SAPMT has reviewed your request and has the following comments:
1. IC must replaced the borrowed communication manhole (dated 10-11-2014) on October 31, 2014 as per your commitment date to SAPMT.
2. IC shall ensure that the new manhole will comply to Saudi Aramco Standard Specifications and undergone Saudi Aramco Inspection through RFIs.
3. IC must expedite the completion of activities such as SONAR/RADAR Cable and Existing IDAS redundant Cable splicing and termination to be installed at the borrowed manhole with no further delay.
4. IC shall expedite the installation of the borrowed manhole as soon as possible.