SAPMT has reviewed the subject submittal dated May 01, 2014 and has the following comments:
1.	IC is urged to find all superseded drawings and destroy them or stamp them as "superseded".
2.	IC shall consider conducting a quick topographic survey between 1+900 to 4+00 for the width "from seaside to the outer edge of KAM utilties" and send to the designer to ensure that the design is done according to the prevailing conditions after removal of road surfaces and backfilling in certain previously depressed areas.
3.	Provide details about the irrigation network.
4.	Show all culvert crossings, conduit banks, pits, duct banks in compliance with KA-714494-001 and KA-714490-002.
5.	Show valve boxes being installed by others along the KAM road, to finalise the landscaping design.
6.	Ensure minimum covers are provided from the finished grade level for all utilities for traffic or non-traffic areas.
7.	Provide a complete set for SAPMT review and to be shared with the proponent according to existing practices.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
