SAPMT has reviewed the subject submittal dated February 10, 2015 and has been rejected with the following comments:

1.	Reflect changes also on transformer secondary section as per existing cable size.
2.	Consider providing this Electrical One line diagram together with the Shelter #2 of SONAR and RADAR installation submittal package.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.

Should you have any questions, please contact Sami A. Al-Gafri, Project Engineer at 012 422-4686.