1. Grounding rods shall meet standard requirements of SAES P-111 para. 5.2
2. Molds and cadweld thermite powders shall be as per Furse manufacturer recommendations.
3. Ensure that the molds sizes were checked based on grounding cables and rods diameter.
4. Observe and follow best installation practices for grounding rods and conductors, grounding bolts are only acceptable within grounding test pit, while all installations that is going to be back-filled shall be cadwelded.
