1. The submitted EGA PVC conduit is not acceptable and does not comply with SAES P-104.
2. Types of Electrical and Communication conduit uses in Saudi Aramco for concrete and direct buried are only the following:
    1. PVC Conduit TYPE DB - 120 (Direct Buried)
    2. PVC Conduit TYPE EB - 35  (Concrete Encasement)
    3. PVC Conduit TYPE EPC - 40 (Direct Buried and Concrete Encasement)
3. Contractor has to ensure that all materials to be used for conduit and fittings will comply with Saudi Aramco Standard and IFC drawing.