SAMPT has reviewed the subject submittal dated February 22, 2015 and has no objection with following comments;

1.	Ensure that all equipment is fastened to the rack with SS or hot dip galvanized     
Hardware/ fittings as per 16-SAMSS-512 Para 11.
2.	Correct the LV system to 400V/230V instead of 480V/277V in all vendor drawings.
3.	Labeling of all enclosures shall be done as illustrated in 16-SAMSS-512 Para 12.1.

IC shall ensure that no scope change or cost/schedule implication arises from this letter.

Should you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.
