SAPMT has reviewed the subject submittal dated March 01, 2014 and has the following comments:
1.	Provide cross sectional cable Drawings for MV Cables with associated dimensions list in mm of the cable.
2.	The 1-3Cx185mm2 MV Cable should be armored (galvanized or steel wire) as per Construction Specification Sec. 2.02 (E) and Cable & Conduit Schedule – Drawing No. VA-846494 Sht-001 to 003.
3.	Ensure that the offered MV Cable meets the S.A. Material Specification 15-SAMSS-502.
4.	Grounding cable 1Cx95mm2 should be indoor and outdoor direct buried type cable.
5.	Submit separate material submittal for MV Cable (Inspectable Item) and LV Cable (Non-Inspectable Item). Specify the description of LV Cable material submittal as “Low Voltage Cable–Grounding Wire with corresponding size of the cable.
6.	Jeddah Cable Company plant ID number for Medium Voltage Cable is 30000598.
Should you have any questions, please contact Yaser A. Al-Johani, Project Engineer on Tel.  No. +966 12 422 4686.
