SAPMT has reviewed the subject submittal dated January 21, 2014 and has no objection with the following comments:

1.	To ensure proper record keeping, prepare a list of all items to be removed with their quantities, models and serial numbers and submit to SAPMT after removing/ dismantling.
2.	The RADAR power supply has to be connected in sonar shelter # 1 prior the removal of IDAS Distribution Panel DP-01.
3.	Any work exclusion mentioned by ESE which comprises of the scope of the project, shall be removed from method statement. ICC shall review the document, perform a quality check and remove such exclusion phrases prior sending to SAPMT for review. 
4.	ICC/ESE shall start on technical submission of the fiber optic cable to be used in this activity and to place purchase order as soon as possible.
5.	Equipment and tools for splicing, terminations and testing of fiber optic cable shall be submitted for approval.
6.	Ensure the fiber optic cable splicers are with certifications approved by ARAMCO or equivalent as per SAES-T-928. List down the name of the splicers and attach their certificates.
7.	Consider the removal of IDAS along the KAM access road as top priority in order to facilitate the construction of KAM access road and laying of utilities for KAM project.
8.	Ensure that all related safety and quality staff along with discipline specialists is present on site during removal, stocking and re-installation.

Should you have any questions, please contact Fahad A. Al-Balawi, Sr. Project Engineer on Tel.  No. +966 12 422 4393.
