SAMPT has reviewed the subject submittal dated August 19, 2014 and has the following comments;
1.	The calculated illumination for waiting area and ID office failed to meet the Saudi Aramco requirements as stated in Table 4 of SAES P-123.
2.	Provide a solution to meet the standard requirements of 500 lux for waiting area and ID office.
Should you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.
