the following comment:\r\n•	The TQ is rejected as SAPMT does not have any objection to follow the IFB.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Irrigation Tie-in', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1256/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1745, 1782, 43, 'SAPMT has reviewed the subject submittal dated December 04, 2014 and has the following comments:\r\n1.	All testing checklists should be as per the Manufacturer’s Testing Procedure.\r\n2.	Item 2.3/3.6 for Inspection Responsibility Assignment shall be deleted and refer it to SATIP-P-104-01.\r\n3.	Item 3.10 for Inspection Responsibility Assignment shall be deleted and refer it to SATIP-P-111-01.\r\n4.	Add one (1) item for pre-commissioning of cables/wires and refer it to SATIP-P-104-01 and SATIP-P-111-01.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Emergency Notification System, ENS', 'Complete', '2014-12-30', 0, 25, 0, 89, 'L-1277/14', '2014-12-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1746, 1800, 43, 'SAPMT has reviewed the subject submittal dated December 15, 2014 and has no objection with the following comments:\r\n1.	Ensure that the general architectural shapes are similar to the existing parking shades in KAUST.\r\n2.	All structural calculations shall be verified by the project designer.\r\n3.	All vendor shop drawings shall be verified by the project designer.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Parking Sun Shades', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1264/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1747, 1785, 43, 'SAPMT has reviewed the subject submittal dated December 07, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Diver Detection', 'Complete', '2014-12-26', 0, 70, 0, 87, 'L-1248/14', '2014-12-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1748, 1786, 43, 'SAPMT has reviewed the subject submittal dated December 04, 2014 and has the following comments:\r\n\r\n1.	ICC-IC-T-101: Add item no. A2. Verify that storage area of the CCTV equipments and accessories is in accordance with detailed instructions issued by the manufacturer; all applicable specifications and Saudi Aramco standards (Refer to Schedule-Q, Att. IV, Sec. 6).\r\n2.	ICC-IC-T-101: Add item no. A3. Verify that the storage area is well secure and provided with environments control for the protection of the equipment’s (Refer to Schedule-Q, Att. IV, Sec.6).\r\n3.	ICC-IC-T-101: Add item no. A4. Verify that the storage area provided is not located near water sources nor flammable materials (Refer to Schedule-Q, Att. IV, Sec.6).\r\n4.	ICC-IC-T-102: Add item no. A4. Verify received CCTV Camera power supply is 220V AC (Input), 24V AC (Output), 60 Hz in compliance with the approved Project Specification & Scope of Work.\r\n5.	ICC-IC-T-102: Add item no. A5. Verify that received CCTV Camera has a high finish tamper resistant camera enclosure and shall have an adjustable swivel/tilt head in compliance with approved Project Specification & Scope of Work.\r\n6.	ICC-IC-T-102: Add item no. A6. Verify that the CCTV camera shall incorporate a color CCD Camera, 8 X or 10 X zoom lens, an integral receiver/ driver unit, and an integral pan/ tilt drive in to a low profile 250mm diameter (minimum) dome. In compliance with the approved Project Specification & Scope of Work.\r\n7.	Item 2.6/3.3/3.8 for inspection responsibility assignment shall be deleted and refer it to SATIP-P-104-01.\r\n8.	Add one (1) item for pre-commissioning of cables/ wires and refer it to SATIP-P-104-01 and SATIP-P-111-01.\r\n9.	All testing checklists should be as per the Manufacturer’s Testing Procedure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'CCTV System', 'Complete', '2014-12-29', 0, 25, 0, 87, 'L-1278/14', '2014-12-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1749, 1787, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1750, 1783, 43, 'SAPMT has reviewed the subject submittal dated December 11, 2014 and has no objection with the following comments:\r\n1.	Ensure that proper color of building wires will be provided (Green for grounding, White for Neutral and Black/ Red/ Blue for the phase).\r\n2.	Building wires shall pass on-site insulation resistance test.\r\n3.	Ensure that building wires were sized according to load requirements and schedule as specified in VE-846472 sht. 8 of 8.\r\n4.	Use for Thermal Camera at building 2 and 5.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Power Cable for CCTV', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1247/14', '2014-12-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1751, 1789, 43, 'SAPMT has reviewed the subject submittal dated December 09, 2014 and has no objection with the following comment:\r\n•	Ensure the cable matches the requirement of the biometric reader and SACS door enclosure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Data Cable SACS', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1270/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1752, 1791, 43, 'SAPMT has reviewed the subject submittal dated December 14, 2014 and has no objection with the following comment:\r\n•	IC shall ensure that the spares are included in the procurement.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Toilet Accessories', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1263/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1753, 1794, 43, 'SAPMT has reviewed the subject submittal dated December 14, 2014 and has the following comments:\r\n1.	Provide samples of all materials, fasteners, rails etc.\r\n2.	The BOQ shall be more detailed to include all materials required to complete the job. Also include the Turnstile inbound building.\r\n3.	A manufacturers/ vendors shop drawing showing the system shall be provided.\r\n4.	Ensure that the revised submittal meets with the Para 1.03 and 2.02 of specifications 09511.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Ceiling', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1255/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1754, 1792, 43, 'SAPMT has reviewed the subject submittal dated December 09, 2014 and has the following comments:\r\n\r\n1.	I/O points are not matching with IFC. All I/O’s to be include in the list with 20% spare.\r\n2.	IFC drawing for HVAC control to be attached with the submittal.\r\n3.	Exhaust fan, Duct Heater and Supply Fans power panel to be include in the submittal or shall be submit separately. \r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'DDC Panel', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1250/14', '2014-12-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1755, 1778, 43, 'No Comments, For Information Only', 'Inspection Schedule', 'Complete', '2015-01-13', 0, 25, 0, -1, 'For Information Only', '2015-01-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1756, 1790, 43, 'SAMPT has reviewed the subject submittal dated December 15, 2014 and has the following comments:\r\n\r\n1.	The manpower recorded in Saudization Report for November 2014 does not tally with the November’s Daily Progress Reports received by SAPMT on December 22, 2014. On November 1st, the number of ICC Saudi staff is 18 and total site manpower is 502. However, in Saudization Report, the number of ICC Saudi staff is 14 and total site manpower is only146.\r\n2.	Ensure that all manpower numbers in Saudization Report are in lined with the Daily Progress Report.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Saudization', 'Complete', '2014-12-30', 0, 25, 0, 89, 'L-1220/14', '2014-12-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1757, 1795, 43, 'SAPMT has reviewed the subject submittal dated December 14, 2014 and has the following comments:\r\n1.	Include FSD matrix for SACS system.\r\n2.	Provide the list of door number and related readers to be used in every building, as per scope of work document and IFC.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'SACS', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1266/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1758, 1784, 43, 'SAPMT has reviewed the subject submittal dated December 11, 2014 and has no objection with the following comment:\r\n\r\n•	In compliance to project specification, use the approved Saudi Aramco Concrete Mix Design with Mix Design ID No. SRN-THUW(2)-2II-11 (OPC) Curb Stone.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Curb Stone', 'Complete', '2015-01-05', 0, 25, 0, 89, 'L-1286/14', '2015-01-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1759, 1798, 43, 'SAPMT has reviewed the subject submittal dated December 14, 2014 and has the following comments:\r\n•	The submittal and the vendor proposal do not include as to how the handrails/ railings are painted and fixed, as they are excluded from the vendor proposal.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Handrails', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1254/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1760, 1799, 43, 'The Invoice # 19 for November 2014 has been approved and SES has been issued to ICC.', 'Invoice', 'Complete', '2015-01-14', 0, 25, 0, -1, 'For Record Only', '2015-01-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1761, 1788, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2014-12-22', 0, 25, 0, -1, 'For Information Only', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1762, 1796, 43, 'SAPMT has reviewed the subject submittal dated December 14, 2014 and has the following comment:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	IL no. 	Description	9com	Manufacturer	Level Of Inspection	Status\r\n25-00026	IAP	IAP- 009	107000102397	UPS\r\n80 KVA	6000001012	Gutor\r\nElectronic 30001163	2	Approved with Comment\r\n\r\n•	The ITP shall be finalized during PIM.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'UPS 80KVA', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1267/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1763, 1779, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0933 dated December 10, 2014 and has the following comment:\r\n\r\n•	IC is urged to update the organization chart and send for information to SAPMT every time a key person is replaced.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Organization Chart', 'Complete', '2015-02-04', 0, 25, 0, 87, 'L-1316/15', '2015-02-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1764, 1797, 43, 'No Comments, For Information Only', 'MQMR', 'Complete', '2015-01-13', 0, 25, 0, -1, 'For Information Only', '2015-01-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1765, 1793, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0948 dated December 15, 2014 and has no objection with the following comment:\r\n•	The current QC Manager shall take full responsibility of all works during the absence of QA Manager and a document showing all pending, ongoing and upcoming activities shall be prepared to handover duties.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QA Manager', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1258/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1766, 1801, 43, 'SAPMT has reviewed the subject submittal dated December 17, 2014 and has no objection with the following comments:\r\n1.	Add an item for pre-commissioning of LV cables. (Refer to SATIP-P-104-01 and P-111-01)\r\n2.	Delete inspection responsibility assignment in item 2.5 and 3.4. (Refer to SATIP-P-104-01 and P-111-01).\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'SONAR System', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1262/14', '2014-12-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1767, 1802, 43, 'SAMPT has reviewed your subject submittal dated December 17, 2014 and has the following comments:\r\n\r\n1.	Item 2.3/3.3/3.4 for inspection responsibility assignment shall be deleted and refer it to SATIP-P-104-01 and SATIP-P-111-01.\r\n2.	Add one (1) item for pre-commissioning of cables/ wires and refer it to SATIP-P-104-01 and SATIP-P-111-01.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Baggage X-Ray', 'Complete', '2014-12-29', 0, 25, 0, 87, 'L-1280/14', '2014-12-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1768, 1803, 43, 'SAPMT has reviewed the subject submittal dated December 17, 2014 and has the following comments:\r\n1.	All testing checklists should be as per Manufacturer’s Testing Procedure.\r\n2.	ICC ITP-T-004 Item No. 3.1 (Z-Portal System Installation and Pre-Commissioning Visual Inspection) – Inspection Responsibility Assignments: change W1 to H for Saudi Aramco.\r\n3.	ICC ITP-T-004 Item No. 4.1 (Pedestal Installation and Pre-Commissioning) – Inspection Responsibility Assignments: change W1 to H for Saudi Aramco.\r\n4.	Quality procedure and records, indicate “See Remarksâ€. For remarks, indicate “See SATIP-P-104-01 and SATIP-P-111-01â€.\r\n5.	For item # 2.5/3.4/3.5/3.7. Delete Inspection Responsibility Assignment and refer it to SATIP-P-104-01 & SATIP-P-111-01.\r\n6.	Add item in the Pre-Commissioning for LV Power Cable and refer it to SATIP-P-104-01 & SATIP-P-111-01.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Z-Portal', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1273/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1769, 1804, 43, 'SAPMT has reviewed the subject submittal dated December 16, 2014 and has the following comments.\r\n\r\n1.	The 9com for “Fire Retardant Paintâ€ is 6000000485 (Non-Inspectable).\r\n2.	The recommended combinations of product to be applied as per Manufacturer’s recommendations mentioned in Firetard Flame Inhibiting Paint product data/ application (page 2/4).\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Fire Retardant Paint', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1346/15', '2015-01-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1770, 1805, 43, 'No Comments, For Information Only', 'Inspection Schedule', 'Complete', '2015-01-13', 0, 25, 0, -1, 'For Information Only', '2015-01-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1771, 1806, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0957 dated December 18, 2014 and has the following comment:\r\n\r\n•	Integrated FAT has been rescheduled to February 10, 2015. IC is urged to revise the procedures according to meeting held on December 30, 2014 with SAPMT and comply with the decisions made during the meeting.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'IDAS FAT Procedure', 'Complete', '2015-02-02', 0, 25, 0, 87, 'L-1315/15', '2015-02-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1772, 1807, 43, 'SAPMT has reviewed the subject submittal dated December 18, 2014 and has no objection with the following comments:\r\n1.	With reference to ICC/WESCOSA response on NMR 601-002-A point # 2, SAPMT confirms that package substation has only one Main breaker installed in LV panel.\r\n2.	With reference to ICC/WESCOSA response on NMR 601-002-A point # 5, the breaker setting shall be as per vendor recommendation, However, ensure that the Molded Case Circuit Breaker Sizing of Ampere Trip and Ampere Frame shall be as per the comment provided on NMR 601-002 dated November 25, 2014.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Package Substation', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1271/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1773, 1808, 43, 'No Comments, For Information Only', 'Procurement Status Report', 'Complete', '2015-02-10', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1774, 1809, 43, 'SAPMT has reviewed the subject submittal dated December 17, 2014 and has no objection with the following comment:\r\n•	Consider providing the checklist for SACS mapping. \r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'SACS', 'Complete', '2014-12-30', 0, 25, 0, 89, 'L-1272/14', '2014-12-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1775, 1810, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-02-18', 0, 70, 0, -1, 'For Information Only', '2015-02-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1776, 1812, 43, 'As agreed in the management meeting held on January 19, 2015, IC shall provide a recovery schedule that ensures that the project slippage is recovered within the next 2 months. It is advisable to expedite all those activities which have no direct relationships and which can be performed in parallel by increasing resources so that the dependent activities can have more lag times if necessary or if any adjustments are required. As the project progress is behind by more than 10%, any justification to start a delayed activity at a later date than now is unacceptable, until the project is back on track. Similarly all pending/ delayed procurements must be delivered to site especially the long lead items.\r\n\r\nAs agreed in the meeting on January 20, 2015, all earthworks shall be completed by late February, so that all other dependent activities like IDAS, roads, Electrical infrastructure and communications can start without any further delays and imminent obstacles from earthworks.\r\n\r\nWith 50% project works remaining it is obvious that a progress of approximately 2.5% is required every week till the end of the project. IC is urged to create a weekly plan to achieve 2.5% at the start of every week and provide an update to SAPMT at the end of every week.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Schedule Recovery', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1332/15', '2015-01-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1777, 1813, 43, 'SAPMT has reviewed the subject submittal dated January 04, 2015 and has the following comments:\r\n\r\n1.	Submittal cover page and attached data sheet shows different vendors.\r\n2.	Attached product specifications and IFC drawings are not related to the subject Video Conferencing System.\r\n3.	Provide Manufacturer’s recommendations and justification letter.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Video Conference', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1306/15', '2015-01-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1778, 1814, 43, 'SAPMT has reviewed the subject submittal dated January 04, 2015 and has the following comments:\r\n\r\n1.	Provide technical data sheet and catalog for Video Wall Screen.\r\n2.	Ensure the latest Video Wall Screen is provided.\r\n3.	Justification letter shall be from the manufacturer and not from the contractor.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Video Wall Screens', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1305/15', '2015-01-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1779, 1815, 43, 'SAPMT has reviewed the subject submittal dated December 04, 2014 and has the following comments:\r\n1.	All testing checklists should be as per the Manufacturer’s Testing Procedure.\r\n2.	Item 2.3/3.6 for Inspection Responsibility Assignment shall be deleted and refer it to SATIP-P-104-01.\r\n3.	Item 3.10 for Inspection Responsibility Assignment shall be deleted and refer it to SATIP-P-111-01.\r\n4.	Add one (1) item for pre-commissioning of cables/wires and refer it to SATIP-P-104-01 and SATIP-P-111-01.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'ENS', 'Complete', '2014-12-29', 0, 25, 0, 87, 'L-1277/14', '2014-12-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1780, 1811, 43, 'SAPMT wish to remind IC that Daily Progress Report should be submitted to SAPMT on daily basis, to record the daily manpower and progress achieved on site. The last Daily Progress Report received by SAPMT is more than two months ago, on October 14, 2014. This is not acceptable and IC is required to submit all outstanding Daily Progress Report from October 15, 2014 onwards.\r\n\r\nThe information of manpower record shown in IC’s Daily Progress Report is also inadequate. More details of the manpower such as number of workers/employees in each trade, expatriate or Saudi national, should be recorded. \r\n\r\nEvaluation of IC Saudization Report for November 2014 will be put on hold until IC submit these outstanding Daily Progress Reports.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'Daily Progress Report', 'Complete', '2014-12-26', 0, 70, 0, 87, 'L-1244/14', '2014-12-18', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1781, 1816, 43, 'SAPMT has reviewed the subject submittal dated December 17, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Gate Security', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1251/14', '2014-12-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1782, 1818, 43, 'With reference to your letter KPSS/SA/B/AKR/14/0926 dated December 4, 2014, find attachd the exception items list with a total of 214 items (116 YES items and 98 NO items). IC is urged to provide response with corrective actions and timelines within 3 working days of issuance of this letter.', 'PMCC', 'Complete', '2014-12-27', 0, 25, 0, 87, 'L-1268/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1783, 1817, 43, 'In response to the subject letter dated December 16, 2014; SAPMT would like to confirm the following;\r\n\r\n1.	All outstanding EIL “NOâ€ items and the Performance Acceptance Certificate (PAC) for PMCC’s 1&2 will be completed by end of February 2015.\r\n2.	Final MCC for additional beautification scope will be achieved by end of February 2015 without the floating jetty.\r\n3.	The new precast wall will be installed from the seashore at Sta. 0+000 to Sta. 2+000, from where the relocated/ existing wall shall be in place from Sta. 2+000 to Sta. 4+000, as shown in the attached sketch by end of February 2015. This will ensure a continuous hard barrier between KAUST and Navy along the length of the KAM road.\r\n4.	A chain-link fence will be installed on the northern side of the KAM road by end of February 2015.\r\n5.	As the northern side of Lagoon is already protected by a chain-link fence, SAPMT proposes that a visibility barrier like a green tarpaulin or mesh be installed on the existing chain-link fence by February 2015 and until the works in the lagoon are completed, which are anticipated by the end of May 2015.\r\n', 'KAM, Readiness', 'Complete', '2015-01-13', 0, 89, 0, 46, 'L-1297/15', '2015-01-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1784, 1819, 43, 'No Comments, For Information Only', 'Company Representative', 'Complete', '2014-12-28', 0, 25, 0, -1, 'For Information Only', '2014-12-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1785, 1820, 43, 'SAPMT has reviewed the subject submittal dated December 22, 2014 and has no objection with the following comments:\r\n1.	Ensure that outdoor receptacles are weather proof with Ingress Protection rating of IP 66 as per SAES P-104.\r\n2.	Ensure that receptacle outlets to be installed outdoor and/ or which are subject to wet and damp locations shall contain a Ground Fault Circuit Interrupter (GFCI) as specified in IFC drawings VA846646 sht.002.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Wiring Devices', 'Complete', '2014-12-29', 0, 25, 0, 87, 'L-1275/14', '2014-12-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1786, 1821, 43, 'SAPMT has reviewed the subject submittal dated December 22, 2014 and has been rejected with the following comment:\r\n\r\n•	Before establishing the ITP, the contractor should have the following minimum requirements;\r\n1.	Approved Method of Statement.\r\n2.	Coat approval attaches with Manufacturer’s data sheets.\r\n3.	Qualified coating applicator.\r\n4.	Client proponent acceptance for finishing mock-up.\r\n5.	ITP should include the applicable reference and complete missing information.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Architectural Painting Work', 'Complete', '2015-01-05', 0, 25, 0, 89, 'L-1285/14', '2015-01-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1787, 1822, 43, 'SAPMT has reviewed the subject submittal dated December 22, 2014 and has the following comment:\r\n\r\n1.	The recovery schedule is not complete as submitted. Please submit a P6 soft copy of the recovery schedule along with progress curves for procurement and construction.\r\n2.	Ensure that the slippage is recovered within the next 2 to 3 months and not spread till the end of the project.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Recovery Schedule', 'Complete', '2015-01-12', 0, 25, 0, 89, 'L-1298/15', '2015-01-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1788, 1823, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0950 dated December 15, 2014 and has been rejected with the following comments:\r\n1.	Mr. Joseph Buban Navarro N. does not possess the minimum year of experience as per Schedule-Q.\r\n2.	Contractor shall immediately provide QC Supervisor (Civil) to avoid NCR.