1. Consider renaming steel box with back boxes. 
2. Ensure that back boxes are UL listed or with approved equal certification. 
3. EMT conduits shall not be embedded in concrete as per SAES-T-916
4. A 4 inch box cover is not acceptable, refer to minumum standard dimensions as per SAES-T-916