SAPMT has reviewed the subject submittal dated September 15, 2014 and has no objection with the following comment:
•	Provide details for light pole bonding to grounding grid.
Should you have any questions, please contact Dr. Ahmed S. Khogeer, Sr. Project Engineer at 012 422-4423.
