1. It is preferrable not to mount an air conditioner above the electrical panels.
2. Improve the drafting quality of submittals by maintaining consistency in line thicknesses, units of measurements and colors etc.
3. Correct the wrongly written title block on DWG IC-SD-846730-101-00 
4. Sleeves penetrating structural concrete shall meet the ACI 318 for reinforced concrete, chapter 6 section 6.3.

