a. According to Aramco Standard SAES – Q - 012 Para 4.6, the minimum is 34.5 Mpa (5000 psi), whereas drawing notes shall be changed from 34 MPa to 34.5 MPa.// b. The drawing titles in SD - FCC – 846521 – 210 & SD - FCC – 846521 – 211  shall be revised to show to 30M. //c. In SD – FCC – 846521 – 207 Section A-A, the rebar space should be maintained to avoid the honeycomb as per ACI 318 - 08 sec. 7.6 // IC is urged to consult with SAPMT Civil team to rectify the above or any other issues before re-submission.