SAPMT has reviewed the subject submittal dated June 03, 2015 and has no objection with the following comments:

1.	Block-out panel/ switch inside JFCC building and switch racks must be coordinated through manual and automatic operation.
2.	Provide interconnection wiring diagram for the proposed control cable looping between switch racks and JFCC building control panel.
3.	Ensure underground control cable installation shall comply with SAES-P-104.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.

Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
