1. Contractor has to identify the enclosure rating of the proposed panel boards.
2. Contractor has to identify the cable entry (Top or Bottom) for each of the panel boards.
3. Provide vendor shop drawing for each of the panel board showing Main Circuit Breakers and its branches.
4. Dry type transformer enclosure shall comply with SAES P-104 para. 7
5. Provide vendor shop drawing for dry type transformer to verify the ventilation details.
