SAPMT has reviewed the subject submittal dated November 04, 2014 and has the following comment:
•	Provide the correct model and specifications in compliance with IFC Drawing i.e. VA-847173 and Saudi Aramco standard SAES-T-795 and SAES-T-916.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
