SAPMT has reviewed the subject submittal dated June 02, 2014 and has no objection with the following comments:
1.	Ensure that the proposed camera is suitable for outdoor environment.
2.	Provide details about manufacturer recommended enclosure/housing for the camera.
3.	Ensure to submit the details of required server for SACS and with capacity calculations in a separate submittal for SAPMT approval.
4.	The quantity of Proximity readers, Bio-metric readers and cameras shall meet the project specification requirements and SACS Functional Specification Document PE-000071.
5.	Ensure that the fingerprint system will comply to FSD document PE-000071 para. 4.8 & 5.2.8.
6.	The pole for proximity readers located in gate # 2 & 3 inbound and outbound, shall be capable for small and big cars.
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
