SAPMT has reviewed the subject submittal dated January 14, 2014 and has no objection with the following comments:

1.	The attached reference standard SAES-O-123 is no longer applicable. Ensure the proposed crash barrier will comply with SAES-O-206 Paragraph 4.4.3.
2.	Use 220 VAC power supply instead of 208 VAC.
3.	Dimensions and measurements shall be provided in the shape of a shop drawing according to IFC drawing VA-847162 007 to indicate the required minimum distance of the barriers to other security elements such as drop arms with reference to SAES-O-203, Paragraph 4.14.
4.	Provide more information, preferably a 3D view, for dimensions and orientation of the remote control panel.
Should you have any questions, please contact Sohail Moughal, Project Engineer on Tel.  No. +966 12 422 4570.
