1. The proposed cable tray mounting plan is not feasible to construct with the existing culvert (see attached photo of the culvert). Provide more details for the cable tray routing plan. 
2. Provide shop drawing for duct bank to cable tray transition.
3. Provide cable profile for the SEC cables running across KAUST Gate 3 road.
4. Provide Saudi Electric Company (SEC) signature acceptance for the shop drawings provided.