1.	Electrical one line diagram of proposed generator is not matching with generator diagram shown in library drawing P- DD-950114 Sht 003.
2.	Incomplete details of Automatic Voltage Regulator, contractor (IC) to provide complete details of Automatic Voltage regulator and shall be in compliance with 17-SAMSS-518 paragraph 8.
3.	Provide the connected load schedule to Generator manufacturer to meet 17-SAMSS-518 para. 7.1.3
4.	Provide a list of scope matrix for SDEC and ICC and other related sub-contractor/s (Arabian Point Eight) scope of work to ensure that scope will be delivered without room for gap. 17- SAMSS-518 compliance matrix and drawings provided by SDEC has so many notes specifying other/customer to supply.
5.	17-SAMSS-518 para. 7.4.10.5 For Generator bearings has to be cleared without prior approval of NMR-601.
6.	Ensure that scrolling pad is a field proven switch for Generator control panel. 17-SAMSS-518 specifically requires Manual, Auto, Off, Reset switches.
7.	Ensure that equivalent ENGLISH words will be written in all drawings, operation and manuals and related spare part data will be indicated to this NMR.
8.	Compliance to 17-SAMSS-518 Para. 9.2.3 Testing of Genset Breaker is necessary as per Saudi Aramco requirements for Molded Case Circuit breakers using SA P- forms series.
9.	Load site testing using load bank shall be part of the scope without any cost to Saudi Aramco.
10.	The weight of the muffler about 925 kilograms, that will be installed in the roof of the generator building has to be concurred and stamped by SCEC designer.