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Supervisor Civil', 'Complete', '2014-12-30', 0, 25, 0, 89, 'L-1274/14', '2014-12-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1789, 1824, 43, 'SAPMT has reviewed the subject submittal dated December 24, 2014 and has no objection with the following comment:\r\n\r\nBI	Trsmit’l Type	Trsmt’l Ref. #	IL\r\nno.	Description	9com	Level of Inspection	Status	Manufacturer \r\n25-00026-0001	MR	RP-031	N/A	Bar Reinforcing Coated Epoxy	6000000684	One (1) 	Approved 	Attieh Steel Company Ltd. \r\nSAP# 30007117\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Bar Reinforcing', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1335/15', '2015-01-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1790, 1825, 43, 'IC is urged to expedite the resolution of quality issues long pending in the shape of Log Book entries and INCR’s. Please propose Corrective actions before December 31, 2014 for all pending quality matters.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Log Book Entries', 'Complete', '2014-12-26', 0, 25, 0, 87, 'L-1269/14', '2014-12-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1791, 1826, 43, 'We seek your support to allocate 8500 tons of bitumen 60/70 to the subject project Contractor, International Center for Contracting Co. (IC) to expedite the asphalting work for Patrol Road, Maintenance Road, Biking Track and Circulation Lanes around the security gates for BI 25-00026. A breakdown of quantities is attached.\r\n\r\nThe earthworks are nearing completion and asphalting shall start immediately. It is requested that the concerned bulk plants in Jeddah region be informed to issue the said quantity to Al-Jeri Establishment (Customer Account No. 400608). This quantity shall, in turn, be used by M/s. Dar Al Manajim Contracting & Asphalt (DARMCO) – Briman, Jeddah, which is one of the suppliers for the asphalt works under the project.\r\n\r\nYour support and quick response will be highly appreciated as it will provide the help necessary to complete the project on time.\r\n\r\nShould you have any inquiry, please contact Tawfiq A. Al-Ubaidi, Sr. Project Engineer on (012) 422-4368.\r\n', 'Asphalt Allocation', 'Complete', '2014-12-30', 0, 89, 0, 46, 'L-075/14', '2014-12-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1792, 1827, 43, 'No Comments, For Information Only', 'Naval Base', 'Complete', '2015-03-01', 0, 25, 0, -1, 'For Information Only', '2015-02-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1793, 1828, 43, 'We seek your support to allocate 8500 tons of bitumen 60/70 to the subject project Contractor, International Center for Contracting Co. (IC) to expedite the asphalting work for Patrol Road, Maintenance Road, Biking Track and Circulation Lanes around the security gates for BI 25-00026. A breakdown of quantities is attached.\r\n\r\nThe earthworks are nearing completion and asphalting shall start immediately. It is requested that the concerned bulk plants in Jeddah region be informed to issue the said quantity to Al-Jeri Establishment (Customer Account No. 400608). This quantity shall, in turn, be used by M/s. Dar Al Manajim Contracting & Asphalt (DARMCO) – Briman, Jeddah, which is one of the suppliers for the asphalt works under the project.\r\n\r\nYour support and quick response will be highly appreciated as it will provide the help necessary to complete the project on time.\r\n\r\nShould you have any inquiry, please contact Tawfiq A. Al-Ubaidi, Sr. Project Engineer on (012) 422-4368.\r\n', 'Bitumen, Asphalt', 'Complete', '2014-12-28', 0, 25, 0, 46, 'L-075/14', '2014-12-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1794, 1831, 43, 'SAPMT has reviewed the subject submittal dated December 27, 2014 and has the following comments:\r\n\r\n1.	Include the Coordinates of Bore Hole referenced to International 1924 Ellipsoid, Ain (Ayn) Al Abd 1970 Datum (stated within SAES-A-100). Include the Zone # (36, 34…...or 40).\r\n2.	General Geotechnical Investigation shall identify the Electrical Resistivity for the soil. Include in the SOW and in Appendix-A as well.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Radar Tower Foundation GI', 'Complete', '2015-01-04', 0, 25, 0, 89, 'L-1291/15', '2015-01-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1795, 1829, 43, 'SAPMT has reviewed the subject submittal dated December 25, 2014 and has no objection with the following comments:\r\n\r\n1.	Chainlink Fence (SSD type-III) on the northern side of KAM road shall be installed according to the Scope of Work.\r\n2.	Prepare shop drawings showing the alignment of the chainlink fence before starting work on site.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Chain Link Fence, SSD Type III', 'Complete', '2014-12-30', 0, 25, 0, 89, 'L-1279/14', '2014-12-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1796, 1830, 43, 'SAPMT has reviewed the subject submittal dated December 24, 2014 and has no objection with the following comments:\r\n\r\n1.	The said material was approved earlier via letter no L-616/14. IC shall ensure that procurement process is not delayed by submitting alternatives.\r\n2.	It is contractor’s responsibility to ensure full compliance with the Functional Specification Documents (FSD), Project Specifications and Standards set by High Commission for Industrial Security HCIS-SEC-05.\r\n3.	Ensure that all proposed systems, materials and equipment’s are compatible with the existing security systems at KAUST.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'IDAS', 'Complete', '2015-01-09', 0, 25, 0, 89, 'L-1300/15', '2015-01-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1797, 1832, 43, 'IC is urged to follow the scope of work and provide the following before January 01, 2015:\r\n\r\n1.	A Method Statement for backfilling and dewatering at the lagoon.\r\n2.	A shop drawing concurred by project designer.\r\n3.	A schedule to start and complete the subject work.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Lagoon, North', 'Complete', '2014-12-29', 0, 25, 0, 87, 'L-1281/14', '2014-12-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1798, 1833, 43, 'SAPMT has reviewed the subject submittal dated December 25, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Ball Valves', 'Complete', '2015-01-06', 0, 25, 0, 89, 'L-1292/15', '2015-01-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1799, 1834, 43, 'No Comments, For Information Only', 'Inspection Schedule', 'Complete', '2015-01-13', 0, 25, 0, -1, 'For Information Only', '2015-01-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1800, 1835, 43, 'SAPMT has reviewed the subject letter dated December 27, 2015 and has the following comments:\r\n\r\n1.	Mr. Yasir Ashraf is permanently approved as “QC Managerâ€ for “KAUST – Perimeter Security Systemsâ€ project (BI-25-00026-0001).\r\n2.	SAPMT reserves the right to revoke this conditional approval based on unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Yasir Ashraf, QC Manager', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1415/15', '2015-02-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1801, 1836, 43, 'SAPMT has reviewed the subject submittal dated December 29, 2014 and has the following comment:\r\n\r\n1.	Mr. Mian Maroof Zafar is rejected for the position of “QC Supervisor – Civilâ€ as he does not have the minimum experience as required in Schedule-Q (General Qualifications).\r\n2.	Contractor shall immediately provide QC Supervisor – Civil to avoid NCR.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Supervisor Civil', 'Complete', '2015-01-05', 0, 25, 0, 89, 'L-1290/14', '2015-01-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1802, 1837, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-02-10', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1803, 1838, 43, 'SAPMT has reviewed the subject submittal dated December 29, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'MS Hydrostatic Pressure', 'Complete', '2015-01-05', 0, 25, 0, 89, 'L-1287/14', '2015-01-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1804, 1839, 43, 'SAPMT has reviewed the subject submittal dated December 29, 2014 and has no objection with the following comments:\r\n\r\n1.	Ensure that the coating thickness of galvanization for the pole matches with the severe corrosive environment close to the sea.\r\n2.	Ensure that grounding lug provision is present for the camera poles and the MIDS pole.\r\n3.	Contractor is advised to provide at least 5 winches for installation and maintenance purposes.\r\n4.	Provide separately shop drawings showing details for the anchor bolts and foundations. Provide wind load calculations along with the foundation details.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'MIDS', 'Complete', '2015-01-09', 0, 25, 0, 89, 'L-1299/15', '2015-01-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1805, 1840, 43, 'Pulled Out by ICC.', 'Procurement Plan', 'Complete', '2015-01-14', 0, 25, 0, -1, 'For Information Only', '2015-01-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1806, 1841, 43, 'Pulled Out by ICC.', 'Subcontracting Plan', 'Complete', '2015-01-14', 0, 25, 0, -1, 'For Information Only', '2015-01-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1807, 1842, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1808, 1843, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0981 dated December 30, 2014 and has no objection with the following comment:\r\n\r\n•	LBE # 254 is granted one time ACD extension up-to February 15, 2015.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'LBE Closing', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1317/15', '2015-01-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1809, 1844, 43, 'Please find attached KAUST letter requesting to delete the security fence ditch around the university and add an electronic screening system to Gate No. 1 similar to Gate No. 2 and Gate No. 3 security systems.\r\n\r\nYou are kindly requested to work with KAUST and FPD for the additional scope to enable SAPMT to include it in the contract amendment along with the ditch deletion. \r\n\r\nShould you have any inquiry, please contact M. Emad Y. Krimly, Project Manager on (012) 422-4175.\r\n\r\n\r\nNote: As per Mr. Eyad Gaishawi, the letter was signed and to maintain confidentiality, it was recorded by Division Secretary and was instructed to close this entry without any attachment.', 'Ditch Removal', 'Complete', '2015-03-01', 0, 91, 0, -1, 'For Information Only', '2015-02-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1810, 1845, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1811, 1847, 43, 'According to para 3.8 of SCH-A, “Key personnel as designated in the organization chart shall be assigned to the WORK and shall not be removed or reassigned without SAUDI ARAMCO''s prior written permissionâ€. In any case for a key position like the company representative, adequate advance information shall be sent to SAPMT so that project activities are not adversely affected at this critical stage of the project. It is noticed that the company representative has already demobilized from the site without SAPMT acceptance, which is a breach of contract and not acceptable.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Senior Project Engineer (A) at 012 422-4423.\r\n', 'Company Representative', 'Complete', '2015-01-27', 0, 87, 0, 46, 'L-1294/15', '2015-01-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1812, 1848, 43, 'No Comments, For Information Only', 'Progress Meetings', 'Complete', '2015-02-11', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1813, 1846, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/14/0982 dated December 30, 2014 and has no objection with the following comment:\r\n\r\n•	It is observed that all reported non-conformances and observations are held open for much longer durations than necessary. IC is urged to address them on urgent basis.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Logbook Entries', 'Complete', '2015-02-02', 0, 25, 0, 87, 'L-1359/15', '2015-02-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1814, 1849, 43, 'SAPMT has reviewed the subject submittal dated December 31, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Hydro Test', 'Complete', '2015-01-12', 0, 25, 0, 89, 'L-1304/15', '2015-01-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1815, 1850, 43, 'SAPMT has reviewed the subject submittal dated January 03, 2015 and has the following comments:\r\n\r\n1.	Mr. Tanveer Iqbal is approved as “QC Supervisor – Civilâ€ for “KAUST-Perimeter Security Systemsâ€ project BI-25-00026-0001.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Supervisor', 'Complete', '2015-01-12', 0, 25, 0, 46, 'L-1301/15', '2015-01-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1816, 1851, 43, 'SAPMT has reviewed the subject submittal dated January 03, 2015 and has the following comment.\r\n\r\n•	Mr. Muhammad Mohsin is rejected as he could not prove his competency in his discipline.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Mohsin', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1345/15', '2015-01-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1817, 1852, 43, 'No Comments, For Information Only', 'Inspection Schedule', 'Complete', '2015-01-13', 0, 25, 0, -1, 'For Information Only', '2015-01-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1818, 1854, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1819, 1857, 43, 'SAPMT has reviewed the subject submittal dated January 04, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Sliding Gate', 'Complete', '2015-01-12', 0, 25, 0, 89, 'L-1307/15', '2015-01-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1820, 1858, 43, 'IC is urged to provide separate method statements for the following:\r\n\r\n1.	Backfilling the lagoon area for the security corridor.\r\n2.	Mitigation of mangroves in the lagoon area.\r\nThe above documents shall be submitted before January 11, 2015 to SAPMT for approval.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Lagoon Area', 'Complete', '2015-01-06', 0, 25, 0, 89, 'L-1293/15', '2015-01-06', 0, '', '', '', '', '');

INSERT INTO `submittal` VALUES(1822, 1860, 43, 'SAPMT has reviewed the subject submittal dated January 04, 2015 and has no objection with the following comment:\r\n\r\n•	The applicable 9com for this material is 6000000572.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Canopy', 'Complete', '2015-01-12', 0, 25, 0, 89, 'L-1303/15', '2015-01-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1823, 1861, 43, 'SAPMT has reviewed the subject submittal dated January 04, 2015 and has no objection with the following comments:\r\n\r\n1.	Ensure the equipment is the latest model.\r\n2.	Ensure the equipment meets FSD and HCIS requirements.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'MIDS', 'Complete', '2015-01-13', 0, 25, 0, 89, 'L-1309/15', '2015-01-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1824, 1853, 43, 'No Comments, For Information Only', 'No Comments', 'Complete', '2015-01-27', 0, 25, 0, -1, 'For Information Only', '2015-01-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1825, 1855, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/15/0988 dated January 04, 2015 and has the following comments:\r\n\r\n1.	Mr. Joseph Buban Navarro is permanently approved as “QC Inspector (Civil)â€ for “KAUST – Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke this permanent approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Joseph Buban', 'Complete', '2015-02-01', 0, 25, 0, 87, 'L-1348/15', '2015-01-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1826, 1856, 43, 'SAPMT has reviewed the subject submittal dated January 04, 2015 and has the following comments:\r\n\r\n1.	Mr. Michael Layog Solis is conditionally approved as “Safety Officerâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Safety Officer Marzouqi', 'Complete', '2015-01-08', 0, 25, 0, 89, 'L-1295/15', '2015-01-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1827, 1862, 43, 'SAPMT has reviewed the subject submittal dated January 04, 2015 and has the following comments:\r\n\r\n1.	Mr. Tanveer Iqbal is approved as “QC Inspector – Communicationâ€ for “KAUST-Perimeter Security Systemsâ€ project BI-25-00026-0001.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Inspector', 'Complete', '2015-01-12', 0, 25, 0, 89, 'L-1302/15', '2015-01-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1828, 1863, 43, 'The chain-link fence in the north between the existing security fence and KAM road is an essential part of KAM road, which was planned to be completed by Nov. 30, 2014. Despite the delay, IC has not been able to start this activity and procure the necessary materials to ensure that this activity is completed on time in order for KAM road to be delivered to KASUT. \r\n\r\nMost recent proposed plan submitted by IC to complete KAM road requires the chain-link fence activity to start on January 10, 2015 and as of to date, no materials are received on site, which shows this activity to be delayed again. IC is urged to procure the materials immediately and store them on site and start civil works to ensure no further delays for this activity.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Chain Link Fence', 'Complete', '2015-01-08', 0, 25, 0, 89, 'L-1296/15', '2015-01-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1829, 1864, 43, 'SAPMT has reviewed the subject submittal dated January 04, 2015 and has no objection with the following comment:\r\n\r\n•	Ensure that a comprehensive Method Statement for site installation is provided separately in line with the Manufacturer’s recommendations.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Vessel Barrier', 'Complete', '2015-01-14', 0, 25, 0, 87, 'L-1314/15', '2015-01-14', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1830, 1865, 43, 'SAPMT has reviewed the subject submittal dated January 05, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Baggage X-Ray', 'Complete', '2015-01-14', 0, 25, 0, 87, 'L-1311/15', '2015-01-14', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1831, 1866, 43, 'SAPMT has reviewed the subject submittal dated December 30, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Z-Portal System', 'Complete', '2015-01-14', 0, 25, 0, 87, 'L-1312/15', '2015-01-14', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1832, 1867, 43, 'SAPMT has reviewed the subject submittal dated January 05, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'ENS', 'Complete', '2015-01-14', 0, 25, 0, 87, 'L-1310/15', '2015-01-14', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1833, 1868, 43, 'SAPMT has reviewed the subject submittal dated January 05, 2015 and has no objection with the following comment:\r\n\r\n•	It is IC responsibility to ensure that all systems/equipment comply with FSD, PE-000005 and Appendix H.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Server, Workstation', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1325/15', '2015-01-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1834, 1869, 43, 'SAPMT has reviewed the subject submittal dated January 05, 2015 and has no objection with the following comment:\r\n\r\n•	IC to ensure compliance with SOW PE-000002 and Appendix H.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n \r\n', 'Server Cabinet', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1324/15', '2015-01-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1835, 1870, 43, 'SAPMT has reviewed the subject submittal dated January 25, 2015 and has no objection. However it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Saudization for December 2014', 'Complete', '2015-02-01', 0, 91, 0, 87, 'L-1344/15', '2015-01-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1836, 1871, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1837, 1872, 43, 'SAPMT has reviewed the subject submittal dated January 01, 2015 and has the following comments:\r\n\r\n1.	The Audit and Corrective Action Report, indicating each CAR status must be included in the report (refer to Schedule-Q para 7.7.1 b).\r\n2.	The rejected electrical cable post marker shall be included in the list of rejected materials received at job site (refer to Schedule-Q para 7.7.1 b).\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'MQMR', 'Complete', '2015-01-14', 0, 25, 0, 87, 'L-1313/15', '2015-01-14', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1838, 1873, 43, 'SAPMT has reviewed the subject submittal dated January 04, 2015 and has been rejected with the following comment:\r\n\r\n•	The Saudi Iron & Steel 30000509 is not an approved manufacturer for reinforced steel bar. (List of approved manufacturers is attached)\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Steel Bar', 'Complete', '2015-01-12', 0, 25, 0, 89, 'L-1308/15', '2015-01-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1839, 1874, 43, 'In reference to SAPMT letter no. K&TPD/KRP&SFPD/SF/L-1268/14 dated December 25, 2014; IC is urged to complete and close all EIL items by January 31, 2015.\r\n\r\nThe advance copy of EIL list has already been provided to IC via emails dated December 17, 2014 and December 21, 2014. It is advised to dedicate a person to coordinate for closure of all items on urgent basis.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'PMCC Mater EIL List', 'Complete', '2015-01-09', 0, 25, 0, 89, 'L-1297/15', '2015-01-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1840, 1875, 43, 'No Comments, For Information Only', 'Air Conditioning', 'Complete', '2015-02-05', 0, 25, 0, -1, 'For Information Only', '2015-02-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1841, 1876, 43, 'SAPMT has reviewed the subject submittal dated January 07, 2015 and has been rejected with the following comments:\r\n\r\n1.	Consider submitting each material separately.\r\n2.	9com numbers and material descriptions are incorrect.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'OSP Materials', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1322/15', '2015-01-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1842, 1877, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1843, 1878, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1844, 1879, 43, 'SAPMT has reviewed the subject submittal dated January 07, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'CCTV', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1323/15', '2015-01-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1845, 1880, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-02-10', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1846, 1881, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-02-10', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1847, 1882, 43, 'SAPMT has reviewed the subject submittal dated January 11, 2015 and has the following comments:\r\n\r\n1.	Mr. Adiyeri Muralee Dharan is approved as “QC Inspector – Civil for Communication OSP Worksâ€ for “KAUST – Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Muralee Dharan', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1334/15', '2015-01-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1848, 1883, 43, 'SAPMT has reviewed the subject submittal dated January 12, 2015 and has the following comments:\r\n\r\n1.	Mr. Adel Abdulqader Alsahafi is approved as “Secretary (Client)â€ for “KAUST – Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Adel Abdulqader Secretary Client', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1327/15', '2015-01-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1849, 1884, 43, 'No Comments, For Information Only', 'Progress Meetings', 'Complete', '2015-02-11', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1850, 1885, 43, 'No Comments, For Information Only', 'Progress Meetings', 'Complete', '2015-02-11', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1851, 1886, 43, 'SAPMT has reviewed the subject submittal dated January 12, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'PVC Conduit', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1328/15', '2015-01-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1852, 1887, 43, 'SAPMT has reviewed the subject submittal dated January 10, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Aluminum Door, Window', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1329/15', '2015-01-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1853, 1888, 43, 'SAPMT has reviewed the subject submittal dated January 13, 2015 and has no objection with the following comment:\r\n\r\n•	Ensure that the proposed models are matching and compatible with systems already installed in KAUST.