1.	Use correct 9Com# 6000000744 for Cable Trays(Aluminium or Steel).
2.	Use Correct 9Com# 6000014116 for Cable Tray accessories.
3.	Use Correct 9Com number while submitting Purchase Requisition for SAPMT approval.
4. Cable tray for electrical works shall be copper free aluminum to meet Saudi Aramco Standard SAES P-104 para. 9.1 2. 
5. Ensure electrical cable tray full compliance with Metal Cable Tray System stated in NEMA VE-1.
6. The Summary list and specifications are for Cable Tray System only. Cable Ladders/Cable Runways are not listed. Provide specification and attach data sheets which are from Chatsworth Manufacturer as per the Scope of work.
7.	The proposed Supplier and Manufacturer Abahsain Cope is not approved to supply Chatsworth Products.
8. Consider submitting products seprately according to the discipline and activity.