SAPMT has reviewed the subject submittal dated August 24, 2014 and has no objection with the following comments:
1.	Units shall be certified at manufacturing facility to comply with UL-1203 and UL-1995 by an approved third party.
2.	Units shall be equipped with necessary field instruments like valves/ dampers, controls, safety systems; pre-wired field interfaces, control system interfaces etc. and such details shall be included in the RP.
3.	Ensure that PACU condenser coils have copper fins as per SAES-K001 para 4.8.4.9.
4.	IC is responsible for delivering materials/ equipment and installation of all units and accessories according to the agreed scope of work and Saudi Aramco standards.
Should you have any questions, please contact Ahmed S. Khogeer, Sr. Project Engineer at (012) 422-4423.