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Biometric Reader', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1331/15', '2015-01-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1854, 1889, 43, 'SAPMT has reviewed the subject submittal dated January 13, 2015 and has no objection with the following comments:\r\n\r\n1.	Correct 9com for copper grounding conductor is 6000000804.\r\n2.	Ensure that the bare conductor is tinned copper, as per construction specification section 16450 para 2.01 A.2.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Bare Copper Conductor', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1320/15', '2015-01-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1855, 1890, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1856, 1891, 43, 'SAPMT has reviewed the subject submittal dated January 15, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Sealant for Expansion Joint', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1347/15', '2015-01-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1857, 1892, 43, 'KAUST concurrence is requested to use existing KAUST MV Network, instead of waiting for SEC2 to be operational in order to energize the KAM access road lighting system.\r\n\r\nThe suggested solution is elaborated in the attached presentation and also with the help of ETAP studies/ short circuit calculations.\r\n\r\nShould you have any question, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) on (012) 422 4423.\r\n', 'Power Source KAM Road Lighting', 'Complete', '2015-01-27', 0, 87, 0, 46, 'L-1319/15', '2015-01-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1858, 1893, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW15/1016 dated January 18, 2015 and has the following comments:\r\n\r\n1.	Mr. Leonardo P. Rodrigo Jr. is approved as “QC Supervisor - Electrical, Instrumentation & Communicationâ€ for “KAUST – Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Supervisor, Leonardo', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1326/15', '2015-01-21', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1859, 1894, 43, 'SAPMT has reviewed the subject submittal dated January 11, 2015 and has the following comments:\r\n\r\n1.	Mr. Hermie A. Antonio is approved as “QC Inspector – Civil for Communication OSP Worksâ€ for “KAUST – Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Inspector', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1318/15', '2015-01-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1860, 1895, 43, 'SAPMT has reviewed the subject submittal dated January 11, 2015 and has no objection with the following comment:\r\n\r\n•	Contractor shall send this report to SAIR also.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Quality Audit Report', 'Complete', '2015-01-21', 0, 25, 0, 87, 'L-1321/15', '2015-01-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1861, 1896, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-02-11', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1862, 1897, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1863, 1898, 43, 'SAPMT has reviewed the subject submittal dated January 17, 2015 and has no objection. However it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Footing Detail', 'Complete', '2015-02-01', 0, 25, 0, 87, 'L-1351/15', '2015-01-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1864, 1899, 43, 'SAPMT has reviewed the subject submittal dated January 19, 2015 and has no objection with the following comments:\r\n\r\n•	Ensure that the Transmission Link Loss Calculation will be provided with an acceptable range.\r\n•	FOC shall be tested with Power Meter and OTDR.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Rectification of FOC', 'Complete', '2015-02-01', 0, 25, 0, 87, 'L-1349/15', '2015-01-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1865, 1900, 43, 'The paint work done by IC as a sample was not acceptable due to the long time (more than two months) IC took to prepare the sample, reflecting that delays will happen to complete the rest of the activities. Thus paint work will not form an extra work to this contract. IC is urged to provide a method statement for removing the paint work from the samples and submit a bill of quantities to process the change order for paint removal.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Wall Painting', 'Complete', '2015-01-27', 0, 25, 0, 87, 'L-1336/15', '2015-01-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1866, 1901, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/15/1017 dated January 18, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'LBE Closing 271', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1340/15', '2015-01-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1867, 1902, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1868, 1903, 43, 'SAPMT has reviewed the subject submittal dated January 21, 2015 and has the following comments:\r\n\r\n1.	Mr. Arunraj Dhanaraj is conditionally approved as “QC Inspector – Civil (Precast)â€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Arunraj Dhanaraj', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1339/15', '2015-01-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1869, 1905, 43, 'SAPMT has reviewed the subject submittal dated January 14, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Irrigation System', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1341/15', '2015-01-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1870, 1907, 43, 'SAPMT has reviewed the subject submittal dated January 21, 2015 and has been rejected with the following comment:\r\n\r\n•	Mr. Abdul Naveed does not have sufficient formal technical education.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Naveed', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1338/15', '2015-01-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1871, 1909, 43, 'The claim made by IC is rejected due to the following reasons;\r\n\r\n1.	The area between Sta. 13+800 to 14+450 is under KAUST Security and IC has been informed that entering secure areas requires that IC does not create a breach in the security on this Security related project. Referring to clause 3.5 and 3.6 of SCH-B, IC must adhere with its contractual obligations.\r\n2.	A key role like Engineering Manager and establishment of a site design office has been neglected by IC throughout the project (refer to letter no’s. K&TPD/KRP&SFPD/SF/L-140/13, 144/13, 219/13, 253/13, 309/13, 576/14, 746/14 and 1027/14) and thus IC is suffering from delays on various activities due to lack of shop drawings. Still a dedicated role is not established as the current Engineering Manager Mr. Ali Elshayal works only part-time.\r\n3.	An interface drawing was created when Mr. Jun Aquino was working with IC as Engineering Manager and all the interfaces were resolved for area between Sta. 13+800 to 14+450. Since IC changed the Engineering Manager in Sep. 2014 and no action has been taken to carry on the subject activity.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Additional Requirement', 'Complete', '2015-01-27', 0, 25, 0, 87, 'L-1337/15', '2015-01-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1872, 1904, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1873, 1908, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1874, 1906, 43, 'No Comments, For Information Only', 'Progress Meeting', 'Complete', '2015-02-10', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1875, 1910, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1876, 1911, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1877, 1917, 43, 'The endorsement letter from Geotechnical contractor submitted by IC is accepted and investigation can be initiated. Geotechnical file number is 2014/110.\r\n\r\nIC shall ensure that the Geotechnical report resulting from this investigation shall be reviewed and endorsed by IC and the following shall be submitted.\r\n\r\n1. Geotechnical Form SA9866 with section C.\r\n2. Report Reviewed and endorsed by Main contractor.\r\n3. Geotechnical Report.\r\n4. Report Checklist fully completed by Geotechnical contractor   \r\n\r\nWithout the above 4 items, SAPMT will not accept the geotechnical report for review/ acceptance.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Radar Tower Foundation', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1342/15', '2015-01-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1878, 1913, 43, 'SAPMT has reviewed the subject submittal dated January 20, 2015 and has no objection with the following comments:\r\n\r\n1.	Ensure that correct materials as per Saudi Aramco standards are used for conduits or flow lines.\r\n2.	The correct 9com for pipe is 6000000030 with level of inspection (0) and shall be procured through an approved source.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'PVC Pipes SCH 40', 'Complete', '2015-02-04', 0, 25, 0, 87, 'L-1350/15', '2015-01-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1879, 1914, 43, 'SAPMT has reviewed the subject submittal dated January 26, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Conduit Pipe', 'Complete', '2015-02-10', 0, 25, 0, 87, 'L-1368/15', '2015-02-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1880, 1916, 43, 'SAPMT has reviewed the subject submittal dated January 26, 2014 and has no objection with the following comments:\r\n\r\n1.	The ballast is approved while IC shall submit the specifications for the concrete base separately.\r\n2.	It is IC’s responsibility to ensure that the excavations and backfill with ballast are done according to manufacturer’s recommendations, so that the base and the sonar stand are stable and upright.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Ballast, Sonar Installation', 'Complete', '2015-02-11', 0, 25, 0, 87, 'L-1361/15', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1881, 1918, 43, 'SAPMT has reviewed the subject submittal dated January 24, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Wiring Devices', 'Complete', '2015-02-04', 0, 25, 0, 87, 'L-1362/15', '2015-02-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1882, 1912, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-02-11', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1883, 1915, 43, 'SAPMT has reviewed the subject submittal dated January 21, 2015 and has the following comments:\r\n\r\n1.	Mr. Adnan Shah is approved as “Safety Officerâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Adnan Shah', 'Complete', '2015-01-31', 0, 25, 0, 87, 'L-1343/15', '2015-01-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1884, 1919, 43, 'SAPMT has reviewed the subject submittal dated January 27, 2015 and has no objection with the following comment:\r\n\r\n•	Saudi Metal Coating Co. 30000873 is limited to sizes from 8mm to 32mm with length up-to 12m.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Bar Reinforcing Steel', 'Complete', '2015-02-02', 0, 25, 0, 87, 'L-1355/15', '2015-02-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1885, 1920, 43, 'SAPMT has reviewed the subject submittal dated January 28, 2015 and has the following comments:\r\n\r\n1.	The jogging and biking tracks shall start from the intersection at existing sliding gate and not from the Jersey barrier at start of road 2.\r\n2.	The expansion joint shall be filled with backer rod and sealant and not with filler board.\r\n3.	Biking track shall pass on the valve boxes with a slope 3% to 5%.\r\n4.	Sharp bends/ turns shall be avoided to allow a biking speed of 30kmph according to AASHTO guidelines for biking tracks.\r\n5.	Shoulders on both sides shall have slopes from original ground to soffit of the select fill and protected with marl where ever necessary as mentioned in Note 7 of KA714497-001.\r\n6.	The Biking track asphalt edges shall be protected or sloped to avoid erosion.\r\n7.	The Biking track shall have a 40 mm binder course and 40 mm wearing course.\r\n8.	The granular base course shall extend 30 cm on both sides of the biking track.\r\n9.	 Provide a separate shop drawing showing guard rails.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Biking, Jogging Track Sections', 'Complete', '2015-02-10', 0, 25, 0, 87, 'L-1366/15', '2015-02-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1886, 1923, 43, 'SAPMT has reviewed the subject letter dated January 29, 2015 and has the following comment:\r\n\r\n•	Provide specific locations and activities where IC requires SAPMT to consider the frequency of FDT points.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.', '', 'Complete', '2015-02-17', 0, 70, 0, 87, 'L-1381/15', '2015-02-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1887, 1924, 43, 'SAPMT has reviewed the subject submittal dated January 25, 2015 and has no objection with the following comments:\r\n\r\n1.	As per submittal the delivery and installation will take 33 weeks which is not matching the recovery schedule submitted by the contractor for approval. The contractor should follow the recovery schedule. \r\n2.	Yamamah Steel Industries Company (10014156) is an Aramco approved vendor and procurement process shall start without further delay.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Yamamah', 'Complete', '2015-02-10', 0, 25, 0, 87, 'L-1371/15', '2015-02-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1888, 1921, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/15/1022 dated January 28, 2015 and has the following comments:\r\n\r\n1.	Mr. Riasat Ali Khan is permanently approved as “QC Inspector – Telecommunication & Securityâ€ for “KAUST – Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke this permanent approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Riasat Ali Khan', 'Complete', '2015-02-04', 0, 25, 0, 87, 'L-1356/15', '2015-02-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1889, 1922, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/15/1018 dated January 19, 2015 and has the following comments:\r\n\r\n1.	Mr. Imran Khan is permanently approved as “QC Inspector – Telecommunication & Securityâ€ for “KAUST – Perimeter Security Systemsâ€ project.\r\n2.	SAPMT reserves the right to revoke this permanent approval based on his unsatisfactory performance during project tenure.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Imran Khan QC Inspector', 'Complete', '2015-02-04', 0, 25, 0, 87, 'L-1357/15', '2015-02-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1890, 1928, 43, 'SAPMT has reviewed the subject submittal dated February 01, 2015 and has no objection with the following comment:\r\n\r\n•	Lifting plan shall be discussed with PMT Safety to avoid any damages or causing extra stresses to concrete.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'Orientation of Visitor Center', 'Complete', '2015-02-11', 0, 25, 0, 87, 'L-1376/15', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1891, 1929, 43, 'SAPMT has reviewed the subject submittal dated February 01, 2015 and has the following comments:\r\n\r\n1.	The recovery plan should recover the schedule within few months.\r\n2.	SAPMT observed that IC did not comply with their recovery plan of some activities.\r\n3.	IC should revisit the recovery schedule based on following comments: \r\n•	Wadi Khulais Box Culvert construction date does not match with dates of the activities.\r\n•	Remaining Fence, Capping and Spikes shall be installed completely at the date of zone completion.\r\n•	Relocation of fence and security system at 0+000 to 1+900 except Pond area should be complete at the end of February 2015.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4423.\r\n', 'Recovery schedule', 'Complete', '2015-02-25', 0, 87, 0, 92, 'L-1394/15', '2015-02-24', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1892, 1927, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-02-10', 0, 25, 0, -1, 'For Information Only', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1893, 1925, 43, 'No Comments, For Information Only', 'Inspection Schedule', 'Complete', '2015-05-23', 0, 25, 0, -1, 'For Information Only', '2015-04-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1894, 1926, 43, 'SAPMT has reviewed the subject letter no. KPSS/SA/B/ANW/14/1021 dated January 31, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'LBE Closing', 'Complete', '2015-02-04', 0, 25, 0, 87, 'L-1360/15', '2015-02-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1895, 1930, 43, 'It has been observed that the de-watering techniques being used by IC at the site of construction of culvert are inadequate to lower the underground water level. The depth of excavation below the water table exceeds the lift capabilities of existing dewatering techniques and the above ground apparatus might interfere with construction. It is IC responsibility to ensure that the recommendations made by the designer, geo-technical consultant and the Aramco CSD are incorporated and best possible means and methods are deployed to meet the site requirements and time schedule. IC is urged to provide calculations to prove that the de-watering systems being used are designed according to the soil conditions and depth of required excavations.\r\n\r\nThe geo-technical investigation provided to IC during bidding stage clearly mentions that the subject area has loose soil. In case IC prefers to improve the soil instead of adopting the adequate de-watering method, such shall be done at no cost to Saudi Aramco.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Dewatering', 'Complete', '2015-02-04', 0, 25, 0, 87, 'L-1363/15', '2015-02-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1896, 1931, 43, 'SAPMT has reviewed the subject submittal dated February 01, 2015 and has no objection with the following comments:\r\n\r\n1.	The spikes should be sharper at the top ends to cause considerable damage to the intruder.\r\n2.	The galvanizing shall be done according to SA standards and according to corrosive environment on site.\r\n3.	The fasteners and their spacing shall be coordinated with precast subcontractor.\r\n4.	A 15m long mockup to be installed for proponent inspection before February 08, 2015.\r\n5.	Ensure there is no deviation from the preliminary designs provided in the IFB.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Spikes', 'Complete', '2015-02-10', 0, 25, 0, 87, 'L-1367/15', '2015-02-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1897, 1932, 43, 'SAPMT has reviewed the subject submittal dated January 31, 2015 and has no objection with the following comments:\r\n\r\n1.	The steel elements such as Bolts, Washers and Plates etc. shall be galvanized as the area is close to sea.\r\n2.	A mock-up for visual inspection and approval shall be provided before delivery of bulk material on site.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Guard Rails', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1410/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1898, 1933, 43, 'SAPMT has reviewed the subject submittal dated February 01, 2015 and has the following comments:\r\n\r\n1.	This material was approved back is September 2014. No alternative submittal shall be approved unless a valid justification is attached.\r\n2.	Ensure that brackets or arms of the lighting pole were coordinated with the lighting fixtures vendor.\r\n3.	Corrosion protection shall be as per ASTM A123. Thickness of galvanization shall be a minimum average of 90 microns as per Saudi Aramco Standard requirements.\r\n4.	Poles shall be designed to withstand wind loading due to a basic wind speed and the gust factor of 1.3 acting on the effective projected area of the pole, bracket, and luminaires.\r\n5.	All components of the pole shall be UL listed or equivalent such as wiring terminal blocks, Fuse Carrier and grounding lugs.\r\n6.	All pole fittings, bolts, nuts and related fittings accessories shall be stainless steel.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'Lighting Pole', 'Complete', '2015-02-11', 0, 25, 0, 87, 'L-1374/15', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1899, 1934, 43, 'SAPMT has reviewed the subject submittal dated January 19, 2015 and has the following comments:\r\n1.	Electrical one line diagram of proposed generator is not matching with generator diagram shown in library drawing P- DD-950114 sht 003.\r\n2.	Incomplete details of Automatic Voltage Regulator, contractor (IC) to provide complete details of Automatic Voltage regulator and shall be in compliance with 17-SAMSS-518 para 08.\r\n3.	Provide the connected load schedule to Generator manufacturer to meet 17-SAMSS-518 para. 7.1.3.\r\n4.	Provide a list of scope matrix for SDEC and ICC and other related sub-contractor/s (Arabian Point Eight) scope of work to ensure that scope will be delivered without room for gap. 17- SAMSS-518 compliance matrix and drawings provided by SDEC has so many notes specifying other/customer to supply.\r\n5.	17-SAMSS-518 para. 7.4.10.5 For Generator bearings has to be cleared without prior approval of NMR-601.\r\n6.	Ensure that scrolling pad is a field proven switch for Generator control panel. 17-SAMSS-518 specifically requires Manual, Auto, Off, Reset switches.\r\n7.	Ensure that equivalent ENGLISH words will be written in all drawings, operation and manuals and related spare part data will be indicated to this NMR.\r\n8.	Compliance to 17-SAMSS-518 Para. 9.2.3 Testing of Genset Breaker is necessary as per Saudi Aramco requirements for Molded Case Circuit breakers using SA P- forms series.\r\n9.	Load site testing using load bank shall be part of the scope without any cost to Saudi Aramco.\r\n10.	The weight of the muffler about 925 kilograms, that will be installed in the roof of the generator building has to be concurred and stamped by SCEC designer.\r\n11.	Provide generator protection required as per SAES-P-116, paragraph 6.0  including controls for auto transfer scheme in the generator cubicle of 13.8KV Switchgear matching with the generator rating\r\n12.	Include generator data as required to finalize the ETAP Study of the project such as positive, negative and zero sequence impedances, negative sequence capability, minimum motoring power, over frequency curves, thermal capability curve, decrement curve and time constants.\r\n13.	Ensure that the neutral grounding for the generator shall be low resistance type as described in ANSI C37.101, Table 1, Grounding Method III (Low Resistance) as per SAES-P-114, paragraph 6.2.2.\r\n14.	Provide Equipment Layout drawing of Generator Room based on the actual dimensions of the Generator Set including Control Panel and accessories to verify if the size of the room as per IFC drawing is adaptable to installed unit with its accessories\r\n15.	Submit shop drawing of foundation details showing the location anchor bolts (if any) based on the dimensions given in the NMR-601 submittal\r\n16.	Include the dummy load specification and catalog in the NMR-601 submittal.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Generator', 'Complete', '2015-02-28', 0, 70, 0, 87, 'L-1411/15', '2015-02-24', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1900, 1935, 43, 'Further to our meeting with you on Wednesday, 11 February 2015, please find attached a list of current obstacles hindering continuous closure of KAUST-Perimeter Security Fence project. Copies of sent letters to KAUST in the past highlighting some of these issues are attached.\r\n\r\nKAUST is kindly requested to provide feedbacks/ directions promptly to those issues to complete the project in timely manner.\r\n\r\nShould you have any question, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) on (012) 422 4423.', 'Obstacles', 'Complete', '2015-02-22', 0, 87, 0, 92, 'L-1380/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1901, 1936, 43, 'In view of the agreed scope of work and quantities for the subject amendment to the contract, please submit your proposal as per attached agreed upon quantities by or before February 09, 2015, at 11:00AM. The proposal shall be submitted in a sealed envelope with the following information printed on the envelope;\r\na.	Number and Title of the Project/ Contract.\r\nb.	Number and Title of Change order\r\nThe envelope shall be deposited at the following location;\r\n\r\n1.	If C.O. value is over SR 3,750,000:		Central Bid Box\r\nSaudi Aramco\r\nNorth Park, Bidg. 2, Dhahran\r\n\r\n2.	If C.O. value is below SR 3,750,000:	KAUST Project Management\r\nRm. 07, Building 100,\r\nSAPMT Site Office, (Thuwal)\r\nSaudi Aramco, Jeddah\r\nIt is your responsibility that all the applicable quantities and units included in the pricing attachment are correct. All costs and expenses incurred by you in preparing your proposal shall be borne solely by you. Your price shall include all resources required to complete the scope of work in all respects to fit the purpose according to applicable standards. It is your responsibility to familiarize yourself with the site conditions. Award of work is contingent upon execution of a formal purchase order by both parties and work shall not commence before a Purchase Order has been issued.