SAPMT has reviewed the subject submittal dated June 03, 2014 and has no objection with the following comments:
1.	Ensure that pipe is cut neatly along the length as demonstrated on site to the construction team.
2.	Use cable ties, insulation tape and plastic sheet wrapped as an extra precaution to avoid any sand moving inside the pipe for future maintenance purposes.
3.	The electrician, permit receiver and site engineer shall be available on the location during the excavation, installation of sleeves and backfilling around the pipe.
4.	Consider replacing the title to "Proposed protection for Existing 13.8 kV cable for Sonar".
5.	A shop drawing should not have options but direct instruction to implement.
6.	Delete the FOC cable shown in option 2 and replace with 1-3C-35mm2 13.8 KV Power Cable.
7.	Work can start but a re-submission is necessary showing these comments.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
