SAPMT has reviewed the subject submittal dated March 01, 2014 and has the following comments:
1.	According to Aramco Standard SAES – Q - 012 Para 4.6, the minimum is 34.5 Mpa (5000 psi), whereas drawing notes shall be changed from 34 MPa to 34.5 MPa.
2.	The drawing titles in SD - FCC – 846521 – 210 & SD - FCC – 846521 – 211 shall be revised to show to 30M.
3.	In SD – FCC – 846521 – 207 Section A-A, the rebar space should be maintained to avoid the honeycomb as per ACI 318 - 08 sec. 7.6.
IC is urged to consult with SAPMT Civil team to rectify the above or any other issues before re-submission.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