\r\nPlease confirm receipt of this letter by a return fax to +966 12 422 4178.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4423.\r\n', 'Bicycle Track', 'Complete', '2015-02-04', 0, 87, 0, 89, 'L-1353/15', '2015-02-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1902, 1937, 43, 'SAPMT has reviewed the subject submittal dated February 01, 2015 and has the following comments:\r\n\r\n1.	Manufacturer’s recommended combinations of products shall be applied as mentioned in Firetard Flame Inhibiting Paint Product Data/ Application.\r\n2.	Consider removing OA 3415 Primer-Sealer Solvent Base as this product is not recommended for Soft or Hardwood surfaces.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Fire Retardant Paint', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1386/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1903, 1938, 43, 'SAPMT has reviewed the subject submittal dated January 26, 2015 and has the following comments:\r\n\r\n1.	IC shall ensure that all boulder accumulation/ spreading is finished before mid-March 2015.\r\n2.	As the boulder spreading progresses near the mangroves, the mangroves can be removed and relocated on either side.\r\n3.	A list of machinery required to finish the activity shall be included to show that the work is completed before mid-March 2015.\r\n4.	IC shall ensure that construction of security corridor with the new and old walls is completed before the end of April 2015.\r\n5.	IC planning department and construction dept. shall closely watch the progress of this activity and update SAPMT on daily basis.\r\n6.	Total volume of boulders required shall be indicated.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Backfilling of Pond', 'Complete', '2015-02-11', 0, 25, 0, 87, 'L-1375/15', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1904, 1939, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1905, 1940, 43, 'SAPMT has reviewed the subject submittal dated February 04, 2015 and has no objection with the following comments:\r\n\r\n1.	Re-schedule of FAT to February 16, 2015 is for Pre-FAT only to check the physical installation of the system, thus as agreed and as per contractor''s proposal to set the FAT date on February 22, 2015 is accepted.\r\n2.	Contractor shall ensure that the system is ready and will comply with all the comments made by KAUST.\r\n3.	Internal testing is highly advised on February 19 & 21, 2015 with SAPMT to ensure system readiness.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'FAT IDAS', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1389/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1907, 1942, 43, 'SAPMT has reviewed the subject submittal dated February 04, 2015 and has no objection.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Eyad E. Al-Gaishawi, Project Engineer at 012 422-4399.\r\n', 'Saudization', 'Complete', '2015-02-17', 0, 91, 0, 87, 'L-1379/15', '2015-02-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1908, 1943, 43, 'SAPMT has reviewed the subject submittal dated February 03, 2015 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Block Work', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1391/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1909, 1944, 43, 'Referring to our letter no. L-1234/14 dated January 12, 2015 where SAPMT requested KAUST acknowledgement for conducting an integrated FAT for IDAS as was agreed during the meeting on December 30, 2014 held between KAUST Projects Department, Security Department, Contractor and SAPMT. This activity has been postponed for the second time due to no acknowledgement from KAUST to participate. The procurement of cameras depends on the success of this FAT and KAUST acknowledgement shall be much appreciated.\r\n\r\nPlease confirm the attendance of your representatives and should you have any question, contact Ahmed S. Khogeer, Sr. Project Engineer (A) on (012) 422 4423.\r\n', 'IDAS FAT', 'Complete', '2015-02-09', 0, 87, 0, 92, 'L-1369/15', '2015-02-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1910, 1945, 43, 'IC agreed to handover the works on the precast wall and chain link fence from ST 0+00 to St 2+250 by February 15, 2015, except the lagoon while the lagoon is to be backfilled by end of March 2015.\r\n\r\nIt is observed that the works are not progressing as they should and meeting the promised target seems unachievable unless adequate resources are employed on urgent basis.\r\n\r\nThe earthworks are lagging behind, the speed of boulder accumulation for the lagoon is unacceptable and backfilling around placed foundations is very slow.\r\n\r\nIC is urged to take necessary steps as agreed to avoid any delays.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n \r\n', 'North Works', 'Complete', '2015-02-09', 0, 25, 0, 87, 'L-1370/15', '2015-02-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1911, 1946, 43, 'SAPMT has reviewed the subject submittal dated February 04, 2015 and has the following comments:\r\n\r\n1.	All coordinate to be verified and confirmed by Aramco surveyor with comparison from IFC and SD drawings to avoid misalignment of the buildings. (Refer to note by designer and concur on the drawings SD-FCC-847025/75-03, SD-FCC-847075-03 and SD-FCC-847118-03).\r\n2.	The Hook length shall be as mentioned in the general notes drawing VA-846498 with min. 310 mm for db=16 mm …etc.\r\n3.	The concrete cover shall be as per the general note VA-846497.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Guard Houses', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1393/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1912, 1947, 43, 'The subject matter is conveyed through attached letter # 1378.', 'EIL Closing', 'Complete', '2015-02-18', 0, 25, 0, -1, 'L-1378/15', '2015-02-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1913, 1948, 43, 'SAPMT has reviewed the subject submittal dated January 27, 2015 and has no objection with the following comments:\r\n\r\n1.	Ensure the correct diameter of CT to pass through 3CX185mm2 MV cable.\r\n2.	Attach copy of characteristics curve for potential transformer and protective relays.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'NMR 602, Switchgear', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1390/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1914, 1949, 43, 'SAPMT has reviewed the subject submittal dated February 07, 2015 and has no objection with the following comment:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	IL no	Description	9com	Level of Inspection	STATUS	MANUFACTURER\r\n25-00026	PR	RP-032	NA	Bar Reinforcing Coated Epoxy	6000000684	One (1) 	Approved with comments 	SAUDI METAL COATING COMPANY \r\nID no. 30000873\r\n\r\n•	The manufacturer is approved for Bar Sizes of 8mm to 32mm with length up-to 12m.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.', 'Bar, Reinforcing', 'Complete', '2015-02-11', 0, 25, 0, 87, 'L-1373/15', '2015-02-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1915, 1950, 43, 'SAPMT has reviewed the subject submittal dated February 05, 2015 and has no objection with the following comments:\r\n\r\n1.	Ensure the dia of anchor bolts is 25mm.\r\n2.	Galvanization shall be as per applicable Saudi Aramco standards.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Patrol Road Foundation', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1392/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1916, 1951, 43, 'No Comments, For Information Only', 'MQMR January 2015', 'Complete', '2015-02-18', 0, 70, 0, -1, 'For Information Only', '2015-02-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1917, 1952, 43, 'SAPMT has reviewed the subject submittal dated February 10, 2015 and has no objection with the following comments:\r\n\r\n1.	Mr. Macaspac, Frank Silvester A is conditionally approved as “Safety Officerâ€ for three (3) months’ probation.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Macaspac Frank, Safety officer', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1385/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1918, 1953, 43, 'SAPMT has reviewed the subject submittal dated February 08, 2015 and has the following comments:\r\n\r\n•	The procedure shall be revised in compliance to KAUST comments dated February 16, 2015 as per below additional requirements: \r\n1.	The FAT is for complete system testing and not by components.\r\n2.	The test shall include the viewing, recording and alarm management, masking in and masking out of alarms, and GUI/mapping.\r\n3.	The algorithm of detection shall be done during day, day to evening and evening to night with flash lights and considering camera resolution and stabilization.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'FAT IDAS', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1387/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1919, 1954, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1920, 1955, 43, 'SAPMT has reviewed the subject submittal dated February 04, 2015 and has no objection with the following comment:\r\n\r\n•	Battery layout in Document No. 1140479001/00 shall be incorporated within JFCC building battery room size and ensure that required clearance will be met.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Switchgear', 'Complete', '2015-02-25', 0, 25, 0, 87, 'L-1399/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1921, 1956, 43, 'SAPMT has reviewed the subject submittal dated February 08, 2015 and has the following comments:\r\n\r\n1.	Drawing revision needs to be updated, insert cloud to highlight the changes.\r\n2.	Ensure that the new size and sets of cable from Package Substations to MDP-01 of Generator building 1 and 2, including the upgraded size of PS-01A and PS-01B were calculated using ETAP.\r\n3.	The lighting arrangement shall give a minimum of 300 lux in all rooms of Generator Building, and 100 lux for emergency lighting, during normal power off as per SAES P-123 table 4.\r\n4.	Ensure that two grounding connections of the Switchgear, Generator and Neutral Grounding Resistor etc. operating greater than 1000 volts  to the grounding electrodes as per SAES P-111 9.14.2\r\n5.	Changes to the upgrade of two (2) Package Substations, two (2) Main Distribution panels, related MV and LV cables, lighting fixtures and accessories and all related civil works, shall be subject for variation order, in case that the final 2500 KW Generators will not use additional electrical requirement for cooling purposes.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Switchgear 13.8KV', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1388/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1922, 1957, 43, 'In view of the agreed scope of work and quantities for the subject amendment to the contract, please submit your proposal as per attached agreed upon quantities by or before February 15, 2015, at 11:00AM. The proposal shall be submitted in a sealed envelope with the following information printed on the envelope;\r\n\r\na.	Number and Title of the Project/ Contract.\r\nb.	Number and Title of Change order\r\n\r\nThe envelope shall be deposited at the following location;\r\n\r\n1.	If C.O. value is over SR 3,750,000:		Central Bid Box\r\nSaudi Aramco\r\nNorth Park, Bldg. 2, Dhahran\r\n\r\n2.	If C.O. value is below SR 3,750,000:	KAUST Project Management\r\nRm. 07, Building 100\r\nSAPMT Site Office, (Thuwal)\r\nSaudi Aramco, Jeddah\r\nIt is your responsibility that all the applicable quantities and units included in the pricing attachment are correct. All costs and expenses incurred by you in preparing your proposal shall be borne solely by you. Your price shall include all resources required to complete the scope of work in all respects to fit the purpose according to applicable standards. It is your responsibility to familiarize yourself with the site conditions. Award of work is contingent upon execution of a formal purchase order by both parties and work shall not commence before a Purchase Order has been issued.\r\n\r\nPlease confirm receipt of this letter by a return fax to +966 12 422 4178.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4423.\r\n', 'Quotation, Street Lights', 'Complete', '2015-02-11', 0, 87, 0, 92, 'L-1354/15', '2015-02-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1923, 1958, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1924, 1959, 43, 'SAPMT has reviewed the subject submittal dated February 10, 2015 and has the following comments:\r\n\r\n1.	Mr. Khalid Ali Murudkar is approved as “QA Managerâ€ for “KAUST – Perimeter Security Systemsâ€ project (BI-25-00026).\r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance during project tenure.\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.\r\n', 'QA Manager', 'Complete', '2015-02-17', 0, 70, 0, 87, 'L-1382/15', '2015-02-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1925, 1960, 43, 'SAPMT has reviewed the subject submittal dated February 10, 2015 and has been rejected with the following comments:\r\n\r\n1.	Reflect changes also on transformer secondary section as per existing cable size.\r\n2.	Consider providing this Electrical One line diagram together with the Shelter #2 of SONAR and RADAR installation submittal package.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Sonar Panel Board', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1383/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1926, 1961, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-02-18', 0, 70, 0, -1, 'For Information Only', '2015-02-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1927, 1962, 43, 'SAPMT has reviewed the subject submittal dated February 04, 2015 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Paint for Buildings', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1405/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1928, 1963, 43, 'The exception items for KAM access road were sent to IC in December 2014 and a closing date of January 30, 2015 was scheduled via letter no. K&TPD/KRP&SFPD/SF/L-1297/15 dated January 8, 2015. IC had agreed to this deadline and thus such date was conveyed to the proponent. The deadline has far surpassed and despite daily reminders from SAPMT, IC has still been unable to close 70 “YESâ€ items and 80 “Noâ€ items out of a total of 208 EIL items. IC is requested to prosecute WORK completion with diligence and dispatch so that the Critical Milestone Dates and Scheduled Completion Date are met and Exception Items are promptly completed or corrected according to para 9.1 of SCH-A.\r\n\r\nThe schedule completion date for KAM access road was November 30, 2014. To avoid any further delays, IC is requested to close all EIL items on February 20, 2015. It is achievable only if IC takes immediate action for the following;\r\n\r\n1.	Increase resources and deliver materials to complete irrigation systems \r\n2.	Increase resources and deliver materials to complete energization of lighting poles\r\n3.	Increase manpower to install chain link fence\r\n4.	Expedite earthworks for installing the old wall \r\n5.	Provide and compact select fill around foundations of the new wall\r\n6.	Start the biking track second layer of asphalt\r\n7.	Start installing cat eyes on the road\r\n8.	Start installing directional boards\r\n\r\nIC is urged to ensure that the target dates for closing EIL items are met so that the KAM road can be handed over to the proponent as mutually agreed.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4423.', 'EIL Items KAM', 'Complete', '2015-02-15', 0, 87, 0, 92, 'L-1378/15', '2015-02-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1929, 1964, 43, 'SAPMT has reviewed the subject submittal dated February 10, 2015 and has no objection with the following comments:\r\n\r\n1.	HSS/Pipes shall confirm to ASTM A500 Grade B or ASTM A53 Grade B.\r\n2.	Nodes shall confirm to BS EN 10083 C45 or equivalent.\r\n3.	Cones shall confirm to ASTM A668 Class B or BS EN 10083 C30.\r\n4.	Bolts shall confirm to ASTM A325.\r\n5.	Sleeves shall confirm to BS EN 10083 C45 or equivalent.\r\n6.	Clearly define the scope of work for M/s. Yamamah to avoid unnecessary conflicts and rework.\r\n7.	Verify the all dimension given by M/s. Yamamah with the approved IFC.\r\n8.	All relevant material shall be approved prior to start the work.\r\n9.	Provide the shop drawing separately to clarify the changes for work to proceed.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Space Frames', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1406/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1930, 1965, 43, 'SAPMT has reviewed the subject submittal dated February 10, 2015 and has no objection:\r\n\r\nBI	Transmittal Type	Transmittal Ref. #	IL no	Description	9com	Level of Inspection	Status	Manufacturer\r\n25-00026	PR	RP-033	NA	PVC Pipe SCH 40	6000000030	Zero(0)	Approved	New Products Industries (NEPRO)\r\nID: 30000736\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4706.', 'PVC Pipe SCH 40', 'Complete', '2015-02-22', 0, 70, 0, 87, 'L-1384/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1931, 1966, 43, 'No Comments, For Information Only', 'Progress Meeting', 'Complete', '2015-02-18', 0, 70, 0, -1, 'For Information Only', '2015-02-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1932, 1967, 43, 'SAPMT has reviewed the subject submittal dated February 08, 2015 and has no objection with the following comments:\r\n\r\n•	Ensure that the specification of the bag can withstand underwater and to be securely close to prevent water penetration.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Sand Bag for Sonar Cable', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1409/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1933, 1968, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1934, 1969, 43, 'SAPMT has reviewed the subject submittal dated February 05, 2015 and has the following comments:\r\n\r\n1.	Provide clear HVAC layout and equipment schedule to check the model of approved units.\r\n2.	Specification requires discharge air upward but the proposed units are with side discharge.\r\n3.	Specification requires shutoff valves with seat connections but the proposed units are not equipped with these valves.\r\n4.	Specification requires class “Fâ€ insulation for condenser fan motor but the proposed insulation is class “Bâ€.\r\n5.	Specification requires R-134a but the proposed units by manufacturer are with R22 Refrigerant.\r\n6.	Compliance sheet indicates fins of both copper and aluminum. Specify that aluminum fins will be used.\r\n7.	IC and Zamil reply regarding copper fin – copper coil is conflicting, clarify that condenser coil shall be copper tube-copper fins.\r\n8.	Outdoor unit shall be constructed with galvanized steel and coated with powder coating paint.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'AC Unit', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1416/15', '2015-02-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1935, 1970, 43, 'IC is urged to refer to the management meeting held on February 10, 2015 to discuss the project progress slippage and procurement delays. As agreed in the meeting IC is requested to prepare a presentation showing the project achievements and bottlenecks and a road map to recover from the existing slippage. Quantifiable milestones like South Culvert, Gate 2 buildings, Gate 3 buildings, Gate 2 infrastructure, Gate 3 infrastructure, K9 wall, K12 wall, relocated wall, relocated IDAS, New IDAS and Lagoon etc. shall be included in the road map to project completion. This presentation will be made in the next management meeting in two weeks, where exact date and time will be intimated.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4423.\r\n', 'Management Meetings', 'Complete', '2015-02-17', 0, 87, 0, 92, 'L-1372/15', '2015-02-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1936, 1971, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1937, 1972, 43, 'SAPMT has reviewed your subject submittal dated March 11, 2015 and has rejected with the following comment;\r\n\r\n•	The construction of Test Manifold with PVC is not recommended as per the advice of inspection Engineering Standards Committee Chairman. \r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Hydro Test Manifold', 'Complete', '2015-05-26', 0, 70, 0, 87, 'L-1453/15', '2015-03-24', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1938, 1973, 43, 'SAPMT has reviewed the subject submittal dated February 11, 2015 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'PVC Conduit Spacers', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1403/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1939, 1974, 43, 'SAPMT has reviewed the subject letter dated February 15, 2015 and has the following comments:\r\n\r\n1.	Mr. Joseph Buban Navarro is conditionally approved as “QC Inspector of Precast Facilityâ€ for three (3) months.\r\n2.	SAPMT reserves the right to revoke this conditional approval based on his unsatisfactory performance.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Joseph Buban', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1414/15', '2015-02-24', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1940, 1975, 43, 'SAPMT has reviewed the subject submittal dated February 12, 2015 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Manhole Cover', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1401/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1941, 1976, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1942, 1977, 43, 'SAPMT has reviewed the subject submittal dated February 03, 2015 and has no objection with the following comments:\r\n\r\n1.	Ensure that all copies to be provided for Non Material Requirements such as vendor drawings, catalogs and shop drawings for the package substations were readable. \r\n2.	Ensure the single line diagram and protection system of proposed Package Substations shall be in compliance with Project Specifications, IFC VA-846412 Sht 001, 002 and SEC standards. \r\n3.	Ensure to select the correct type of Trip functions from catalogue for LV Main Circuit Breaker which is to be based on IFC VA-846412 Sht 001, 002. \r\n4.	Ensure to select the accurate internal dimensions of CT’s which can accommodate the size of cables.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Package Substation', 'Complete', '2015-03-02', 0, 70, 0, 87, 'L-1424/15', '2015-03-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1944, 1979, 43, 'SAPMT has reviewed the subject submittal dated February 12, 2015 and has the following comment:\r\n\r\n•	Attach SATIP-T-744-01 and SAIC-T-5608 Communication Facilities - Security IDAS/CACS for Installation and Pre-commissioning Activity.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'IDAS', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1400/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1946, 1981, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1947, 1982, 43, 'SAPMT has reviewed the subject submittal dated February 17, 2015 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Pfeifer Polyamide Socket', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1407/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1948, 1983, 43, 'SAPMT has reviewed the subject submittal dated February 17, 2015 and has no objection with the following comment:\r\n\r\n•	Consider bringing EMS locator to test all EMS installed in the project are working.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686', 'Marker System', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1408/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1949, 1984, 43, 'SAPMT has reviewed the subject submittal dated February 17, 2015 and has no objection. It is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Sprinklers', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1417/15', '2015-02-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1950, 1985, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1951, 1986, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1952, 1987, 43, 'In view of the agreed scope of work and quantities for the subject amendment to the contract, please submit your proposal as per attached agreed upon quantities by or before 23rd February 2015, at 11:00AM. The proposal shall be submitted in a sealed envelope with the following information printed on the envelope;\r\na.	Number and Title of the Project/ Contract.\r\nb.	Number and Title of Change order\r\nThe envelope shall be deposited at the following location;\r\n\r\n1.	