1. Consider to plot the layout of battery charger, panels and related batter racks and cells into the NMR.
2. Ensure that the required minimum maintenance working clearance of 1 meter were considered and applied.
3. Ensure that Rectifier/charger enclosure doors shall be hinged and designed to open at least 120 degrees to facilitate maintenance access.
4. Ensure that an alarm to indicate the battery circuit breaker open condition (or fused disconnect switch open or blown fuse condition) shall be provided on the charger cabinet.
5. Consider to provide shop drawings for the equipment arrangement showing all related dimensions.