SAPMT has reviewed the subject submittal dated May 25, 2014 and has no objection with the following comments:
1.	Mention in the subject whether the shop drawing for structural or architectural works.
2.	Provide rebar schedule for masonry.
3.	Provide more details about the texture of CMU, finishes at ramps etc.
4.	Provide more details about lintel beams.
5.	Provide more details about bituminous coatings under the NGL.
6.	Provide interface details between silicone sealants and bitumen sealants.
7.	Provide details for adjustable hanger rods, fixtures, supports for acoustic ceilings, roof access cage etc.
8.	Provide more details about the wall insulation.
9.	Provide drawings for doors and windows.
10.	Dowel spacing in IC-SD-846859-102 (Block Wall Plan) and IC-SD-846860-102 (Block Wall Plan) are different.
11.	Explain why the width of groove is 32mm in conflict with IFC VA-846861-001.
12.	Consult with SAPMT to discuss all conflicts between IFC and shop drawings before revised submittal.
13.	Structural works can start but the revised submittal conforming to the above comments shall be provided within 3 days.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