If C.O. value is over SR 3,750,000:		Central Bid Box\r\nSaudi Aramco\r\nNorth Park, Bldg. 2, Dhahran\r\n\r\n2.	If C.O. value is below SR 3,750,000:	KAUST Project Management\r\nRm. 08, Bldg. 100\r\nSAPMT Site Office, (Thuwal)\r\nSaudi Aramco, Jeddah\r\nIt is your responsibility that all the applicable quantities and units included in the pricing attachment are correct. All costs and expenses incurred by you in preparing your proposal shall be borne solely by you. Your price shall include all resources required to complete the scope of work in all respects to fit the purpose according to applicable standards. It is your responsibility to familiarize yourself with the site conditions. Award of work is contingent upon execution of a formal purchase order by both parties and work shall not commence before a Purchase Order has been issued.\r\nPlease confirm receipt of this letter by a return fax to +966 12 422 4178.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4423.', 'Barhi Trees, Irrigation Controls', 'Complete', '2015-02-22', 0, 87, 0, 92, 'L-1395/15', '2015-02-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1953, 1988, 43, 'SAPMT instructs ICC to cease any works related to the Ministry of Interior (MOI) security wall that interfaces with the MOI property. All available resources shall be re-distributed to other on-going activities. SAPMT will arrange a meeting with ICC to agree and sign a detailed Scope of work and MTO. A contract change request with a brief scope of work is attached for ICC signature. \r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4423.', 'Change Request', 'Complete', '2015-02-22', 0, 87, 0, 92, 'L-1396/15', '2015-02-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1954, 1989, 43, 'SAPMT has reviewed the subject submittal dated February 19, 2015 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Back Flow Preventer', 'Complete', '2015-02-25', 0, 70, 0, 87, 'L-1412/15', '2015-02-24', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1955, 1990, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1956, 1991, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1957, 1992, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1960, 1995, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1961, 1996, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1962, 1997, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1963, 1998, 43, 'SAMPT has reviewed the subject submittal dated February 22, 2015 and has the following comments;\r\n\r\n1.	Provide the latest Raw Material Test Report.\r\n2.	Submit Job Mix Formula Test Reports for Bituminous Wearing Course and Bituminous Base Course for review and evaluation.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Asphalt Mix Design', 'Complete', '2015-05-26', 0, 70, 0, 87, 'L-1437/15', '2015-03-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1964, 1999, 43, 'SAPMT has reviewed the subject submittal dated February 26, 2015 and has the following comments:\r\n\r\n•	The corrective actions are not sufficient and should contain the following:\r\n\r\n1.	Revised method statement or Safe Work Procedure.\r\n2.	Revised Risk Assessment.\r\n3.	Retraining of drivers, spotters and supervisors (submit proof thereof).\r\n4.	Toolbox talks addressing such matters.\r\n5.	Proof that required spotters are equipped and sufficient number of spotters are assigned to the job.\r\n\r\n•	SAPMT strongly advise to implement the corrective measures to avoid such repeated incidents. \r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Lighting Pole', 'Complete', '2015-05-26', 0, 70, 0, 87, 'L-1422/15', '2015-03-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1965, 2000, 43, 'No Comments, For Information Only', 'Near Miss', 'Complete', '2015-02-28', 0, 70, 0, -1, 'For Information Only', '2015-03-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1966, 2001, 43, 'SAPMT has reviewed the subject submittal dated February 24, 2015 and has no objection. It is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Protective Waterproofing', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1418/15', '2015-02-25', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1967, 2002, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1968, 2003, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1969, 2004, 43, 'In view of the agreed scope of work and quantities for the subject amendment to the contract, please submit your proposal as per attached agreed upon quantities by or before 25th February 2015, at 11:00AM. The proposal shall be submitted in a sealed envelope with the following information printed on the envelope;\r\na.	Number and Title of the Project/ Contract.\r\nb.	Number and Title of Change order\r\nThe envelope shall be deposited at the following location;\r\n\r\n1.	If C.O. value is over SR 3,750,000:		Central Bid Box\r\nSaudi Aramco\r\nNorth Park, Bidg. 2, Dhahran\r\n\r\n2.	If C.O. value is below SR 3,750,000:	KAUST Project Management\r\nRm. 08, Building 100\r\nSAPMT Site Office, (Thuwal)\r\nSaudi Aramco, Jeddah\r\nIt is your responsibility that all the applicable quantities and units included in the pricing attachment are correct. All costs and expenses incurred by you in preparing your proposal shall be borne solely by you. Your price shall include all resources required to complete the scope of work in all respects to fit the purpose according to applicable standards. It is your responsibility to familiarize yourself with the site conditions. Award of work is contingent upon execution of a formal purchase order by both parties and work shall not commence before a Purchase Order has been issued.\r\nPlease confirm receipt of this letter by a return fax to +966 12 422 4178.', 'Integration of Roads', 'Complete', '2015-02-26', 0, 87, 0, 92, 'L-1398/15', '2015-02-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1970, 2005, 43, 'SAPMT conducted a major safety inspection of IC and subcontractor site offices and precast factory yards on February 02, 2015 and found over 50 deviations as per attached list that were already reported in prior inspections but the actions were not taken. \r\n\r\nIC is urged to implement the control/ corrective measures immediately and the repeated such deviations in future will not be tolerated.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.', 'Safety Concerns', 'Complete', '2015-02-26', 0, 70, 0, 87, 'L-1397/15', '2015-02-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1972, 2007, 43, 'SAMPT has reviewed the subject submittal dated February 24, 2015 and has the following comments;\r\n\r\n1.	Show slope of floor falling towards pit.\r\n2.	Specify filler material between pipe and sleeve.\r\n3.	Show lid angle iron support connection and handle details.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Washout Plan', 'Complete', '2015-05-26', 0, 70, 0, 87, 'L-1449/15', '2015-03-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1974, 2009, 43, 'SAMPT has reviewed the subject submittal dated February 24, 2015 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Clear Cleaner ', 'Complete', '2015-03-05', 0, 70, 0, 87, 'L-1432/15', '2015-03-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1976, 2011, 43, '\r\nSAMPT has reviewed the subject submittal dated February 24, 2015 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'PVC Solvent Cement', 'Complete', '2015-03-05', 0, 70, 0, 87, 'L-1433/15', '2015-03-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1978, 2013, 43, 'SAMPT has reviewed the subject submittal dated February 22, 2015 and has the following comment:\r\n\r\n•	ABB 30000298 is not approved manufacturer for control panels (a List of approved manufacturer is attached).\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Lighting Control Panel', 'Complete', '2015-05-26', 0, 70, 0, 87, 'L-1431/15', '2015-03-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1979, 2014, 43, 'SAMPT has reviewed the subject submittal dated February 17, 2015 and has no objection with following comments;\r\n\r\n1.	All Exhaust fans to be controlled from DDC as per the IFC drawing ( HVAC air flow and control diagram ) and necessary interlocking devices shall be included.\r\n2.	Air flow switch shall be required for DDC interface as per IFC.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Exhaust Fans', 'Complete', '2015-05-26', 0, 14, 0, 87, 'L-1436/15', '2015-03-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(1994, 2029, 43, 'SAMPT has reviewed the subject submittal dated February 22, 2015 and has no objection with following comments;\r\n\r\n1.	Ensure that all equipment is fastened to the rack with SS or hot dip galvanized     \r\nHardware/ fittings as per 16-SAMSS-512 Para 11.\r\n2.	Correct the LV system to 400V/230V instead of 480V/277V in all vendor drawings.\r\n3.	Labeling of all enclosures shall be done as illustrated in 16-SAMSS-512 Para 12.1.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.\r\n', 'Switchrack', 'Complete', '2015-05-19', 0, 70, 0, 87, 'L-1444/15', '2015-03-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2000, 2035, 43, 'No Comments, For Information Only', 'Incident Report', 'Complete', '2015-05-26', 0, 25, 0, -1, 'For Information Only', '2015-03-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2002, 2034, 94, 'SAMPT has reviewed the subject letter dated March 02, 2015 and has rejected with the following comments:\r\n\r\n1.	The IC proposal for the project shows highly experienced people for these key positions, some of them containing 20 years and more with advanced degrees, whereas the personnel mentioned in IC reply ANW/15/1086 do not have comparable magnitude of experience, thus IC justification is rejected.\r\n2.	IC proposals are evaluated based on the listed key personnel nominated for the project by IC and not providing same or comparable people is a breach of contract. IC shall provide a comparative chart of qualifications and experiences between the personnel pledged in the bid and the ones available on site for key positions mentioned in Para 5.4.4 of SCH-B.\r\n\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n', '', 'Complete', '2015-03-14', 0, 14, 0, 87, 'L-1441', '2015-03-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2003, 2030, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2004, 2031, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2005, 2032, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2006, 2036, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2007, 2025, 94, '\r\nSAMPT has reviewed the subject Letter dated March 01, 2015 and has the following comments;\r\n\r\n          The following decisions were made in the meeting held on 11 MARCH 2015. \r\n1.	Introducing an operator room in the security infrastructure of the Gate houses cannot be considered as a change order, as IC could not provide an automated and viable alternative during the design phase.\r\n2.	IC will provide a single card reader for high and low vehicles. In case the SAT fails for this equipment, IC will rectify or provide a second reader at no extra cost. \r\n3.	Two HID readers in the design of JFCC building are subject to change order. \r\n4.	IC will provide a detailed breakdown of all outlets, patch chords, panels etc which IC considered to be extra. \r\n5.	Relocation of IDAS in the North shall be associated with the KAM road changes. \r\n6.	Change from monitor to LCD is subject to a change order \r\n7.	Changes to IDAS due to deletion of ditch shall be associated with the amendment for deletion of ditch. \r\n8.	ICC/ESE shall send a technical proposal for re-using any equipment available at gate 4 after the closure of gate 4. \r\nReferences and more details are attached. IC is urged to avoid any further delays and take all necessary steps to follow the approved schedule. \r\n', 'Communication, Security, Change, Order', 'Complete', '2015-05-02', 0, 14, 0, 87, 'L-1450/15', '2015-03-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2008, 2033, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2009, 2021, 94, 'KAUST concurrence is requested to use existing KAUST MV Network, instead of waiting for SEC2 to be operational in order to energize the KAM access road lighting system.\r\n\r\nThe suggested solution is elaborated in the attached presentation and also with the help of ETAP studies/ short circuit calculations.\r\n\r\nShould you have any question, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) on (012) 422 4423.\r\n', 'Power Source', 'Complete', '2015-05-19', 0, 87, 0, 46, 'L-1319/15', '2015-01-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2010, 2026, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2011, 2027, 94, 'SAMPT has reviewed the subject submittal dated February 28, 2015 and has no objection with following comments;\r\n\r\n•	IC shall ensure that the backer rods are compatible with the types of sealants used in various applications and as recommended by the sealant manufacturers\r\n', 'Backing, Rod, Sealant', 'Complete', '2015-04-11', 0, 70, 0, 87, 'L-1438/15', '2015-03-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2012, 2028, 94, '\r\nSAMPT has reviewed the subject submittal dated February 28, 2015 and has no objection with following comments;\r\n\r\n•	 IC to comply with the manufactures recommendation during application of the product to minimize reworks or deviations.\r\n', 'Joint, Sealant, Fire, Rated ', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1440/15', '2015-04-09', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2013, 2012, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2014, 2015, 94, '\r\nSAPMT has reviewed your subject submittal dated March 01, 2015 and has no objection with the following comments;\r\n\r\n1.	Provide the installation detail of the aerial rod and the down conductor.\r\n2.	Locate the tie in point of the lightning system into the existing roof lightning system.\r\n3.	500 mm rod lenght is too short for equipment coverage zone protection, provide technical justification if necessary, or Use 1000 mm aerial rod to ensure good coverage.\r\n4.	Ensure that down conductor will match with the saddle.\r\n', 'Lighting, System, Accessories', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1452/15', '2015-03-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2015, 2016, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2016, 2017, 94, 'SAPMT has reviewed the subject submittal dated February 26, 2015 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification. ', 'Guard, Rails', 'Complete', '2015-05-02', 0, 14, 0, 87, 'L-1427/15', '2015-03-03', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2017, 2019, 94, 'SAMPT has reviewed the subject submittal dated February 26, 2015 and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification.\r\n', 'Fire, Retardant, Paint', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1435/15', '2015-03-08', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2018, 2020, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2019, 2022, 94, 'SAMPT has reviewed the subject submittal dated February 26, 2015 and has no objection with following comment;\r\n\r\n•	Consider Providing spare conduit for every stub-up and conduit run\r\n', 'ShopDrawing,  Truck, Z-Portal ', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1447/15', '2015-03-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2020, 2023, 94, '\r\nSAMPT has reviewed the subject submittal dated February 26, 2015 and has no objection with following comments;\r\n\r\n•	IC to provide more detail of the 50 mm protective cover as per material submittal MS – 0210 Protective water proofing for box culvert – A wazer PY-40-200E  to complete this shop drawing to avoid any construction deviation .\r\n', 'Shop, Drawing, proposed, section, Soil Improvement, Wadi, Khulais', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1439/15', '2015-03-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2021, 2008, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2022, 2018, 94, '\r\nSAMPT has reviewed the subject submittal dated March 01, 2015, and has no objection with following comments;\r\n\r\n•	All conduiting and cabling works shall meet the Standard requirement of SAES P-104.\r\n', 'Shop, Drawing,  Turnstile, X-Ray, Building, Outbound', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1536/15', '2015-04-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2023, 2024, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2024, 1994, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2025, 1941, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2026, 2039, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2027, 2040, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2028, 2042, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2029, 2041, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2030, 2038, 94, '\r\nSAMPT has reviewed the subject submittal dated March 08, 2015, and has no objection with following comment;\r\n\r\n•	Include information and details about mounting plate, J-bolts, screws and nuts and ensure that they are to be purchased from same manufacturer.\r\n', 'Cable, Runway, Ladders ', 'Complete', '2015-05-02', 0, 14, 0, 87, 'L-1463/15', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2031, 2037, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2032, 2043, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2033, 2044, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2034, 2047, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2035, 2045, 94, 'SAMPT has reviewed the subject submittal dated March 09, 2015 and has the following comment;\r\n\r\n•	Provide valid technical reasons and justifications as to why an alternative is being submitted.\r\n', 'Concrete, Repair, Materials', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1469/15', '2015-03-31', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2036, 2046, 94, '\r\nSAMPT has reviewed the subject submittal dated March 09, 2015 and has the following comment;\r\n\r\n•	Provide valid technical reasons and justifications as to why an alternative is being submitted.\r\n', 'Additive, Admixture, Bonding, Agent ', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1468/15', '2015-03-31', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2038, 2048, 94, 'SAPMT has reviewed the subject submittal dated February 26, 2015 and has the following comments:\r\n\r\n•	The corrective actions are not sufficient and should contain the following:\r\n\r\n1.	Revised method statement or Safe Work Procedure.\r\n2.	Revised Risk Assessment.\r\n3.	Retraining of drivers, spotters and supervisors (submit proof thereof).\r\n4.	Toolbox talks addressing such matters.\r\n5.	Proof that required spotters are equipped and sufficient number of spotters are assigned to the job.\r\n\r\n•	SAPMT strongly advise to implement the corrective measures to avoid such repeated incidents. \r\n', 'Lighting, Pole, Accessories', 'Pending', '2015-05-02', 0, 14, 0, 87, 'L-1422/15', '2015-03-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2039, 2006, 94, '\r\nReferring to IC letter ANW/15/1080 dated 24 Feb 15, where IC is proposing to make changes to SCH-C attachment 1, SAPMT has the following comments;\r\n\r\n1.	Para 2 of IC letter refers to SCH-C as un-contractual. The amendment to the contract was signed by both parties and is contractual.\r\n2.	Items or activities which are suspended or terminated (e.g. ditch) shall not be adjusted in SCH-C till resolved. This was conveyed to IC much earlier during various management meetings.\r\n3.	The value for pre-commissioning is based on the number of systems that are to be installed in the project. While pre-commissioning will be part of the progress and invoicing breakdown of each and every system, the line item for final pre-commissioning may be set to approximately SAR 10,000,000.00\r\n4.	All other line items are acceptable as proposed by IC\r\n\r\nIn case IC agrees with the above, a revised SCH-C may be provided by IC to SAPMT, in order to be sent to SA contracting department for review. IC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\n', 'Ditch, Amendment, OrdeR', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1443/15', '2015-03-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2040, 1993, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2041, 2053, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2042, 2052, 94, 'Referring to SAPMT letter No L-1396 dated 10 February 2015, where the work on the boundary wall for MOI land was stopped and IC was requested to prepare a scope of work and MTO for the works to be deleted, demolished and reworks to be executed.\r\n\r\nIC shall clear the area for site surveys and for expected works and prepare and submit conceptual sketches to clearly define the scope of work. Preliminary plans and sections of existing conditions and proposed changes shall be attached.\r\n\r\nMutually agreed SOW, MTO and preliminary sketches shall be submitted to SAPMT by IC before 15 March 2015, so that the change order approval process and works can start without further delay.\r\n', '', 'Complete', '2015-03-15', 0, 14, 0, 92, 'L-1445', '2015-03-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2043, 2049, 43, 'SAPMT has reviewed the subject submittal dated March 11, 2015 and has the following comments:\r\n\r\n1.	Provide accurate manufacturers address for ID 30006889 in Jeddah to ensure that inspections are done without delay.\r\n2.	Provide an acknowledged PO showing the address as explained above.\r\n3.	The approved MR shall be referenced in the PO.\r\n4.	IC is urged to meet to SAPMT to understand complete requirements.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Air Conditioning', 'Complete', '2015-05-23', 0, 25, 0, 87, 'L-1456/15', '2015-03-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2044, 2050, 94, '\r\n\r\nSAMPT has reviewed the subject Letter dated March 11, 2015 and has the following comments;\r\n\r\n1.	On a security related project, it is contractor''s responsibility to ensure that prevailing security arrangements/ requirements are maintained according to the sensitivity of the location set by the proponent and HCIS standards. The contractor has to ensure that no breach in security occurs due to the works being done.\r\n2.	IC is urged to discuss the matter in more detail with SAPMT.\r\n', 'Handingو Over ', 'Complete', '2015-04-09', 0, 14, 0, 87, 'l-1480/15', '2015-04-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2045, 2051, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2046, 2054, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2047, 2055, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2048, 2056, 94, 'SAPMT has reviewed the subject submittal dated March 10, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.\r\n', 'FRP Tank', 'Complete', '2015-05-26', 0, 12, 0, 87, 'L-1579/15', '2015-05-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2049, 2060, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2050, 2066, 94, 'SAPMT has reviewed the subject submittal dated March 23, 2015 and has the following comments:\r\n1.	Include power cable for relocation of security system (IDAS/MIDS), also attach as-built drawing and cable specification details. \r\n2.	5 KV insulation tester is not required for testing of LV cable, remove from the list of equipment shown in paragraph 5.3.1\r\n3.	Contractor to make sure that there will not be any damages to existing utilities during the removal and relocating of existing fence, light poles and security systems (IDAS/MIDS)\r\n4.	Consider only applicable points from the description of sequence of U/G cable pulling shown in paragraph 5.3.4 for LV cable installation work.\r\n5.	Prior the removal of IDAS system and Perimeter lighting in the affected area, ICC is urged to provide the plan to install IDAS system and Lighting System in the designated corridor using the available cameras, MIDS and lighting poles. \r\n6.	The plan shall include the point of connection to the existing KAUST utilities/network to provide power and connection for Lighting system and IDAS system. \r\n7.	ICC is urged to provide accurate documentation, red line and as-built.\r\n8.	The attached as-built drawing VA-207593 is outdated. Update the drawing as per site conditions. \r\n9.	The proposed new manhole and relocated manhole is not acceptable. This will initiate down time on existing IDAS System and manhole construction will take a lot of time. Propose optipeds instead in replacement of manholes if applicable. \r\n10.	Propose vacant fiber cores on existing IDAS 96 core FOC for reservation. \r\n11.	Contractor to ensure the IDAS on the relocated fence is running smoothly and satisfied KAUST operation prior to disabling the existing IDAS.