SAMPT has reviewed the subject submittal dated August 20, 2014 and has the following comments;
1.	All conduits penetrating inside concrete shall be PVC type as stated in SAES P-104, para. 15.4.1.
2.	Support for conduits and boxes shall be through channel erector components such as unistrut as per SAES P-104 para. 8.10.1.
3.	The flexible conduit for floodlight mounted outdoor shall be approved liquid type flexible conduit and not ordinary flexible conduit.
4.	Provide grounding/bonding connections for the turnstile metal body, and x-ray machine body, metal detector body.
5.	Replace flexible conduit with Rigid Steel PVC coated conduit connecting disconnect switch & Main power feeder.
Should you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.
