SAPMT has reviewed the subject submittal dated November 16, 2014 and has the following comments:
1.	All testing checklists should be as per Manufacturer’s Testing Procedure.
2.	ICC ITP-T-005 Item # 3.3 (Cable Pulling, Identification, Termination Visual Inspection Low Voltage Copper Cable). Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.
3.	ICC ITP-T-005 Item # 4.1 “Baggage X-Ray Machine System – Installation and Identification Visual Inspectionâ€. Inspection Responsibility Assignments: Change W1 to H for Saudi Aramco.
4.	For “Material Receiving, Installation and Pre-Commissioning of LV Power Cableâ€ for column “Quality Procedure & Recordâ€ change to “See Remarksâ€. Add in the remarks column of ITP to “Refer to SATIP-P-104-01 and SATIP-P-111-01â€.
5.	Pre-commissioning and Commissioning of Baggage X-ray Machine shall be a hold point to Saudi Aramco and KAUST Proponent. Change W to H in the ITP.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
