SAPMT recommends using SEC-2 instead of Sub-Station # 4 as the source for the KPSS project power requirements for the following reasons;
1.	Substation 4 is not ready and thus studies required for KPSS power design may be delayed.
2.	SEC-2 is only 200 meters away from the KPSS Generator building where as SS4 is about 1600 meters away.
3.	Running the power cable to SS4 shall require various road crossings and putting at risk other utilities in an already congested areas, where as connecting to SEC-2 avoids any road crossings and delays.
Based on the above, feeder breakers number 8 and 19 of SEC main substation (which is under construction) shall be reserved for the KPSS project. Enclosed in this letter are Building locations of Generator Building, Substation # 4 and New SEC-2 Building, and new SEC-2 switchgear breaker assignment for your reference.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
