SAPMT has reviewed the subject submittal dated December 17, 2014 and has the following comments:
1.	All testing checklists should be as per Manufacturer’s Testing Procedure.
2.	ICC ITP-T-004 Item No. 3.1 (Z-Portal System Installation and Pre-Commissioning Visual Inspection) – Inspection Responsibility Assignments: change W1 to H for Saudi Aramco.
3.	ICC ITP-T-004 Item No. 4.1 (Pedestal Installation and Pre-Commissioning) – Inspection Responsibility Assignments: change W1 to H for Saudi Aramco.
4.	Quality procedure and records, indicate “See Remarksâ€. For remarks, indicate “See SATIP-P-104-01 and SATIP-P-111-01â€.
5.	For item # 2.5/3.4/3.5/3.7. Delete Inspection Responsibility Assignment and refer it to SATIP-P-104-01 & SATIP-P-111-01.
6.	Add item in the Pre-Commissioning for LV Power Cable and refer it to SATIP-P-104-01 & SATIP-P-111-01.
IC shall ensure that no scope change or cost/schedule implication arises from this letter.
Should you have any questions, please contact Sohail Moughal, Project Engineer at 012 422-4570.
