SAPMT has reviewed the subject submittal dated June 04, 2014 and has the following comments:
1.	Regarding HVAC Sleeves Schedule - XB-S7, XB-S8, XB-S9, XB-S10, XB-S11 & XB-S12 in all drawings are 230 mm from Grid C and not from Grid B.
2.	Locations of HVAC sleeves XB-S3, XB-S4, XB-S9 and XB-S10 in all drawings shall be revised as per IFC drawings.
3.	It is preferable that the SPU-05-IU is not mounted above the Power Panel and Lighting Contactor Panel. (Refer to VA-846676-01 and VA-846685-01).
4.	It is preferable that the SPU-01-IU is not mounted above the Fire Alarm Control Panel. (Refer to BA-846682-01 and VA-846685-01).
5.	Sleeves penetrating structural concrete shall meet the requirements of the ACI 318 for reinforced concrete, chapter 6 section 6.3.
6.	Unless the codes specify, maintain consistency in usage of units of measurement.
7.	Provide the related standards in the notes.
8.	Provide sections to show elevations and also to show enough concrete cover.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
