SAPMT has reviewed the subject submittal dated October 06, 2013 and has the following comments:

1.	This method statement does not provide information about logistics and interfaces.
2.	It is important that ICC visualizes all scenarios and addresses them in the method statement. Only removing the wall and reinstalling it has been covered in the statement, but other affiliated activities are not mentioned at all.
3.	Refer to associated documents/ method statements, e.g. relocation of mangroves.
4.	Provide colored dwgs showing the existing and relocated fence alignments.
5.	Instead of using dot bullets, use numbers or alphabets, so that reference can be easily made.
6.	Conduct a land survey to mark the dividing line between KAUST and Naval base boundaries, so that the relocation can be as away as possible from the lagoon.
7.	As discussed in the 90 pc DD technical review meeting, consider installing a chain link fence at the mutual boundary line instead of temp mesh to ensure that no breach in the security concepts of naval base and KAUST occur and the dividing line is established physically. Safety and security measures shall be incorporated before any construction activities begin.
8.	Provide an area/ zone specific site engineer/ foreman and an interface engineer in your manpower.
9.	All existing gates, routes and roads whether belonging to or used by KASUT or NAVY or Others shall remain operational and alternative traffic plans or arrangements shall be studied and suggested.
10.	Show proposed storage areas on the drawings.
11.	In DWG VA-846502-001, at 0=900, the Patrol road is wrongly annotated.
12.	Provide quantities of equipment/ manpower to be used.
13.	Attach the details of existing and proposed foundations and existing wall details to visualize the work involved.
14.	Attach pictures to show the site conditions at existing and proposed locations.
15.	Acquire inputs from the communications and security contractor to reflect the relocation of Fibre Optic cables or connectivity for radars in the area etc.
Should you have any questions, please contract Fahad A. Al-Balawi, Sr. Project Engineer on Tel. No. +966 12 422 4393.
