SAPMT has reviewed the subject submittal dated August 25, 2014 and has the following comments:
1.	Provide detail for the lighting pole bonding to the grounding grid conductor.
2.	Extend the PVC pipe with at least 150mm stub-up, till the top of the pole foundation grade level.
3.	Base plate material in the shop drawing is different from the sample provided. Sample has steel plate whereas the drawing mentions die cast aluminum.
4.	The brand name of the sample of lighting fixture is different from the one mentioned in the drawing. Consider mentioning the required fixture specifications only without the brand name.
5.	Consider re-writing the type of the pole with "Hot Dipped Galvanized steel with finish powder coating".
Should you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.
