SAPMT has reviewed the subject submittal dated May 14, 2014 and has no objection. However, it is contractor’s responsibility to ensure full compliance of applicable Saudi Aramco standards & specifications. 
Should you have any questions, please contact Sohail Moughal, Project Engineer at Tel No. +966 2 422-4570.
