1.	WESCOSA has limitations to use only Cutler Hammer Model breakers under license from Cutler Hammer.
2.	Submit requisition package at the earliest ande use special SA-175 form as per the inspection test plan(ITP) produced by WESCOSA for these Package substations.
3.	Ensure that the fuse rating of Ring Main Unit (RMU) for tee-off circuit is rated according to the rating of transformers of different sizes as indicated in the Single Line Diagrams
•	The enclosure of the Package shall be adequately protected against corrosion and painted according to relevant clauses of SEC standard 01-SDMS-01
•	Provide Datasheet for each Package Substation concurred by the designer and manufacturer.
•	LV Panelboard shall be according to the Panel Schedule drawings of the project

