Below comment is from Wenceslao Angeles: I have no further comment.


* Protective devices  and controls shall comply with Appendix A of 16-SAMSS-504 for the list of approved manufacturer and model with its corresponding ANSI function number that will be used in the proposed 13.8KV Switchgear at Generator Building
• Comply with all the required protection for Generator as per SAES-P-114, paragraph 6.0 in the breaker compartment of Emergency Generator 
• Provide all the required vendor drawings such as Single Line Diagram, Three Line Diagram, set up 13.8KV Switchgear with corresponding dimensions of each compartment, mounting details  and accomplished Data Schedule in the NMR-601 submittal
