SAPMT has reviewed the subject submittal dated April 14, 2014 and has the following comments:

1.	IC shall submit missing items which are part of SACS system deliverables as per FSD document, PE 000071 section 4.4.3, section 5.1, section 5.2.5 /5.2.9 such as Badging Station, Operator workstation, Fingerprint System and door control accessories.
2.	Ensure that Reader interface shall be supplied with internal DC battery backup for minimum 8 hour including power to energize door lock as per FSD document PE-000071 section 5.2.3.
3.	IC is urged to provide technical data for all remaining materials stated in IFC and/ or project specifications.
Should you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer at Tel No. +966 2 422-4393.
