SAPMT has reviewed the subject submittal dated March 26, 2014 and has the following comments:

1.	The piping material is acceptable but the submittal is incomplete.
2.	The subject of the submittal shall be more specific. Rename the description of the submittal with "PVC CONDUITS NEMA TYPE DB and EB for ELECTRICAL AND COMMUNICATION conduits and duct banks".
3.	Include in the submittal the proposed conduit spacers and conduit fittings.
4.	Ensure that the PVC conduits to be used will comply with SAES P-104, IFC drawings and Project Specification.
5.	Discuss with electrical and communication engineers from SAPMT to include necessary documents, summaries and drawings.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