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\n', 'Method, Statement, Relocation, Fence', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1466/15', '2015-03-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2052, 2064, 94, '\r\nSAMPT has reviewed the subject submittal dated March 19, 2015, and has no objection with following comment;\r\n\r\n1.	Use correct 9Com# 6000012391 for Metal Detectors\r\n2.	Ensure that the monitoring station is included\r\n', 'Metor, Metal, Detectors', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1462/15', '2015-03-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2053, 2070, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2054, 2062, 94, 'SAMPT has reviewed the subject submittal dated March 17, 2015, and has no objection with following comment;\r\n\r\n•	IC is urged to ensure that the materials are according to the SA standards and meeting with the requirements set in FSD.\r\n', 'AWG, Armored, Power, cables', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1475/15', '2015-04-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2055, 2059, 94, '\r\nSAMPT has reviewed the subject submittal dated March 15, 2015, and has no objection with following comment;\r\n\r\n•	Include equipment Data sheet and Specifications with NMR 601 as per Saudi Aramco Non Material Requirement form 9597.\r\n', 'NMR, UPS ', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1477/15', '2015-04-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2056, 2067, 94, '\r\nSAMPT has reviewed the subject submittal dated March 19, 2015, and has no objection with following comment;\r\n\r\n•	Indicate power source for PP-Gen panel in panel board schedule. Attach single line diagram showing power feeding from 300KVA package substation (PS-01A) to PPA-Gen with Power cable number.\r\n', 'IFC, Electrical, One, Line, Diagram, ', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1465/15', '2015-03-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2057, 2058, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2058, 2061, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2059, 2065, 94, 'SAMPT has reviewed the subject submittal dated March 19, 01, 2015, and has no objection with following comment;\r\n\r\n          NMR-601 shall include the following documents.\r\n1.	Provide the dimensional outline drawing plan, elevation and cable entrance details. \r\n2.	Foundation loading and footing drawings.\r\n3.	Equipment specification and data sheets.\r\n', 'NMR, UPS-80', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1483/15', '2015-04-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2060, 2071, 94, '\r\nSAMPT has reviewed the subject submittal dated March 22, 201526, 2015 and has no objection with following comment;\r\n\r\n1.	The pressure test manifold (ID LL-00MF-999) is approved.\r\n2.	The equipment shall be drained by air blowing after each test\r\n3.	The maximum test pressure is 100psi.\r\n', 'Pressure, Testing, Manifold, Approval', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1458/15', '2015-03-24', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2061, 2057, 94, 'No Comments, For Information Only', 'Management Meeting', 'Complete', '2015-05-13', 0, 25, 0, -1, 'For Information Only', '2015-05-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2062, 2063, 94, '\r\n\r\nSAMPT has reviewed the subject submittal dated March 17, 2015 and has the following comments;\r\n\r\n•	Contractor shall modify the ITP to be in accordance to the related 175 form. For example, hydro tests are not included and shall be mentioned to be a hold point for the contractor. Contractor shall be aware of Level of inspection “2â€ requirement. Final inspection shall be a hold point for contractor TPI and important in process activity.\r\n', 'IAP, 12', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1479', '2015-04-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2063, 2068, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2064, 2069, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2065, 2072, 94, 'SAMPT has reviewed the subject submittal dated February 23, 2015 and has the following comments;\r\n\r\n1.	Ensure that contractor should have COMMSCOPE Certified technician to handle all UTP cable termination and testing. Certificates must be submitted to SAPMT including the calibration certificates of testing equipment’s.\r\n2.	IC is urged to plan a meeting with PMT to ensure that the proposed subcontractor understands the scope of work and is capable to cover all aspects of ISP works including production of shop drawings and coordination with other trades.\r\n3.	Provide complete manpower list dedicated for the project with designations and qualifications.\r\n', 'Prequalification, 3D,  ISP', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1461/15', '2015-03-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2066, 2073, 94, '\r\nSAMPT has reviewed the subject submittal dated March 23, 2015, and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification.\r\n', 'Insulation, Board, Water, Proofing', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1464/15', '2015-03-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2067, 2074, 94, '\r\nYou are kindly requested to review and approve the Manifold to be used for Hydrotest of underground utility piping for BI-25-00026 KAUST Perimeter Security Fence. Attached the following supporting document:\r\n\r\n1.	Contractor request letter\r\n2.	Manifold Hydro test Report\r\n3.	Manifold schematic diagram\r\n4.	Valves Material certificates\r\n\r\n\r\nThe details of the manifold are shown below:\r\n\r\nProject	BI-25-00026 KAUST Perimeter Security Fence\r\nContract	6600029847\r\nContractor	International Center for Contracting Co. \r\nManifold Assembly	Threaded (no welding)\r\nService	Irrigation Water\r\nMaximum Hydro test Pressure	100 psi\r\n', '', 'Complete', '2015-04-11', 0, 14, 0, 89, 'L-1457/15', '2015-03-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2068, 2081, 94, '\r\nSAMPT has reviewed the subject submittal dated March 26, 2015 and has the following comments;\r\n\r\n1.	The System submittal must consist of IPTV, STB, remote controllers and all associated cabling.\r\n2.	Provide the sizes/model of IPTV for each location.\r\n3.	All proposed model should be the latest in the market at the time of procurement as mentioned in the contract.\r\n', 'Internet, Protocol, Television', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1473/15', '2015-04-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2069, 2078, 94, 'SAMPT has reviewed the subject submittal dated March 22, 2015 and has been rejected with following comments;\r\n\r\n1.	Ensure that the quality of carpets proposed by IC match with the color schemes and quality being used in KAUST.\r\n2.	The sample provided by IC does not match with what is proposed in the submittal.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Carpet', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1554/15', '2015-05-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2070, 2080, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2071, 2076, 94, '', '', 'Complete', '2015-04-11', 0, 14, 0, 22, 'CWRPID/L-004/2015', '2015-03-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2072, 2077, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2073, 2079, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2074, 2083, 94, '\r\nSAMPT has reviewed the subject submittal dated March 26, 2015, and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification.\r\n', 'PVC, Conduit, Spacers', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1474/15', '2015-04-01', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2075, 2075, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2076, 2084, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2077, 2085, 94, '\r\nSAMPT has reviewed the subject submittal dated March 29, 2015, and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification.\r\n', 'APCS3, Coal, Tar', 'Complete', '2015-04-11', 0, 14, 0, 87, 'L-1467/15', '2015-03-31', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2078, 2086, 94, 'SAMPT has reviewed the subject submittal dated March 29, 2015, and has no objection with following comment;\r\n\r\n1.	Use correct and approved Manufacturing ID: 30006251 for ZAMIL AIR CONDITIONER Dammam Plant, where AC Mini Split DX type Units are manufactured.\r\n2.	HVAC Back up Unit for TER room and server room unit shall meet SAES K-002 and design drawing.\r\n', 'AC, unit, Mini, Split ', 'Complete', '2015-04-14', 0, 14, 0, 87, 'L-1498/15', '2015-04-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2079, 2087, 94, '\r\nSAMPT has reviewed the subject submittal dated March 29, 2015, and has rejected with following comment;\r\n\r\n1.	Original submittal MS-0050 for the same material has been already approved Vide SAPMT Letter No: K&TPD/KRP&SFPD/SF/L-488/14 dated Feb 05, 2015. Justification given by contractor to submit alternative is not acceptable.\r\n\r\n2.	Alternative submittal can be accepted if approved manufacturer/Vendor cannot supply the required material in time, and provides in writing. \r\n', 'Plastic, Shim, Pads', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1476/15', '2015-04-02', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2080, 2088, 94, 'SAMPT has reviewed the subject Letter dated March 30, 2015 and has the following comments;\r\n\r\nProvide all documents required by NMR - 602 such as the following: \r\n1.	Wiring and interconnection diagrams with terminal identification numbers. \r\n2.	Dimensional outline drawing- Plan, Elevation and cable entrance details.\r\n3.	Certified test reports. \r\n4.	Recommended spare parts list.\r\n5.	Bill of Materials including catalog data of all major parts and components.\r\n6.	Priced list special tools or devices required for maintenance.\r\n', 'NMR, UPS-10', 'Complete', '2015-04-09', 0, 14, 0, 87, 'l-1484/15', '2015-04-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2081, 2089, 94, '\r\nSAMPT has reviewed the subject submittal dated March 30, 2015, and has no objection with following comment;\r\n\r\n•	IC is urged to ensure that the appropriate gypsum boards are used for applications where moisture resistance or fire resistance is required according to the SA standards and project requirements.\r\n', 'Gypsum, Panel', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1470/15', '2015-03-31', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2082, 2092, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2083, 2091, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2084, 2090, 94, 'SAMPT has reviewed the subject Submittal dated March 30, 2015 and has the following comments;\r\nProvide all the missing documents being required by NMR - 602 such as the following:\r\n1.	Power & Control Schematic Diagrams\r\n2.	Equipment Specification and Data Sheets\r\n3.	Certified test reports\r\n4.	Recommended spare parts list.\r\n5.	Bill of Materials including catalog data of all major parts and components.\r\n6.	Priced list special tools or devices required for maintenance.\r\n', 'NMR, UPS', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1485/15', '2015-04-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2085, 2093, 94, 'Your request was forwarded to Aramco Domestic Sales and Logistics Department and scheduled for delivery the following month. Al-Jeri Transporter designated by IC had been unable to pick up on time. \r\n\r\nIC is urged to follow up with the Transporter and make arrangements to pick up 3500 Tons before the end of this month, otherwise your quota for this month will expire.\r\n\r\nAs the transporter is unable to pick up large quantities, Aramco Domestic Sales and Logistics Dept. has advised to that IC should submit new requests for the remaining quantities, every month for every following month. \r\n', 'Bitumen, Paterol, Road', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1486/15', '2015-04-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2086, 2094, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2087, 2095, 94, 'No Comments, For Information Only', 'Progress Meeting', 'Complete', '2015-05-26', 0, 25, 0, -1, 'For Information Only', '2015-04-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2088, 2096, 94, 'SAMPT has reviewed the subject submittal dated March 31, 2015, and has no objection with following comments;\r\n\r\n1.	IC shall ensure that all requirements mentioned in the FSD are met.\r\n2.	Shop drawings must be provided showing details of the cabling and conduit works required. \r\n3.	Ensure that the LED Display is designed to withstand the outdoor environment.\r\n', 'LED, Picture, Sign, Display', 'Complete', '2015-04-19', 0, 14, 0, 87, 'L-1503/15', '2015-04-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2089, 2097, 94, 'In view of the agreed scope of work and quantities (Attached) for the subject change, please submit your proposal by or before 8 April 2015, 11:00AM. \r\n\r\nThe proposal shall be submitted in a sealed envelope with the following information printed on the envelope;\r\n\r\na. Number and Title of the Project/ Contract.\r\nb. Number and Title of Change order.\r\n\r\nThe envelope shall be deposited at the following location;\r\n\r\n1. If C.O. value is over SR 3,750,000:                                                \r\nCentral Bid Box, Saudi Aramco, North Park, Bidg. 2, Dhahran\r\n\r\n2. If C.O. value is below SR 3,750,000:\r\nKAUST Project Management, Rm. 08, Building 100, SAPMT Site Office, (Thuwal), Saudi Aramco, Jeddah\r\n\r\nIt is your responsibility that all the applicable quantities and units included in the pricing attachment are correct. All costs and expenses incurred by you in preparing your proposal shall be borne solely by you. Your price shall include all resources required to complete the scope of work in all respects to fit the purpose according to applicable standards. It is your responsibility to familiarize yourself with the site conditions. Award of work is contingent upon execution of a formal purchase order by both parties and work shall not commence before a Purchase Order has been issued.\r\n\r\nPlease confirm receipt of this letter by a return fax to +966 12 422 4178.\r\n', 'CHANGE, REQUEST  PROTECTION, CABLES, TEMPORARY, OPENINGS', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1472/15', '2015-04-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2090, 2098, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2091, 2099, 94, '\r\nSAMPT has reviewed the subject submittal dated March 26, 2015, and has no objection with following comments;\r\n\r\n1.	SAIR will monitor the progress and the quality of submittals\r\n \r\n2.	Saudi Aramco will have the right to revoke this approval in case of unsatisfactory performance. \r\n\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570\r\n', 'CV, Procurment,Supervisor', 'Complete', '2015-03-31', 0, 25, 0, 87, 'L-1471', '2015-03-31', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2092, 2100, 94, 'SAMPT has reviewed the subject submittal dated April 01, 2015 and has no objection with following comment;\r\n\r\n1.	Contractor shall mention and submit First page all the applicable Standards as part of Requisition Package after approval of this Material submittal, particularly 34-SAMSS-820 and SAEP-302.\r\n2.	Contractor to ensure the proposed lighting contactor is magnetic type and complies with NEMA ICS2 as per VE-846472 sheet 05 off 07. \r\n3.	Ensure the rating and number of main poles for lighting contactor are suitable for intended application. \r\n4.	List the quantity required. \r\n5.	Lighting contractor for indoor/outdoor application shall meet the requirements as specified in SAES-P-100.\r\n', 'Lighting, Control, Panel, System', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1492/15', '2015-04-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2093, 2101, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2094, 2102, 94, 'SAMPT has reviewed the subject submittal dated March 15, 2015, and has no objection with following comment;\r\n\r\n•	Contractor (IC) proposed Switch Socket Outlet based on KAUST Technical Bulletin issued on Sept 12, 2012 in regards to the “implementation of SASO 2203 for 220V Plugs and Socket outlets which is UK 3-Pin and in compliance with BS-1363â€. However the IFC VA-846899 Sheet 001 and Construction Specification shows non UK pin which is to be red-lined or incorporated in as-built drawings as stated in KAUST Technical Bulletin.\r\n', 'Floor, Boxes', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1481/15', '2015-04-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2095, 2103, 94, '\r\nSAMPT has reviewed the subject submittal dated April 01, 2015, and has no objection with following comment;\r\n1.	Provide the sample of doors face metal as per VE 846472 section 1.07-D. \r\n2.	Use correct 9Com# 6000008995 with correct description of material as “Metallic Doors, Building, and Fire Ratedâ€. 9Com#6000001074 as mentioned in Material submittal is depleted and no more in use.\r\n3.	Submit applicable SA-175-120400 with Requisition Package.\r\n4.	Mention and attach First page of all the applicable standards of 9Com# 6000008995 in Requisition Package. Applicable Standards are 2006,AWS D1.1 and AWSD1.3. Also mention and attach First page of SAEP-302 in Requisition package.\r\n5.	Doors shall be certified to UL10C for Fire Rating and UL1784 for smoke and draft control.\r\n6.	IC shall ensure that all doors, frames and accessories are according to the door schedule mentioned in the IFC drawings and meet SA standards.\r\n', 'Metal, Doors, Frames  ', 'Complete', '2015-04-09', 0, 14, 0, 87, 'L-1482/15', '2015-04-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2096, 2105, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2097, 2106, 94, 'This letter is to inform IC of the ONE-TIME approval of the two mix designs of General Agencies and Contracting (GAC) based on the following comments;\r\n\r\n1.	The two corrective actions mentioned in the attachments shall be completed before June 20, 2015.\r\n2.	This approval is not valid for sulfur extended asphalt.\r\n3.	IC shall notify PMT in writing when the project is completed and/ or when the mix designs are no more valid.\r\n4.	The approval is valid for the 2 attached mix designs only.\r\n\r\n', 'Asphalt, Mix, Designs, GAC ', 'Complete', '2015-04-25', 0, 14, 0, 93, 'L-1522/15', '2015-04-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2099, 2107, 94, 'The attached layout for re-aligning the Security Corridor to avoid the package substations and pump stations in the cornice area is approved. IC is urged to provide revised IFC and shop drawings for PMT approval\r\n', 'ALTERNATE, ROUTE, SECURITY, CORRIDOR, CORNICHE', 'Complete', '2015-04-14', 0, 14, 0, 87, 'L-1487/15', '2015-04-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2100, 2109, 94, 'SAMPT has reviewed the subject submittal dated April 06, 2015, and has no objection with following comments;\r\n\r\n•	Ensure the single line diagram and protection system of proposed Package Substations shall be in compliance with Project Specifications, IFC VA-846412 Sheet 001, 002 and SEC standards.\r\n', 'NMR, 601, Substraction, 300, KVA', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1504/15', '2015-04-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2101, 2113, 94, 'SAMPT has reviewed the subject Submittal dated April 06, 2015 and has the following comments;\r\n\r\n1.	Provide missing Single line diagram and protection diagram for RMU inside package substations.\r\n2.	Explain why Package Substations 01A & 01B are not included with this submittal.\r\n3.	From the manuals, correct rating or sizing of LV main breaker, Current Transformers and other accessories shall be selected which are to be as per IFC and construction specifications.\r\n', 'NMR, Packaged, Substation', 'Complete', '2015-04-19', 0, 14, 0, 87, 'L-1511/15', '2015-04-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2102, 2108, 94, 'SAMPT has reviewed the subject submittal dated April 06, 2015, and has rejected with following comment;\r\n\r\n1.	The quality of furniture in the submittal shall meet the existing quality being used in KAUST and consider the vendors shown in project specifications.\r\n2.	IC is urged to provide various options to choose from for specialized furniture required for the project especially for JFCC.\r\n3.	IC is urged to hold meetings with SAPMT to understand the quality requirements.\r\n4.	Ensure that all fabrics, frames used in upholstery comply with applicable UBC Fire Retardant Standards. \r\n', '', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1538/15', '2015-04-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2103, 2110, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2104, 2111, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2105, 2112, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2106, 2114, 94, 'SAMPT has reviewed the subject submittal dated April 6, 2015 and has no objection with following comment;\r\n\r\nContractor shall conduct detailed investigation to find out the Root Cause of the Incident and implement Corrective Actions accordingly.\r\n\r\nAs a preliminary measure \r\n1.	Contractor shall identify assets that are prone to traffic movement and, protect them with appropriate barricading in all areas under Contractor’s sphere of influence.\r\n2.	Provide Flagman at congested areas of Work, where Heavy Vehicle/ Equipment Movement is expected.\r\n3.	Provide Refresher training to Drivers/ Equipment Operator on Safe Maneuvering of Equipment.    \r\n', 'Preliminary, Incident', 'Complete', '2015-04-08', 0, 14, 0, 87, 'L-1489/15', '2015-04-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2107, 2115, 94, 'An IC employee Mr. Roland Manasala failed to report the loss of his ID to KAUST Security Department and subsequently attempted to procure Temporary ID which is considered as duplication of access. Roland has been interviewed by KAUST security and it is found that despite the fact that Mr Manasala reported the loss of ID to IC Management, the temporary duplicate was still initiated by IC without reporting the loss to PMT or KAUST.\r\n\r\nKAUST is an important national asset and the above mentioned breach in Security Procedures requires the Contractor to take appropriate disciplinary action against the personnel involved after conducting a full investigation and providing the incident report for PMT review. IC is urged to ensure that such breach is not repeated.\r\n\r\nIC must take the following steps to ensure compliance\r\n\r\n1.	KAUST IDs shall be kept in safe custody and if lost, shall be immediately reported to KAUST Security and SAPMT be informed.\r\n2.	ID Cards of Employees, who are demobilized from the Project, shall be surrendered to KAUST Security and SAPMT be informed.\r\n3.	Proper Tracking list to be maintained to ensure No Duplication of Access is requested; and this list to be made available to SAPMT on request.\r\n4.	A list of all existing valid or invalid IDs in possession of IC employees be prepared and submitted to SAPMT. List shall include names, Iqama numbers and KAUS ID nos.\r\n5.	Every long-term, short term access request for personnel or cars shall be signed by IC Project Manager or the Construction Manager with IC stamp.\r\n6.	Appropriate Training to be provided to Concerned Personnel, including the Contractor ID Representatives, to prevent a repeat of similar Issues\r\n', 'Duplicate, Access, ID', 'Complete', '2015-04-08', 0, 14, 0, 87, 'L-1488/15', '2015-04-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2108, 2116, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2109, 2117, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2110, 2118, 94, 'SAMPT has reviewed the subject submittal dated April 07, 2015, and has no objection with following comment;\r\n\r\n1.	Mr. Anand Erulandi is permanently approved as “QC Inspector – Electricalâ€ for the “KAUST-Perimeter Security Systemsâ€ Project. \r\n2.	SAPMT reserves the right to revoke this approval based on his unsatisfactory performance during project tenure\r\n', 'Permanent, Approval, Anand ', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1513/15', '2015-04-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2111, 2119, 94, 'SAMPT has reviewed the subject Submittal dated April 07, 2015 and has the following comments;\r\n\r\n1.	Attach 2 week look ahead schedule.\r\n2.	Attach the summary of quality document submittals for the month. \r\n3.	