SAPMT has reviewed the subject submittal dated March 01, 2014 and has rejected with the following comments:
1.	Provide Data Schedule 1 & 2 according to 16-SAMSS-504 properly filled by the supplier and concurred by the designer.
2.	Change the rating of the feeder breakers to 600 Ampere according to the meeting held on February 10, 2014 with the designer.
3.	The dimensions of the proposed 13.8KV Switchgear shall suitably accommodate to the Switchgear Room of Generator Bldg. # 1 & 2 meeting the required working clearance as per SAES-P-116, paragraph 7.1.
4.	Ensure the Switchgear and Generator vendor drawings shall coordinate with each other with respect to controls, protection and auto-transfer scheme for proper operation of the project electrical system during commissioning.
5.	Correct the single line diagram of the IFC drawing by removing one spare and space as discussed in the meeting held on March 10, 2014.
6.	WESCOSA has limited approval for the following;
a.	Powl VAC (Vacuum) 36â€ 1200A, 2000A, 3000A.
b.	Powl VAC-ND (Vacuum Narrow Design) 26â€ is for 1200A only.
c.	The manufacturer is not approved for 600A, attached is the list of approved manufacturers.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
