General notes are not correct which are related to MV cables. Please revise them.
Duct Bank 1:
1.	The elevation 2.96 is not correct, please check the remaining elevation and raise the duct bank to the minimum depth requirement by Aramco standard to avoid the water table area. 
2.	ICC pipe sleeve should be the first one and RABYA is the second pipe sleeve to avoid crossing each other.
3.	The Duct height is not mentioned.
4.	Delete the soil improvement word because no soil improvement will be there.
Duct Bank 2:
1.	Add elevation to the section.
2.	The hook length 300 mm of the horizontal (top and bottom) rebar is not correct
