SAPMT has reviewed the subject letter no. KPSS/SA/B/AKR/14/0456 dated March 15, 2014 and has the following comment:
•	IC is urged to provide all planning documents especially shop drawings, interface drawings, traffic control drawings for ICC/other Contractor’s movements in the area, detailed activity schedules and related material submittals/approvals according to the scope of work, before mobilizing the construction team to work around or on top of the Wadi Wesami culvert.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
