SAPMT has reviewed the subject submittal dated May 10, 2015 and has no objection with the following comments:

1.	Ensure that the proposed lighting contactor shall be magnetic type and comply with NEMA ICS2 as per VE-846472 sht. 05 of 07.
2.	Make sure the rating and number of main poles for lighting contactor shall be suitable for intended application.
3.	Provide wiring diagram for lighting contactor panel (LCP) and shall match with typical wiring diagram of LCP as shown in IFC VA-846492 sht. 001.
4.	Lighting contractor for indoor/outdoor application shall meet the requirements as specified in SAES-P-100.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Yaser A. Al-Johani, Project Engineer at 012 422-4686.