Provide initiatives and planned activities for project process improvements\r\n', 'MQMR, March, 2015', 'Complete', '2015-04-19', 0, 14, 0, 87, 'L-1506/15', '2015-04-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2112, 2120, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2113, 2122, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2114, 2123, 94, '3D international Technical Service Est. is conditionally approved for ISP works with the following comments; \r\n\r\n1.	The staff mentioned in the site organization shall be available on site and dedicated for KPSS project only, throughout the duration of the project till completion of subcontract scope. \r\n2.	A detailed time schedule for completing the ISP works shall be provided within the next three days. \r\n3.	Any additional manpower, tools or equipment required on site to complete the works and to avoid slippage shall be made available pro-actively. \r\n4.	This approval will be revoked if slippage from the approved schedule is observed.\r\n', 'Prequalification, 3D, Intenational, Technical,  ISP, Works', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1500/15', '2015-04-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2115, 2124, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2116, 2125, 94, '', '', 'Complete', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2117, 2126, 94, '', '', 'Complete', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2118, 2127, 94, 'SAMPT has reviewed the subject submittal dated April 09, 2015, and has no objection with following comments;\r\n\r\n1.	IC to ensure that the manufacturer is aware of the requirements set in the scope of work for the Gatehouse area where the roof shall consist of pre-painted single skin aluminum roof panels supported by steel space frame system on concrete circular columns. \r\n2.	It is IC responsibility that all finishes and metals are according to the Aramco standards. \r\n3.	Provide calculations and also 3D models if necessary concurred by the project designer. \r\n4.	It is IC responsibility to ensure that all joints, welds, connections, bolts and plates adhere with Saudi Aramco standards. \r\n5.	IC to ensure that the architectural appearances of the structures match with the existing schemes at KAUST. \r\n6.	The IC shall provide separately a schedule for procurement and construction.\r\n', 'Space, Frames', 'Complete', '2015-04-19', 0, 14, 0, 87, 'L-1501/15', '2015-04-14', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2119, 2128, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2120, 2129, 94, 'Sent by Email ', 'KAM, road, PMCC', 'Complete', '2015-04-14', 0, 14, 0, -1, 'L-1496/15', '2015-04-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2121, 2130, 94, 'Reference to your letter KPSS/SA/B/AKR/14/0926 dated 04 December 2014 requesting PMCC of KAM road, IC is advised to provide a solution for maintaining the power source for the lights at KAM road, without which the work cannot be considered complete, KAM road cannot be used for its purpose, and cannot be handed over to KAUST.\r\n\r\nUnless the KAM road is usable by KAUST and ready for handover, it is IC responsibility to maintain all systems on the road including irrigation systems, trees health, electrical systems, lighting systems, road surfaces, tracks etc., so that the work is not damaged and in an acceptable condition according to SA standards. \r\n\r\nIC is also urged to expedite works on the construction of new Precast Wall, relocated wall, related IDAS systems and Patrol/ Maintenance roads to ensure a secure and safe handover of works.  \r\n', 'PMCC, KAM, Access, Road', 'Complete', '2015-04-13', 0, 14, 0, 87, 'L-1495/15', '2015-04-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2122, 2131, 94, 'Reference to the “Summary of weekly progress Report #85â€ submitted by IC as of April 09, 2015, it is noticed that the negative variance in construction is growing every week despite the fact that IC had recovered by 12 March 2015 from the previous slippage in procurement totally and construction variance had reduced to -5.55%. \r\n\r\nSince March 12, 2015, ICC has started to slip the weekly target again which has created negative variance in procurement; and a higher slippage in construction reaching -8.66%. It has been agreed in various meetings with IC management that to complete the project as per approved schedule, ICC must achieve a weekly progress of more than 2.00%. IC is urged to meet with PMT on April 20, 2015 and provide causes of delay, effects to Project, and the proposed CONTRACTOR’s remedial measures according to Para 7.6 of the contract scope of  work, and Para 8 of SCH-A. \r\n\r\nThe following items shall be discussed in the proposed meeting;\r\n\r\n1.	The progress on security buildings has slipped to -65% behind schedule. \r\n2.	The MEP shop drawings are delayed despite confirmation by IC to expedite in previous meetings, MEP materials are not procured and MEP manpower is not available on site.\r\n3.	Electrical works for street lights and MC cable laying have stopped due to lack of resources and conflicts with subs\r\n4.	Works for fabrication of foundations for MIDS,  PTZ, SSD have not started\r\n5.	Masonry Works on South island and Gate 1 have not started\r\n6.	Earthworks have stopped\r\n7.	Base Course works have stopped\r\n8.	Asphalt works have stopped\r\n9.	Processing time for change orders is very slow\r\n10.	Installation of Security systems delayed due to lack of equipment and resources\r\n11.	Relocation of wall and IDAS has delayed\r\n\r\nAccording to Para 9.1 of SCH-A, CONTRACTOR shall prosecute WORK completion with diligence and dispatch so that the Critical Milestone Dates and Scheduled Completion Date are met and Exception Items are promptly completed or corrected. Contractor''s failure to comply with Paragraph 9.1 above shall, unless otherwise excused pursuant to this Contract, constitute a substantial breach of this Contract; provided, however, that failure to achieve any Critical Milestone Date shall not constitute a substantial breach if CONTRACTOR promptly develops a revised WORK Schedule which SAUDI ARAMCO approves and to which CONTRACTOR conforms within seven (7) calendar days after receipt of SAUDI ARAMCO''s approval (or such longer period as SAUDI ARAMCO may authorize in writing).\r\n', 'Project, Progress, Slippage', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1497/15', '2015-04-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2123, 2132, 94, 'SAMPT has reviewed the subject submittal dated April 12, 2015, and has no objection with following comments;\r\n\r\n•	Floor Tiles (Red Concrete) 20x40x5cm are approved for Electrical Trenches only\r\n', 'Floor, Tiles', 'Complete', '2015-04-19', 0, 14, 0, 87, 'L-1505/15', '2015-04-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2124, 2133, 94, '\r\nSAMPT has reviewed the subject Submittal dated April 12, 2015 and has the following comments;\r\n\r\n1.	Correct the responses in the response sheet adhering with the previous comments on the subject.\r\n2.	Attach drawings showing full system components of SACS.\r\n3.	Attach an MTO list according to the drawings.\r\n', ' SACS', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1525/15', '2015-04-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2125, 2134, 94, 'SAMPT has reviewed the subject submittal dated April 12, 2015, and has no objection with following comments;\r\n\r\n1.	Ensure that the systems meet the requirements according to the scope of work and are of latest model when procured.\r\n2.	Provide shop drawings showing the layout of screens and associated cabling works.\r\n', 'Video, Wall, Screens', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1524/15', '2015-04-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2126, 2136, 94, '\r\nIC is requested to develop and submit the quantities breakdown for Change Order for  “South beach gate 3rd party security servicesâ€ as per the attached Scope of Work for SAPMT review and approval.\r\n\r\nContingent upon successful review of quantities. IC will be officially requested to submit a bid proposal for the change order in the bid box under a separate invitation letter in line with contractual requirements and procedures.   \r\n', 'SOUTH, BEACH, GATE', 'Complete', '2015-04-13', 0, 14, 0, 89, 'L-1494/15', '2015-04-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2127, 2137, 94, '\r\nIC is requested to develop and submit the quantities breakdown for Change Order for “Third gate on vessel barriersâ€ as per the attached Scope of Work for SAPMT review and approval.\r\n\r\nContingent upon successful review of quantities; IC will be officially requested to submit a bid proposal for the change order in the bid box under a separate invitation letter in line with contractual requirements and procedures\r\n', 'Third, gate, vessel, barriers', 'Complete', '2015-04-13', 0, 14, 0, 89, 'L-1493/15', '2015-04-12', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2128, 2135, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2129, 2139, 94, 'IC claims in letters Nos. KPSS/SA/B/ANW15/1138 dated April 15, 2015 and KPSS/SA/B/ANW15/1132 dated April 11, 2015 cannot be accepted by PMT based on the following reasons;\r\n\r\n1.	It is IC responsibility that activities are completed according to the approved schedule. IC has already been requested via PMT letter L-1495/15 to perform all obligations, work and services and furnish all other things which are required by the terms of this Contract or which can reasonably be inferred from the terms of this Contract as being necessary for the successful and timely completion of the work, according to Para 2.16 of SCH-A.\r\n\r\n2.	The completion date of KAM access road was 30 November 2014 and complete installation of all 37 Package substations for the project is 19 May 2015. This implies that all package substations (at least 2 required for KAM road) should arrive on site much earlier than 19 May to complete these works. It is noted that IC has not been able to deliver a single package substation to site to date (just a month before the activity completion date) and instead the deliveries will be delayed for two months as verbally stated by IC in various meetings. \r\n\r\n3.	IC submitted the request for PMCC of KAM road on 04 December 2014. It was also presented by IC during the walkthrough that even though the package substations were not installed on site; the KAM road will have a power source for the lights. The generators were brought by IC on site for testing the lights and to prove the functionality during the PMCC process. There are several exception items related to the lights not closed as of date, 4 months after the PMCC request date. IC is urged to plan the PMCC request dates to ensure that exception items are closed before the schedule completion dates.\r\n\r\n4.	IC is urged to perform works according to Saudi Aramco standards and mutually binding contractual obligations. According to para 9.1 of SCH-A, Contactor shall prosecute WORK completion with diligence and dispatch so that the Critical Milestone Dates and Scheduled Completion Dates are met and Exception Items are promptly completed or corrected. Contractor''s failure to comply with Paragraph 9.1 above shall, unless otherwise excused pursuant to this Contract, constitute a substantial breach of this Contract.\r\n\r\n5.	According to the first Para of SCH-H, SAUDI ARAMCO may, at its sole discretion, withhold any and all payments otherwise due CONTRACTOR under Paragraph 6 of Schedule "C," until such time CONTRACTOR achieves or completes the required action.\r\n\r\n6.	The generators are deemed as temporary but necessary equipment required during construction by the Contractor to ensure that the lighting systems are working and tested according to ARAMCO standards and can be removed by IC according to Para 10 of the scope of work when the facility under PMCC is fit for purpose.\r\n\r\n7.	The verbal instruction by PMT as highlighted by IC, to provide a source of power to test the lights and ensure that they are working as per SA standards; is a part of contractual obligation of IC; and does not create a claim. Since, IC did not have the package substations and MV cables procured or installed during the construction activities at KAM road; and thus provided a power source as necessary to fulfill the contractual requirements of the project.\r\n\r\n8.	The PMCC for KAM road cannot be signed by the proponent if the street lights are not working and IC has to ensure the provision of a reliable power source, without which the PMCC requested by IC on AKR/14/0926 will be rejected and IC may request the PMCC again when the facility is complete and ready for handover. \r\n\r\nBased on the above, and if IC desires for carry on with PMCC of KAM road, IC is urged to consider that the temporary generators may be kept in operational state by IC till the permanent solution is provided by IC at no extra charge to Saudi Aramco. In such case a plan for closing the remaining "NO" items within the prescribed durations shall be provided by IC according to the GI and IC shall provide a date when the required package substations shall be procured. \r\nIC is also urged to expedite the alternate solution proposed by PMT for the permanent power source from the existing loop.\r\n', 'Temporary, power, supply', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1502/15', '2015-04-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2130, 2140, 94, 'No Comments, For Information Only', 'Inspection Schedule', 'Complete', '2015-05-26', 0, 25, 0, -1, 'For Information Only', '2015-04-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2131, 2141, 94, 'SAMPT has reviewed the subject submittal dated April 13, 2015, and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification.\r\n', 'Coating, Isolation, Under, Water', 'Complete', '2015-04-19', 0, 14, 0, 87, 'L-1510/15', '2015-04-16', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2132, 2142, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2133, 2143, 94, 'SAMPT has reviewed the subject submittal dated April 13, 2015 and has the following comments;\r\n\r\n1.	Provide corrective action plan with ACD\r\n2.	Provide resolution and verification\r\n3.	Provide root cause analysis and preventive actions\r\n4.	Ensure to document the audit report and correction actions/ resolutions\r\n', 'First, Partry, Internal, Quality, Audit, Report, #02', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1533/15', '2015-04-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2134, 2145, 94, 'SAMPT has reviewed the subject letter dated April 13, 2015, and has rejected with following comment;\r\n\r\n•	It is observed that progress percentages given by IC for the mentioned data dates for MEP shop drawings and related construction are less as observed on the site.\r\n', 'Slow, Construction, Progress', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1520/15', '2015-04-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2135, 2144, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2136, 2146, 94, 'SAMPT has reviewed the subject submittal dated April 13, 2015, and has no objection with following comment;\r\n\r\n1.	Ensure that the Video Conference System is the latest Model from the manufacturer.\r\n2.	Ensure that the system is integratable and compatible with KAUST existing systems.\r\n', 'Video, Conference, System', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1526/15', '2015-04-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2137, 2147, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2138, 2148, 94, 'SAMPT has reviewed the subject submittal dated April 15, 2015, and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification', 'Cat, Cable, CCTV, Camera', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1512/15', '2015-04-20', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2139, 2149, 94, 'SAMPT has reviewed the subject submittal dated April 16, 2015, and has no objection with following comment;\r\n\r\n1.	It is Contractor''s responsibility to ensure that the proposed height of 6 Meter Tower provides full security coverage according to KAUST Security requirements and especially for the areas not covered by the existing RADAR systems.\r\n2.	Contractor to ensure that the RADAR signal has no health risk to the people and will not interfere with other wireless devices nearby.\r\n3.	The complete system shall function without any interference or interruption.\r\n4.	Provide shop drawings for connection / fastening / details.\r\n5.	Provide foundation details. \r\n', 'Radar, Tower', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1518/15', '2015-04-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2140, 2150, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2141, 2151, 94, 'SAMPT has reviewed the subject submittal dated April 16, 2015, and has no objection with following comment;\r\n\r\n1.	Use Correct 9Com#6000001099 for IDAS (CCTV System for Security and Surveillance). This submittal caters to the fixed and PTZ cameras only. \r\n2.	The Pan/Tilt and zoom (PTZ) assessment camera shall be integrated in terms of tracking and zooming and directed to the intruder.\r\n3.	The camera refresh rate shall be adjusted to avoid image flickering. \r\n4.	Image should not flicker when the image is refreshed. \r\n5.	The major alarm shall be configured to trigger at detection of humans.\r\n6.	Ensure Camera stabilization and day and night functions must meet the FSD requirements and HCIS.\r\n', 'IDAS', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1516/15', '2015-04-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2142, 2152, 94, '\r\nSAMPT has reviewed the subject submittal dated April 16, 2015, and has no objection with following comment;\r\n\r\n1.	Ensure that handrails are hot dip galvanized and painted and reflected on the shop drawings.\r\n2.	Provide shop drawings for installation details. \r\n', 'Handrails', 'Complete', '2015-05-02', 0, 14, 0, 93, 'L-1517/15', '2015-04-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2143, 2153, 94, 'In view of the agreed scope of work and quantities (Attached) for the subject change, please submit your proposal by or before 21 April 2015, 11:00AM. \r\n\r\nThe proposal shall be submitted in a sealed envelope with the following information printed on the envelope;\r\n\r\na. Number and Title of the Project/ Contract.\r\nb. Number and Title of Change order.\r\n\r\nThe envelope shall be deposited at the following location;\r\n1. If C.O. value is over SR 3,750,000:                                                \r\nCentral Bid Box, Saudi Aramco, North Park, Bidg. 2, Dhahran\r\n\r\n2. If C.O. value is below SR 3,750,000:\r\nKAUST Project Management, Rm. 08, Building 100, SAPMT Site Office, (Thuwal), Saudi Aramco, Jeddah\r\n\r\nIt is your responsibility that all the applicable quantities and units included in the pricing attachment are correct. All costs and expenses incurred by you in preparing your proposal shall be borne solely by you. Your price shall include all resources required to complete the scope of work in all respects to fit the purpose according to applicable standards. It is your responsibility to familiarize yourself with the site conditions. Award of work is contingent upon execution of a formal purchase order by both parties and work shall not commence before a Purchase Order has been issued.\r\n', 'Commercial, Proposal, Sewerage, Lines, Lift, Station', 'Complete', '2015-04-22', 0, 91, 0, 89, 'L-1509/15', '2015-04-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2144, 2154, 94, 'In view of the agreed scope of work and quantities (Attached) for the subject change, please submit your proposal by or before 23 April 2015, 11:00AM. \r\n\r\nThe proposal shall be submitted in a sealed envelope with the following information printed on the envelope;\r\n\r\na. Number and Title of the Project/ Contract.\r\nb. Number and Title of Change order.\r\n\r\nThe envelope shall be deposited at the following location;\r\n1. If C.O. value is over SR 3,750,000:                                                \r\nCentral Bid Box, Saudi Aramco, North Park, Bidg. 2, Dhahran\r\n\r\n2. If C.O. value is below SR 3,750,000:\r\nKAUST Project Management, Rm. 08, Building 100, SAPMT Site Office, (Thuwal), Saudi Aramco, Jeddah\r\n\r\nIt is your responsibility that all the applicable quantities and units included in the pricing attachment are correct. All costs and expenses incurred by you in preparing your proposal shall be borne solely by you. Your price shall include all resources required to complete the scope of work in all respects to fit the purpose according to applicable standards. It is your responsibility to familiarize yourself with the site conditions. Award of work is contingent upon execution of a formal purchase order by both parties and work shall not commence before a Purchase Order has been issued.\r\n', 'Commercial, Proposal, Vessel, Barriers', 'Complete', '2015-04-22', 0, 91, 0, 89, 'L-1508/15', '2015-04-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2145, 2155, 94, 'In view of the agreed scope of work and quantities (Attached) for the subject change, please submit your proposal by or before 19 April 2015, 11:00AM. \r\n\r\nThe proposal shall be submitted in a sealed envelope with the following information printed on the envelope;\r\n\r\na. Number and Title of the Project/ Contract.\r\nb. Number and Title of Change order.\r\n\r\nThe envelope shall be deposited at the following location;\r\n1. If C.O. value is over SR 3,750,000:                                                \r\nCentral Bid Box, Saudi Aramco, North Park, Bidg. 2, Dhahran\r\n\r\n2. If C.O. value is below SR 3,750,000:\r\nKAUST Project Management, Rm. 08, Building 100, SAPMT Site Office, (Thuwal), Saudi Aramco, Jeddah\r\n\r\nIt is your responsibility that all the applicable quantities and units included in the pricing attachment are correct. All costs and expenses incurred by you in preparing your proposal shall be borne solely by you. Your price shall include all resources required to complete the scope of work in all respects to fit the purpose according to applicable standards. It is your responsibility to familiarize yourself with the site conditions. Award of work is contingent upon execution of a formal purchase order by both parties and work shall not commence before a Purchase Order has been issued.\r\n', 'Commercial, Proposal, South, Beach,  Security, Service', 'Complete', '2015-04-22', 0, 91, 0, 89, 'L-1507/15', '2015-04-15', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2146, 2156, 94, 'SAMPT has reviewed the subject submittal dated April 19, 2015, and has no objection with following comment;\r\n\r\n\r\n1.	Ensure that all equipment is fastened to the rack with SS or hot dip galvanized hardware/ fittings as per 16-SAMSS-512 Para. 11 \r\n2.	Ensure that for outdoor locations, enclosures shall be: (a) NEMA Type 3R, 3 or 4; or (b) IEC 60529 Type IP34 or better as per SAES-P-104 Para 7.4\r\n', 'NMR, 602, Switchrack', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1542/15', '2015-04-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2147, 2157, 94, 'SAMPT has reviewed the subject submittal dated April 19, 2015 and has the following comments;\r\n\r\n1.	Manufacturer Plant ID for VIKING PUMP INC Cedar falls USA is 30002989 and its Vendor ID is 100123641.\r\n2.	Pumps and motor assemblies shall be factory assembled on a structural steel channel and rotating parts shall have a steel guard.\r\n3.	Provide a complete submittal which includes strainers, isolation valves, check valves and pressure relief valve as per the project spec VE 846472 page 57 and 58. \r\n4.	Selected model to be highlighted. \r\n5.	Provide details for all electrical and Instrumentation accessories including level transmitter, level gauge, pressure gauge and control panel.\r\n', 'Fuel, Oil, Transfer, Pump, Generator', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1528/15', '2015-04-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2150, 2160, 94, 'No Comments, For Information Only', 'Incident Report', 'Complete', '2015-06-14', 0, 25, 0, -1, 'For Information Only', '2015-06-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2151, 2161, 94, 'SAMPT has reviewed the subject submittal dated April 19, 2015, and has no objection with following comment;\r\n\r\n•	Ensure that waterproofing materials are installed in strict compliance with the manufacturers recommendations especially for overlaps and built-up terminations on flat or uneven surfaces.\r\n', 'Waterproofing, Materials', 'Complete', '2015-04-25', 0, 14, 0, 87, 'L-1519/15', '2015-04-22', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2153, 2164, 94, 'SAMPT has reviewed the subject submittal dated April 20, 2015, and has no objection with following comment;\r\n\r\n1.	