SAPMT has reviewed the subject submittal dated June 28, 2014 and has the following comments:
1.	The 9com and level of inspection are acceptable.
2.	Provide test report for 1800mm dia manhole instead of the wrongly attached report.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
