1. Provide Lighting Control Panel shop drawing that shows the dimension of the enclosure, wiring and devices arrangements.
2. Provide the catalog and specification for the control transformer and pilot lamps.
3. Indoor Lighting Control Panel shall be type NEMA 1, while Outdoor Lighting Control Panel shall be type NEMA 4X to meet enclosure requirements specified in SAES P-104.
4. Include dedicated LCP tagging identification, for indoor shall be phenolic type, for outdoor shall be stainless steel.