Ensure that the method statement is attached with the work permit to start the works for tie-in.\r\n2.	Upon completion as-built dwgs shall be provided.\r\n3.	Ensure that the work is done according to KAUST requirements with no impact to Saudi Aramco.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Tie in Procedure', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1548/15', '2015-05-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2155, 2166, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2156, 2163, 94, 'No Comments, For Information Only', 'Incident Report', 'Complete', '2015-06-14', 0, 25, 0, -1, 'For Information Only', '2015-06-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2158, 2168, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2159, 2169, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2160, 2170, 94, '\r\nSAMPT has reviewed the subject submittal dated April 22, 2015, and has no objection with following comment;\r\n\r\n1.	Provide a list of locations where the break glass is being installed\r\n2.	Ensure the devices are placed inside the room where two readers are installed as the application depends upon the type of door to be used.\r\n', 'Emergency, Break, Glass', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1545/15', '2015-04-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2162, 2172, 94, 'IC is hereby requested to arrange for immediate replacement for all damaged submarine cable as illustrated on the attached photos. IC immediate course of action is required in order to avoid any further delays in the completion of SONAR system installation.  ', 'Replacement, Submarine, Cable, SONAR', 'Complete', '2015-04-25', 0, 14, 0, 93, 'L-1521/15', '2015-04-23', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2163, 2173, 94, 'SAMPT has reviewed the subject submittal dated April 26, 2015, and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification\r\n', 'IFC, Drawings', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1541/15', '2015-04-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2164, 2174, 94, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2165, 2175, 94, 'SAMPT has reviewed the subject submittal dated April 22, 2015 and has the following comments;\r\n\r\n1.	Provide the following documents/ details \r\na)	Proposed system details /system architecture/ block diagram\r\nb)	MTO\r\nc)	BMS Drawing (The one attached is incorrect)\r\nd)	Data sheets for all equipment’s /Instruments\r\ne)	Workstation details\r\nf)	BMS Software details\r\ng)	Enclosure details \r\n', 'DDC, Panel, Package, HVAC, Unit', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1529/15', '2015-04-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2166, 2177, 94, 'IC is requested to provide recovery plan along with delay analysis report according to Para 5.6.3.4 of SCH-B for the following activities;\r\n\r\n          1. SONAR System cabling materials have damaged due to mishandling on site     \r\n              and the work quality is being adversely effected due to lack of appropriate     \r\n              resources.\r\n          2. Vessel Barrier Assembly, the contractor has been advised to continue at             \r\n              locations 2 and 3 according to IFC, while a variation has been agreed for \r\n              Location 1. Various parts necessary to start the installation have not been \r\n              procured and more delay is anticipated in  activity completion.\r\n          3. Various technical submittals for the RADAR System have been delayed.\r\n          4. Construction of Vehicle X-ray machines has been delayed by 04 months due to \r\n              incomplete site works.\r\n\r\nDespite Saudi Aramco repetitive reminders during weekly meetings and via letters (L-1365/15 and L-1441/15), lacking of IC Key personnel as per contractual requirements are adversely affecting the project progress. IC is urged to provide a plan of action in light of the approved schedule before 30 April 2015.\r\n', 'Delay, Security, Systems, Progress', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1523/15', '2015-04-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2167, 2178, 94, 'SAMPT has reviewed the subject submittal dated April 19, 2015, and has no objection with following comment;\r\n\r\n1.	Ensure the size of ground bus bar complies with the dimensions shown in the IFC drawings and specifications.\r\n2.	Ensure outside ground bus bar complies with environmental conditions as stated in SAES-P-100 & SAES-P-104\r\n3.	Use correct Vendor ID: 10018108 for ERICO INC USA.\r\n', 'Grounding, Bus, Bar, Electrical', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1527/15', '2015-04-26', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2169, 2180, 94, 'SAMPT has reviewed the subject submittal dated April 26, 2015, and has no objection with following comment;\r\n\r\n\r\n1.	Use Correct Plant ID#30000764 for QANBAR DYWIDAG PRECAST CONCRETE LTD JUBAIL.\r\n2.	Inspection Level is ZERO (0). \r\n3.	Material shall be Procured from Saudi Aramco approved Plant. QANBAR DYWIDAG as quoted by Contractor is an approved plant.\r\n\r\n', 'Precast, Bench', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1544/15', '2015-04-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2170, 2181, 94, '\r\nSAMPT has reviewed the subject submittal dated April 26, 2015, and has no objection with following comment;\r\n\r\n•	Provide Manufacturer/Vendor drawing showing the loads for X-Ray machines and turnstile machine readers\r\n', 'FC, Drawing, Panel, Board, Schedule', 'Complete', '2015-05-02', 0, 14, 0, 93, 'L-1546/15', '2015-04-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2172, 2182, 94, 'SAMPT has reviewed the subject submittal dated April 26, 2015, and has been rejected with following comment;\r\n\r\n•	The proposed rip-rap has to match with the elevations of the existing rip-rap on the sides of lagoon.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Pond Area', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1547/15', '2015-05-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2173, 2184, 94, 'SAMPT has reviewed the subject submittal dated April 26, 2015, and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification\r\n', 'MQMR, March, 2015', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1540/15', '2015-04-29', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2177, 2188, 94, 'SAMPT has reviewed the subject submittal dated April 26, 2015, and has no objection. However, it is Contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and project specification\r\n', 'Protective, Waterproofing, Box, Culvert, Henkel', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1534/15', '2015-04-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2178, 2189, 94, 'SAMPT has reviewed the subject submittal dated April 23, 2015, and has no objection with following comments;\r\n\r\n1.	Ensure that approved materials are reflected on the drawings.\r\n2.	Provide the structural drawing for protective slab separately.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Soil Improvement', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1539/15', '2015-05-05', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2179, 2190, 94, 'SAMPT has reviewed the subject submittal dated April 23, 2015 and has no objection with following comments;\r\n\r\n1.	Provide the Conduit for communication cable to TER room.\r\n2.	Location of FDAS sensor shall be away from A/C indoor unit.\r\n3.	Fire Alarm Drawings shall be stamped by approved Fire Engineer.\r\n4.	Work may proceed under the supervision of IC MEP engineers and any conflicts on site may be corrected with red lines on drawings.\r\n5.	It is IC responsibility to ensure that all required cables, conduits, pipes, panels, appliances, equipments, furniture, fixtures, fasteners and fittings in buildings are installed without any conflicts or obstacles according to SA standards.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Security Gate House', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1558/15', '2015-05-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2180, 2191, 94, 'SAMPT has reviewed the subject submittal dated April 23, 2015 and has no objection with following comments;\r\n\r\n1.	Provide the Conduit for communication cable to TER room.\r\n2.	Location of FDAS sensor shall be away from A/C indoor unit.\r\n3.	Fire Alarm Drawings shall be stamped by approved Fire Engineer.\r\n4.	Work may proceed under the supervision of IC MEP engineers and any conflicts on site may be corrected with red lines on drawings.\r\n5.	It is IC responsibility to ensure that all required cables, conduits, pipes, panels, appliances, equipments, furniture, fixtures, fasteners and fittings in buildings are installed without any conflicts or obstacles according to SA standards.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Security Gate House', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1559/15', '2015-05-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2181, 2192, 94, 'SAMPT has reviewed the subject submittal dated April 26, 2015 and has no objection with following comments;\r\n\r\n1.	Provide the Conduit for communication cable to TER room.\r\n2.	Location of FDAS sensor shall be away from A/C indoor unit.\r\n3.	Fire Alarm Drawings shall be stamped by approved Fire Engineer.\r\n4.	Work may proceed under the supervision of IC MEP engineers and any conflicts on site may be corrected with red lines on drawings.\r\n5.	It is IC responsibility to ensure that all required cables, conduits, pipes, panels, appliances, equipments, furniture, fixtures, fasteners and fittings in buildings are installed without any conflicts or obstacles according to SA standards.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Pavilion', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1560/15', '2015-05-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2182, 2193, 94, '1.	IC is requested to provide the status of the following procurements required for the project;\r\n\r\na.	Air conditioning units of all types\r\nb.	HVAC accessories\r\nc.	Doors\r\nd.	Frames \r\ne.	Drainage pipes, fittings and fixtures \r\nf.	Water supply pipes, fittings and fictures\r\ng.	Fuel system accessories including pump, control systems, Instrumentation systems\r\nh.	Fire water Lines, accessories and fittings i. Hydro testing manifolds\r\n\r\n2.	It is observed that most of the above-said items are either awaiting POs, shop drawings, predecessor activities and/ or have not been delivered on site. IC is urged to provide a plan of action in comparison with the approved schedule and expedite activities to avoid any slippage.\r\n', 'Mechancial, Works', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1535/15', '2015-04-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2183, 2010, 94, '\r\nSAMPT has reviewed the subject submittal dated March 15, 2015, and has no objection with following comment;\r\n\r\n•	Ensure that lighting panels and fire alarm panels are not installed directly under the air conditioners. \r\n', 'Mechanical, Shop, Drawing, Turnstile,  X-Ray Building, SG2, Outbound', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1537/15', '2015-04-28', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2184, 2194, 94, 'SAMPT has reviewed the subject submittal dated April 27, 2015 and has no objection with following comment;\r\n\r\n•	It is IC responsibility to ensure that all works are performed according to the Scope of Work and SA standards.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Lintel Beam Turnstile X-Ray Building', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1561/15', '2015-05-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2186, 2195, 94, 'SAMPT has reviewed the subject submittal dated April 26, 2015, and has no objection with following comments;\r\n\r\n1.	The printouts are not legible. IC to ensure that the site staff is provided with clear set of drawings.\r\n2.	IC is urged to start the construction at an expedited rate to recover from the slippage on building construction due to delays in development of shop drawings.\r\n3.	It is IC responsibility to ensure that all required cables, conduits, pipes, panels, appliances, equipment’s, furniture, fixtures, fasteners, embedded items and fittings in buildings are installed without any conflicts or obstacles according to SA standards.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Visitor Buildings', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1551/15', '2015-05-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2187, 2196, 94, 'SAMPT has reviewed the subject submittal dated April 26, 2015, and has no objection with following comments;\r\n\r\n1.	The printouts are not legible. IC to ensure that the site staff is provided with clear set of drawings.\r\n2.	IC is urged to start the construction at an expedited rate to recover from the slippage on building construction due to delays in development of shop drawings.\r\n3.	It is IC responsibility to ensure that all required cables, conduits, pipes, panels, appliances, equipment’s, furniture, fixtures, fasteners, embedded items and fittings in buildings are installed without any conflicts or obstacles according to SA standards.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Visitor Buildings', 'Complete', '2015-05-17', 0, 25, 0, 87, 'L-1550/15', '2015-05-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2188, 2198, 94, 'KAUST is requested to takeover KAM access road as all "YES" items in the Exception items list have been corrected and closed. \r\n\r\nSAPMT is committed to maintain a reliable power source for the street lights at KAM road with temporary generators; which have already been installed and operational; until the permanent source is available.\r\n\r\n\r\n', 'PMCC, KAM, Access, Road', 'Complete', '2015-04-30', 0, 14, 0, 93, 'L-1543/15', '2015-04-30', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2190, 2199, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2191, 2200, 43, 'No Comments, For Information Only', 'Progress Meetings', 'Complete', '2015-05-13', 0, 12, 0, -1, 'For Information Only', '2015-05-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2192, 2197, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2193, 2185, 43, 'SAMPT has reviewed the subject letter dated April 26, 2015, and has been rejected with the following comments;\r\n\r\n1.	Mr. Khalid Murudkar is not accepted as a replacement of Mr. Yousaf Bari, because he is not an approved “Procurement QC Supervisorâ€ and holds an important key role in the project.\r\n2.	Mr. Ammar Hussain Baig has already been approved for the position of “Procurement QC supervisorâ€ Vide letter No: K&TPD/KRP&SFPD/SF/L-1471/15 dated April 01, 2015 as a replacement of Mr. Yousaf Bari. SAPMT has already requested in this letter that Mr. Yousaf Bari cannot be relieved from duty until the newly approved Procurement QC Supervisor “Mr. Ammar Hussain Baigâ€ arrives and takes over his duties.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'Procurement QC Supervisor', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1549/15', '2015-05-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2194, 2183, 43, 'SAMPT has reviewed the subject submittal dated April 21, 2015, and has no objection with following comment;\r\n\r\n•	It is IC responsibility to ensure that all products and systems meet with the requirements of the scope of work and SA standards.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'CCTV', 'Complete', '2015-05-11', 0, 25, 0, 87, 'L-1553', '2015-05-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2195, 2186, 43, 'SAMPT has reviewed the subject letter dated April 26, 2015, and has no objection with following comments;\r\n\r\n1.	The conditional approval of Mr. Joseph Buban Navarro as “QC Supervisor - Civilâ€ has been extended for a period of Three (3) months from the date of expiry of previous approval.\r\n2.	SAPMT reserves the right to revoke this conditional approval extension based on his unsatisfactory performance.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.\r\n', 'QC Supervisor Civil', 'Complete', '2015-05-19', 0, 25, 0, 87, 'L-1552/15', '2015-05-04', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2196, 2179, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2197, 2159, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2198, 2171, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2199, 2201, 43, 'SAMPT has reviewed the subject submittal dated April 30, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.\r\n', 'Control Cable', 'Complete', '2015-05-17', 0, 12, 0, 87, 'L-1566/15', '2015-05-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2200, 2187, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-05-13', 0, 12, 0, -1, 'For Information Only', '2015-05-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2201, 2162, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2202, 2202, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-05-13', 0, 12, 0, -1, 'For Information Only', '2015-05-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2203, 2203, 43, 'No Comments, For Information Only', 'Progress Report', 'Complete', '2015-05-13', 0, 12, 0, -1, 'For Information Only', '2015-05-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2204, 2204, 43, 'Your support is kindly requested to allow access to Marine gate area to continue the works for precast wall, gatehouse and the guardhouse. The permission to access the area was granted by KAUST on April 28, 2015 as per attached letter but access was rejected by National Guards.\r\n\r\nThe existing chain-link fence is closed from the east entrance but wide open on the south side for any possible intrusions and hence cannot be considered as a security feature. The road to the chain-link gate has also been declared redundant due to the MOT bridge construction and any future access from public will be blocked.\r\n\r\nMost of the wall construction in the north is completed and works in the Marine gate area have to commence to avoid any further delays and assure timely completion.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4570.\r\n', 'Marine Gate', 'Complete', '2015-05-17', 0, 87, 0, 92, 'L-1557/15', '2015-05-10', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2205, 2205, 43, 'References are made to the above mentioned subject and further to your letter No. KPSS/SA/B/ANW/15/1164 dated May 03, 2015; the negative progress variance in procurement and construction are still growing every week since March 19, 2015. SAPMT informed IC Management in various meeting to complete the project as per the approved schedule, and IC committed to achieve a minimum weekly progress of 2% to recover some of the project delay.\r\n\r\nPursuant to the contract para 9.1 & 9.2 of SCH-A, Contractor’s failure to comply with the approved schedule constitutes a substantial breach of this contract.\r\n\r\nSAPMT is requesting IC to provide causes of the delay and submit an updated recovery work schedule according to para 8 of SCH-A.\r\n\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.\r\n', 'Progress Slippage', 'Complete', '2015-06-01', 0, 87, 0, 92, 'L-1588/15', '2015-05-27', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2206, 2206, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2207, 2207, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2208, 2208, 43, 'SAMPT has reviewed the subject submittal dated May 04, 2015 and has no objection with the following comment:\r\n\r\n•	IC to ensure that the final appearance/ view is acceptable to SAPMT and proponent.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.\r\n', 'UPS Building', 'Complete', '2015-05-26', 0, 12, 0, 87, 'L-1565/15', '2015-05-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2209, 2209, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2210, 2210, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2211, 2211, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2212, 2212, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2213, 2213, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2214, 2214, 43, 'KAUST is kindly requested to takeover KAM access road and sign the related PMCC # 01 for the Perimeter Security Fence project considering the following;\r\n\r\n1.	Energizing KAM road with Generators is proposed as a temporary solution. When the permanent power is available, the work will be completed as per project scope of work.\r\n2.	There is no “YESâ€ item for the trees. The contractor is responsible for one year warranty after PMCC according to the contract.\r\nShould you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer (A) at 012 422-4570.\r\n', 'PMCC', 'Complete', '2015-05-17', 0, 87, 0, 92, 'L-1555/15', '2015-05-07', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2215, 2215, 43, 'The attached document shows the breakdown of activities which will be processed as separate PMCCs for the project. It is being suggested that items are seperated to faciliate the handover involving different disciplines and/ or which are not interdependant. Support from KAUST to start processing the PMCCs for independant completed works shall be much appreciated.', 'PMCC KAM Rd', 'Complete', '2015-05-17', 0, 87, 0, -1, 'For Information Only', '2015-05-06', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2216, 2167, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2217, 2216, 43, '', '', 'Pending', '', 0, 0, 0, 0, '', '0000-00-00', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2218, 2217, 43, 'SAMPT has reviewed the subject submittal dated May 04, 2015 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards and specifications.\r\n\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.\r\n', 'Rod Holes', 'Complete', '2015-05-26', 0, 12, 0, 87, 'L-1567/15', '2015-05-11', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2219, 2218, 43, 'SAPMT has reviewed the subject submittal dated May 05, 2015 and has no objection with the following comments:\r\n\r\n1.	For 9Com# 6000000030, SAPPCO is approved for pipe sizes ½ inch to 10 inch.\r\n2.	Submit Requisition Package as the material is Level Zero (0).\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686\r\n', 'PVC Pipe', 'Complete', '2015-05-26', 0, 12, 0, 87, 'L-1586/15', '2015-05-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2220, 2219, 43, 'SAMPT has reviewed the subject submittal dated May 05, 2015 and has no objection with the following comment:  \r\n\r\n•	Describe the plan and initiative taken for process improvement in the next month submittal of MQMR.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.\r\n', 'MQMR', 'Complete', '2015-05-26', 0, 12, 0, 87, 'L-1576/15', '2015-05-17', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2221, 2220, 43, 'SAPMT has reviewed the subject submittal dated May 05, 2015 and has no objection with the following comment;\r\n\r\n•	IC is urged to replace from 3m to 6m stub-out.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.\r\n', 'Mainhole Side Duct Entrance', 'Complete', '2015-06-01', 0, 12, 0, 87, 'L-1580/15', '2015-05-19', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2222, 2221, 43, 'SAMPT has reviewed the subject submittal dated May 05, 2015 and has the following comments:\r\n\r\n1.	Underground Power and Control Cable shall be installed as per SAES-P-104 para 10.\r\n2.	Minimize the number of Splicing of Conductors for main cable from SEC SS-2 to Switchgear (SWGR 1&2) as per SAES-P-104 para 5.6.\r\n3.	Control Cable shall not be installed directly above the Power Cable (13.8kV MV Cable) as per SAES-P-104 para 10.14.\r\n4.	Consider to use latest revision of Electrical One Line Diagram for 13.8KV switchgear (SWGR 1 & 2).\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.\r\n', 'One Line Diagram', 'Complete', '2015-05-17', 0, 12, 0, 87, 'L-1570/15', '2015-05-13', 0, '', '', '', '', '');
INSERT INTO `submittal` VALUES(2223, 2222, 43, 'SAMPT has reviewed the subject submittal dated May 05, 2015 and has no objection with the following comments:\r\n\r\n1.	Underground 13.8KV Power Cable shall be installed as per SAES-P-104 para 10.\r\n2.	Ensure a minimum separation between redundant direct buried power cables, power cable and control cable shall be maintained as per SAES-P-104 para 14.\r\nIC shall ensure that no scope change or cost/schedule implication arises from this letter.\r\nShould you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.\r\n', 'Cable Layout', 'Complete', '2015-05-17', 0, 12, 0, 87, 'L-1569/15', '2015-05-13', 0, '', '', '', '', '');
